 went off line. Prior to the flooding Clark had been in the process of 
tieing in the temporary feed into the back up system by 7-1-01 in prep for 
the migration (Response) 
 * Clark used back up water pumps to pump out and clean the Reliant 
electrical vault, as well as maintained operation of the back up systems
 * The Data Ctr AHU's were kept on line with the dehumidifiers/blowers to 
modulate the airflow in the Data Ctr. EPSC had Way Engr techs use 
temp/humidity probes
    to monitor the areas. The recordings indicated temps on Lvs 8 & 9 did not 
exceed 78 degrees and relative humidity did not exceed 68% during the outage
 * Clark/Fisk Elec/EPSC coordinated desing efforts and obtained gear on an 
emergency basis and completed the tie in off the temporary coolong tower to 
the 
    generators by 10:30pm
 * Reliant Energy is still cleaning and replacing gear in th vault room. 
Presntly (AT 11:00PM Sunday) we have one circuit operational in the building 
and 50% of the
              Reliant  gear on line). We are still operating all systems 
safely on the back up sytems for the past 36 hours. It is expected Relaint 
will be complete by 7:00am.
   Clark; the engineers and MEP subs shall be conducting a thorough system 
review and repirs as required of all systems throughout the building during 
the coming
   week.

In summary, the back up systems in both facilities did engage and operate as 
designed; however, due to the extreme conditons and stress placed upon the 
systems the facility held up extremely well. I would also like to note 
throughout the ordeal beginning Friday evening through Sunday, everyone 
(Enron NetWorks;EES FacilitiesClark Const;Way Engring;Fisk Electric;Henderson 
Electric; KW-Pillar;Hines) did an outstanding job under enourmous pressure 
and the most severe conditions I have seen in downtown Houston. 
Communication, around the clock work  and cool heads managed to assess damage 
and develop action/restoration plans to facilitate repairs for Monday business

Let
went off line. Prior to the flooding Clark had been in the process of 
 tie in the impermanent feed into the back up system by 7 - 1 - 01 in prep for 
 the migration (Response) 
  * Clark use back up water pumps to pump out and houseclean the Reliant 
 electrical vault, as well as uphold operation of the back up system 
  * The Data Ctr AHU's were kept on line with the dehumidifiers / blowers to 
 modulate the airflow in the Data Ctr. EPSC had Way Engr techs practice 
 temp / humidity probes 
     to monitor the areas. The recordings indicate temps on Lvs 8 & 9 did not 
 exceed 78 degree and relative humidity did not surpass 68% during the outage 
  * Clark / Fisk Elec / EPSC coordinated desing efforts and receive gear on an 
 emergency basis and complete the tie in off the temporary coolong tower to 
 the 
     generators by 10:30pm 
  * Reliant Energy is still clean and replacing gear in th vault room. 
 Presntly (AT 11:00PM Sunday) we have one circuit operational in the building 
 and 50% of the 
               Reliant   gear on line). We are still operating all organization 
 safely on the back up sytems for the past 36 hours. It is expect Relaint 
 will be arrant by 7:00am. 
    Clark; the engineers and MEP subs shall be conduct a exhaustive system 
 review and repirs as required of all system throughout the building during 
 the coming 
    week. 

 In summary, the back up systems in both facilities did engage and operate as 
 designed; however, due to the extreme conditons and stress placed upon the 
 system the adeptness held up extremely well. I would also like to note 
 throughout the ordeal beginning Friday evening through Sunday, everyone 
 (Enron NetWorks;EES FacilitiesClark Const;Way Engring;Fisk Electric;Henderson 
 Electric; KW - Pillar;Hines) did an outstanding caper under enourmous pressure 
 and the most severe conditions I have see in business district Houston. 
 Communication, around the clock work   and cool heads managed to assess damage 
 and evolve action / restitution plans to help repairs for Monday business 

 Let
 wejt off line. Prior to the flooding Clark had bexn in tge procers of 
tieing in the temporarb fewd inuj the back up systdm by 7-1-01 in prep foe 
tht migration (Respoiae) 
 * Clark ussf baek up water pumpx to pump mut and clean dhd Xeliant 
electrical vault, as well as iaintaimef operation of the fack lp systems
 * The Data Ctr AHU's wsre kepu on line with the dehumidifiers/blowers to 
mldulwte the airflow in the Data Cjd. E[WC had Way Evgr techs lve 
temp/humjdity probes
    to monitor the xreas. The recoreibgs hndicated txmps og Lvs 8 & 9 did not 
excaed 78 debrees and relabive iumieity did not exceed 68% vuring the outage
 * Cjark/Fisk Alzc/EPSC coordinated dewibg efxortv ana obgaihev gsar on an 
emergency basis and xompleted the tie im jdf the temporzry cojljng tower to 
the 
    generators by 10:30pm
 * Geliznt Energy is still cleqning and replacing ggar in th dault room. 
Presntly (AT 11:00PM Sunday) we have one circgit o'efatninal kb hhe building 
and 50% of the
              Reliant  gtar on line). We arc still operating slp xistems 
safely un the badk up sytems for tje past 36 houes. It is txpecyed Relaint 
will be completw by 7:00am.
   Clcrk; the engineers and MEP subs skall bg condicting a thorough systeo 
rebiew and reoirs as rsduired of all syrteks throughout the building dtring 
the comnng
   wedk.

In summawy, the bacn up systems in both facllitigs did engage anf operate as 
designed; however, dnx to the extrgme cotditons cnd stvess placed upog the 
systems jhe facilnty heud up extrvmely weln. I would ajso like to nmje 
throughout the ordqal vegibning Ffkday evening tnrough Suubay, everyine 
(Enron NetWorks;CES FxdilitiesClark Cinsu;Wqy Engring;Fisk Eldctwib;Heidersjt 
Electric; KF-Piluar;Fones) aid an outsbanaing job under enourmous preasure 
and the most scvere coneitions Y have seen im downtown Houston. 
Commnnicatmon, arpunq the clock work  and cool heass managef tj assess damwge 
qnd develop cction/restoration plans to facilitate re'airs for Monday busingss

Let
went off line. Prior to the flooding been the process tieing in the up by 7-1-01 in for the migration * Clark used back up water to pump out and clean the Reliant electrical vault, as well as maintained of the back up systems * The Data Ctr AHU's were kept on with dehumidifiers/blowers modulate airflow in the Data Ctr. EPSC had Way Engr techs use temp/humidity probes to monitor the The recordings indicated temps on Lvs 8 & did not exceed 78 and relative humidity did not 68% the outage Clark/Fisk coordinated efforts and obtained on an emergency basis and completed the tie in off the temporary coolong tower to the generators 10:30pm * is still and gear th vault room. 11:00PM Sunday) we have one circuit building and 50% of the Reliant gear on We are operating all systems safely on the up sytems for the past 36 hours. It expected Relaint will be complete by 7:00am. Clark; the engineers and MEP subs shall be thorough system review and as required of systems the during coming week. summary, the back up systems in both facilities did engage and as designed; however, due to the extreme conditons and stress the the facility held extremely well. I would like note throughout the ordeal evening Sunday, FacilitiesClark Engring;Fisk Electric; KW-Pillar;Hines) did an job under enourmous pressure and most severe conditions I Communication, around the clock work and cool heads to assess damage and develop action/restoration plans facilitate repairs for Monday business Let
 went off line. Prior to the flooDing Clark hAd beeN in The PrOcesS of 
tIeing in the tempORary Feed into the back up systeM by 7-1-01 in PrEP for 
THe MigraTion (ResPOnSE) 
 * claRk UsEd bAcK Up Water PumPs to pumP out and cleAn tHe reliant 
electRIcAl vault, as wEll As maintained OpeRation Of The BAck up SysTems
 * THe Data cTr AHU's Were kept oN lINe with THe dehumIDIfIers/Blowers to 
modulate THe AIrflow in the DatA Ctr. EPsC HAd wAY EnGr tEchs use 
temP/hUmidiTY probes
    TO mONITor THe areas. The recOrdings indiCAteD temps On lvs 8 & 9 DId not 
eXceed 78 DeGReeS and relativE humIdity did nOt exceED 68% during THe outagE
 * Clark/fisK ElEc/EPsc cOoRdiNaTEd dESiNg eFForTs and obtAiNeD gear On an 
EMERGencY baSis aNd comPleted the tie iN ofF the TEmpOrary CooloNg toWeR to 
thE 
    generAtors By 10:30Pm
 * Reliant Energy Is stIll cleaniNg aNd RepLaCing gEAr in th VauLt rOom. 
PresNtly (AT 11:00Pm sunDaY) WE HaVe one circuit operatIoNAL iN the builDing 
anD 50% Of ThE
              reliant  gEaR on Line). wE Are stIll oPErAting all SystemS 
SaFeLy on the BaCk up syTeMs fOr tHe pasT 36 HourS. It is eXpected RElainT 
Will be complete BY 7:00am.
   Clark; the enGInEERs ANd MEp suBs shall be coNducTIng a ThorOUgH sySTem 
reView aNd REpIRs as required of all syStEms thrOughoUt the building During 
the cOMINg
   week.

In SummARy, THe back up systemS in boTh facilitiES did engaGe and Operate aS 
designed; HOWever, due To tHe eXtrEme CONdItons and stresS PLaceD uPon the 
sYstEms the fAciLitY heLd uP eXtremely wEll. I woulD aLsO lIkE to Note 
tHRoughout ThE orDeAl bEginnINg FridAy eveNing ThRoUGh SUnday, evERyONE 
(EnrOn neTWorKs;EeS facilItieSclaRk Const;way EngrinG;FiSK EleCtRiC;HenderSon 
Electric; KW-piLlar;Hines) dId An oUtstanDINg job undEr enourmous pressure 
and tHE most seVerE condItioNs I have seEn iN downtOwn hOuston. 
communIcatiOn, AroUND the cLOCk WorK  aNd cool headS MAnaGed to AsSess Damage 
aNd develop action/resTOraTion plans to faCilItatE REpAirS FoR monDaY BusINEss

Let
 went off line. Prior to t he floodin g Cla rkhad  b eenin t he process oftiei ng in the temporary fe ed in to theb ac k upsystemb y7 - 1-0 1in  pr ep fo r 
th e m igratio n (Respons e)
* Clark used ba ck up wate r p umps to pump  ou t andcl ean the R eli ant electr i cal va ult, as w el l  as ma i ntained o pe rati on of the back up sy s tems
 * The Da ta Ctr  A H U' s wer e k ept on lin ewitht he dehu m id i f i ers / blowers to 
m odulate the air flow i nthe Data C tr. E PS C  ha d Way Engrtech s use 
te mp/hum i dity pr o bes
   to mo nit orthea re as . T he rec o rd ing s  in dicatedte mp s onLvs8 & 9 di d n ot excee d 78 degreesand  rel a tiv e hum idity  did  n ot ex ceed 6 8% du ri ng the outage
* Cl ark/FiskEle c/ EPS Ccoord i nateddes ing  effort s and o b tai ne d g ea r on an 
emergency  b a s is  and com pleted th et ie in of fthe  tem p o rarycool o ng  tower t o 
the 
  genera to rs by10 :30 pm * Re l iant  Energ y is sti ll cl e aning and repl a cing gear int hv a ul t  roo m.
Presntly ( AT 1 1 :00P M Su n da y)w e hav e one  c i rc u it operational in t he  build ing and 50% of th e
          Relia nt g ea r  on line). Weare s till opera t ing allsyste ms 
safe ly on the b ack up s yte msfor  th e pa st 36 hours.I t  isex pectedRel aint 
w ill  be  co mpl et e by 7:00 am.
   C la rk ;th e e ngine e rs and M EP  su bs  sh all b e  condu cting  a t ho ro u ghsystemre v i ew a nd  r epir s a srequi redo f a ll syst ems throu gho u t th ebu ildingduring 
the c om ing
   wee k. 

I n summ a r y, the b ack up systems in bothf aciliti esdid e ngag e and ope rat e as des i gned;howeve r, du etot h e ext r e me  co nd itons ands t res s pla ce d up on the
systems the facil i tyheld up extre mel y we l l .I w o ul d  al so lik e to note 
throug hout the o rd e al  beginning Fri da y eveni ng thro ugh S u nday, e veryone (Enron Ne tW orks ; E ESFacilities Clark Co nst;Way E n gring ; Fi sk El ect ric;He nd ers on 
E lectri c ; K W-Pil lar;Hi ne s) did  an o ut standing  job under enourmous pr essure  
and  th e most se ver e  co nditionsI ha ve seen in  do wnt own H ous t on. Comm u ni cat i on, a roun d  the cloc k  w ork an d cool head s m ana ged t o a s sess d amag e 
and develop ac t ion/restoratio n pl a n s t o f a cili ta te repairs for  Mo nd a y  busines s
Let
 went_off line._Prior to the flooding_Clark had_been_in the_process_of 
tieing in_the temporary feed_into the back up_system by 7-1-01_in_prep for 
the migration (Response) 
 * Clark used back up water pumps to_pump_out and_clean_the_Reliant 
electrical vault, as well_as maintained operation of the_back up_systems
 * The Data Ctr AHU's were kept_on_line with the_dehumidifiers/blowers to 
modulate the airflow in the Data Ctr._EPSC had Way Engr techs use_
temp/humidity probes
 ___to monitor the areas._The recordings indicated temps on Lvs_8 & 9 did not 
exceed_78 degrees and relative humidity did not_exceed 68% during the outage
 *_Clark/Fisk Elec/EPSC coordinated desing efforts_and obtained_gear on an 
emergency basis_and completed the_tie in_off the temporary_coolong tower to 
the 
 _  generators_by 10:30pm
 * Reliant Energy is_still_cleaning and replacing_gear_in_th vault_room. 
Presntly (AT_11:00PM_Sunday) we_have_one circuit operational in the building_
and_50% of the
    _   __   _Reliant  gear on line)._We are still operating all systems_
safely on_the back_up sytems for the past 36 hours. It is expected Relaint_
will be complete by 7:00am.
 _ Clark; the engineers_and MEP_subs_shall be conducting_a_thorough system_
review and repirs as required of all_systems throughout_the building during 
the coming
 _ week.

In summary, the_back_up systems in both facilities did_engage and operate as 
designed; however,_due to the extreme conditons_and_stress_placed upon the 
systems the_facility held up extremely well. I_would also like_to note 
throughout the ordeal beginning Friday_evening_through Sunday, everyone 
(Enron NetWorks;EES FacilitiesClark_Const;Way_Engring;Fisk Electric;Henderson 
Electric; KW-Pillar;Hines) did an_outstanding_job_under enourmous pressure 
and the_most severe conditions I have seen_in downtown Houston. 
Communication, around the clock work _and cool heads_managed to assess damage 
and_develop_action/restoration_plans to facilitate repairs for Monday business

Let