Title: +039=442.001-UP015T_01-UP15 Fagerhult Notor 23558-402  innfelt 3K 1200 25W, Start Produktblad.pdf
1Prin ted fro m fagerh u lt.co m 2021-11-18Art.no. 23558-402 EAN 7320046503765Notor recessed LED Delta Direct, Start, DALI/Ph ase-p u lse, HLDESIGN Louvre Delta RAL 9016 Length, mm 1170 Height, mm 102Colour W h ite Weight, kg 4.8 Width, mm 90 M odule 1200TECHN ICAL DATA Installation Start IP rating 20 M ax. ambient temperature, °C 25 Brand of driver Trido n icProtective class 1 M in. ambient temperature, °C -25 Light control DALI/Ph ase-p u lseELECTRICAL DATA M CB B10A 13 M CB C10A 21 Switch control, max no. 25 Power on last level Tru e Stand by W 0.15 M ains frequency, Hz 0, 50, 60 Average W 25 Power factor, 100 % 0.94 Surge protection DM , kV/kA 1 No of Dali Addresses 1M CB B16A 22 M CB C16A 36 AM Tru e Corridor function Tru e Rated supply voltage, V 220-240 Start W 23 End W 27 Surge protection CM , kV/kA 2 THD, % 12A recessed luminaire for all types of suspended ceilings. Delta louvres provide high efficiency and optimal lighting comfort. Single or continuous installation.