Title: Hardware Installation Guide.pdf
The manufacturing parameters which include the serial number, etc. are invalid. The module must be returned for repair.revision 6 — 313LNL-1200-U Output Control Module58MountingThe OCM can be mounted in the LNL-AL400ULX or LNL-AL600ULX-4CB6 and the LNL-CTX or LNL-CTX6 enclosure using the Universal Mounting Plate (UMP) LNL-CONV-U1.Mounting the OCM in the LNL-AL400ULX and LNL-CTX314 — revision 6Hardware Installation GuideMounting the OCM in the LNL-AL600ULX-4CB6 or LNL-CTX6revision 6 — 315LNL-1200-U Output Control Module59WiringFor UL installations, refer to section UL Listed Installations on page 321.59.1Unsupervised Alarm Inputs: Power Fail and External (Cabinet) TamperThe Output Control Module features two (2) unsupervised alarm inputs that can be used for power fail and external (cabinet) tamper monitoring. These inputs are connected using the PFL (power fail) and EXTMP (cabinet tamper) contact terminals located on the Output Control Module.