Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-36 15.4 487.0 11.5 45 16.0 418.0 9.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 19.9 37.3 38.2 45 19.9 33.5 37.0SR 36-78 22.0 36.3 38.5 36 21.2 36.3 36.1MAIN 12-45 33.1 499.0 -12.3 36 32.5 499.0 -15.2SR 36-45 31.4 499.0 -12.3 36 32.0 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.4 480.0 8.0SR 12 6.1 499.0 8.0MAIN 12 6.4 480.0 8.0SR 12 6.1 499.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00438.3 m60Insertion Loss (dB)504030201000250 MHz500