Title: 360.002 - Tilluft.pdf.pdf
4.40.0 +0.05.71.5 +0.05.60.1 +0.06.61.5 +0.06.30.1 +0.07.11.5 +0.06.70.2 +0.0Lp [dB]LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeBEND-90DUCT165 SUPPLYDUCTBEND-90DUCTREDUCERDUCT166 T-BRANCHDUCTProductSizeMAGIB-C4-*-*160160NETTING-160160250MAGIB-C4-*-*250250MAGIR-CC1-*-* 250/200200TCPU_DK-*-*0,0 200/200200L [m]1,40,00,32,62,8Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]1001,40,5 Sound in:Attenuation: Addition:1001,40,3 Sound in:Attenuation: Addition:1001,46,3 Sound in:Total Lw:3301,90,0 Sound in:Attenuation: Addition:3301,90,7 Sound in:Attenuation: Addition:3301,90,1 Sound in:Attenuation: Addition:3301,90,2 Sound in:3302,91,6 Sound in:Attenuation: Addition:3302,95,7 Sound in:Attenuation: Addition:Dividing:2502,21,1 Sound in: