Title: økernvn 94.pdf
604020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: D4089 Date / Time: 09/10/2013 01:25:53 Headroom 12.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]98 156 11 4.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.8 79.5 33.9 36 14.6 79.8 30.9SR 12-36 13.1 62.8 35.6 36 15.4 79.5 30.9MAIN 12-36 13.3 92.8 32.8 36 15.2 96.5 29.6SR 12-36 13.2 89.5 33.1 36 15.5 96.3 29.6100806040