Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]6.5 29 1 1.41Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]37.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 4.7 484.0 28.6 36 5.2 484.0 25.7SR 36-78 6.4 484.0 28.6 36 5.6 485.0 25.7MAIN 36-78 5.4 500.0 27.8 36 5.9 500.0 25.0SR 36-78 6.5 485.0 28.5 36 5.6 485.0 25.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.2 5.9 49.9 45 21.1 7.3 45.0SR 78-45 19.2 5.9 49.9 45 20.7 4.6 48.9MAIN 45-36 20.9 497.0 11.3 36 23.8 498.0 8.3SR 36-45 21.0 497.0 11.3 45 23.4 496.0 8.30100806040200250 MHzACR-F (dB)