Title: 370.011 RP100, RP400 og RP500 Siemens Trykkfoler.pdf
0…10 V 0…10 V 0…10 V 0…10 V 0…10 V 0…10 V 0…10 V 0…10 V 0…10 V 0…10 V 4…20 mA 4…20 mA 4…20 mA 4…20 mA 4…20 mA4…20 mA 4…20 mA 4…20 mA 4…20 mA 4…20 mAWhen ordering a pressure sensor, please provide quantity, type reference, stock number and product name.Quantity 1Type ref. (ASN) QBE2003-P1Stock number (SSN) S55720-S290Product Name Pressure sensorAny accessories required must be ordered separately.Type ref.AQB2004AQB2001Stock number (SSN) S55720-S318S55720-S116NameFixing bracket for sensor (for remote mounting). Mounting kit for remote mounting with 1 m copper capillary line. Pressure connection with G ⅛" or G ½" outer threadingData sheetA6V10434028A6V10434028The pressure sensors operate on the piezo-resistive measuring principle. The ceramics diaphragm (thick-film hybrid technology) acquires the pressure through direct contact with the medium. The measurement is converted electronically into a linear output signal of DC 0...10 V or DC 4…20 mA.Pressure sensors QBE2x03-P...