Title: 2 etg del2.pdf
Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94Cable ID: T2006 Date / Time: 10/10/2013 03:09:32 PM Headroom 13.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]307 486 34 13.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.9 64.0 35.5 36 15.9 99.3 29.4SR 12-36 13.7 94.0 32.7 36 15.3 94.0 29.7MAIN 12-36 13.9 99.5 32.3 36 15.9 99.5 29.3SR 12-36 13.7 94.0 32.7 36 15.5 99.3 29.410080604020NEXT (dB)