Title: Hardware Installation Guide.pdf
data 1/data 0 (Wiegand) output95.2TTL InterfaceThe TTL interface has the standard 6-wire interface widely used in access control applications. In addition, an input to control the buzzer is provided. Cable with minimum of 24 AWG wires should be used. Refer to the following tables for specific wiring information.444 — revision 695.2.1Wiring the LNL-1300From LNL-1300To LNL-2005W ReaderReader TerminalPinWireDescriptionGNDBlackGroundBZROrangeRed LEDLEDBrownGreen LEDTB4CLK D1WhiteData/D1DAT D0GreenClock/D0V0RedPower (5-12 VDC)95.2.2Wiring the LNL-1320From LNL-1320To LNL-2005W ReaderReader 1 or Reader 2 PinWireDescriptionGNDBlackGroundDAT D0GreenData/D0CLK D1WhiteClock/D1BZROrangeRed LEDLEDBrownGreen LEDV0RedPower (5-12 VDC)95.2.3Wiring the LNL-1300-UFrom LNL-1300-U