Title: 1 etg del 2.pdf
50 MHz75100100NEXT @ Remote (dB)80604020002550 MHz75100100ACR-F @ Remote (dB)80604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: T1006 Date / Time: 10/17/2013 02:27:31 PM Headroom 5.8 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]90 137 5 4.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.3 203.5 36.8 78 8.4 219.0 33.7