Title: økernvn 94.pdf
Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T4110 Date / Time: 09/10/2013 09:58:44 Headroom 14.8 dB (NEXT 36-45) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]100 159 11 4.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.4 79.0 34.0 36 19.4 59.0 33.1SR 36-45 14.8 79.5 33.9 36 15.9 59.0 33.1MAIN 36-45 18.4 92.5 32.9 45 19.7 92.8 29.8SR 36-45 14.9 99.8 32.3 36 16.3 100.0 29.310080604020NEXT (dB)