Title: Tørrsprinkler.pdf
Install horizontal sidewall sprinklers in the horizontal position with their centerline of waterway perpendicu- lar to the back wall and parallel to the ceiling. Ensure the word “TOP” on the Deflector faces the ceiling. Step 1. With a non-hardening pipe- thread sealant such as TEFLON applied to the inlet threads, hand-tighten the sprinkler into the sprinkler fitting.Step 2. Wrench-tighten the sprinkler using either:a pipe wrench on the Inlet Band or the Casing, see Figure 1a pipe wrench on the Inlet Band or the Casing, see Figure 1the W-Type 7 Sprinkler Wrench on the Wrench Flat, see Figure 2the W-Type 7 Sprinkler Wrench on the Wrench Flat, see Figure 2Apply the wrench recess of the W-Type 7 Sprinkler Wrench to the wrench flat.Note: If sprinkler removal becomes necessary, remove the sprinkler using the same wrenching method noted above. Sprinkler removal is easier when a non-hardening sealant was used and torque guidelines were followed. After removal, inspect the sprinkler for damage.