Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Cable ID: 521.10.03-UF107 Date / Time: 27-02-2020 23:28:27 Headroom 7.3 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]23.1 100 1 3.52Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]30.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.3 429.0 30.7 36 8.6 494.0 25.3SR 12-45 9.1 429.0 30.7 36 9.1 463.0 26.8MAIN 12-45 8.6 496.0 28.0 36 8.9 499.0 25.0SR 36-78 9.2 490.0 28.3 36 9.4 490.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)