Title: +038=433.000-NI003._05-Testrapport elektriske anlegg - DM3.E3.433.09.02, Pareto plan 09.pdf
Uln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E3.433.09.02 / XF051 C16/2 10.06.2020 15:06Tallberg Elektro A/S Tlf.22796640Side:14GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.106106107107108108109109110110111111112112113113TEST RAPPORTResultatR ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF052 C16/2 10.06.2020 14:42SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E3.433.09.02 / XF052 C16/2 10.06.2020 15:06R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF053 C16/2 10.06.2020 14:43SPĆNDINGUln: 233V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E3.433.09.02 / XF053 C16/2 10.06.2020 15:06R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF054 C16/2 10.06.2020 14:43SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0Hz