Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.03.04-UF084 Date / Time: 14-08-2020 08:40:35 Headroom 7.0 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]30.2 130 1 4.44Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.2 463.0 30.0 36 6.8 499.0 26.4SR 12-36 7.0 496.0 29.3 36 7.1 499.0 26.4