Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
defrost interval (0= excluded) defrost type (0= resistance, 1= hot-gas) end-of-defrost temp. (relating to evaporator temper.) max. defrost duration (0= defrost never activated) defrosting display (0=actual cell temperature, 1=stopped cell temperature, 2=dEF label) dripping time defrost interval count: 0= actual hours; 1=hours comp. ON; 2= autodeterm. protection defrost interval (0= de-activated)ALARMSA0 A1 A2 A3 A4 A5 A6 A7alarm hysteresis (differential) min. operating setpoint alarm (0= excluded) max. operating setpoint alarm (0= excluded) alarm exclusion from device start buzzer activation mode for alarm : 0= always; 1= timer-controlled time limit for buzzer acoustic signal (only if A4 = 1) temperature alarm exclusion time (only if A1 and/or A2 0) temp. alarm exclusion time after evap. stop (for A1 and/or A2 0)EVAPORATOR FAN ADJUSTMENTF1F2 F3