Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
AC 230V 50/60 Hzpower requirement: -during spring tensioning -during sustaining10 W4 W8 W 4.5 Wsizing (apparent power) protection class18 VAII13,5 VAprotection degreeIP 54 with cable aperture connection PG 11auxiliary switch: - point of activation3 (1.5) Amp 230 V 5(cid:176) , 85(cid:176)torque: - motor16 Nmrotation anglesteel adapter (…*)90(cid:176) 10/11/12/14 mmrunning time : (90°C) - motor - return spring90…120 s » 10 sambient temperature20 ...+50°Csound intensity level:max 50 dB (A)ab1234212223242526sbez without sensor czujnikaN~ + L1AC 24V DC 24V AC 230Vczujnik temperature temperatury sensor ST 1,72 N or ST 1.72 N lub ST 1,90 N ST 1.90 N3 (1.5) Amp 230VFigure 13. Connection diagram for JOVENTA SFL1.90/…; JOVENTA SFL 1.90T/…; JOVENTA SFL2.90/…; JOVENTA SFL 2.90T/…. actuators.MERCOR SA – The company reserves the right to make modifications and changes16/21mcr WIP multi-plane fire dampers EDELWEISS actuators