Title: 364_orion-lov Tilluftsventil.pdf
Diagram 16, Orion-LØV m/Luna 315-400Luna 315-400_LØV 1 4[m/s ][l/s ][m³/h][m/s ][l/s ][m³/h][m/s ][l/s ][m³/h]Orion-LØV∆pt[P a] 505 2 1 Ø0 6 1 Ø0 0 2 Ø0 5 2 Ø5 1 3 Ø0 0 4 Ø403040203515301025520304050 60 70 80 90100 120140160180200 250 300350100200[l/s ]100150200300400550 700900 1100[m³/h]Diagram 17, Kapasitetsdiagram for Orion-LØV i kanalendeLØV 14 i kanalendeOrion-LØVLunaStengt spjeldDim.Dim.63125 250 500 1K125100-12542037125-12572247160100-16041138125-160512510160-16061135200125-200600511160-20051158200-20083136250160-250422912200-25061147250-25051135315200-315714912250-31540268315-31552134400250-40091389315-40063146Tabell 5, korreksjonsfaktor [KO], Orion-LØV med LunaOrion-LØVDemping [dB]Dim.