Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Connection for 0 … 20 mA (W615)DAVOLTAGE CONTROLLED CURRENT SOURCE124 (A2)+ 24 VDCI5 13R = 0...500 ΩAn external 24 VDC supply is required for current outputs.5-90PCD2.W6x5Block diagramA0 COM A1 COM A2 COM A3 COM A4 COM A5 COMp m A P Oe g a t st u p t u oC A DVCCGalvanically separated interfaceDC / DC converterμControllerI/O BusCOM+Uin -UinFilterReference Voltage 2.5 Vn o i t a o sl+5 V GNDia c i r t c e ElPCD BusProgramming Classic: For programming the modules, an FBox is available. xx7 and RIOs: the firmware reads in the values according to the configuration (I/O Builder or network configurator)Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs. For details, please refer to the “Watchdog” section, which describes the correct use of the watchdog in conjunction with PCD2 components.5-91Analogue input and output modules5.12Analogue input and output modulesPCD2.W500