Title: +038=370.104-OE004T_01-Multical 801 Energimåler Kamstrup - Installasjons- og brukerguide.pdf
2.2 Pocket sensors The sensor pockets can be mounted in e.g. a welding sleeve or in a 45° lateral Y-piece. The tip of the sensor pocket must at least reach the center of the flow pipe. Push the temperature sensors as deep as possible into the pockets. If a short response time is required, “nonhardening” thermally conductive paste can be used. Push the plastic sleeve on the sensor cable into the sensor pocket and secure the cable by means of the enclosed M4 sealing screw. Fasten the screw with your fingers only. Seal the pockets using seal and locking wire.3 Mounting of flow sensorPrior to installation of the flow sensor, the system should be flushed and protection plugs/plastic diaphragms removed from the flow sensor. Correct flow sensor position (inlet or outlet pipe) appears from the front label of the MULTICAL® 801. The flow direction is indicated by an arrow on the flow sensor.8Kamstrup A/S • 5512603_C1_GB_03.2016