Title: V20-06-01 VVS-anlegg plan 6 - DM1-1.pdf
ø200 UK=2643WISE IAQSF002T-160SF002T-200ø160 UK=2685370.101: 28 mm +c 2790370.101: 28 mm +c 279035mm35mm+06 = 370.101 - OE 066 0.270 L/sLD018T Maks:220 m³/h Kjøling: 470 W 0.037 L/s Varme: 515 W 0.012 L/s9LD018T Maks:230 m³/h Kjøling: 630 W 0.050 L/s Varme: 410 W 0.010 L/s10LD018T Q: 200 m³/h Varme: 260 W 0.006 L/sLD018T Maks:220 m³/h Kjøling: 335 W 0.026 L/s Varme: 420 W 0.010 L/s11LD018T Maks:220 m³/h Kjøling: 200 W 0.016 L/s Varme: 490 W 0.012 L/sOpp/ned 370.101: DN 100mm 370.101: DN 100mmSTAP/STAD DN25LD018T Maks:220 m³/h Kjøling: 200 W 0.016 L/s Varme: 490 W 0.012 L/s12LD018T Maks:220 m³/h Kjøling: 200 W 0.016 L/s Varme: 490 W 0.012 L/s13AUtsparing ø100 mmPlan 07Plan 07C400x600 UK=2350 400x600 UK=2350 400x1000 UK=2380400x1000 UK=2380Sluk 75mm400x1000 UK=2380Plan 07Plan 07ø500 UK=1995ø500 UK=1995Plan 0754 mm54 mm0 2 7 225.07 m25.07 m400x600 400x600400x1000 300x1200400x1000400x1000 400x1000360.024VBKBLF