Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 20,0 10,2 9,8 498,00Remote: 12-45 20,4 10,2 10,2 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,0 23,8 4,2 498,00Remote: 36 28,3 23,8 4,5 500,00Worst Value: Local: 36 28,0 23,8 4,2 500,00Remote: 36 28,3 23,8 4,5 500,00PS-ACRF: Pass Worst Margin: Local: 12 66,1 54,3 11,8 2,20Worst Value: Local: 45 19,7 7,2 12,5 500,00Remote: 45 66,2 54,3 11,9 2,20Remote: 45 20,0 7,2 12,8 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:14Signature:______________________ Page: 135Copper Certification ReportCable Label: 521.002-UD-32 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:11:21 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: