Title: +038=360.019-#####._05-360.019 Gold SD-30 Ventilasjonsaggregat Swegon - Installasjonsanvisning.pdf
Input for 0-10 VDC. The input signal influences the supply air/extract airflow setpoint if the unit is operating in the demand control mode. For connection of a sensor, for example CO2, CO and VOC Independent contact, max. 5 A/AC1, 2 A/AC3, 250 VAC. Closes on a heating load.22,23Circulation pump, cooling circuit or cooling on/off, 1-step operationIndependent contact, max. 5 A/AC1, 2 A/AC3, 250 VAC. Closes on a cooling load.24,25Cooling, on/off, 2-step operation Independent contact, max. 5 A/AC1, 2 A/AC3, 250 VAC. Closes on a cooling load.26,27In-service indicationIndependent contact, max. 5 A/AC1, 2 A/AC3, 250 VAC. Closes when the unit is operating.28,29,30Damper control24 VAC. 28= Controlled 24 VAC (G), 29= 24 VAC (G), 30= 24 VAC (G0).31,32Control voltage 1)24 VAC control voltage. Terminals 31-32 are loaded with a total of 16 VA. Opened by means of the safety isolating switch.33,34Reference voltageOutput for constant 10 VDC. Max. permissible load: 8 mA.35,36,37,38