Title: 360.002 - Tilluft.pdf.pdf
3.06.30.2 +0.07.11.5 +0.04.12.52.50.0 +0.0Lp [dB]11,11. Etasje1. Etasje1. EtasjeHavnivåHavnivå1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje42 SUPPLYDUCTDUCT43 TAPDUCT44 SUPPLYDUCT45 PLUGDUCT46 PLUGFKV-250 Cooling250315315MAGIO-RC-*315/250250FKV-250 Cooling250315ESU_SE-*0315315ESU_SE-*03153,20,30,10,20,2qv [m³/h]30030030030030030017v [m/s]1,71,11,11,71,71,7dpt [Pa]10,8 Sound in:Attenuation: Addition:Total Lw:0,2 Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:Dividing:1,0 Sound in:0,0 Sound in:Attenuation: Addition:12,3 Sound in:Attenuation: Addition:Total Lw:Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:63 [dB]35.013.0 +0.0 22.013.0 +0.0 22.037.00.3 +0.036.70.0 +5.04.132.632.60.0 +3.632.613.0 +0.0 19.613.0 +0.0 19.634.60.0 +0.039.20.0 +0.0125 [dB]28.39.0 +4.9 19.5