Title: Data tester Smestad skole - Detaljert.pdf
Limit 100,0 - 555,0 50,0 25,0Margin 67,6 - 387,0 41,0 19,1Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,5 3,0 2,5 1,75Worst Value: Local: 36 13,9 43,6 29,7 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 15,2 9,0 6,2 313,00Remote: 12 23,7 16,8 6,9 52,00Worst Value: Local: 12 15,2 9,0 6,2 313,00Remote: 36 16,8 8,0 8,8 483,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 30,5 26,7 3,8 499,00Remote: 36-45 29,2 26,7 2,5 498,00Worst Value: Local: 36-45 30,5 26,7 3,8 499,00Remote: 36-45 29,2 26,7 2,5 498,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):