Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
TEST RAPPORTResultatSPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 09:30Z-LINEZ: 0.79ΩIsc: 290A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 09:31Zs(rcd)Z: 0.73ΩIsc: 315A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 09:32RCD UbUc: 0.0V Rl: 1Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 09:32RCD tt: 57.2msUc: 0.3V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 09:33RCD II: 27.0mAUci: 0.0V t: 162.3ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 12:13Tallberg Elektro A/S Tlf.22796640Side:35GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.239239240240