Title: økernvn 94.pdf
Cable ID: D4007 Date / Time: 09/10/2013 01:11:01 Headroom 17.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]142 218 8 6.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.9 91.3 33.0 36 19.5 39.8 35.9SR 36-78 17.9 39.0 39.0 36 19.0 39.8 35.9MAIN 12-36 17.9 91.5 32.9 12 19.9 96.3 29.6SR 45-78 17.9 93.0 32.8 45 19.8 92.8 29.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 21.8 100.0 18.6 12 22.9 3.5 44.7