Title: økernvn 94.pdf
Cable ID: T4029 Date / Time: 09/11/2013 09:58:10 Headroom 12.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]98 155 10 4.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.3 96.5 32.6 36 14.5 96.8 29.5SR 12-36 13.2 86.5 33.3 36 15.3 96.8 29.5MAIN 12-36 12.3 96.8 32.5 36 14.5 96.8 29.5SR 12-36 13.2 96.8 32.5 36 15.3 96.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 24.9 5.5 43.8 45 25.3 4.0 43.6