Title: Data tester Smestad skole - Detaljert.pdf
dB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,7 23,8 2,9 498,00Remote: 45 28,7 23,8 4,9 500,00Worst Value: Local: 36 26,7 23,8 2,9 498,00Remote: 45 28,7 23,8 4,9 500,00PS-ACRF: Pass Worst Margin: Local: 12 71,4 60,0 11,4 1,15Worst Value: Local: 45 19,7 8,2 11,5 444,00Remote: 12 72,2 61,2 11,0 1,00Remote: 45 20,2 8,2 12,0 445,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:02Signature:______________________ Page: 53Copper Certification ReportCable Label: 521.002-UD-131 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 12:03:07 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: