Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 29,1 68,0 151,0 8,0 5,3Limit 100,0 - 555,0 50,0 25,0Margin 70,9 - 404,0 42,0 19,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,4 3,0 2,6 1,60Worst Value: Local: 36 12,8 43,4 30,6 493,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 22,5 15,9 6,6 64,50Remote: 78 16,7 12,8 3,9 131,00Worst Value: Local: 12 16,9 8,6 8,3 345,00Remote: 45 15,1 8,0 7,1 483,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,1 26,7 2,4 499,00Remote: 36-45 30,2 26,7 3,5 500,00Worst Value: Local: 36-45 29,1 26,7 2,4 499,00Remote: 36-45 30,2 26,7 3,5 500,00dB 0601200Local250500 MHzdB 060