Title: 32 Pumper modbuss teknisk data.pdf.pdf
Indicates the type of the next bearing service (not available on all E-pumps). 0: Lubricate bearings 1: Change bearings.Dynamic drive state variable: 0: Stopped 1: Accelerating 2: Decelerating 3: Steady state/closed loop 4: - 5: Accelerating halt 6: Decelerating halt 7: Start on the run (flying cut-in) Only MGE motors and CUE drives.Indicates the unit of the feedback sensor. 0: 1: mbar 2: m kPa 3: psi 4: 5: ft 6: m3/h 7: m3/s 8: 9: 10: °C 11: °F 12: % 13: K 14: W.barl/s gpmMinimum value of the feedback sensor. Unit of the sensor minimum is defined by register 00209.Maximum value of the feedback sensor. Unit of the sensor maximum is defined by register 00209.Nominal pump frequency. The scale is 0.1 Hz. Only available on MAGNA3 and MGE model H and later.Minimum pump frequency in % of nominal frequency. The scale is 0.01 %. Only available on MAGNA3 and MGE model H and later.Address Register name00214MaxFrequency00215SetpointRangeMin00216SetpointRangeMax00217RESERVED00218