Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
28.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.6 493.0 29.4 36 7.4 462.0 26.8SR 36-45 4.9 476.0 29.7 36 6.4 462.0 26.8MAIN 36-45 7.6 493.0 29.4 36 8.3 493.0 25.3SR 36-45 5.0 498.0 29.3 36 7.1 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.1 444.0 12.3 45 16.5 5.9 46.9SR 78-45 16.0 471.0 11.8 45 16.2 475.0 8.7MAIN 45-78 16.6 500.0 11.3 45 17.4 496.0 8.3SR 78-45 16.2 500.0 11.3 45 16.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 28.5 60.8 31.7 78 29.0 67.5 27.7SR 36-45 24.1 59.5 32.0 36 24.6 68.5 27.5MAIN 36-45 36.5 498.0 -12.3 36 36.2 493.0 -14.8SR 36-45 33.7 499.0 -12.3 36 35.0 498.0 -15.10804000250 MHzACR-N (dB)