Title: 4. Leieavtaler.pdf
10. Most ignitable liquid floats on water and as such automatic sprinkler protection alone will not control the fire without emergency drainage. Depending on the quantities stored within the building, it may be recommended to install drainage within certain parts of the facility. The drainage should be installed in accordance with FM Global Property Loss Prevention Data Sheet 7-83, Drainage and Containment Systems for Ignitable liquids and designed to handle the total of the expected ignitable liquid release and the actual sprinkler discharge.This recommendation will be confirmed once the type and quantities of ignitable liquid has been established.2015-01-07: Only minor quantities to be used. No dedicated room in need of drainage.11. Design Cleanrooms in accordance with FM Global Property Loss Prevention Data Sheet 1-56, Cleanrooms. Please send specifications for the Cleanrooms to FM Global for review prior to any installation.