Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]163 255 15 6.9163 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 0.6 * 228.5 36.0 36 0.1 * 244.5 32.9SR 36-450.5 *242.0 35.6 36 0.4 *238.0 33.1MAIN 36-45 0.6 248.5 35.4 36 0.1 244.5 32.9SR 36-45 0.5 242.0 35.6 36 0.4 238.0 33.110080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.1 242.5 16.5 36 17.3 181.5 16.0SR 45-36 14.9 243.5 16.5 45 16.7 210.5 14.7MAIN 45-36 15.2 248.5 16.3 36 17.8 249.0 13.3SR 45-36 15.1 250.0 16.2 36 17.8 249.5 13.2010080604020050100150MHzACR-F (dB)2002500100