Title: Eurotester målerestultat.pdf
Isc: 250A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 95.1A Isc(0.76%): 190A Isc(1.15%): 288ABytesteinen 1 / =433.202 / SIKRING13 30.03.2021 13:45:45RCD II: 22.5mAUc: 9.1V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING13 30.03.2021 13:46:07R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING13 30.03.2021 13:46:26R LOW OhmR: 0.08ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING14 30.03.2021 13:59:24Z-LINEZ: 0.44ΩIsc: 524A Sikringstype: C SIKRING I: 25A SIKRING T: 0.4s Isc_lim: 250.0A Isc(0.38%): 199A Isc(0.76%): 398A Isc(1.15%): 603ABytesteinen 1 / =433.202 / SIKRING14 30.03.2021 13:59:44Testet av: Andreas PedersenSide:5GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr.3333343435353636373738383939TEST RAPPORTResultatRCD II: 22.5mAUc: 9.5V Idn: 30mA type: AC Ulim: 50V