Title: økernvn 94.pdf
002550 MHz75100100ACR-F @ Remote (dB)80604020100002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: D4134 Date / Time: 09/10/2013 02:27:22 Headroom 13.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]56 89 6 2.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.2 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.4 70.3 34.8 36 14.5 82.0 30.7