Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]5.6 24 0 1.23Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]36.3 491.0 41.2Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 4.2 472.0 29.2 45 6.4 473.0 26.3SR 36-45 4.6 473.0 29.1 45 6.9 473.0 26.3MAIN 36-45 4.3 473.0 29.1 36 6.6 495.0 25.2SR 36-45 4.6 473.0 29.1 36 7.1 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.0 411.0 13.0 45 13.8 2.9 53.1SR 36-45 15.1 470.0 11.8 45 13.8 2.3 55.2MAIN 36-45 15.5 487.0 11.5 45 15.1 491.0 8.4SR 36-45 15.4 487.0 11.5 45 14.9 491.0 8.40100806040200250 MHzACR-F (dB)