Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 22,1 10,2 11,9 500,00Remote: 12-45 21,9 10,2 11,7 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,6 23,9 2,7 496,00Remote: 45 27,4 23,8 3,6 498,00Worst Value: Local: 36 26,6 23,9 2,7 496,00Remote: 45 27,4 23,8 3,6 498,00PS-ACRF: Pass Worst Margin: Local: 45 72,3 61,2 11,1 1,00Worst Value: Local: 45 19,5 7,2 12,3 500,00Remote: 12 72,1 61,2 10,9 1,00Remote: 45 19,6 7,2 12,4 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:56Signature:______________________ Page: 8Copper Certification ReportCable Label: 521.002-UD-159 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 10:03:59 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: