Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Technical dataAutomatic mode Output ranges: Channels:Resolution: Digital representation: Load resistance: Accuracy at 25°C:* Temperature error (0…+55°C): Short circuit protection: Time constant of output filter: * Tolerance value for output signals > 100 mV Manual operation mode Output ranges Range of settings for potentiometer Output voltage at 0° Output voltage at 140° Output voltage at 280° Accuracy at end stop Linearity error of potentiometer moment of potentiometer Lifetime of potentiometer Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: ConnectionsVoltage 0..+10 V 4 analogue outputs O0…O3 (3 with manual operation O0…O2) 10 mV 10 bits (0..1023) > 3 kΩ ±0.4 % ± 0.25 %, 100 ppm/K or 0.01 %/K Yes (permanent) typically 1 msVoltage 0…10 V 0°…280° ±5° typically 0 V typically 5 V typically 10 V ±5 % ±20 % < 0.01 Nm > 5000 cycles typ. 35 mA / max. 45 mAtyp. 20 mA / max. 35 mA