Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
see module overview 500 V, galvanic separation of outputs to Saia PCD®, channels themselves not separated 12 bits (0 … 4095)Resolution (digital representa- tion): Measuring principle: Input resistance:non-differential, single-ended W305: W315: W325: ± 0.15 % Accuracy at 25 °C Repeating accuracy: ± 0.05 % Temperature error (0 … +55 °C) ± 0.25 % Conversion time A/D: Overvoltage protection:13.5 kΩ / 0.1 % 120 Ω / 0.1 % 13.7 kΩ / 0.1 %≤ 2 ms W305: W325: W315: yes Typically 2.4 ms < 60 mA± 40 VDC (permanent) ± 40 VDC (permanent) ± 35 mA (permanent)