Title: Aggregatkjøring.pdf.pdf
82Heating coil, Output, kW37.1Fluid flow rate, l/s0.61Fluid pressure drop, kPa9.4Sound data dB(A)Supply air77Outdoor air64Exhaust air79Extract air64Sound break out58Operation hours8760Operational hours yearly8760Systemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Unit no. 10Date 18.06.2021Page 3/40UnitPakWAverage15000150001.461.6082.18237.10.619.4Quotation no. Project Plant no.brandengen-2 Brandengene 360.001-1/Unit no. 10Date 18.06.2021Page 4/40Ecodesign2018ValueLimitUnit type (Non-residential - Bidirectional)ApprovedFan with multispeed or Var.Speed DriveApprovedHeat recoveryApprovedThermal efficiency of Heat Recov. SystemApproved8273Pressure gaugeApprovedSFP internal in W/(m³/s)Approved6601074Total checkApprovedSupplyExtractManufacturer