Title: +038=360.012-#####._06-BA-ESR NI-DV Controller Nicotra Gebhardt - Operating Instruction.pdf
„NC“ „C“ „C“ „NC“ „C“ „C“ „NC“ „C“ „C“ „NC“ „C“ „NC“ „C“ „C“ „NC“ „NC“Insufficient supply voltage Excessive supply voltage Excessive power consumption by motor Excessive temperature inside NI-DV (> 95°C) Phase fault; one or more phases disconnected (L1, L2, L3) Blocked motor Motor current has reached its limit Internal hardware fault Wrong direction of rotation Fault in internal EEPROM circuit Stopped after 5 attempted restarts within 60 min Fault in braking chopper Phase fault on motor power supply (U, V, W) Internal communication error Excessive ripple voltage External 24VDC power supply overloaded Table 5-1: Abbreviations: „C“ „NC“ „RP“ „SA5“ „S“Critical alarm Non-critical alarm Reduced performance Motor stops after 5 restarts caused by same fault within 60 min Motor stops immediately„RP“ „SA5“ „SA5“ „RP“ „SA5“ „SA5“ „RP“ „SA5“ „SA5“ „RP“ „S“ „RP“ „SA5“ „SA5“ „RP“ „RP“DE-24/36BA-ESR_NI-DV 1.0 – 11/2015EnglishLED indications • NI-DV is equipped with a two- indicates