Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 36]36.9 160 2 5.47Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 476.0 29.7 36 7.0 475.0 26.9SR 12-36 7.3 499.0 29.3 36 7.4 500.0 26.4MAIN 12-36 7.4 476.0 29.7 36 7.1 478.0 26.8SR 12-36 7.3 499.0 29.3 36 7.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.8 469.0 11.8 45 18.0 500.0 8.3SR 78-45 16.5 468.0 11.8 45 17.5 468.0 8.8MAIN 45-78 16.8 469.0 11.8 45 18.0 500.0 8.3