Title: 1 etg del 2.pdf
2550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 8.1Cable ID: D1070 Date / Time: 10/17/2013 12:19:40 PM Headroom 14.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 78]302 475 30 13.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]4.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.9 81.8 33.7 36 17.2 82.8 30.7SR 12-36 14.8 85.0 33.5 36 15.9 96.3 29.6MAIN 12-36 16.8 98.3 32.4 36 17.8 98.3 29.4SR 12-36 15.1 100.0 32.3 36 16.0 100.0 29.310080604020NEXT (dB)