Title: +135.01=564.007-XO001T_01-Montasje 5WG1_220_2DB31_bma_de_en_pille_norsk.pdf
Additional InformationExample of Operationwith push buttons: with LED’s:see figure 1a see figure 1bTechnical SpecificationsPower supply • Bus voltage: via KNX bus lineInputs • input signal voltage:provided by the push button interface. approx. 29 V DC (bus voltage) when the contact is openedinput signal current:when contact is closed: 0.2 mA DC per channel at moment of closing: pulse 0.1 Ainput signal delay:50 ms including contact debounceduration of input signal: min. 50 msduration of input signal: min. 50 msinput characteristic: configurable • signal cable set:input characteristic: configurable • signal cable set:length: 280 mm unshielded, may be extended up to 10 m (per channel) with twisted, unshielded cable Unused free ends must be insulated! - cross-section: approx. 0.22 mm² (0.56 mm Ø)Outputs • output signal voltage: