Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Tallberg Elektro A/S Tlf.22796640Side:3MISLYKKESMISLYKKESMISLYKKESGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.2121222223232424252526262727TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF015 16C2/003 30.11.2020 10:33SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 49.9HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF016 16C2/003 30.11.2020 12:28 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF016 16C2/003 30.11.2020 10:34SPĆNDINGUln: 236V Ulpe: 236V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF017 16C2/003 30.11.2020 12:25 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩ