Title: økernvn 94.pdf
SR 36-12 15.0 108.0 23.5 45 16.6 205.5 14.9MAIN 45-36 16.0 245.0 16.4 36 16.9 229.0 14.0SR 36-45 16.6 245.0 16.4 45 17.3 245.5 13.4010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.0 24.4 42.9 45 16.0 24.4 40.5SR 36-45 15.0 24.4 42.9 36 16.9 18.9 43.4MAIN 36-78 23.6 232.5 6.4 36 23.8 233.0 3.7SR 36-78 25.1 250.0 4.7 36 25.0 246.0 2.4010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.8 20.3 19.5SR 45 2.3 20.3 19.5MAIN 36 4.7 208.5 10.8SR 36 5.6 204.5 10.9010080050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040200050100150MHzProject: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASS