Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]17.3 75 1 2.79Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.1 359.0 32.3 36 7.3 359.0 29.6SR 12-36 5.0 401.0 31.3 36 7.1 456.0 27.1MAIN 12-36 6.8 482.0 28.7 36 8.4 482.0 25.8SR 12-36 6.7 497.0 28.0 36 8.2 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 20.1 425.0 12.7 12 21.1 374.0 10.8SR 12-36 20.2 425.0 12.7 36 21.0 474.0 8.7MAIN 36-45 20.8 496.0 11.3 45 21.9 500.0 8.3