Title: 360.013 Hybra Modul A 8,00-2,0 +- 22.800 m³h -Datakjøring Fra leverandør.pdf
Plug fan Volume flow operating mode Designation Number of width and height Pressure loss external / static (Pa) Pressure loss total / dynamic (Pa) Shaft output / performance class Sound p. suction / pressure dB(A) Efficiency total / static (%) System-efficiency total / static (%) System p. consumption V/E (kW) Speed (U/min) / C-factor Differential pressure (dp at Vn) Operating frequency Maximum frequency Motor Size / Number of terminals Energy class / Protection item x Nominal output (kW) Rated current (A) Nominal speed (U/min) Voltage (V) / Frequency (Hz) revision door with dual hinge18.240 m³/h parallel RLM E0-BE 560 2 x 1 290 / 610 647 / 37 2,030 kW / P1 74,8 / 79,6 81,0 / 76,0 72,4 / 68,3 4,010 / 4,520 1.463 / 242 852 Pa 73 Hz 103 Hz220-55 / 4 (IE5) / IP55 2 x 4,30 10,00 1.700 3x400 / 50Inspection window Diameter190 mmHeat wheel Condensation ST1-XL-WV-2375-CS-V1-C1-0,W2477,H2477