Title: Data tester Smestad skole - Detaljert.pdf
Overall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 52,2 68,0 271,0 15,0 8,9Limit 100,0 - 555,0 50,0 25,0Margin 47,8 - 284,0 35,0 16,1Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,0 3,0 2,0 2,80Worst Value: Local: 45 22,0 43,5 21,5 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 19,3 13,4 5,9 116,00Remote: 78 17,6 12,5 5,1 141,00Worst Value: Local: 78 16,3 8,0 8,3 472,00Remote: 36 13,4 8,0 5,4 465,00dB -2030800Local250