Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 49,4 68,0 257,0 14,0 8,3Limit 100,0 - 555,0 50,0 25,0Margin 50,6 - 298,0 36,0 16,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 2,05Worst Value: Local: 36 20,8 43,8 23,0 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 20,5 15,6 4,9 68,75Remote: 12 18,7 14,1 4,6 97,25Worst Value: Local: 12 14,8 8,0 6,8 487,00Remote: 36 16,0 8,0 8,0 500,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: Pass