Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
[Pair 36] [Pair 36] [Pair 36]30.8 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.7 305.0 33.9 36 7.1 310.0 31.1SR 36-78 6.9 191.0 37.3 36 8.4 218.0 33.7MAIN 12-36 7.5 492.0 28.2 36 7.8 470.0 26.4SR 12-36 9.8 498.0 27.9 36 9.8 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.8 499.0 11.3 45 19.6 493.0 8.4SR 36-45 17.9 495.0 11.3 45 19.4 494.0 8.4MAIN 45-36 17.8 499.0 11.3 45 19.7 499.0 8.3SR 36-45 17.9 495.0 11.3 45 19.4 494.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.0 89.5 26.0 36 22.1 90.0 23.4SR 36-45 21.2 89.5 26.0 36 21.7 89.3 23.5MAIN 12-36 36.9 492.0 -11.9 36 38.5 492.0 -14.7SR 12-36 39.3 499.0 -12.3 36 39.3 498.0 -15.10804000250 MHz