Title: Hardware Installation Guide.pdf
0 1 2 3 4 5 6 7 8 9 * #Hardware Installation Guide32 Downstream Devices TotalDownstream Communications • Four 2-wire ports • Two 4-wire ports • Combination 2 and 4 wire portsEOL Termination RequiredInput/Output Control Module(s)revision 6 — 267LNL-1100 Input Control Module44Specifications**The LNL-1100 series 2 is for use in low voltage, class 2 circuits only. These specifications are subject to change without notice.Primary power: 12 to 24 VDC + 10%, 350mA maximum - -12 VDC @ 300 mA nominal 24 VDC @ 220 mA nominalOutput: Two (2) outputs, Form-C, 5A @ 28 VDC resistiveInputs: - -Sixteen (16) unsupervised/supervised, standard EOL: 1k/1k ohm, 1%, 1/4 watt Two (2) unsupervised, dedicated for cabinet tamper and UPS fault monitoringCommunication: RS-485, 2-wire, 9600 to 115,200 bps-Cable requirements: - -