Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
Protect electrical insulation of the wall clips. We recommend using a cable conduit based on French standard NF C15-100 or on the legal standards applicable in the relevant country (IEC 60204/IEC 60335), separated from the refrigerant line.Protect the housing during tube soldering.See annex 1 for the refrigeration connection■ 3.8. Electrical connectionsAlways connect cables while the unit is switched off. Make sure that the power and control circuits areswitched off when performing any action on the unit. Any cabling on-site must conform to standard NFC15-100 in France or to the applicable legal standards for the relevant country (IEC 60204/IEC 60335). According to IEC 60335, the degree of pollution is 3.NOTES To maintain the quality of the TECUMSEH unit and ensure that it functions properly, we recommend that you: - Check the compatibility of the supply voltage for the installation with the supply voltage for the unit (see iden- tification label).