Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
SR 12-36 21.9 500.0 11.3 12 22.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 36.5 322.0 0.6 36 38.1 321.0 -2.0SR 12-36 36.4 322.0 0.6 36 37.8 321.0 -2.0MAIN 36-45 40.9 500.0 -12.4 36 41.5 499.0 -15.2SR 12-36 42.4 497.0 -12.2 36 42.5 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.7 486.0 8.0SR 45 6.6 496.0 8.0MAIN 45 5.7 486.0 8.0SR 45 6.6 496.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasjeTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00411.0 m60