Title: LNL_TS_1320s2.pdf
SpecificationsPrimary Power12 to 24Vdc ±10%, 550mA maximum (plus reader current) 12Vdc @ 450mA (plus reader current) nominal, 18.41 BTUs 24Vdc @ 270mA (plus reader current) nominal, 22.09 BTUsOutputs6 outputs, Form-C, 5A @ 28Vdc, resistiveInputs8 unsupervised/supervised, standard EOL: 1k/1k ohm, 1% 1/4 watt 2 unsupervised, dedicated for cabinet tamper and UPS fault monitoringReader InterfaceReader power: 12Vdc ±10% regulated, 125mA maximum each reader (jumper selectable and input voltage (VIN) must be 20Vdc mini- mum) or 12 to 24Vdc ±10% (input voltage passed through) 125mA maximum each readerReader Port CompatibilityWiegand Data 1/Data 0 Magnetic Clock/Data F/2F Single Wire Open Supervised Device ProtocolMechancialDimension: 6” (152mm)W x 8” (203mm)L x 1” (25mm)H Weight: 11 oz. (312g) nominalEnvironmental Temperature Operating: 32°F to 158°F (0°C to +70°C)Storage: -67°F to 185°F (-55°C to +85°C)Humidity0% to 95% RHNCCompliance Approvals