Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]41.4 180 3 6.01Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.8 455.0 30.1 36 6.9 500.0 26.4SR 36-45 7.3 500.0 29.2 36 7.4 500.0 26.4MAIN 12-36 8.2 500.0 29.2 36 6.9 500.0 26.4SR 36-45 7.3 500.0 29.2 36 7.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.3 350.0 14.4 45 19.2 391.0 10.4SR 45-78 17.4 350.0 14.4 45 19.4 402.0 10.2MAIN 78-45 17.9 395.0 13.3 45 19.4 408.0 10.0SR 45-78 17.9 395.0 13.3 45 19.5 403.0 10.10100806040200250 MHzACR-F (dB)