Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
TEST RAPPORTBruker: Teststed:Tallberg Elektro A/S Dronning Mauds Gate 1-3 Stanseveien 4 0250 OsloInstrument data Rapport opprettet Tyoe; EUROTEST COMBO Ser.Nr. : 13250825 21.04.2020 Model: MI 3125BT Produsent: Metrel d.d.R LOW Ohm GODKJENTR: 0.02QR+: 0.0QR: 0.0QGrenseverdi: 1.0QDronning M.g.1-3 / Jording / Ventilasjonsror GODKJENT | 12.03:2020 15434KONTINUITET GODKJENTR: 0.1QGrenseverdi: 1.0QKONTINUITET GODKJENTR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / Jording / Kabelbro GODKJENT 120 3M202/0) 602 .R LOW Ohm GODKJENTR: 0.05QR+: 0.1QR: 0.1QGrenseverdi: 1.0QKONTINUITET GODKJENTR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / Jording / Opphengt tak GODKJENT 12.03.2020 14:35R LOW Ohm GODKJENTR: 0.03QR+: 0.0QR: 0.0QGrenseverdi:R ISO GODKJENTR: >200MQ Um:Uiso: 250VGrenseverdi:TEST RAPPORTDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 001 GODKJENT * 11.03.2020 10:02SPENDINGUln: 234VUlpe: 235VUnpe: 0OVf: 50.0HzR ISO GODKJENT