Title: økernvn 94.pdf
SR 45-36 24.9 90.5 19.5 36 25.5 90.3 16.501008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.7 10.6 41.8 12 19.8 9.3 40.2SR 12-36 18.0 13.3 39.5 12 20.2 9.1 40.3MAIN 12-36 21.9 99.5 12.0 36 23.5 99.5 9.0SR 12-36 21.9 99.5 12.0 36 23.6 99.5 9.001008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.1 6.1 19.0SR 45 4.5 6.1 19.0MAIN 36 6.0 29.5 17.3SR 36 10.4 96.0 12.201008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 4.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002244 ft60Insertion Loss (dB)50