Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 25,6 68,0 133,0 7,0 4,4Limit 100,0 - 555,0 50,0 25,0Margin 74,4 - 422,0 43,0 20,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,4 3,0 2,6 2,20Worst Value: Local: 36 11,1 43,4 32,3 493,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 15,9 10,3 5,6 237,00Remote: 78 16,6 13,9 2,7 102,00Worst Value: Local: 78 14,4 8,6 5,8 346,00Remote: 36 13,9 10,3 3,6 236,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,7 26,7 2,0 500,00Remote: 36-45 29,8 26,7 3,1 500,00Worst Value: Local: 36-45 28,7 26,7 2,0 500,00Remote: 36-45 29,8 26,7 3,1 500,00dB 0501000Local250500 MHzdB 0