Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 55,8 68,0 290,0 16,0 9,8Limit 100,0 - 555,0 50,0 25,0Margin 44,2 - 265,0 34,0 15,2Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 1,1 3,0 1,9 2,80Worst Value: Local: 36 23,5 43,6 20,1 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 11,8 8,0 3,8 484,00Remote: 78 20,7 15,5 5,2 71,25Worst Value: Local: 78 11,8 8,0 3,8 484,00Remote: 78 14,5 8,0 6,5 397,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 30,0 26,7 3,3 500,00Remote: 36-45 30,0 26,7 3,3 499,00Worst Value: Local: 36-45 30,0 26,7 3,3 500,00Remote: 36-45 30,0 26,7 3,3 499,00dB 060