Title: Motorventiler fyrrom - VQE DN65-150.pdf
ActuatorAVM234SF132AVF234SF132 AVF234SF232Actuating power2500 N2000 NControl signal2-/3-pt., 0...10 V, 4...20 mA2-/3-pt., 0...10 V, 4...20 mARunning time DN 65, DN 8040/80/120 s40/80/120 sRunning time DN 100...15080/160/240 s80/160/240 s∆p [bar]Closes against the pressure∆pmax∆pmax∆psVQE065F3003.03.05.1VQE080F3003.03.03.4VQE100F3002.02.02.2VQE125F3001.51.41.4VQE150F3001.01.01.1Cannot be used to close with the pressureA Spring return: AVF234SF132 normally closed (NC); AVF234SF232 normally open (NO) A At temperatures above 130 °C, accessories are requiredDescription of operation