Title: Climate Controls Ltd - MG Series 2000.pdf
Remove the cover plate to gain access to the limit switches.Start the motor running in one direction.You can then observe the limit switch assembly in operation.For motors with travel limit switches ( i.e. MG2000, MG4000, MG5000 MG7000 ), note the direction inwhich the setting wheels are moving. By pressing the switches at the end of the assembly towardswhich the wheels are moving, the motor should stop.If the opposite switches to those described above stop the motor, then either change the powersupply connections to the motor in order to reverse the direction of rotation, or exchange theconnections to the switches from the controller.Climate Controls Limited, Les Reines, Forest, Guernsey, Great Britain, GY8 0JD Tel: + 44 (0)1481 263860 Fax: + 44 (0)1481 265294 E-mail: mail@climate-controls.com Climate Controls Limited is registered in Guernsey under number 1569.Setting the Travel LimitsFor motors with travel limit switches ( MG2000), connect the motor output shaft to the rack and pinion