Title: Hardware Installation Guide.pdf
Jumper J4 is used to configure the EOL termination status the Single Reader Interface Module board. There are two possible configuration options that can be used to install this jumper: “On” and “Not On.”Termination ON position for J4J4Termination OFF position for J4J4338 — revision 6Hardware Installation Guide64SpecificationsThe LNL-1300 series 2 is for use in low voltage, class 2 circuits only.Primary power: 12 to 24 VDC + 10%, 150mA maximum (plus reader current) - -12 VDC @ 110mA (plus reader current) nominal 24 VDC@ 60mA (plus reader current) nominalOutputs: Form-C contacts: K1: 5A @ 28 VDC, K2: 1A @ 28 VDCInputs: - -2 supervised, End of Line resistors, 1k/1k ohm, 1% 1/4 watt standard 1 unsupervised, dedicated for cabinet tamperReader Interface: - - - -