Title: 32 Varmepumpe brukermanual.pdf.pdf
Communication interfaces for integration in 3rd party systems:Modbus RTUModbus TCPBACnet/IPLive data view in the browser.Mimic view in the browser (contact support for more information)Supported DevicesAll Danfoss AK2(A) controllers are supported as long they support the MMIGRS2 display,since the same protocol is used by both the display and the M2M2 gateway.3M2M2-10, User Guide - Rev. 2020-09-04Technical SpecificationsDimension:84x54x52 mmPower supply:12-24 V DCInterfaces:RS-485 (master) Built-in biasing Built-in termination (120 ohm)RS-485 (slave)CANbusEthernetMiscellaneous:1x button1x red status LED1x blue status LED1x green status LED4M2M2-10, User Guide - Rev. 2020-09-04Electrical WiringDanfoss AK2(A) controllerThere are two ways to connect the M2M2 to the Danfoss AK2(A) controller, eitherconnection via MMIGRS2 or through a direct connectionConnection via MMIGRS2