Title: økernvn 94.pdf
100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: D4017 Date / Time: 09/10/2013 11:57:05 Headroom 5.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]170 259 9 7.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]14.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.3 235.0 35.8 78 8.7 234.5 33.2SR 36-78 5.2 243.5 35.5 36 5.8 244.0 32.9MAIN 36-78 7.3 235.0 35.8 78 8.7 234.5 33.2SR 36-78 5.2 243.5 35.5 36 5.8 244.0 32.910080604020NEXT (dB)