Title: økernvn 94.pdf
Cable ID: D3031 Date / Time: 09/12/2013 08:55:40 Headroom 13.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]134 212 15 5.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.6 58.5 36.1 36 15.5 99.8 29.3SR 12-36 13.2 58.5 36.1 36 15.0 95.3 29.7MAIN 12-36 14.7 97.8 32.5 36 15.5 99.8 29.3SR 12-36 13.4 97.5 32.5 36 15.2 99.8 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)