Title: +175=324.001_KA001_Ventilmotor kjølebatterier 36.01 og .02 - AVM115.Produktinformasjon.pdf
A Auxiliary change-over contacts: Infinitely variable 0...100°, admissible load 5(2) A, 24...230 V A Potentiometers: Only one potentiometer or one set of auxiliary contacts can be fitted for each actuatorDescription of operationWhen voltage is applied to the cable, the control unit to be activated is moved to any desired position by means of the coupling rod. Direction of the stroke for 3-point control: • The coupling rod moves out and the valve opens when the actuator is connected to the voltage viathe blue (MM/N) and brown (01) cables.The coupling rod moves in and the valve closes when the actuator is connected to the voltage viathe blue (MM/N) and black (02) cables.