Title: Aggregatkjøring.pdf.pdf
Cascaded extract air temperature controlFan controlAir flow control m³/h (CAV)Damper motor supply airMotor spring returnDamper motor extract airMotor spring returnFree coolingYesCoil configurationHeatingFrost protection heatingContact sensorFor selection of sensors - study flow chart in control system printoutMains power supply for control systemSupply cableL1 + L2 + L3 + N + PEVoltage3x400VACHz50HzFuse for supply air fan (in main cabinet)16AFuse for extract air fan (in main cabint)16ARated fuse PSCC max (in main cabinet)10kAMax. consumed current25.4AMax. consumed current in neutral wire3.0AMinimum fuses for unit (L1-L2-L3)32AMinimum fuses for unit (L1-L2-L3-N)32AThe electrical installation (wiring, mounting of components, connection plugs, etc.) for the unit is done as an machineinstallation according to 60204-1The supply unit consist ofDamperPressure drop2PaDamper bladesStandardActuator force21Nm