Title: 1 etg del 2.pdf
Cable ID: T1004 Date / Time: 10/17/2013 02:08:54 PM Headroom 3.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]78 119 4 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.4 247.5 35.4 36 6.4 247.0 32.8SR 12-36 3.9 225.5 36.1 36 4.7 95.3 39.7MAIN 12-36 5.4 247.5 35.4 36 6.4 247.0 32.8SR 12-36 4.3 247.0 35.4 12 5.4 247.0 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.8 4.1 51.9 45 17.4 3.1 51.3