Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
2.08 • (261.8 + T) 1 + (0.509 • 10-³ • (261.8 + T))DV = digital value (0 … 1023)T = temperature in ° CExample 2: preset temperature T= –10°Ccorresponding digital value DV?DV =2.08 • (261.8 - 10) 1 + (0.509 • 10-³ • (261.8 - 10))= 464Resistance measurement up to 2.5 kΩSpecial temperature sensors or any other resistances up to 2.5 kΩ can be connected to the PCD2.W220. The digital value can be calculated as follows:4092 • RDV =(7500 + R)where 0 ≤ DV ≤ 1023 and R = the resistance to be measured in Ω.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-54Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W3x06.8.2 PCD2.W3x0, analogue inputs, 8 channels, 12 bit resolutionApplicationHigh-speed input module for general use with 8 channels, each with 12 bit resolution. Different variants for voltage 0...10 V, current 0...20 mA and the use of different resistance thermometers are available.Module overviewRsolution *)PCD2.W300: