Title: økernvn 94.pdf
SR 36 2.7 31.8 18.5MAIN 36 8.1 182.5 11.4SR 45 6.4 229.5 10.4010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T4073 Date / Time: 09/11/2013 12:01:48 Headroom 0.0 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002