Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Watchdog: This module cannot be used on the base address 240, because it would interact with the watchdog, and would cause a malfunction.For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD2 components.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-92Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.H1106.15.2 PCD2.H110, general purpose counting and measuring moduleup to 100 kHzApplicationMeasuring and fast counting module for general counting and simple motion control tasks; also for specific applications such as frequency measurement, period and pulse length measurement, etc. The module is equipped with an FPGA (Field Programmable Gate Array) and can be programmed for special high volume applications by using a plug-in PROM.Technical dataNumber of systems: Counting range: Counting frequency: Data protection: