Title: Hardware Installation Guide.pdf
Eight (8) supervised, End of Line resistors, 1k/1k ohm, 1% 1/4 watt standard One (1) unsupervised, dedicated external (cabinet) tamper One (1) unsupervised, AC power failReader interface: -Reader power (per reader): voltage 12 VDC +/-10% (optional 5 VDC +/-5% jumper selectable, current 400 mA maximum to 50°C, derate to 300 mA for 70°C) Reader LED output: open collector type switching (sinking) 10 mA each Reader buzzer output: open collector type switching (sinking) 10 mA each Reader data inputs: 2-wire RS-485, Wiegand Data1/Data0, Clock and Data Does not support Bioscrypt readers or the LNL-CK keypad- - -Upstream communication: RS-485, 2-wire, 2400 to 38400 bps -Does not support encryptionDownstream communication: Does not support RS-485 -- -Cable requirements: - -