Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 36]18.2 79 1 2.82Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.1 406.0 31.2 36 8.7 458.0 27.0SR 12-36 7.4 399.0 31.4 36 8.6 458.0 27.0MAIN 12-36 10.2 498.0 27.9 36 9.2 499.0 25.0SR 12-36 8.8 497.0 28.0 36 9.5 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.0 8.9 46.3 36 21.9 459.0 9.0SR 45-78 20.0 7.1 48.2 36 22.0 472.0 8.8MAIN 45-36 21.0 496.0 11.3 36 22.2 500.0 8.3