Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]215 341 24 9.3215 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.3 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.3 * 250.0 35.3 36 0.4 * 250.0 32.7SR 36-78 8.4 186.5 37.4 36 10.0 147.5 36.5MAIN 36-45 0.3 250.0 35.3 36 0.4 250.0 32.7SR 12-45 9.7 246.0 35.5 36 10.2 247.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.4 178.0 19.2 36 14.9 182.5 16.0SR 36-45 13.8 178.0 19.2 45 15.1 167.0 16.7MAIN 45-36 13.7 232.5 16.9 36 15.7 232.5 13.9SR 45-36 14.4 250.0 16.2 45 16.6 250.0 13.2010080604020050100150MHzACR-F (dB)20025001008060