Title: Aggregatkjøring.pdf.pdf
0 - 2000 Pa (Geniox10 - Geniox31)Operating temperatures40/+40 °C (Standard)40/+60 °C (Special design)ClassificationsEN 1886, 2. edition 2008Mechanical StrengthClass D1(M)Casing air leakage400 Pa: Class L1(M)+700 Pa: Class L1(M)Filter by-pass leakage400 Pa: Class G1-F9+400 Pa: Class G1-F9Thermal transmittanceClass T2(M)Thermal bridging factorClass TB2(M)Acoustic insulation of casingOctave band HzInsulation dB6310125172502150028100028200029400032800040Systemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.002-3/Unit no. 20Date 18.06.2021Page 29/40Control systemLanguage in controller menuEnglishNaviPad navigation tablet deliveredYesExternal communicationMODBUS RTU, RS485Temperature control