Title: +038=320.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Nettserverhåndbok.pdf
The visualization of the plant data allows a simple and fast overview of the system In this view the stored data of the last 8 days are automatically read in for the display The 'Read more data' button reads in all the data stored in the actuator The Delta-T values can be determined using the "coil characteristic" buttonDisplay of recorded energy consumption as well as cumulative water flow:T5-Webserver Manual Energy Valve• en • v3.3 • 03.2019 • Subject to changes19 / 20EV..R+BAC / P6..W..EV-BACAttachmentDefinition of VnomDefinition of VmaxDefinition of PnomDefinition of Pmax20 / 20Characterised control valve (CCV) with adjustable flow rate and sensor-operated flow control, and power and energy-monitoringIs the maximum possible flow rate. Vnom represents the as-delivered condition.Is the maximum flow rate which has been set with the greatest control signal, e.g. 10V /100%Pnom is the maximum controllable power output Qnom at the heat exchanger.