Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
The PCS is designed for indoor applications, and contains safety shields behind the door and front panels. However, the PCS is a sophisticated power system and should be handled with appropriate care. Note that xStorage PCS can only be installed in a dry, indoor environment, free of conductive contaminant by qualified personnel, that is, Eaton Customer Service Engineer or Eaton's Certified Installer who must fully understand and apply provided safety instructions in order to avoid electric hazard shock, potential death and severe product damage.xStorage battery packs can only be installed within the 42U Eaton type rack and connected with the Eaton xStorage range of PCSs. Table 1: Eaton xStorage PCS Commercial & IndustrialPCS unit type / Discharging power capacity XSTCIS / 20 kW & 40 kW XSTCIM/ 50 kW & 200 kW XSTCIL / 275 kW & 550 kW & 825 kW & 1100 kWSECOND LIFE XSTC1U12 4.2 kWhBattery type / Battery packGEN2 XSTC2N1 2 6 kWhGEN4 XSTC4 N6 10 kWh2.1 Warnings and cautions related to logistics