Title: V20-05-02 VVS-anlegg plan 5 - DM3-1.pdf
XC111400x400 UK=2174SZ002T 1400 x400SZ002T 1400 x400700x600 UK=253 1400x600 UK=253 1400x600 UK=11581400x400 UK=2414 1400x400 UK=19521400x400 UK=2414 1400x400 UK=1702Gold RXF 30 360.005310.102: Cu 28mm370.104: DN 100mm 370.104: DN 100mm320.101: 42mm 320.101: 42mm 310.001: MA 58mm1400x600 1400x400310.003: MA 110mmLD022T Maks:90 m³/h Kjøling: 300 W 0.025 L/s Varme: 240 W 0.006 L/sSnitt 1InntakAvkastTeknisk 5-5161:60+05 = 360.005 - OE 902+05 = 360.005 - OE 90100LD022T Maks:115 m³/h Kjøling: 300 W 0.025 L/s Varme: 650 W 0.015 L/s1LD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/sLD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/sLD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/s2LD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/s3LD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/sLD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/s