Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Isc: 530A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF041 C16/2 10.06.2020 12:42RCD II: 28.5mAUci: 0.1V t: 104.4ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF041 C16/2 10.06.2020 12:42RCD UbUc: 0.2V Rl: 7Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF041 C16/2 10.06.2020 12:42RCD tt: 58.3msUc: 0.0V Idn: 30mA type: AC MUL.: x1 Ulim: 25VTallberg Elektro A/S Tlf.22796640Side:29GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 197197198198199199200200201201202202203203204204TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF041 C16/2 10.06.2020 12:43Zs(rcd)Z: 0.38ΩIsc: 610A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF041 C16/2 12.06.2020 12:03KONTINUITET R: 0.2ΩGrenseverdi: 1.0Ω