Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]37.2 161 2 5.41Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.9 483.0 29.6 36 9.2 495.0 26.5SR 36-78 8.8 477.0 29.7 36 8.8 477.0 26.8MAIN 36-78 9.9 483.0 29.6 36 9.3 500.0 26.4SR 36-45 9.3 500.0 29.2 36 9.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.5 430.0 12.6 45 14.7 4.9 48.5SR 78-45 15.4 482.0 11.6 45 14.6 3.0 52.7MAIN 45-78 15.8 482.0 11.6 45 15.8 497.0 8.3SR 78-45 15.7 499.0 11.3 45 15.2 475.0 8.70100806040200250 MHzACR-F (dB)