Title: FAS - Flussiggas.pdf
zone II, with 2 solenoid valves at inlet of vaporizer and one safety relief valve at outlet of vaporizer, power supply 24 kW, threephase current 400 V/50 Hz, control box at vaporizer, wired ready for connectionliquid trap with backlogpressure gauge 025 bar with shuttoff valve before and behind the gas pressure regulator ;gas pressure regulator type RB 4700 (FAS No. 164130), with safety shutoff valve and safety blowoff valve for upper and lower shutdown, DN 25 PN 25, pre pressure up to 16 bar, back pressure is adjustable between 0,52,5 bar,*** outlet pressure 300 mbar *** documentation:CERegistration according to PED 97/23/EGcategory Il, module A1,with name plate CE 0685 ,including certificate of conformityCountry of Origin: European UnionR R L L R e S ewith preferential origin: item 1subtotal EURFliissiggas-Antagen GmbH Norddeutsche LandesbankTelefon: +49/53 41/86 97-0 Konto 3 552 387 BLZ 250 500 00Telefax: +49/53 41/86 97-11 SWIFT: NOLADE 2H nitp: Nlwww.fas.de