Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]10.5 46 1 1.84Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]36.0 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.5 468.0 29.4 36 7.5 469.0 26.5SR 12-45 6.4 453.0 30.1 45 7.5 396.0 28.7MAIN 36-45 6.5 468.0 29.4 36 8.5 492.0 25.4SR 36-45 6.8 469.0 29.3 36 7.9 479.0 26.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 3.5 54.4 45 14.3 3.5 51.4SR 36-45 14.7 3.4 54.7 45 14.3 3.4 51.7MAIN 36-45 15.2 476.0 11.7 45 16.3 476.0 8.7