Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF034 16C2/003 05.11.2020 11:14KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF035 16C2/003 06.11.2020 09:47SPĆNDINGU12: 234V U1pe: 234V U2pe: 0V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF035 16C2/003 06.11.2020 09:48Zs(rcd)Z: 0.49ΩIsc: 474A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF035 16C2/003 06.11.2020 09:48Tallberg Elektro A/S Tlf.22796640Side:16GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.109109110110111111112112113113114114115115TEST RAPPORTResultatZ-LINEZ: 0.68ΩIsc: 337A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 128A Isc(0.76%): 256A Isc(1.15%): 387ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF035 16C2/003 06.11.2020 13:21R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩ