Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
LABEL r0 r1 r2MIN. 0.1 -99 r1MAS. 15 r2 99U.M. °C/°F (1) °C/°F (1) °C/°F (1)MAIN REGULATOR working setpoint differential minimum working setpoint maximum working setpointLABEL C0 C2MIN. 0 0MAS. 240 240U.M. min minCOMPRESSOR PROTECTIONS compressor delay since you turn on the instrument minimum time the compressor remainsturned offLABEL d0d3 d4 d5 d6MIN. 00 0 0 0MAS. 9999 1 99 1U.M. Hmin - min -DEFROST defrost interval; also look at d8 (5) 0=the defrost at intervals will never be activated defrost duration (0=the defrost will never be activated) defrost when you turn on the instrument (1=YES) defrost delay when you turn on the instrument (only if d4 = 1) temperature shown during the defrost 0=cabinet temperature1=if to the defrost activation the cabinet temperature is below “working setpoint+ r0”, at most “working setpoint + r0”; if to the defrost activation the cabinet temperature is above “working setpoint +r0”, at most the cabinet temperature to the defrost activation (6)