Title: FDV 16678-2.pdf
25 - 75 Connectable conductor cross section multi-wired mm² 1 - 25 Connectable conductor cross section solid-core mm² 1 - 25 Approvals Product Standards IEC/EN 60947-2; IEC/EN 60898; UL 1077; CSA-C22.2 No. 235; CE marking UL File No. E177451 UL Category Control No. QVNU2, QVNU8 CSA File No. 204453 CSA Class No. 3215-30 North America Certiﬁcation UL recognized, CSA certiﬁed Conditions of Acceptability Supplementary Protector only Suitable for Branch Circuits; not as BCPD Current Limiting Circuit-Breaker No Max. Voltage Rating 480Y/277 VAC; 96 VDC Degree of Protection IEC: IP20; UL/CSA Type: - 03/07/2019Eaton 278760 ED2019 V53.0 EN3 / 9