Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
DM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 05.11.2020 11:32R LOW OhmR: 0.25ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 05.11.2020 11:18KONTINUITET R: 0.4ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 05.11.2020 09:58SPĆNDINGU12: 234V U1pe: 0V U2pe: 234V f: 50.1HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 05.11.2020 12:30Z-LINEZ: 0.60ΩIsc: 381A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 145A Isc(0.76%): 290A Isc(1.15%): 438ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 05.11.2020 12:30Zs(rcd)Z: 0.56ΩIsc: 411A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATallberg Elektro A/S Tlf.22796640Side:12GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTNr. 8383848485858686878788888989TEST RAPPORTResultat