Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
29.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.1 449.0 30.3 36 8.1 458.0 27.0SR 12-36 9.8 453.0 30.1 36 9.2 500.0 25.0MAIN 12-36 8.2 500.0 27.8 36 8.2 500.0 25.0SR 12-36 10.1 500.0 27.8 36 9.2 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.7 499.0 11.3 45 21.3 499.0 8.3SR 45-78 20.0 500.0 11.3 45 21.3 500.0 8.3MAIN 78-45 19.7 499.0 11.3 45 21.3 499.0 8.3SR 45-78 20.0 500.0 11.3 45 21.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.6 68.5 30.0 45 23.9 68.5 27.5SR 36-45 22.4 68.5 30.0 36 24.6 73.0 26.6MAIN 12-36 36.6 500.0 -12.4 36 36.7 500.0 -15.3SR 12-36 38.5 500.0 -12.4 36 37.7 500.0 -15.30804000250 MHzACR-N (dB)