Title: Bytesteinen 1 - =514.202-FS001.pdf
37.6 mLinkWare™ PC Version 10.4Cable ID: 521.202-UD029 Date / Time: 30/03/2021 10:41:33 Headroom 7.2 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]25.6 131 9 4.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]28.3 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-4,5 7.4 250.0 33.1 4,5 8.7 250.0 30.2SR 4,5-7,8 7.2 77.3 41.8 1,2 8.5 250.0 30.2MAIN 1,2-4,5 7.4 250.0 33.1 4,5 8.7 250.0 30.2SR 1,2-4,5 8.1 250.0 33.1 1,2 8.5 250.0 30.2