Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]29.2 127 2 4.41Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.6 474.0 29.7 45 10.1 475.0 26.9SR 36-45 7.8 500.0 29.2 45 7.6 498.0 26.4MAIN 12-45 9.6 474.0 29.7 36 11.4 499.0 25.0SR 36-45 7.8 500.0 29.2 36 8.9 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.8 31.1 35.4 45 14.6 2.6 53.9SR 36-45 15.8 31.1 35.4 45 14.5 2.6 53.9MAIN 78-45 16.7 500.0 11.3 45 17.4 500.0 8.3SR 45-78 17.0 500.0 11.3 45 17.5 497.0 8.30100806040200250 MHzACR-F (dB)