Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Z-LINEZ: 0.29ΩIsc: 790A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 11:32Zs(rcd)Z: 0.24ΩIsc: 978A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 11:33Zs(rcd)Z: 0.20ΩIsc: 1.16kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 11:33RCD II: 28.5mAUci: 0.1V t: 17.8ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 13:11R LOW OhmR: 0.05ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 13:12KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:12GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 8686878788888989909091919292TEST RAPPORTResultat