Title: BNNY-80P DM1-3 Omrapport.pdf
a. Office and circulation spaces b. In office areas, zones of no more than four workplaces c. Workstations adjacent to windows/atria and other building areas separately zoned and controlled. d. Seminar and lecture rooms: zoned for presentation and audience areas e. Library spaces: separate zoning of stacks, reading and counter areas.The electrical engineer confirms in Hea6.v03 that in cell offices the lighting is controlled through motion sensors, as well as manual switches. In office landscape the lighting can be controlled through motion sensors in areas <40 m2.Zones for lighting controls are shown on plans (Hea3.v01-02).Conclusion: the credit can be awarded.BREEAM-NOR ver.1.1 (2012) New Construction Assessment Report Template rev. 04: 15.01.2019BREEAM ID: BNNY-80PDronning Mauds gate 1-3Minimum BREEAM StandardsHealth & WellbeingRating LevelPGVGEOHea 7 – Potential for Natural VentilationMin. credits to achieve ratingNumber of credits achieved:0Aim