Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.1 77.5 28.2 36 25.9 77.0 25.8SR 45-78 24.8 71.3 29.5 45 24.7 71.5 26.9MAIN 36-45 38.1 479.0 -11.0 36 38.6 496.0 -15.0SR 36-45 36.6 499.0 -12.3 36 36.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.9 500.0 8.0SR 45 5.8 392.0 8.1MAIN 12 6.9 500.0 8.0SR 45 5.8 392.0 8.140010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00425.0 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)