Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The following table gives the heights of the run components that can be connected to a Canalis interface of a given height:Height of the Canalis interface (J) (mm)Height of the run component (K) (mm)16474, 104, 124, 164244164, 204, 244404244, 324, 404The position of the guides on the Canalis interface must be adapted to the rating of the run component.QGH3492101-01 11/201851Switchboard Connections52QGH3492101-01 11/2018Canalis KTTap-off UnitsQGH3492101-01 11/2018Installation of Tap-Off UnitsChapter 5 Installation of Tap-Off UnitsWhat Is in This Chapter?This chapter contains the following topics:Installation of Plug-In Tap-Off UnitsInstallation of Bolted Tap-Off UnitsQGH3492101-01 11/2018TopicPage545853Tap-off UnitsInstallation of Plug-In Tap-Off UnitsIntroductionTap-off units are used to connect loads or secondary runs. They comply with installation standards and regulations (IEC 60364) irrespective of the earthing system (TT, TNS, TNC, or IT).