Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
30.2 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.6 473.0 29.1 36 6.6 473.0 26.3SR 36-45 4.2 469.0 29.3 36 6.0 468.0 26.5MAIN 36-45 6.4 499.0 27.9 36 7.0 498.0 25.1SR 36-45 4.2 469.0 29.3 36 7.0 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.6 5.9 49.9 45 16.8 3.3 52.0SR 78-45 17.5 5.0 51.3 45 16.9 3.9 50.5MAIN 36-78 19.3 493.0 11.4 78 19.7 500.0 8.3SR 78-45 19.2 500.0 11.3 45 19.1 471.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 29.2 173.0 14.5 12 30.2 81.3 25.0SR 36-45 25.0 87.3 26.4 36 24.6 87.8 23.8MAIN 36-45 35.4 499.0 -12.3 36 36.3 498.0 -15.1SR 36-45 34.9 499.0 -12.3 36 36.3 498.0 -15.10804000250 MHzACR-N (dB)