Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
For a complete description of the software features, refer to the UniVision and UniVision Pro documentation.ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0017H S I L G N E1810. TROUBLESHOOTINGWARNING! If problems persist or recur frequently after following the procedures indicated in this section contact the SOCOMEC After Sales Service, providing a full description of the problem.ProblemPossible causeSolutionPoor connection to the input mainsCheck the connection of the cable to the UPS and to the mains outletThe UPS works in battery mode even if mains power is availableThe mains voltage is out of rangeNo solution because mode of operation is correctInput protection triggered (blown fuse or automatic switch)Replace the input fuse with another of the same type or reset the automatic switchBack-up time shorter than expectedBatteries not fully chargedBatteries not working properlyLeave the batteries to charge for 8 hours consecutively