Title: DM1-3 plan 05 lysberegningsrapport.pdf
Ē(Target)311 lx (≥ 33.3 lx)782 lx (≥ 500 lx)473 lx (≥ 300 lx)190 lx (≥ 100 lx)450 lx (≥ 500 lx)401 lx (≥ 300 lx)177 lx (≥ 100 lx)Emin27.2 lx701 lx218 lx75.5 lx370 lx310 lx53.1 lxEmax816 lx914 lx674 lx329 lx509 lx490 lx248 lxg1(Target)0.087 (≥ 0.10)0.90 (≥ 0.60)0.46 (≥ 0.40)0.40 (≥ 0.10)0.82 (≥ 0.60)0.77 (≥ 0.40)0.30 (≥ 0.10)g20.0330.770.320.230.730.630.21IndexS170S174S175S173S177S178S17642201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M1/M2 SummaryGround area: 50.33 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.520 m | Mounting height: 2.600 m43201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M1/M2 SummaryResultsSymbolCalculatedVisual task areasĒ Task Area583 lxg1 Task Area0.38Ē Surrounding area313 lxg1 Surrounding area0.36Ē Background area148 lxg1 Background area0.18Consumption values