Title: 32 Pumper modbuss teknisk data.pdf.pdf
Start address LO0x000x67Setpoint address = 00104 (0x0068)Value HIValue LO0x150x7CNew setpoint value = 5500 (0x157C)If there is no response from the slave, see section 14.1.2 CIM/ CIU 200 Modbus communication faults or 14.2.2 CIM/CIU 260 3G/4G cellular communication faults.13.11 Setting the control modeThis section shows how to set a control mode.In the example, slave address 0x01 is used, and the control mode is set to 1 (Constant frequency).Request from master to slaveFieldValueDescriptionSlave address0x01Function code0x06Write single registerStart address HIStart address LO0x000x65ControlMode address: = 00102 (0x0066)Value HIValue LO0x000x01New ControlMode value = 1 (0x0001)Example of response from slave to masterFieldValueDescriptionSlave address0x01Function code0x06Write single registerStart address HIStart address LO0x000x65ControlMode address: = 00102 (0x0066)Value HIValue LO0x000x01