Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
LED 1 = amberManual Value (85%) LED 2 = red (strong)Digital/analogue values Output signalsDigital valuesClassicxx7Simatic+ 10.0 V1023102327684+ 5.0 V511511138240 V000The user is able to set application-specific parameters. It is possible for example to work directly in %. For this purpose, the appropriate parameters should be set to 0…1,000 in the FBox, corresponding to 0…100% in the HeaVAC library.6-105PCD3.W800Block diagramBus Interface (CPLD)LED’s Aut/ManAut/Man SwitchesPoti’s Man.LED’s OutValPCD3 I/O BusMicro ControllerMux 2→1Output AmplifierD/A ConverterMux 2→1Output AmplifierSpring Clamp ConnectorPower Supply +14V +5V +3.3VVoltage ReferenceMux 2→1Output Amplifier8 polesOutput AmplifierProgrammingFor programming the modules PCD3.W800, an FBox is available.xx7 and RIOs: the firmware reads and writes the values according to the configuration (I/O Builder or network configurator)