Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3068 Date / Time: 09/12/2013 03:38:40 Headroom 10.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]190 300 20 8.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.4 88.0 33.2 36 15.4 79.5 30.9SR 12-36 10.4 84.5 33.5 36 12.8 98.5 29.4MAIN 12-36 13.9 98.5 32.4 36 15.9 98.5 29.4SR 12-36 10.4 98.5 32.4 36 12.8 98.5 29.410080604020NEXT (dB)