Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
[Pair 12] [Pair 12] [Pair 12]32.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.0 242.0 35.6 78 8.2 256.0 32.5SR 36-78 5.3 399.0 31.4 36 7.3 457.0 27.1MAIN 12-36 8.6 498.0 27.9 36 9.4 498.0 25.1SR 12-36 7.1 499.0 27.9 36 8.0 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.5 498.0 11.3 45 20.9 500.0 8.3SR 36-45 20.6 500.0 11.3 36 21.4 464.0 8.9MAIN 36-45 20.5 498.0 11.3 45 20.9 500.0 8.3SR 36-45 20.6 500.0 11.3 45 21.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 24.8 132.0 19.5 78 26.1 125.5 17.8SR 36-78 26.2 129.5 19.8 36 26.2 142.5 15.5MAIN 12-36 40.3 498.0 -12.3 36 41.1 498.0 -15.1SR 12-36 38.8 499.0 -12.3 36 39.7 498.0 -15.10804000