Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Isc: 813A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF052 C16/2 15.06.2020 14:00Zs(rcd)Z: 0.25ΩIsc: 927A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF052 C16/2 15.06.2020 14:22RCD II: 28.5mAUci: 0.2V t: 47.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF053 C16/2 16.06.2020 10:11R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:01SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:01Z-LINEZ: 0.40ΩIsc: 580A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATallberg Elektro A/S Tlf.22796640Side:19GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENT*GODKJENTNr. 134134135135136136137137138138139139140140TEST RAPPORTResultat