Title: økernvn 94.pdf
MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.4 13.0 20.4SR 45 3.7 32.0 18.5MAIN 45 8.9 220.5 10.6SR 36 5.1 237.0 10.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3136 Date / Time: 09/13/2013 08:54:54 Headroom 12.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%