Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Information about the installation of PER in a Prisma P or Okken switchboard can be found in the relevant chapter (seepage50).Checking the Phase Order of the End Feed UnitsDuring installation, you must compare the phase order of any transformer or switchboard that is fed by an end feed unit, with the phase order of the end feed unit. This is necessary to enable the proper alignment of the conductors before making connections.QGH3492101-01 11/201817Preparation and OrganizationRun Component DimensionsIntroductionThe dimensions of the different run components, straight lengths, flat elbows, edgewise elbows, flat zed units, and edgewise zed units, are indicated on the labels.Dimensions of Straight Lengths - Edgewise and FlatwiseThe length L of a straight length is the distance in millimetres between the vertical axes located on either side of the run component. The vertical axis is located 20 mm from the end of the conductor. The length can be found on the label.