Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]23.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.4 492.0 29.4 45 9.4 492.0 26.5SR 36-45 6.0 489.0 29.5 36 6.9 496.0 26.5MAIN 12-45 8.4 492.0 29.4 45 9.4 492.0 26.5SR 36-45 6.2 495.0 29.3 36 6.9 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.1 420.0 12.8 45 13.5 2.9 53.1SR 78-45 13.9 435.0 12.5 45 13.5 2.6 53.9MAIN 45-78 14.4 441.0 12.3 45 14.6 466.0 8.9SR 78-45 14.1 441.0 12.3 45 15.1 478.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.0 30.5 40.6 45 18.4 28.0 39.2SR 45-78 18.5 39.0 37.6 45 19.0 27.9 39.2MAIN 12-45 31.4 492.0 -11.9 45 32.3 492.0 -14.7