Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
“MERCOR” S.A. – the Company reserves the right to make modifications and changes. Version: mcr WIP 21.07.30.2113/18mcr WIP type multi-blade fire dampersConnection diagram for the BE24, BLE24, BE230 and BLE230 actuatorsConnection diagram for the BEE24, BEN24, BEE230 and BEN230 actuatorsNote:The BE and BLE actuator operating control requires a three-wire system. The actuator sense of rotation is switched by applying the supply voltage to terminal 2 or 3, depending on the desired sense.The location of the limit switches for all types of actuators is shown for the position without voltage.For proper operation of a device equipped with electrical actuators, it is recommended that the rated voltage housed tolerance of 24V±10% or 230V±10%. Power supply devices other than listed above may cause malfunction and will not be covered by the warranty conditions.EXBF actuators