Title: +135.01=370.003-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Max. flow rate qs exceeded12Soiling prewarning13Mains voltage off14CRC error occurred15Adjustment values parameterized16F7 (EEPROM) prewarning17Reset made18Date/time of day parameterized19Yearly set day parameterized20Monthly set day parameterized21Master reset performedCE2N5324en 2018-08-18Building TechnologiesSerial no.Description22All times deleted23Error time was deleted24Maximum was deletedThe service software configures and reads out the data via the optical interface.Data logger The data logger (optional) permits archiving of data that the user can select from a predefined set of values. The data logger contains 4 archives to which 8 channels can be assigned. The data can be assigned to any of the channels. The service software is used for the configuration.ArchiveTime baseStorage depthAveraging time for maximumHourly archive1 hour45 days1 hourDaily archive1 day65 days1 hourMonthly archive1 month15 months