Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]26.4 115 2 4.12Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.4 454.0 30.0 36 9.3 458.0 27.0SR 12-36 8.2 421.0 30.9 36 9.6 465.0 26.7MAIN 12-36 9.3 499.0 27.9 36 9.9 499.0 25.0SR 12-36 9.7 491.0 28.3 36 10.8 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.1 5.4 50.6 45 20.4 5.4 47.6SR 45-78 18.2 5.9 49.9 45 20.4 5.0 48.3MAIN 36-45 19.9 498.0 11.3 36 20.7 475.0 8.7SR 45-36 20.1 497.0 11.3 45 21.6 500.0 8.30100806040200250 MHzACR-F (dB)