Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Check the phase order and position of the neutral conductors of all the run components (seepage15).4Install the horizontal run components on the supports.5Compensate for the gaps due to the asymmetric profiles in KT••••ED•• and KT••••EH•• components (seepage27).6Adjust the distance between the ends of the run components. It must be 40 ±2 mm, which is the space required to install the joint block.7Check the alignment of the run components with a 1-meter long leveling instrument. The maximum tolerance for misalignment is 2 mm to conform to the IP55 protection rating (seepage28).8Install the joint block (seepage30).Installing Run Components for Tap-Off UnitsNOTICEHAZARD OF EQUIPMENT DAMAGE