Title: +038=433.000-NI003._27-Testrapport Elektriske Anlegg Pactum Plan 10 UF 433.10.01.pdf
GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr. 1818191920202121222223232424TEST RAPPORTResultatDronningMaudsgat / 433.10.01 Plan10 / SIKRING29 13.02.2020 11:40RCD II: 28.5mAUci: 0.1V t: 3.2ms Idn: 30mA type: AC Ulim: 50VDronningMaudsgat / 433.10.01 Plan10 / SIKRING29 13.02.2020 11:41SPÆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDronningMaudsgat / 433.10.01 Plan10 / SIKRING29 13.02.2020 11:41Z-LINEZ: 0.50ΩIsc: 462A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADronningMaudsgat / 433.10.01 Plan10 / SIKRING29 13.02.2020 11:42Z-LINE dUdU: 3.5%Sikringstype: C SIKRING I: 16A SIKRING T: 35ms dU_lim: 4.0% Isc: 457A Z: 0.50Ω Zref: ___ΩDronningMaudsgat / 433.10.01 Plan10 / SIKRING29 13.02.2020 11:42Zs(rcd)Z: 0.44ΩIsc: 526A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A