Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
3 1500 8,77 6,49 1508 25,0 8,56 736 15,3 53 44 120 0,53SK 64 2 1280 6,93 5,18 1192 22,1 9,98 858 25,3 48 39 95 0,42 3,0 1,41 710 4,52 3,25 777 10,3 6,45 555 11,5 34 25 42 0,183 1820 8,89 6,84 1529 34,7 12,70 1092 38,8 58 49 170 0,74SK 66 2 1280 7,84 5,73 1348 20,0 7,74 666 13,0 48 39 95 0,42 3,6 1,11 710 4,99 3,53 858 9,0 5,23 450 6,5 34 25 42 0,183 1820 10,20 7,68 1754 32,0 9,80 843 19,5 58 49 170 0,74Condensate pump absorption: 10 W(E) = Eurovent certified performance. (*) = The sound pressure levels are 9 dB(A) lower than the sound power levels and apply to the reverberant field of a 100 m3 room and a reverberation time of 0.5 sec.5EmissionSkyStarCooling emission of 1 battery units (2 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.Model SpeedAir flowEWT 5 - LWT 10°C Total emissionWater flowSensible emissionEWT 7 - LWT 12°C Total emissionWater flowSensible emissionEWT 9 - LWT 14°C Total emissionWater flowSensible emission