Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: D3401 Date / Time: 09/12/2013 12:17:50 Headroom 6.9 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]269 411 14 12.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]5.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.4 224.0 36.1 36 8.6 224.0 33.5SR 36-78 6.9 238.0 35.7 78 8.3 245.5 32.8MAIN 36-78 8.4 224.0 36.1 36 8.6 224.0 33.5SR 36-78 6.9 238.0 35.7 78 8.3 245.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.5 4.4 51.4 12 17.2 4.4 48.4