Title: +038=360.011-#####._05-360.011 RGOLD25FRXHC Ventilasjonsaggregat Swegon - Installasjon- og vedlikeholdsanvisning.pdf
Luftmengde ved SFPv 1,8 (m3/s)Min. l uftmengde (m3/s)Kjøle- medium (kg)Stør- relseKjøleeffekt (kW)1)Varmeeffekt (kW)2)EER1)COP2)Kraftmating0110,890,4514,8 / 8,244,0 / 4,163 x 400 V ±10%, +N +PE 16A4,73,50120,970,5015,9 / 8,947,4 / 4,883 x 400 V ±10%, +N +PE 25A4,63,50141,480,7524,2 / 13,672,0 / 7,983 x 400 V ±10%, +N +PE 25A5,33,60201,530,7525,0 / 14,174,1 / 8,4103 x 400 V ±10%, +N +PE 25A4,43,40252,070,9533,7 / 19,1100,1 / 11,5103 x 400 V ±10%, +N +PE 25A4,43,40302,100,9534,1 / 19,4101,4 / 11,8133 x 400 V ±10%, +N +PE 32A4,93,40353,121.5051,2 / 28,5152,0 / 16,4183 x 400 V ±10%, +N +PE 50A4,53,20403,301.5853,8 / 30,3159,7 / 18,3203 x 400 V ±10%, +N +PE 50A4,93,30504,222.0568,8 / 38,9204,4 / 23,217,53 x 400 V ±10%, +N +PE 63A4,33,10604,252.0869,3 / 39,2205,7 / 23,5203 x 400 V ±10%, +N +PE 63A3,93,00705,512.87