Title: Eurotester målerestultat.pdf
848485858686878788888989TEST RAPPORTResultatRCD II: 22.5mAUci: 7.6V t: 27.9ms Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING36 30.03.2021 15:03:26RCD II: 22.5mAUc: 8.7V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING37 30.03.2021 15:03:52RCD II: 22.5mAUc: 9.8V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING38 30.03.2021 14:50:10Z-LINEZ: 0.35ΩIsc: 663A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 252A Isc(0.76%): 504A Isc(1.15%): 763ABytesteinen 1 / =433.202 / SIKRING38 30.03.2021 14:50:31RCD II: 21.0mAUc: 9.6V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING38 30.03.2021 14:51:30R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING38 30.03.2021 14:51:44Testet av: Andreas PedersenSide:14GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT