Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36-45 28,9 26,7 2,2 498,00Worst Value: Local: 36-45 29,0 26,8 2,2 494,00Remote: 36-45 28,9 26,7 2,2 498,00dB 0701400Local250500 MHzdB 0701400Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 68,4 57,3 11,1 2,20Remote: 12-36 21,5 10,4 11,1 492,00Worst Value: Local: 12-45 22,1 10,5 11,6 481,00Remote: 12-36 21,6 10,4 11,2 492,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,7 24,0 3,7 493,00Remote: 45 28,0 23,8 4,2 498,00Worst Value: Local: 36 27,6 23,9 3,7 494,00Remote: 45 28,0 23,8 4,2 499,00PS-ACRF: Pass Worst Margin: Local: 45 72,7 61,2 11,5 1,00Worst Value: Local: 12 20,0 7,4 12,6 488,00Remote: 12 71,7 60,0 11,7 1,15Remote: 36 19,5 7,3 12,2 497,00