Title: økernvn 94.pdf
Cable ID: D4087 Date / Time: 09/10/2013 01:25:07 Headroom 12.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]86 137 10 3.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.4 99.0 32.4 36 15.2 95.3 29.7SR 12-36 12.4 79.8 33.9 36 14.7 98.8 29.4MAIN 12-36 13.4 99.0 32.4 36 15.3 99.3 29.4SR 12-36 12.7 98.8 32.4 36 14.7 98.8 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.6 94.0 19.2 45 22.9 94.0 16.2