Title: Swegon Ventiler_baffler-Injusteringsguide.pdf
Spjällposition 1315 85,3400 119,0500 218,0630 325,0800 540,02 3 4 5 6 7 8 9 10 11 12 13 1465,3 52,1 42,9 35,6 29,8 24,9 20,7 17,0 13,9 11,195,3 78,5 65,7 55,6 47,2 40,1 34,0 28,7 23,8 19,5 15,6 12,3176,0 148,0 124,0 107,0 93,1 81,2 71,0 62,0 54,0 46,7 40,4 34,4 29,4272,0 233,0 202,0 177,0 156,0 139,0 123,0 109,0 63,7 85,8 75,6 66,8 58,9446,0 379,0 325,0 282,0 247,0 216,0 190,0 167,0 147,0 129,0 112,0 98,7 85,6Injusteringsguide 2014:12www.swegon.com35VAV/CAV och injusteringsspjällREACT – RektangulärStorlek 200-200 300-200 400-200 500-200 600-200 700-200 800-200 1000-200 300-300 400-300 500-300 600-300 700-300 800-300 1000-300 400-400 500-400 600-400 700-400 800-400 1000-400 1200-400 1400-400 1600-400REACTa 33,5 50,0 66,5 83,5 100,0 117,0 133,0 167,0 76,0 102,0 127,0 152,0 178,0 203,0 254,0 136,0 171,0 205,0 239,0 273,0 341,0 409,0 478,0 546,034Injusteringsguide 2014:12