Title: 360.013 Hybra Modul A 8,00-2,0 +- 22.800 m³h -Datakjøring Fra leverandør.pdf
set WIKA 0-500 Pa build up -revision door with dual hinge360,013 /26,0 / 55 22,8 / 67 80,4 / % 25,8 kWCooling mode: intake Temperature °C / humi. % outlet Temperature °C / humi. %22,0 / 50 25,2 / 41190 mm22.800 m³/h 2,3 m/s 62,4 / 66,4 14,0 / 22,0 Water 70 / 30 6,1 kPa 0,38 / 40 DN 1 / 16 2,0 / 15 1 / 1 Stk CU / AL / GICondenser coil Volume flow Air speed Heating output (kW) Temperature air intake / outlet °C Medium type Evaporation temperature Pipe rows / Pressure loss, air (Pa) Blade spacing (mm) / Content (l) Number of coils vertically / horizont. Connection nom. width, inlet / outlet Material pipes / blades / framework connection decoupled (temperature/structure-borne sound) Dimensions WxD (mm) Material22.800 m³/h 2,3 m/s 84,6 26,0 / 37,4 R407C 47 °C 5 / 38 4,0 / 57 1 / 1 Stk 54 / 35 DN CU / AL / GI2.480 / 1.240 galvanized steelDamper Pressure loss / Air speed (m/s) material Frame / Blade Total torque / Number of axes Dimensions WxD (mm)