Title: Data tester Smestad skole - Detaljert.pdf
Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 47,8 68,0 248,0 14,0 8,2Limit 100,0 - 555,0 50,0 25,0Margin 52,2 - 307,0 36,0 16,8Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 2,35Worst Value: Local: 45 20,1 43,5 23,4 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 18,0 11,0 7,0 198,00Remote: 78 25,1 17,6 7,5 43,75Worst Value: Local: 12 16,2 9,1 7,1 308,00Remote: 36 18,2 8,0 10,2 459,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,3 26,7 2,6 500,00