Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF023 16C2/003 30.11.2020 09:44Zs(rcd)Z: 0.49ΩIsc: 470A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF023 16C2/003 30.11.2020 09:45Tallberg Elektro A/S Tlf.22796640Side:7GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.4848494950505151525253535454TEST RAPPORTResultatRCD II: 28.5mAUci: 1.6V t: 28.2ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF023 16C2/003 30.11.2020 11:52 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF023 16C2/003 27.11.2020 11:48R LOW OhmR: 0.15ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF023 16C2/003 27.11.2020 11:49KONTINUITET R: 0.1ΩGrenseverdi: 0.7Ω