Title: +038=310.101-SC020T_01-FDV-dokumentasjon - Danfoss AS - VA_VVS 5640741 med flere - EV220B 15-50_1.pdf
1) EPDM is recommended for water. (steam max. +140° C / 4 bar).2) FKM is suitable for oil and air. For water at max. +60 °C 3) Low pressure steam, 4 bar: Max. +140 °C BA AC/DC and BB/BE DC coils: Max. +100 °C BO and BP coils: Max. +90 °C 4) For water: Max. +60 °C BO and BP coils: Max. +90 °CTechnical data, stainless steel valve body, NCMain typeTime to open [ms] 1)EV220B 15SS40EV220B 20SS40EV220B 25SS300EV220B 32SS1000EV220B 40SS1500EV220B 50SS5000Time to close [ms] 1)3501000100025004000100001)The times are indicative and apply to water. The exact times will depend on the pressure conditions. Closing times can be changed by replacement of the equalizing orifice.InstallationOptional, but vertical solenoid system is recommended.Max. test pressure25 barViscosityMax. 50 cStValve body:Stainless steelW.no. 1.4581 / AISI 318Armature:Stainless steelW.no. 1.4105 / AISI 430 FRArmature tube:Stainless steel