Title: 1 etg del 2.pdf
Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: D1058 Date / Time: 10/17/2013 12:17:14 PM Headroom 0.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]290 458 30 12.3290 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]5.3 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 0.9 * 229.0 36.0 36 1.0 * 246.0 32.8SR 12-360.5 *244.5 35.5 36 0.0 *243.0 32.9