Title: 291Stopemasse GPG Firesafe Produktdatablad .pdf
sylinder/diameter ............................................... Ø20 mm (MPa) : 13 - sylinder/diameter .............................................. Ø40 mm (MPa) : 11(Last:4kN) (Last:15kN)Termiske Spesifikk varme ................................................................... v/20°C (J/kg°C) : 575 ..................................................................................... v/1000°C (J/kg°C) : 986 Varmeledningsevne ............................................................. v/10°C (W/m°K) : 0.14 ..................................................................................... v/100°C (W/m°C) : 0.15 ..................................................................................... v/500°C (W/m°C) : 0.17 Glødetap .............................................................................. v/950°C (vekt-%) : 7.7 Max anvendelsestemp. .......................................................................... (°C) : 700(0.14 kcal/kg°C) (0.25 kcal/kg°C)