Title: +038=433.000-NI003._07-Testrapport elektriske anlegg - DM1.E7=433.08.05, Pareto plan 08.pdf
TEST RAPPORTBruker:Teststed:Tallberg Elektro A/S Stanseveien 4UF+DM1.E7=433.08.05 Dronning Mauds gate 1-3Instrument dataType:EUROTEST COMBOSer.Nr.:13250825Modell:MI 3125BTProdusent:Metrel d.d.Nr. 11ResultatDM1-3. Plan 8 / DM1.E7.433.08.05 / XF021 16/2/C/003 19.11.2020 14:22R ISOR: 111.2MΩ Um: 10VUiso: 250V Grenseverdi: 1MΩ22DM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 12:28SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0Hz33DM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 12:29Z-LINEZ: 0.30ΩIsc: 756A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A44DM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 12:29Zs(rcd)Z: 0.28ΩIsc: 831A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A55DM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 12:29RCD II: 28.5mAUci: 0.1V t: 19.6ms Idn: 30mA type: AC Ulim: 50V66