Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
34.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.4 466.0 29.5 45 9.4 428.0 27.9SR 36-45 8.1 458.0 29.8 45 8.4 458.0 27.0MAIN 12-45 10.2 489.0 28.4 36 10.4 495.0 25.2SR 36-45 8.6 472.0 29.2 36 9.4 487.0 25.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.0 3.5 54.4 45 13.8 2.3 55.2SR 78-45 14.0 3.5 54.4 45 13.8 3.4 51.7MAIN 45-36 18.0 470.0 11.8 36 20.1 466.0 8.9SR 36-45 18.0 470.0 11.8 45 20.1 466.0 8.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 32.0 175.0 14.2 36 32.7 180.0 11.1SR 12-45 32.4 182.0 13.5 12 33.4 181.5 10.9MAIN 12-45 43.2 489.0 -11.7 36 43.3 495.0 -14.9SR 36-45 41.6 472.0 -10.5 36 42.9 495.0 -14.90804000250 MHzACR-N (dB)