Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]23.1 100 1 3.47Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 451.0 30.2 36 7.9 456.0 27.1SR 36-45 7.1 469.0 29.3 36 7.3 456.0 27.1MAIN 12-36 8.9 497.0 28.0 36 8.6 498.0 25.1SR 36-45 7.6 499.0 27.9 36 7.5 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.9 6.5 49.0 45 21.2 26.3 33.9SR 45-78 18.9 9.8 45.5 45 21.1 5.9 46.9MAIN 36-12 21.7 478.0 11.6 36 23.1 500.0 8.3SR 12-36 21.6 478.0 11.6 36 22.1 479.0 8.60100806040200250 MHzACR-F (dB)