Title: økernvn 94.pdf
SR 45-12 25.4 92.0 19.3 45 26.0 90.3 16.501008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.9 14.8 38.4 12 20.2 14.6 35.5SR 12-36 17.8 22.1 33.8 36 20.1 22.1 30.8MAIN 12-36 19.7 98.0 12.3 12 21.5 98.0 9.3SR 12-36 20.5 99.5 12.0 12 22.3 99.8 8.901008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 5.2 17.6 19.0SR 36 4.2 17.6 19.0MAIN 36 7.8 40.3 16.0SR 36 8.2 75.8 13.201008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002221 ft60Insertion Loss (dB)