Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.03.04-UF011 Date / Time: 14-08-2020 07:48:25 Headroom 7.8 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 36]18.2 79 1 2.79Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.8 399.0 31.4 36 8.0 458.0 27.0SR 12-36 8.2 464.0 29.6 36 8.7 464.0 26.7MAIN 12-36 8.7 498.0 27.9 36 8.6 499.0 25.0SR 12-36 9.0 498.0 27.9 36 9.5 500.0 25.010080604020NEXT (dB)