Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]37.9 164 2 5.65Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 445.0 30.3 36 8.5 500.0 26.4SR 36-45 8.8 52.0 46.4 36 8.8 480.0 26.8MAIN 12-36 7.9 500.0 29.2 36 8.5 500.0 26.4SR 36-78 9.6 477.0 29.7 36 9.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.5 494.0 11.4 45 17.9 500.0 8.3SR 45-78 18.9 496.0 11.3 45 18.8 500.0 8.3MAIN 78-45 18.6 497.0 11.3 45 17.9 500.0 8.3SR 45-78 18.9 496.0 11.3 45 18.8 500.0 8.30100806040200250 MHzACR-F (dB)