Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Tallberg Elektro A/S Tlf.22796640Side:48GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.332332333333334334335335336336337337338338TEST RAPPORTResultat R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF097 16C2/003 27.11.2020 11:45KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF097 16C2/003 30.11.2020 12:00 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF097 16C2/003 26.11.2020 13:54RCD II: 27.0mAUci: 0.1V t: 204.8ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF098 16C2/003 15.12.2020 10:21 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩ