Title: 2 etg del2.pdf
RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: D2206 Date / Time: 10/10/2013 02:21:04 PM Headroom 1.3 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]240 380 27 10.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 246.0 35.5 36 1.6 246.0 32.8SR 36-78 8.8 229.0 36.0 78 9.5 241.5 33.0MAIN 36-45 1.3 246.0 35.5 36 1.6 246.0 32.8SR 36-78 9.1 241.5 35.6 78 9.5 242.0 32.910080604020NEXT (dB)