Title: 1 etg del 2.pdf
SR 36 3.0 24.5 19.1MAIN 45 6.9 235.5 10.3SR 36 8.6 238.5 10.260500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T1166 Date / Time: 10/21/2013 08:07:46 AM Headroom 13.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]202 319 21 8.5