Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12-45 20,8 10,2 10,6 499,00Worst Value: Local: 12-45 20,5 10,2 10,3 500,00Remote: 12-45 20,8 10,2 10,6 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,2 23,9 4,3 496,00Remote: 45 28,5 23,8 4,7 500,00Worst Value: Local: 36 28,1 23,8 4,3 497,00Remote: 45 28,5 23,8 4,7 500,00PS-ACRF: Pass Worst Margin: Local: 12 72,6 61,2 11,4 1,00Worst Value: Local: 12 18,9 7,2 11,7 499,00Remote: 45 18,4 7,2 11,2 500,00Remote: 45 18,4 7,2 11,2 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:05Signature:______________________ Page: 74Copper Certification ReportCable Label: 521.002-UD-201 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:01:24 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein