Title: Data tester Smestad skole - Detaljert.pdf
Worst Margin: Local: 36-45 30,0 26,7 3,3 500,00Remote: 36-45 30,0 26,7 3,3 499,00Worst Value: Local: 36-45 30,0 26,7 3,3 500,00Remote: 36-45 30,0 26,7 3,3 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,4 10,3 10,1 496,00Remote: 45-12 20,9 10,3 10,6 496,00Worst Value: Local: 12-45 20,4 10,3 10,1 496,00Remote: 45-12 20,9 10,3 10,6 496,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,0 23,8 4,2 500,00Remote: 36 29,2 23,8 5,4 500,00Worst Value: Local: 36 28,0 23,8 4,2 500,00Remote: 36 29,2 23,8 5,4 500,00PS-ACRF: Pass Worst Margin: Local: 12 73,2 61,2 12,0 1,00Worst Value: Local: 45 19,4 7,2 12,2 498,00Remote: 45 72,0 60,0 12,0 1,15Remote: 45 19,3 7,2 12,1 499,00