Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-45 15.5 500.0 11.3 45 16.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.6 66.8 30.4 45 23.4 67.3 27.8SR 36-45 24.0 66.8 30.4 45 24.6 67.3 27.8MAIN 36-45 39.3 500.0 -12.4 36 39.2 500.0 -15.3SR 36-45 38.7 500.0 -12.4 36 37.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.0 491.0 8.0SR 12 6.3 469.0 8.0MAIN 12 7.0 491.0 8.0SR 12 6.3 469.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00426.0 m60Insertion Loss (dB)504030201000250 MHz500