Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]13.6 59 1 2.30Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]34.7 493.0 41.3Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.3 461.0 29.7 45 9.1 461.0 26.9SR 36-45 8.1 409.0 31.1 36 8.7 477.0 26.1MAIN 36-45 8.3 461.0 29.7 36 10.2 496.0 25.2SR 36-45 8.4 477.0 28.9 36 9.2 486.0 25.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.4 4.3 52.7 45 14.7 2.4 54.7SR 12-45 16.4 4.4 52.4 45 14.6 2.5 54.3MAIN 36-45 17.3 475.0 11.7 45 19.2 466.0 8.9SR 45-36 17.3 476.0 11.7 36 19.6 476.0 8.70100806040200250 MHzACR-F (dB)