Title: E.433.SK.021.pdf
BJORN JORGENSRADGIVENDE INGENIBRFIRMA ELEKTRO Sofiesgate 60 0168 OSLO t1f 22853700N A/SXS001LateskillebryterIn=200Ao%\n: xxA%MsllomvernIL433.021-0E001 xso02 |<Wh [l In=63A | lkmax: 6,6kA Felt for lys, side 2 Ikmin: 2,1 kA | XS003 | In=160Aﬁ Felt for teknisk, side 3I—— —Maélersignal til 434fordeling. MBUS—UHest overspenningvern signaltil SD 434001 fordelingStiger fra fordeling 433.U21, via 433.011[0 Lx50mm225.01.19 Som bygget ;lRev.nr Dato Revisjonstekst SignaturDato Tegn.Smestad skole 25.01.19 TSPlan 02 Mo okUNDERFORDELING Prosieit Se™ 1630 1av3HAIKO ELEKTRO 433.021—400V TN5 433.5K.021KURS ENLINJESKJEMA KABELTYPE KABELNR. : ADRESSE kW [ MERKNADER2x10A/BXF100 —|Styrestrem2x10A/CXF101 I 3G1,5mm2 —Lys taviekott 244m 1 DALI-kabel KX001 —System 564.006 - Linje 1 - Lepenummer 001-064§ § Liie 2 DALI-kabel KX002 —System 564.006 - Linje 2 - Lepenummer 065-128&R B5 : wr Cat Se KX003 —|Komm. DALI-router. il 433.U12=o=