c6de1369_ditioning_Vent__Vent__Air_Vent__Symptoms
[Possible cause] 1. Pilot light not lit. 2. System Switch not set to Heat. 3. Loose connection to thermostat or system. 4. Furnace Lockout Condition. Heat may also be intermittent. 5. Heating System requires service or thermostat requires replacement. [Corrective Action] Re-light pilot Set system switch to Heat and raise set point above room temperature. Verify thermostat and system wires are securely attached. Many furnaces have safety devices that shut the system down when a lockout condition occurs. If the heat works intermittently contact the furnace manufacturer or local service person for assistance. Diagnostic: Set system switch to heat and raise the set point above room temperature. Within a few seconds the thermostat should make a soft click sound. This sound usually indicated the thermostat is operating properly. If the thermostat does not click, try the reset operation listed above. If the thermostat does not click, it may indicate the need for a new thermostat. If the thermostat clicks, contact the furnace manufacturer or a service person to verify the heating system is operating correctly. [Symptoms] 
No Heat
Atlanta Supply :: Air Diffusers, Vent Covers, Air Conditioning Vent, Vent, Air Vent
Symptoms