Title: EP..R_MOD_ BACdatasheet_en-gb.pdf
Communicative characterised control valve with sensor-operated flow control, 2-way, Internal thread, PN 16 (EPIV), • Nominal voltage AC/DC 24 V • Control modulating, communicative,hybrid modeFor closed cold and warm water systemsFor closed cold and warm water systemsFor modulating control of air-handling and heating systems on the water sideCommunication via BACnet MS/TP, Modbus RTU, Belimo-MP-Bus or conventional controlConversion of active sensor signals and switching contactsConversion of active sensor signals and switching contactsType overviewTypeDN [ ]Rp [“]Vnom [ l/s]Vnom [ l/min]kvs theor. [ m³/h]PN [ ]n(gl) [ ]EP015R+MOD EP020R+MOD EP025R+MOD EP032R+MOD EP040R+MOD EP050R+MOD15 20 25 32 40 501/2 3/4 1 1 1/4 1 1/2 20.35 0.65 1.15 1.8 2.5 4.821 39 69 108 150 2882.9 4.9 8.6 14.2 21.3 32.016 16 16 16 16 163.2 3.2 3.2 3.2 3.2 3.2kvs theor.: Theoretical kvs value for pressure drop calculationTechnical dataElectrical data Nominal voltage