Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Tallberg Elektro A/S Tlf.22796640Side:1Rapport opprettet25.11.2020GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.7788991010111112121313TEST RAPPORTResultatSPĆNDINGU12: 233V U1pe: 0V U2pe: 233V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 05.11.2020 12:26Zs(rcd)Z: 0.11ΩIsc: 2.19kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 05.11.2020 12:27RCD II: 28.5mAUci: 0.3V t: 102.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 06.11.2020 13:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF002 10C2/003 06.11.2020 13:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF002 10C2/003 05.11.2020 10:12SPĆNDINGU12: 235V U1pe: 0V U2pe: 235V f: 50.1Hz