Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
KT••••EH•• run components:SpacersExample of position of supportsASupport under upper hood profile of the tap-off unit outletBSupport under sheet metal enclosurePosition of neutral conductorAligning the Run ComponentsNOTICELOSS OF IP55 PROTECTION RATINGThe run components must be correctly aligned.Failure to follow these instructions can result in equipment damage.The maximum tolerance for misalignment is 2 mm.The alignment must be checked on both sides of the run components:  Check alignment on the top of the run components: Check alignment on the side of the run components:28QGH3492101-01 11/2018Supports and Run ComponentsInstalling KTA5000/KTC6300 Run ComponentsKTA5000 run components are made of two KTA2500 run components. KTC6300 run components are made of two KTC3200 run components.The two run components are linked together and they can be installed flatwise or edgewise.