Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF017 16C2/003 30.11.2020 10:40SPĆNDINGUln: 0V Ulpe: 236V Unpe: 236V f: ___HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF018 16C2/003 30.11.2020 12:28 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF018 16C2/003 30.11.2020 11:39Tallberg Elektro A/S Tlf.22796640Side:4GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.282829293030313132323333TEST RAPPORTResultatSPĆNDINGUln: 236V Ulpe: 236V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF019 32C4/003 23.12.2020 10:10 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF020 25C4/003 15.12.2020 15:06 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253V