Title: FDV BFSI.pdf
Vi reserverer oss mot forandringer som følge av løpende produktutvikling og/eller eventuelle normendringerELEKTRISKE VERDIERStandard konstruksjonLeder resistans v/ 20°C [Ohm/km]Strømbelastningsevne [A]Kortslutningsstrøm leder (1 sek.) [kA]Kortslutningsstrøm leder (5 sek.) [kA]2x1.5ER/1.5mm212,1260,210,092x2.5ER/2.5mm27,41360,350,162x6FR/6mm23,08630,840,383x1.5ER/1.5mm212,1230,210,093x2.5ER/2.5mm27,41320,350,163x4FR/4mm24,61420,560,253x6FR/6mm23,08540,840,383x10FR/10mm21,83751,40,633x16FR/16mm21,151002,2413x25FR/16mm20,7271273,51,573x35FR/16mm20,5241584,92,193x50FV/25mm20,38719273,134x1.5ER/1.5mm212,1230,210,094x2.5ER/2.5mm27,41320,350,164x4FR/4mm24,61420,560,254x6FR/6mm23,08540,840,384x10FR/10mm21,83751,40,634x16FR/16mm21,151002,2414x25FR/16mm2