Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
If the meter is to be in stock for a long period, it is possible to disconnect the back-up battery. Before installation, the back-up battery must be reconnected, and the clock must be adjusted and the data logger reset via METERTOOL.After a storage period of three years, we recommend that you scrap the back-up battery.84Kamstrup A/S · Technical Description · 5512-571_R1_GB_11_2016MULTICAL® 80110.2 230 VAC supplyIncludes a double-chamber safety transformer that fulfils the requirements to double-isolation. The power consumption is lower than 3 W (without analog outputs) or less than 9 W with analog outputs.National regulations for electric installations must be observed. The heating station’s personnel can connect/ disconnect the 230 VAC module, whereas an authorized electrician must carry out the fixed 230 V installation into the meter panel.10.3 24 VAC supply