Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
33.5 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.8 473.0 29.1 36 7.7 463.0 26.8SR 36-45 7.9 463.0 29.6 45 7.3 457.0 27.1MAIN 12-45 7.8 473.0 29.1 36 8.2 498.0 25.1SR 36-45 9.4 500.0 27.8 45 8.2 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.0 97.5 25.5 45 14.5 8.0 44.2SR 36-45 14.9 402.0 13.2 45 14.4 3.3 52.0MAIN 45-36 15.1 475.0 11.7 36 17.8 475.0 8.7SR 36-45 15.0 475.0 11.7 45 17.5 475.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 27.8 148.5 17.4 45 30.1 148.5 14.8SR 36-78 28.8 168.5 15.0 78 30.0 161.0 13.3MAIN 36-45 41.6 500.0 -12.4 36 40.7 498.0 -15.1SR 36-45 41.6 500.0 -12.4 45 40.5 500.0 -15.30804000250 MHzACR-N (dB)