Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
29.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.6 458.0 29.8 36 6.7 453.0 27.3SR 12-36 8.7 453.0 30.1 36 8.1 453.0 27.3MAIN 36-78 8.9 499.0 27.9 36 7.5 499.0 25.0SR 12-36 9.5 498.0 27.9 36 8.6 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.2 500.0 11.3 45 21.2 500.0 8.3SR 78-45 18.9 500.0 11.3 45 20.1 500.0 8.3MAIN 45-78 19.2 500.0 11.3 45 21.2 500.0 8.3SR 78-45 18.9 500.0 11.3 45 20.1 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.0 66.8 30.4 36 25.0 66.8 27.9SR 36-45 23.8 66.8 30.4 36 24.8 66.8 27.9MAIN 36-78 37.3 499.0 -12.3 36 35.8 499.0 -15.2SR 36-45 37.7 498.0 -12.3 36 36.9 499.0 -15.20804000250 MHzACR-N (dB)