Title: 32 Varmepumpe brukermanual.pdf.pdf
Export Alarms - Select if BACnet objects should be created for all the alarms in theconnected AK2 device.Port - The UDP port that the BACnet server listens to (default 47808 = 0xBAC0)Device ID - The BACnet Device ID used by the gateway, should be unique on the siteCANbusEnable - Enable/disable the CANbus serviceM2M2 CAN ID - Node ID that the gateway should use on the CAN network.Baudrate - Transmission speed (kbps) used on the networkOptions■ 50 kbps■ 100 kbps■ 125 kbps■ 250 kbpsModbus RTUEnable - Enable/disable the Modbus RTU slave serviceM2M2 Slave ID - Modbus slave/unit id (station address) used by the gatewayBaudrate - Baudrate that should be usedOptions■ 9 600 bps14M2M2-10, User Guide - Rev. 2020-09-04■ 19 200 bps■ 38 400 bpsSettings - RS485 settings that should be usedOptions■ 8E1 (8 data bits, even parity, 1 stop bit)■ 8N1 (8 data bits, no parity, 1 stop bit)■ 8N2 (8 data bits, no parity, 2 stop bits)■ 8O1 (8 data bits, odd parity, 1 stop bit)