Title: Operating instructions - K3G560PC0401.pdf
If several devices are switched in parallel on the supply side so that the line current of the arrangement is in the range of 16- 75 A, then this arrangement conforms to IEC 61000-3-12 provided that the short-circuit power Ssc at the connection point of the customer system to the public power system is greater than or equal to 120 times the rated output of the arrangement. It is the responsibility of the installation engineer or operator/ owner of the device to ensure, if necessary after consultation with the network operator, that this device is only connected to a connection point with a Ssc value that is greater than or equal to 120 times the rated output of the arrangement.With regard to cyclic speed loads, note that the rotating parts of the device are designed for a maximum of one million load cycles. If you have special questions, consult ebm-papst for support.; Use the device in accordance with its degree of protection.Information on surface quality4. CONNECTION AND STARTUP