Title: Operating instructions - K3G500PB3301.pdf
alternative to input Ain2 I; SELV Fixed voltage output 20 VDC, +20 V +25/-10%, max. 50 mA, short-circuit-proof, power supply for external devices (e.g. sensors); SELV Alternatively: +24 VDC input for parameterization without line voltage Analog input 2, measured value: 4-20 mA, Ri = 100 Ω, adjustable curve, only usable as alternative to input Ain2 U; SELV Analog output 0-10 V, max. 5 mA, output of current motor modulation level; adjustable curve; SELV