Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]23.1 101 2 3.65Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 411.0 31.1 36 9.2 477.0 26.1SR 12-36 8.6 453.0 30.1 36 9.2 453.0 27.3MAIN 12-36 9.1 495.0 28.1 36 9.6 495.0 25.2SR 12-36 9.5 500.0 27.8 36 9.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.4 7.4 47.9 45 20.4 498.0 8.3SR 45-78 18.4 6.9 48.5 45 20.4 500.0 8.3MAIN 36-45 20.3 498.0 11.3 45 20.4 498.0 8.3