Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
11.1.15 BACnet MS/TP (B-ASC) RS485 + 2 pulse inputs (VA, VB) (67-00-66) (PCB- 5550-1240) The BACnet module is used for data transfer from MULTICAL heat cooling and water meters into BACnet systems. The BACnet module transfers Meter number (programmable), Serial number, Accumulated heat energy (E1), Accumulated cooling energy (E3), Accumulated volume flow (V1), Flow temperature, Outlet temperature, Temperature difference, Actual flow, Actual power, Accumulated values from additional meters via puls InA, InB, Info codes from the heat, cooling and water meter to the BACnet system. BACnet is a widespread and established field bus protocol used within building automation. The BACnet module for MULTICAL ensures simple integration from Kamstrup’s heat, cooling and water meters to BACnet based systems. The Module can be used as either master or slave, depending on the used MAC address.Further details about the BACnet MS/TP module appear from data sheet 5810-1055, GB-version.