Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]43.0 186 2 6.37Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]22.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.5 451.0 30.2 36 6.9 500.0 26.4SR 12-36 9.2 460.0 30.0 36 10.3 471.0 27.0MAIN 12-36 6.7 500.0 29.2 36 6.9 500.0 26.4SR 12-36 9.6 500.0 29.2 36 10.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.2 461.0 12.0 45 18.3 464.0 8.9SR 78-45 18.7 461.0 12.0 45 17.9 500.0 8.3MAIN 45-12 19.7 498.0 11.3 45 18.6 500.0 8.3SR 12-45 19.3 498.0 11.3 45 17.9 500.0 8.30100806040200250 MHzACR-F (dB)