Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-45 18.3 500.0 11.3 45 18.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.4 73.5 29.0 36 24.2 74.5 26.3SR 36-45 26.1 78.8 28.0 36 27.0 78.8 25.4MAIN 36-45 40.4 500.0 -12.4 36 40.2 500.0 -15.3SR 36-45 37.3 500.0 -12.4 36 37.6 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.2 500.0 8.0SR 12 5.8 500.0 8.0MAIN 12 7.2 500.0 8.0SR 12 5.8 500.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00425.0 m60Insertion Loss (dB)504030201000250 MHz500