Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 16.8 463.0 11.9 45 17.2 475.0 8.7MAIN 78-45 17.5 493.0 11.4 45 17.9 493.0 8.4SR 78-45 17.3 499.0 11.3 45 17.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.2 46.5 35.4 45 23.5 43.0 33.9SR 12-36 27.0 135.5 19.0 36 27.1 46.3 33.0MAIN 12-36 35.2 498.0 -12.3 36 34.4 499.0 -15.2SR 36-45 33.4 499.0 -12.3 36 33.6 488.0 -14.50804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 9.2 32.0 18.5SR 12 6.3 481.0 8.0MAIN 45 9.5 490.0 8.0SR 12 6.3 481.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS