Title: økernvn 94.pdf
SR 36-12 17.8 4.8 50.7 12 18.2 3.6 50.0MAIN 12-45 19.8 223.0 17.2 45 20.9 223.5 14.2SR 12-45 19.8 223.0 17.2 45 21.2 223.5 14.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.5 30.8 40.2 36 17.5 30.8 37.7SR 12-36 11.9 31.5 39.9 36 14.0 32.3 37.2MAIN 36-78 27.3 235.5 6.1 78 28.4 249.5 2.1SR 36-45 18.3 249.5 4.7 36 18.7 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 6.1 244.5 10.1SR 45 6.5 101.0 14.0MAIN 36 6.1 244.5 10.1SR 45 6.8 244.0 10.1010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active