Title: Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.pdf
DisposalWhen disposing of the product, observe the currently applicable local laws. More information on materials can be found in the Declaration on materials and the environment for this product.Characteristic for actuators with positionerOn actuator AVM 105S, AVM 115S or AVM 321S Equal-percentage/linear Can be set using coding switchRight of amendment reserved © 2015 Fr. Sauter AG10.156.1157/10Product data sheetDimension drawingsDN 15…50DNØkdVUE, BUE015020025032040050DN152025324050A70758095100115c41,54854,560,570,571L130150160180200230H888888k657585100110125bcLAb141616181820Hd14 x 414 x 414 x 419 x 419 x 419 x 4278/1010.156.115Right of amendment reserved © 2015 Fr. Sauter AGProduct data sheetCombinationsAVM 104 / 105 / 114 / 115 /SK10439107,1c32372145, 372286AVM 321/S160>150187.5c4444Right of amendment reserved © 2015 Fr. Sauter AG10.1AVF / 124 / 125 /S39,6c>150>4044,6AVMK10440203,556.1159/10Product data sheet