6c129ed5_Trouble_Shooting__Possible_Cause
[Sr.No.] 3 [Check] Using an ohmmeter, X1000 scale, determine the resistance across the disconnected starting capacitor. When contact is made, the ohmmeter should jump toward 0, and then drift back slowly toward infinity. No movement indicates an open capacitor; low resistance. [Corrective Action] Replace defective components. [Possible Cause] 
Defective control box components (For three wire pumps only - skip this for two-wire models)
Trouble Shooting
Possible Cause