Title: +175=324.001_KA001_Ventilmotor kjølebatterier 36.01 og .02 - AVM115.Produktinformasjon.pdf
In the end positions (limit stop in valve or maximum stroke reached) or in the case of an overload, the magnetic coupling is activated. The positioning signal is switched off by the electronic cut-out after 3 minutes or 60 seconds (F100). The manual adjustment is performed by releasing the gear unit (slide switch beside the connection cable) and simultaneously turning it with the hex spanner on the top part of the actuator. 8 mm stroke achieved with 1½ turns. The actuator position can be determined by looking at the actuator bracket or the indicator knob on the top part of the actuator.)Note After manually moving the slide switch, put it back into its original position (engage gear unit).Intended useThis product is only suitable for the purpose intended by the manufacturer, as described in the “De- scription of operation” section. All related product documents must also be adhered to. Changing or converting the product is not ad- missible.Engineering and fitting notes