Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]30.9 134 2 4.70Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]27.8 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 10.2 499.0 29.3 36 9.5 500.0 26.4SR 36-45 8.1 499.0 29.3 45 8.3 497.0 26.4MAIN 36-78 10.2 499.0 29.3 36 9.5 500.0 26.4SR 36-45 8.2 500.0 29.2 45 8.3 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.5 486.0 11.5 45 13.9 2.5 54.3SR 78-45 14.5 494.0 11.4 45 13.9 2.5 54.3MAIN 45-78 14.7 497.0 11.3 45 15.5 487.0 8.5SR 78-45 14.6 497.0 11.3 45 15.4 496.0 8.30100806040200250 MHzACR-F (dB)