Title: +038=242.003-QZ001T_02-FR Brannplate Protecta - Teknisk Datablad.pdf
Platekanter ma60mm FRBrannplate 2Sutenpa vegg med50mm overlapp pabegge sidermales med FRDekkmaling pabegge siderKabler < @50mm,single, buntede ogpa kabelbroer0g apninger mafuges med FR Akrylpa begge siderKABLER OG KABELBROER BRANNMOTSTAND EI 60 (E 240MUR ELLER BETONGVEGGERPlatekanter ma60mm FR males med FR Brannplate 2-S Dekkmaling pa utenpa vegg med begge sider50mm overlapp pabeqge sider]0g apninger mafuges med FR Akrylpa begge siderKabler s @80mm,single, buntede ogpa kabelbroerwww.protecta.noProtecta® FR Brannplate ProtectaKABLER OG KABELBROER BRANNMOTSTAND EI 180 (E 240 ISOLERTE STALR@R BRANNMOTSTAND EI 45 (E 120 MUR ELLER BETONG - VEGGER MUR ELLER BETONG - VEGGERMaksimum utsparing600 x 600mm 2| 1lag 60mm FRBrannplate 2SMaksimum utsparing2400mm bred og1200mm hoyPlatekanter mamales med FRDekkmaling pabegge sider60mm FRBrannplate 2Sutenpa vegg med50mm overlapp pa