Title: 2 etg del2.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.9 10.1 52.1 12 8.1 8.8 51.2SR 12-36 6.9 10.1 52.1 12 8.6 8.8 51.2MAIN 12-36 10.6 248.5 4.8 36 9.5 249.5 2.1SR 36-45 9.1 246.5 5.0 36 9.0 246.5 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.8 44.0 17.6SR 45 4.4 21.9 19.3MAIN 45 6.6 233.0 10.3SR 36 7.1 239.5 10.260500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1