Title: +038=360.000-LC008T_04-Major line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
The water coil will be made of copper tubes and continuous fins in seamed aluminium. To ensure the best energy efficiency possible, different variants will be available thus limiting surplus power. The hydraulic connections will be fitted with female rotary couplings with flat faces to facilitate the fitting of regulation valves. The PN16 coils will be equipped with air bleed and draining valves. They must be tested with a minimum test pressure of 24 bar.The main condensate pan, in class V0 non-corrodible smooth ABS-type material, will as standard have reinforced insulation of at least 20 mm for use in all climates. An auxiliary pan will be available to collect condensate from the regulation valves. All metal trays will be prohibited. Condensate draining must be of the raised type, raised by at least 30 mm to facilitate the gravity drain.