Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 20,2 10,2 10,0 500,00Remote: 45-12 20,4 10,2 10,2 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,9 3,7 496,00Remote: 36 29,1 23,8 5,3 499,00Worst Value: Local: 36 27,6 23,9 3,7 496,00Remote: 36 29,1 23,8 5,3 500,00PS-ACRF: Pass Worst Margin: Local: 45 19,0 7,2 11,8 500,00Worst Value: Local: 45 19,0 7,2 11,8 500,00Remote: 12 21,2 9,5 11,7 383,00Remote: 12 19,5 7,2 12,3 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:15Signature:______________________ Page: 142Copper Certification ReportCable Label: 521.002-UD-41 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:18:30 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein