Title: etg u1.pdf
02550 MHz75100100ACR-F @ Remote (dB)80604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 8.1Cable ID: D0002 Date / Time: 10/21/2013 02:39:11 PM Headroom 12.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 36]62 98 6 2.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.4 96.8 20.0Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.8 63.0 35.6 36 14.4 84.3 30.5SR 12-36 13.8 63.3 35.6 36 15.5 95.0 29.7