Title: Hardware Installation Guide.pdf
24 VDC @ 150 mA (plus reader current) nominalLNL-330012 to 24 VDC ±10%, 300 mA maximum12 VDC @ 240 mA (325mA with CoBox-Micro) nominal24 VDC @ 135 mA (175mA with CoBox-Micro) nominalLNL-442012 to 24 VDC, ± 10%, 500 mA maximum (plus reader current)12 VDC @ 250 mA (plus reader current) nominal24 VDC @ 150 mA (plus reader current) nominalLNL-110012 to 24 VDC + 10%, 350mA maximum12 VDC @ 300 mA nominal24 VDC @ 220 mA nominalrevision 6 — 25Hardware Installation GuidelinesDevicePower RequiredLNL-1100-UNote:For UL installations, refer to section UL Listed Installations on page 286 for this device.12 to 24 VDC ± 10%12 VDC @ 300 mA nominal24 VDC @ 150 mA nominalLNL-120012 to 24 VDC ± 10%, 1100mA maximum12 VDC @ 850 mA nominal24 VDC @ 450 mA nominalLNL-1200-UNote:For UL installations, refer to section UL Listed Installations on page 321 for this device.12 to 24 VDC ± 10%12 VDC @ 805 mA nominal24 VDC @ 407 mA nominalLNL-1300