Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]32.0 140 3 4.88Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.0 458.0 30.1 36 6.8 469.0 27.0SR 36-45 6.0 477.0 29.7 36 6.8 488.0 26.6MAIN 12-36 7.0 458.0 30.1 36 7.2 499.0 26.4SR 36-45 6.0 477.0 29.7 36 6.8 488.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.2 466.0 11.9 45 17.8 18.4 37.0SR 78-45 16.8 463.0 11.9 45 17.2 475.0 8.7MAIN 78-45 17.5 493.0 11.4 45 17.9 493.0 8.4SR 78-45 17.3 499.0 11.3 45 17.5 500.0 8.30100806040200250 MHzACR-F (dB)