Title: etg u1.pdf
Project: OKERNVEIEN 94 ETG.U1 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T0013 Date / Time: 10/22/2013 01:25:35 PM Headroom 11.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]231 367 26 10.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 11.8 45.0 38.0 78 13.8 44.8 35.0SR 12-36 11.3 86.0 33.4 36 13.0 86.0 30.4MAIN 45-78 13.1 95.0 32.7 45 15.4 95.0 29.7SR 12-36 12.0 100.0 32.3 36 13.5 100.0 29.310080604020NEXT (dB)