Title: 564 KNX Værstasjon GPS  5 fasader 70155.pdf
Only use suitable fixing material (screws, dowels) to fix the wall installation plate and make sure that the subsurface is stable.Dimensions Fix:Fig. 16Sensor offset to the right (or the left).Fig. 9Mounting plate Sensor2.3.3. Attaching and connecting the deviceWall mounting plate3Wall mounting plate Fix:154 mmFig. 10 Hole diameter 6.2 mmm m 4 32Fig. 17 1. Slide the device onto the mounting from above. 2. Tighten the screw of the mount to secure the device. 3. Screw the M8 connectors of the connection cable onto the connectionAffix sensor mounting plate:socket on the bottom side of the device.Fig. 11 (Schema sequence screw fastening)Connect the loose end of the connection cable to KNX bus and auxiliary voltage. Use the connection sockets and clips included for this purpose.Screw the sensor mounting plate onto the boom with the countersunk screw DIN 7991 M8x10. Place the Schnorr tooth lock washers between the moun- ting plate and the boomKNX bus: + red - black2.4.