Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group)Internal current consumption: (from +5 V bus)1…20 mA typically 10 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption:max. 48 mATerminals:Plug-in 10-pole spring terminal block (4 405 4954 0) or pluggable 10-pole screw terminal block (4 405 4955 0), both for wires up to 2.5 mm²1) With external protective diode 3) These ratings are not UL-listed2) With reverse voltage protectionThe Annex, Section A.3 "Relay contacts" contains measurement details and suggested wir- ing for the relay contacts. For safe switching and a long service life, these figures must be observed.6-36PCD3.A220LEDs and connection terminalsLED 0...7 Terminal 0Terminal01234567Description LabelAddress LabelA2 2 00 1 2 3 4 5 6 7 8 9A0 A1 A2 C C A3 A4 A5 + –24VDC0 2 2 A . 3 D C PC A V 0 5 2 A 2/s t u p t u O. l e R 6Terminal 9Output circuits and terminal designation