Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
GODKJENT*GODKJENTGODKJENT*Nr.575758585959606061616262TEST RAPPORTResultatSPĆNDINGU12: 236V U1pe: 236V U2pe: 0V f: 50.1HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 05.11.2020 11:18KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 05.11.2020 11:24R LOW OhmR: 0.32ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF028 16C2/003 05.11.2020 11:37SPĆNDINGU12: 235V U1pe: 0V U2pe: 235V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF028 16C2/003 05.11.2020 11:41Z-LINEZ: 0.58ΩIsc: 399A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 152A Isc(0.76%): 303A Isc(1.15%): 459ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF028 16C2/003 05.11.2020 11:39Zs(rcd)Z: 0.73ΩIsc: 316A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF028 16C2/003 05.11.2020 11:41RCD II: 28.5mAUci: 1.5V t: 17.2ms Idn: 30mA type: AC Ulim: 25V