Title: 2 etg del2.pdf
MAIN 36-45 16.4 248.5 4.8 36 15.9 248.5 2.2SR 36-45 15.3 246.5 5.0 36 15.9 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.3 17.8 19.8SR 45 2.8 36.5 18.2MAIN 36 7.6 228.5 10.4SR 45 6.4 229.5 10.4010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94