Title: 40 Bender brukermanual.pdf.pdf
RCMS460-490_D00067_03_M_XXEN/12.201759OperationExample 2: Connection of external Bender measuring current transformersBender-MessstromwandlerBender- MessstromwandlerSettings: Factor = (X / N)= 100/1 = *100Measuring current transformer monitoring: On60RCMS460-490_D00067_03_M_XXEN/12.2017OperationExample 3: The wire to be monitored is "wound" several times through the Bender current transformer in order to amplify the signalSetting: Factor: Measuring current transformer monitoring: On/32. Response value The response value is the value at which an alarm is output. In case of digital inputs, set the status (0 or 1) at which an alarm is to be signalled.