Title: økernvn 94.pdf
MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D4189 Date / Time: 09/10/2013 05:02:52 Headroom 6.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]188 289 12 8.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.3 247.0 35.4 36 7.0 247.0 32.8SR 36-78 6.3 157.5 38.6 78 8.1 157.5 36.0MAIN 36-78 8.3 247.0 35.4 36 7.0 247.0 32.8SR 36-78 7.4 238.5 35.7 78 9.2 238.5 33.010080604020NEXT (dB)