Title: økernvn 94.pdf
002550 MHz75100100ACR-F @ Remote (dB)80604020100002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: T3005 Date / Time: 09/11/2013 04:58:22 Headroom 13.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]149 236 16 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 20.9 33.8 40.0 36 22.2 88.3 30.2SR 12-36 13.8 79.3 34.0 36 14.4 99.5 29.3