Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
00250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD04 Date / Time: 05/19/2022 10:37:44 AM Headroom 9.2 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 12] [Pair 36] [Pair 36] [Pair 78]27.1 125 3 8.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]28.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.2 486.0 29.5 36 10.4 486.0 26.7SR 36-78 10.0 73.3 44.0 36 11.4 81.5 40.8MAIN 36-45 9.2 486.0 29.5 36 10.4 486.0 26.7SR 36-45 10.2 498.0 29.3 45 11.7 498.0 26.4100