Title: Aggregatkjøring.pdf.pdf
OACF1.02Purging sector1pcsTwin fan, PlugAir flow15000m³/hExternal pressure250PaPressure drop22PaStatic pressure (Designed at wet conditions)564PaTotal pressure583PaFan speed1519RPMMaximum fan speed1950RPMTotal efficiency by static pressure, incl. motor and speed control69.6%Total efficiency by total pressure, incl. motor and speed control72.0%K-factor (p=1.2 kg/m³)(2 x 280) 560Fan type - 2xLargeGR50I-ZID.GG.CRErP efficiency n(stat,A)75.2%ErP efficiency class N(actual)/ N(target)80.0 / 62ErP-conformityYesDirect driveMotorMotor typesEC motorMotor types-sizeZID.GG.CRMotor protectionTotal power(2 x 3.50 kW) 7.00kWSpeed (nominal)1950RPMSystemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.001-1/