Title: etg u1.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.8 26.4 42.0 12 12.4 26.1 39.7SR 12-36 12.1 26.4 42.0 36 13.6 26.4 39.6MAIN 36-45 18.9 248.5 4.8 36 18.6 246.5 2.4SR 36-45 19.0 248.5 4.8 36 20.3 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.9 55.5 16.6SR 45 4.4 55.3 16.6MAIN 36 5.8 241.5 10.2SR 36 6.3 241.5 10.260500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1