Title: V20-10-01 VVS-anlegg plan 10 - DM1.pdf
LD001T Maks:175 m³/h Kjøling: 440 W 0.031 L/s Varme: 360 W 0.010 L/sLD001T Maks:215 m³/h Kjøling: 535 W 0.043 L/s Varme: 480 W 0.012 L/s89ASnitt 1530x820 UK=2660JV001T Ø160Plan 11MA 75mm38.62 mInntaksristLFø400ø500360.029Plan 1035.07 m10Motorisert åpne-/lukkespjeld. Normalt stengt, åpner ved brann.Avkastrist Mål: H1500x B1145 44mm fra senter profil Utvendig isolert111145x1500 UK=596LD006T Maks:150 m³/h Kjøling: 740 W 0.059 L/s Varme: 200 W 0.005 L/sLD006T Maks:165 m³/h Kjøling: 425 W 0.034 L/s Varme: 240 W 0.006 L/s370.101: 54 mm UK = 3153370.101: 54 mm UK = 3153LD006T Maks:150 m³/h Kjøling: 740 W 0.059 L/s Varme: 200 W 0.005 L/sLD006T Maks:165 m³/h Kjøling: 425 W 0.034 L/s Varme: 240 W 0.006 L/s12DN 50 Ned =370.101+10 = 370.101 - OE 103 0.595 L/sLD006T Maks:165 m³/h Kjøling: 425 W 0.034 L/s Varme: 240 W 0.006 L/sLD006T Maks:165 m³/h Kjøling: 425 W 0.034 L/s Varme: 240 W 0.006 L/s