Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Site 1/ Building 1/ Storey 10 / Kontor 5 / Room summaryKontor 5B a2Clearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 46.1%, Floor 20.0%, Light loss factor: 0.80EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 3 Perpendicular illuminance (adaptive) [Ix] 578 (= 500) 395 669 0.68 0.59 Surrounding area: 0.500 m 2 Sunounding area 3 Perpendicular illuminance (adaplive) [IxX] 422 (= 300) 290 535 0.69 0.54 3 Background area 3 Perpendicular illuminance (adaptive) [Ix] 235 (= 100) 121 350 0.51 0.35 Wall zone: 0.500 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 4 iGuzzini illuminazione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 114.3HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 11248 98.4 114.3Lighting power density: 6.61 W/m? (Floor area of room 14.88 m?) Consumption: 170 - 270 kWh/a of maximum 550 kWh/a