Title: +038=564.001-##001T_03-Wise IAQ Luftkvalitetsgiver Swegon - Produktdatablad.pdf
Power supply:24 V AC ±10% 50-60 Hz, 15-30 V DCMax. power consumption: 2 VAGlass fuse:250V 0.5A Time Lag (Slo-Blo)Cable rating, connector: Max. 1.5 mm 2, push-in -spring force connectionFrequency band: 2.45 GHzIMS band (2400--2483 MHz)The sensor is available in 3 variants:Output (ERP):50 mWWISE IAQ Multi: measures VOC, CO2, RH and tem- perature.WISE IAQ Multi: measures VOC, CO2, RH and tem- perature.Range of measurementTemperature:0 – 50°C ± 0.5°CWISE IAQ CO2: measures CO2, RH and temperature.RH: 20 – 80 rH% +3%,WISE IAQ VOC: measures VOC, RH and temperature. VOC:WISE IAQ VOC: measures VOC, RH and temperature. VOC:0 – 100 rH% +5%450 – 2000 ppmMaterials and surface treatment The front-piece is made of PC and the back-piece is made of PP.CO2:IP class:400 – 2000 ppmIP20The front-piece is finished in white NCS S1002-Y and the back-piece is finished in grey NCS S5500-N.Ambient temperatureOperation:20 – + 55°C