Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
For a complete description of the software features, refer to the UniVision and UniVision Pro documentation.19.4. DRY CONTACT INTERFACEThis series UPS has an independent dry contact interface. Please contact your local distributor for details. The following is the pin assignment and description of the DB-9 connector.19.4-1PinDescriptionI/OUPS Fail11UPS FailOutputSummary Alarm267BypassBattery Low23Summary AlarmGNDOutputInputGND34Remote ShutdownInputRemote Shutdown489UPS ONLine Loss56CommonBypassInputOutputCommon57Battery LowOutput8UPS ONOutput9Line LossOutputITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0020. TROUBLESHOOTINGPlease have the following information at hand before calling the After-Sales Service Department:Model number, serial numberDate on which the problem occurredLCD display status, Buzzer alarm status