Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12-45 22,8 12,2 10,6 399,00Worst Value: Local: 45-12 22,9 12,2 10,7 399,00Remote: 12-45 22,7 12,2 10,5 399,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 32,4 29,3 3,1 345,00Remote: 45 27,9 23,8 4,1 500,00Worst Value: Local: 45 27,2 23,8 3,4 500,00Remote: 45 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,4 61,2 11,2 1,00Worst Value: Local: 45 21,2 9,2 12,0 399,00Remote: 45 20,8 9,2 11,6 399,00Remote: 45 20,8 9,2 11,6 399,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:16Signature:______________________ Page: 150Copper Certification ReportCable Label: 521.002-UD-50 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:24:50 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein