Title: 4. Leieavtaler.pdf
~ \(\/l w19. The design basis for each area of the facility is dependent on a number of factor's including, occupancy, and ceiling height. In general the following design and data sheets should be utilized:19. The design basis for each area of the facility is dependent on a number of factor's including, occupancy, and ceiling height. In general the following design and data sheets should be utilized:a. Offices & Canteen:FM Global Property Loss Prevention Data Sheet 3-26, Fire Protection Water Demand for Non Storage Sprinklered Properties.Design Density: HC-1 - 4 mm/min over 140 m2 (wet type system) Sprinkler Head Type: FM Approved (K80, 70°C) Sprinkler Line Spacing: 2. l - 4.5 m2 Sprinkler Area Spacing: 6.5 - 21.0 m3 Hose Demand: 950 L/min Water Duration: 60 minutes