Title: 2 etg del2.pdf
MAIN 12-36 10.6 41.8 36.3 36 12.3 41.8 33.9SR 12-36 11.1 41.8 36.3 36 12.8 41.8 33.9MAIN 36-45 20.3 249.0 4.8 36 19.9 246.0 2.4SR 36-45 20.5 246.0 5.1 36 20.5 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.8 47.3 17.3SR 45 3.7 47.0 17.3MAIN 45 7.3 219.0 10.6SR 45 7.6 240.5 10.2010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flw