Title: Ahlsell.pdf
4030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 22 Test Limit: EN50173 PL2 Class Ea Limits Version: V3.0 Date / Time: 05/20/2022 04:33:16 PM Operator: Pam Headroom 10.2 dB (NEXT 1,2-3,6) Cable Type: Cat 6 F/UTP NVP: 70.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 7,8]42.0 204 4 7.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]20.9 498.0 41.5Worst Case Margin Worst Case Value