Title: 1 etg del 2.pdf
MAIN 12-36 8.5 16.9 47.0 36 10.1 16.9 44.6SR 12-36 11.8 13.8 49.1 36 12.8 13.8 46.7MAIN 12-36 13.8 248.5 4.8 36 12.9 248.0 2.2SR 12-36 19.1 247.5 4.9 36 20.3 247.5 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.5 34.5 18.3SR 36 3.7 10.5 20.9MAIN 45 10.1 231.5 10.4SR 36 7.0 248.5 10.060500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94