Title: VR-PL-01-004 Gulvvarme Plan 01 Del 2.pdf
EDCBAFordeler 01.03L=54,5 m55Fordeler 01.04 10 kurser dT 5 °C 0,27 l/s L=826,8 m03.09 L=65,8 m c/c=20003.08 L=79,9 m c/c=20003.04 L=87,0 m c/c=20003.03 L=80,1 m c/c=2006603.07 L=94,0 m c/c=20006.10 L=72,6 m c/c=20006.08 L=78,8 m c/c=20003.06 L=97,5 m c/c=20003.05 L=96,0 m c/c=20006.11 L=83,6 m c/c=20006.09 L=90,6 m c/c=2007706.07 L=76,7 m c/c=200Fordeler 01.05 9 kurser dT 5 °C 0,20 l/s L=573,4 m8805.04 L=59,9 m c/c=20005.05 L=19,0 m c/c=20005.09 L=60,0 m c/c=200Fordeler 01.06 11 kurser dT 5 °C 0,32 l/s L=957,3 m06.01 L=34,3 m c/c=20006.02 L=103,7 m c/c=20006.03 L=103,9 m c/c=20006.04 L=109,4 m c/c=20006.05 L=101,3 m c/c=2009905.03 L=53,9 m c/c=20005.02 L=58,1 m c/c=2001005.08 L=73,0 m c/c=20006.06 L=102,5 m c/c=2001005.01 L=90,7 m c/c=20005.06 L=79,5 m c/c=20005.07 L=79,1 m c/c=2001111EDCBATur/retur gjennom "transportrom", legges med 30-40 mm CC-avstand og isoleres.TegningsnummerRevisjon