Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 16.6 5.0 51.3 45 17.3 84.8 23.7MAIN 78-45 17.9 499.0 11.3 45 19.8 499.0 8.3SR 45-78 18.3 499.0 11.3 36 19.5 473.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 28.9 92.0 25.6 36 30.9 97.3 22.1SR 12-45 28.4 92.0 25.6 36 28.7 96.5 22.3MAIN 36-45 39.7 497.0 -12.2 36 39.4 499.0 -15.2SR 36-45 37.1 497.0 -12.2 45 38.3 497.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.4 474.0 8.0SR 12 5.3 412.0 8.0MAIN 45 8.4 474.0 8.0SR 12 5.3 412.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS