Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD85 Date / Time: 28/01/2022 14:01:27 Headroom 7.6 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]34.8 179 13 6.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.2 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 9.7 101.0 39.9 3,6 10.3 101.0 37.0SR 4,5-7,8 7.6 102.5 39.7 4,5 9.4 102.5 36.9MAIN 1,2-3,6 9.9 222.5 34.0 3,6 11.8 222.0 31.1SR 4,5-7,8 8.7 233.0 33.6 7,8 10.9 233.5 30.7PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)