Title: +038=370.002-RP011T_01-Siemens Trykkføler vann QBE2003-P10.pdf
QBE2003-P10, QBE2003-P16, QBE2003-P25, QBE2103-P10, QBE2103-P16, and QBE2103-P25**) Cannot be used on types QBE2003-P10, QBE2003-P16, QBE2003-P25, QBE2103-P10,QBE2103-P16, and QBE2103-P25. A solution on the construction side using the ½" threadedconnection is possible.Mounting Instructions are enclosed with the sensor. For further information about mounting location and mounting position refer to the sensor mounting user's manual at the BT download center: http://siemens.com/bt/download. Appropriate measures must be taken to ensure a leak-proof fitting. To provide for test measurements without leakage of the medium, it is strongly recommended that an appropriate test adapter and shutoff device be fitted.The tapping point should be at the side, near the bottom of the pipe. Do not measure the pressure from the top of the pipe (where it may be affected by airlocks) or the bottom (where it may be affected by dirt).Always purge the system.1909Z03