Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 78-36 16.6 470.0 11.8 45 16.3 410.0 10.00100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.9 39.8 37.4 45 22.5 39.5 35.0SR 36-45 22.0 32.8 39.7 36 22.3 32.8 37.3MAIN 36-45 31.5 500.0 -12.4 45 31.9 495.0 -14.9SR 36-45 32.7 500.0 -12.4 36 31.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.4 471.0 8.0SR 12 5.9 488.0 8.0MAIN 45 6.4 471.0 8.0SR 12 5.9 488.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00438.8 m60Insertion Loss (dB)504030201000250 MHz500100