Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
There are two factors, which have filtering effects to the acquired values:The base hardware filter with a time constant of 2 ms. This filter attenu- ates the input signal by 6 dB/decade at a cut-off frequency of 80 Hz.The second influence is caused by software and results in a delay of the acquired value for 2 ms with a notch filter characteristics at 500 Hz if no software based 50 Hz / 60 Hz filter is selected.5-100