Title: 2 etg del2.pdf
SR 36-45 10.3 75.8 26.6 45 12.8 80.3 23.1MAIN 45-36 12.4 242.5 16.5 36 15.4 242.5 13.5SR 45-36 12.5 246.5 16.4 45 14.6 229.0 14.0010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.8 19.8 45.3 12 9.8 16.1 45.1SR 12-36 9.1 23.4 43.4 36 9.6 19.8 42.9MAIN 36-45 16.1 249.0 4.8 36 16.0 247.0 2.3SR 36-45 15.8 249.0 4.8 36 16.0 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.9 15.9 20.0SR 36 3.2 15.9 20.0MAIN 36 6.8 233.5 10.3SR 45 7.4 222.5 10.5010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active