Title: 91290FDV Campus F13 433.04 West elektro.pdf
The material of input cable can be aluminium or copper. Output wirings can be only done with copper conductors.OJL 200STK codeProduct codeProduct name*Input conductor (mm2)Output conductor (mm2)Un (V)In (A) Al/CuTightening torqueWeight (g)Package (pce)19 120 09VG03-0006OJL 2001xAl/Cu 10-706xCu 2,5-161000160/2003 Nm (2,5-16 mm2), 6 Nm (25-35 mm2), 10 Nm (50-70 mm2)842419 120 08VG03-0003OJL 2801xAl/Cu 35-1202xCu 6-35, 5xCu 2,5-16, 4xCu 2,5-101000250/2803 Nm (2,5-16 mm2), 6 Nm (25-35 mm2), 10 Nm (50-70 mm2), 19 Nm (95-120 mm2)1781219 120 93VG03-0007OJL 400 C1xAl/Cu 95-2404xCu 2,5-35, 3xCu 6-501000380/4256 Nm (2,5-35 mm2), 10 Nm (6-50 mm2), 25 Nm (95-240 mm2)2508OJL 280W E N19 120 9419 120 95VG03-0008 OJL 400 C SVG03-0009 OJL 400 FBB1xAl/Cu 95-240Flexible busbar Cu 10x(1x25)4xCu 2,5-35, 3xCu 6-504xCu 2,5-35, 3xCu 6-5010001000380/425380/4256 Nm (2,5-35 mm2), 10 Nm (50-70 mm2), 25 Nm (95-240 mm2)