Title: Instructions manual - THGT fan.pdf
Minimum 10 turns1 month√SignMotor Insulation testDateS3Values M ohm3 monthsSignDateS4Motor Anti-Condensation heater on - if fitted3 months√SignS5Review with supplier, if storage beyond 1 year, to assess need for inspection of motor, bearings, grease, belts, to assess for damage and possible replacement.1 yearDateSignS6Competent Inspector identifed. Refer IEC EN 60079-14IEC EN 14986 Annex D: identifies "Storage damage" as potential hazard. Regular inspection by competent personnel avoids / reduces this hazard.Annex 2. Fixing TorqueAnnex 2.1: Typical bolt fixing torqueTORQUE SETTINGS ( Nm )Bolt sizeElectrical TerminalsFixingsMetricM 2 M 2.5 M 3 M 4 M 5 M 6 M 8 M 10 M 12 M 14 M 16 M 18 M 20 M 22 M 24 M 27 M 30BRASS0.14 0.29 0.5 1.2 2.2 3.9 9 17STAINLESS STEEL A2 - 70 --- --- 0.9 2.1 4.1 7.1 17.5 34 59 91 140 --- 273 --- 472 682 930STAINLESS STEEL A2 - 80 --- --- 1.2 2.7 5.4 9.3 22 44 76 121 187 --- 364 --- 659 909 1240STEEL