Title: 2 etg del2.pdf
264 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 248.5 35.4 36 1.4 239.0 33.0SR 36-450.8 *244.5 35.5 36 0.6 *241.5 33.0MAIN 36-45 0.9 248.5 35.4 36 1.4 249.0 32.7SR 36-45 0.8 244.5 35.5 36 0.6 241.5 33.010080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 11.5 46.0 30.9 36 14.3 46.0 27.9SR 36-45 11.7 46.0 30.9 45 14.0 36.8 29.9MAIN 36-45 16.0 174.5 19.4 45 17.6 174.0 16.4SR 45-36 15.4 174.0 19.4 45 19.3 233.0 13.8010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)