Title: økernvn 94.pdf
Cable ID: D3118 Date / Time: 09/11/2013 02:49:32 Headroom 15.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]171 271 19 7.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.4 64.8 35.4 36 20.4 64.8 32.4SR 12-36 15.3 89.8 33.1 36 16.5 80.5 30.9MAIN 36-45 18.4 64.8 35.4 12 22.4 95.8 29.6SR 12-36 15.3 96.0 32.6 36 16.5 96.5 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.1 70.5 21.7 45 24.3 63.3 19.6