 sunk or the Liquid Crystal may be broken.
into a same wiring tube with the circuit.
The shield cable must be connected stable to the ground, or transmission may fail.
to C, D and E on the terminal.
General functions and integrates FOLLOW ME function.
Bases on the KJR-12B/DP (T)-E and with backlight, vertical and level swing function.
FOLLOW ME and configured with a 20M wire. Theres no brand and backlight on it.
5. Follow me function.
this function will be ineffective.
If press this button in heating mode, electrical heater function become effective.
change in turn as follow.
When press MODE button, the following mode can be selected in circle.
Notes: For cooling only model, heat mode is invalid.
available under cooling, heating, and auto mode.
When it is on, the icon display, otherwise it is extinguished.
NOTES: some air conditioners without MED fan speed, and then the MED is regarded as HIGH.
for LOCK button.
there is no display here.
Make sure the following pasts has been prepared.
Never turn screws too tightly, or else the cover would be sunk or the Liquid Crystal breaks.
Installation of wired controller KJR-12B/DP (T)-E is the same to KJR-10B/DP (T)-E.
switch board, then connecting the terminal +5V, GND and Run in the switch board to C, D, E respectively.
with the actual conditions.
KJR-29B is the touch-style key wired controller.
wired remote controller to control the indoor unit for swinging.
the ON/OFF button, the unit will be turned off and the operating icon lights off.
When the controller has been set to cool-only, then there is no HEAT mode.
Under AUTO and DRY modes, the fan speed is not adjustable and the default fan speed is auto.
adjusting range is 17~30 (or 62~88). The setting temperature cannot be adjusted under FAN mode.
exit the time on setting.
timer will be canceled simultaneously.
position of the clock will flash, and can press Temp setting buttons to adjust the hour value.
the button or wait for 5seconds to confirm and exit the setting state.
Under AUTO, COOL, DRY, HEAT modes, press the 26/OK button can set the operating temperature to 26.
adjusting instruction from the wireless remote controller.
Long press 26/OK button for 3seconds, can unlock the 26operation locking state.
press temperature adjusting buttons again can cancel the locking state.
wired controller will re-accumulate the total running time of the indoor unit.
hours. The setting methods please refer to the installation manual.
function is turned on, the swing icon will be lighted up.
the temperature value to the indoor unit every 3 minutes.
into address setting mode.
Querying address: Press MODE button, the corresponding indoor unit will display its address.
record it. After about 4 seconds, this displaying will fade out and indoor units turn to normal display mode.
After setting addresses, users can press the 26/OK button can exit the address setting mode.
re-power, this address will be cleared.
In the address setting mode, wired controller does not respond to any command from remote controller.
sequence of signal switching wires (A/B/C/D).
is0.8~1.2N.m (8~12 kgf. cm).
2) Use three GB950-86 M4X20 screws to directly install the back cover on the wall.
M4X20 screw for fixing the wall.
2. Over fasten the screw will lead to deformation of the back cover.
wired controller while during maintenance.
wire during installation.
front cover drop off.
the second code "Y" means the detailed configuration of this function.
4) When the first code value is "6", press 26/OK button again to exit the parameters setting.
states; otherwise there is no need to do the setting.
1) Can compatible with the V4 plus heat recycling 3-pipe system and V4 plus 2-pipe system.
When the unit is turned off, press the ON/OFF button, the unit will be turned on and the operation LED lights on.
Notes: Heat-only mode can only set to HEAT mode.
indoor unit may be COOL or HEAT. If the setting mode is DRY, the actual operation mode of the indoor unit is COOLING.
or wait for 5s to exit the clock setting automatically.
5s will exit the timer setting and back to normal display.
When the timer on/off has been set, set the timer to 0.0 hour can cancel the timer.
Press the CHECK button to display room temperature (TF) and evaporator temperature (t2 and t2b) of the unit.
the query display and back to normal display.
3) Setting the fan speed to AUTO then the indoor unit will actually run at LOW speed.
AUTO/COOL/DRY/HEAT operating mode can set the temperature, the setting range: 17-30(62-88).
again can deactivate the swing function (This function is effective when it is used with the relative indoor unit).
temperature is higher than 15 then it will stop heating and the operation LED lights off.
Press the 10 Heat button again or ON/OFF button can exit 10 Heat mode.
2) Under heat-only mode, the controller can only be set to HEAT mode.
setting status of the controller will be saved.
for 5 seconds to enter the T setting, then press or button to adjust the value of T.
remote controller, central remote controller, etc.
mode. Please refer to the INSTALLATION MANUAL for details.
the F1 flag will auto disappear after 8s, and it will appear and flash for 8s again every time turn on the unit.
keys to adjust between the different codes.
1. This manual contains information about the procedure of installing the controller.
Tube with the circuit, and the interval must be more than300~500mm.
3. The shield cable must be connected stable to the ground, or transmission may fail.
4. Do not to attempt to extend the shield cable by cutting, if it is necessary, use Terminal Connection Block to connect.
5. After finished connection, do not use Megger to do installation check to the signal wire.
NotesUse the 4-cores wire and 2-cores wire accessories to connect the same wired control and indoor unit.
3-pipe system mode.
then press the other end of the controller board.
joint extrudes out of the controller back cover.
2) Please do not connect the wired controller and a CCM. to the same X, Y,E port, otherwise it will lead to conflict.
General control function.
stop flashing automatically.
once every 10 minutes; long pressing the keys it will increase/decrease once 10 minutes/0.2 seconds.
Low cost and low price, exquisite appearance and LCD display.
pressure duct series. And it also suits for other kind of indoor units.
the electric cabinet.
The KJR-90A-E has the same functions with KJR-10B.And the KJR-90AI-E can not select running mode.
There are nine function buttons.
Pre-embed it into the wall.
should not more than 15M.
pre-embedded into wall.
If there is no terminal,the 5-core wire should be connected directly.
1) Over tighten the screw would cause the rear covers deformed and LCD damage.
2) When installation, please maintain the screws and wired controller at the same height level without deformed.
hospital and school etc.
Press the ON/OFF button can turn on or turn off air conditioner.
2) Setting the fan speed to AUTO when the indoor unit will actually run at LOW speed.
setting temperature, the setting range is 17C-30C.
1) Wiring figure of the wired controller connect with the four-way cassette type indoor unit.
2) Wiring figure of the wired controller connect with the courtyard-style duct type indoor unit.
3) Wiring figure of the wired controller connect with the high-static pressure duct type indoor unit.
4) Wiring figure of the wired controller connect with the wall hanging type indoor unit.
5) Wiring figure of the wired controller connect with the stand-hanging type indoor unit.
Connective wires to the signal receive panel.
with the 4-core shielding wire.
the wall in advance.
should be less than 15m.
For installing the cross head screw.
can be up to 1200m. Both of the following wiring modes centralized monitor and indoor units are applicable.
page, and sets the first in-service air conditioner by default.
differentiated by bit selection address. The configurable range is 0~15.
in the network is faulty, or the centralized controller network itself is faulty, the indicator will blink at 2Hz.
start/shutdown, the indicator will be luminous. Otherwise, the indicator is off.
the remote controller of all air conditioners.
controller, and will not vanish after the power supply is restored, unless the command of unlocking is received.
non-conflict mode can be selected freely. The centralized controller can also lock modes of all indoor units.
remote controller after startup) until the foregoing switch is opened.
inc re