Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
SkyStarEmissionCooling emission of 1 battery units (2 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.ECM Mod.SK 12SK 22SK 32SK 42SK 52Speed VdcHigh Med Low High Med Low High Med Low High Med Low High Med Low10 5 1 10 5 1 10 5 1 10 5 1 10 5 1EWT 5 - LWT 10°C Total emission kW 3,32 2,60 2,2 5,17 3,61 2,63 6,02 4,61 3,02 7,58 6,13 4,99 12,85 9,15 6,21Air flow Water flow l/h 570 448 379 888 621 453 1035 793 520 1304 1055 859 2210 1574 1068Sensible emission kW 2,33 1,80 1,51 3,55 2,43 1,75 4,18 3,15 2,02 5,27 4,21 3,39 8,88 6,18 4,12m3/h 535 380 310 710 445 310 880 610 360 1165 870 630 1770 1130 710EWT 7 - LWT 12°C Total emission kW 2,75 2,17 1,84 4,33 3,05 2,24 5,02 3,87 2,56 6,33 5,15 4,21 10,75 7,72 5,29Water flow l/h 473 373 317 744 524 385 864 666 441 1089 885 723 1848 1328 909Sensible emission kW 2,09 1,61 1,35 3,18 2,17 1,57 3,74 2,81 1,81 4,72 3,77 3,03 7,94 5,53 3,69