Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
6 (100×5)6 (120×5)8 (120×5)Cross section (mm2)1000150020002500300036004800QGH3492101-01 11/201847Switchboard ConnectionsDistance Between Supports According to IcwKTB0000YS1 bar supports must be used to support the flexible links or connection bars. The number of bar supports depends on the length of the flexible links or connection bars and the value of Icw.The following table shows the maximum distance between two supports, depending on the Icw, and allows you to calculate the number of supports needed for the length of flexible links or connection bars used:Rated short-time withstand current IcwMaximum distance x between 2 supportsIcw ≤ 43 kA400 mm43 kA < Icw ≤ 50 kA225 mm50 kA < Icw ≤ 100 kA150 mmBar supports are installed as shown:Maximum distance between bars supports (x):48QGH3492101-01 11/2018Switchboard ConnectionsConnection to Prisma P and Okken SwitchboardsIntroduction