Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
DM1-3. Plan 9 / DM1.E5.433.09.04 / XF051 C16/2 15.06.2020 13:12KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF051 C16/2 16.06.2020 09:54R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 10:25KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13R LOW OhmR: 0.01ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:16GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKES