Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
For programming the modules, an FBox is available.xx7 and RIOs:the firmware reads in the values according to the configuration (I/O Builder or network configurator)Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs. For details, please refer to the “Watchdog” section, which describes the correct use of the watchdog in conjunction with PCD2 components.5-77Analogue output modules5.10Analogue output modulesPCD2.W400 PCD2.W410 PCD2.W600 PCD2.W6104 analogue outputs 8 bit, 0 … 10 V 4 analogue outputs 8 bit, 0 … 10 V, 0 … 20 mA, 4 … 20 mA *) 4 analogue outputs 12 bit, 0 … 10 V 4 analogue outputs 12 bit, 0 … 10 V, 0 … 20 mA, 4 … 20 mA *)) jumper selectableI/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24 V are disconnected from the power supply.5-78PCD2.W4x05.10.1PCD2.W4x0, analogue outputs, 4 channels, 8 bit resolutionApplication