Title: +038=30.001-NI004._04-V67--02 Oppleggskjema kjøling.pdf
MM 35x,X kW, xXxX l/hIkke utleidDN20+03=370.101-OE032 0.182 L/sMM 35Uniconsult2.3 kW, 655 l/hDN 100Nord / akse A370.101DN 1007HiFiSOMA370.101 Kombibaffel og reserver (syd / akse D)Beregnet behov bafler plan 3-10 v/ 100% samtidighet 48 kW (15 / 18°C) -Antatt behov kjøl/frys pareto plan 9 16 kW (15 / 30°C)DN25+10=370.101-OE105 0.321 L/sMM 424.0 kW, 1156 l/hParetoDN32+09=370.101-OE095 0.397 L/sMM 425.0 kW, 1429 l/hParetoDN32+08=370.101-OE085 0.423 L/sMM 425.3 kW, 1523 l/hParetoDN 32+07=370.101-OE075 0.459 L/sMM 425.8 kW, 1652 l/hDN40+06=370.101-OE065 0.541 L/sMM 546.8 kW, 1948 l/hParetoDN40+05=370.101-OE055 0.522 L/sMM 426.6 kW, 1879 l/hColliers/McKinsey+04=370.101-OE045MM 42x,X kW, xXxX l/hIkke utleidDN25+03=370.101-OE035 0.214 L/sMM 352.7 kW, 770 l/hUniconsultDN 100Syd / akse DDN 100Kjøling purewater+U1=370.104-OE90188HiFi