Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
Red Wire TerminationBlack Wire TerminationRed Wire = Supply (+)Black Wire = Common (-)White Wire =OutputP499 Transducer for 0.5 to 4.5 VDC and 0 to 10 VDC Applicationss e r iw _ c d v _ 9 9 4 p : G I FWhite Wire TerminationFigure 6: Pin terminations at P499 Packard connector socket by wire colorConnect cable shield lead at one point only; typically to Common (or ground) at the control.Figure 3: Wire designations for 0.5 VDC to 4.5 VDC and 0 VDC to 10 VDC transducer applicationsP499 Series Electronic Pressure Transducers Product/Technical Bulletin45. Using your multimeter, measure the DC voltage between the transducer Output (white) wire and Common (black) wire. (See Figure 3.) This is the measured output voltage.6. Compare the calculated output voltage (Step 4) and the measured output voltage (Step 5). If the measured output voltage differs greatly from the calculated output voltage, replace the transducer. It is normal for the transducer reading to differ