Title: +038=370.001-IK009._04-Dynaciat LG 300 A Varmepumpe EPTEC - Igangkjøringsrapport.pdf
Heating Capacity Heating Efficiency (COP) Fluid Type Leaving/Entering Temperatures Fluid Flow Total Pressure Drop Fouling Factor Connection Diameter Cooling Capacity Cooling Efficiency (EER) Fluid Type Fluid Concentration Leaving/Entering Temperatures Fluid Flow Total Pressure Drop Fouling Factor Connection Diameter: 92,0 kW : 3,25 kW/kW : Fresh Water : 50,0/45,0 °C : 4,43 l/s : 32,0 kPa : 0,0000 (sqm-K)/kW : 60,2 mm : 64,0 kW : 2,26 kW/kW : Ethylene Glycol : 30,0 % : 2,0/5,0 °C : 5,62 l/s : 48,6 kPa : 0,0000 (sqm-K)/kW : 60,2 mmCIAT Optimization Chiller 1.07Non contractual photo09.12.2018Page 1 of 2References: Dr. Maudsgt 1-309.12.2018Sound Power Level (LwA) Sound Pressure Level at 1,0m (LpA): 70 dB(A) : 55 dB(A)Unit Power Input Unit Voltage Maximum Current Start Up Current Start Up Current C1/C2: 28,29 kW : 400-3-50 V-Ph-Hz : 58 A : 137 A : 137/0 AAcoustic Sound Power Level RadiatedLoad(%)125 HzSound Power at Acoustic Center(dB Lin) 500 Hz250 Hz1000 Hz2000 Hz4000 Hz