Title: +038=30.001-NI003._29-V20-04-02 VVS-anlegg plan 4 - DM3.pdf
LD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:180 m³/h Kjøling: 0 W 0.000 L/s Varme: 175 W 0.004 L/s320.102: 54mm0.090 L/sLD018T Maks:180 m³/h Kjøling: 0 W 0.000 L/s Varme: 175 W 0.004 L/sLD018T Maks:180 m³/h Kjøling: 0 W 0.000 L/s Varme: 175 W 0.004 L/sSTAP/STAD 0.090 L/s +04 = 320.102 - OE 041 0.090 L/sLD018T Maks:180 m³/h Kjøling: 0 W 0.000 L/s Varme: 175 W 0.004 L/sLD018T Maks:180 m³/h Kjøling: 0 W 0.000 L/s Varme: 175 W 0.004 L/s370.101: DN 1000.212 L/sSTAP/STAD DN20+04 = 370.101 - OE 041 0.212 L/sSF001T-125 100 m³/hLD024T Maks:200 m³/h Kjøling: 0 W 0.000 L/s Varme: 770 W 0.019 L/sø125 UK=2678ø125 UK=2678Opp/ned DN 100mmSkap tørroppleggLD018T Maks:200 m³/h Kjøling: 665 W 0.036 L/s Varme: 455 W 0.016 L/sST001T-160-250 200 m³/hOverstrøm: Spalte under dør eller rist i dørSTAP/STAD DN25