Title: økernvn 94.pdf
MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3406 Date / Time: 09/11/2013 03:26:29 Headroom 6.7 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]159 244 9 7.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]15.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 7.7 237.0 35.7 78 8.5 249.5 32.7SR 36-78 6.7 232.0 35.9 45 7.9 241.5 33.0MAIN 45-78 7.7 237.0 35.7 78 8.5 249.5 32.7SR 36-78 6.7 232.0 35.9 45 7.9 242.0 32.910080604020NEXT (dB)