Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Lighting power density: 6.56 W/m? (Floor area of room 14.09 m? ), Lighting power density: 8.22 W/m? = 2.73 W/m?/100 Ix (Area of working plane 11.24 m?)Consumption: 110 - 180 kWh/a of maximum 500 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels. The results are informative. The energy consumption of a building results from the sum of all consumptions in the rooms.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 99Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ’ S ’ < Site 1/ Building 1/ Storey 11/ Waiting room 2 / ViewsWaiting room 2Waiting room 2DIALux Page 100Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 11 / Waiting room 2 / Workplane (Waiting room 2) / Perpendicular illuminance (adaptive)Workplane (Waiting room 2) / Perpendicular illuminance (adaptive)L