Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
[Pair 12] [Pair 12] [Pair 12]30.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.8 463.0 29.6 36 10.2 474.0 26.2SR 36-45 7.0 466.0 29.5 36 7.1 475.0 26.2MAIN 12-45 9.7 493.0 28.2 45 10.5 489.0 25.5SR 36-45 7.4 496.0 28.0 36 7.8 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.4 44.0 32.4 45 13.3 2.6 53.9SR 36-45 14.4 94.0 25.8 45 13.3 3.4 51.7MAIN 78-45 16.5 500.0 11.3 45 17.0 493.0 8.4SR 78-45 16.4 500.0 11.3 45 16.7 497.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.1 88.5 26.2 45 24.5 88.8 23.6SR 36-45 26.8 83.5 27.1 36 27.0 84.3 24.4MAIN 12-45 39.2 493.0 -11.9 12 40.2 493.0 -14.8SR 36-45 37.2 500.0 -12.4 36 37.6 500.0 -15.30804000250 MHz