Title: økernvn 94.pdf
100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: D4056 Date / Time: 09/10/2013 01:01:01 Headroom 14.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]268 424 29 11.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]5.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.5 67.0 35.2 36 16.5 88.3 30.2SR 36-45 19.3 25.1 42.1 36 21.4 25.4 39.0MAIN 12-36 14.6 100.0 32.3 36 16.5 99.8 29.3SR 36-45 23.4 92.3 32.9 36 24.4 91.5 29.91008060