Title: V20-07-01 VVS-anlegg plan 7 - DM1.pdf
400x600 UK=2350 400x600 UK=2350400x600 400x600 400x1000 300x1200ø500 UK=2205650x700 UK=726ø500 UK=174 ø630Plan 07Plan 0725.07 m25.07 m400x1000 400x1000360.026VB310.001: MA 75 UK = 2466530x800 UK=2315LF400x1200 UK=1790 300x1200320.101: 18 mm 320.101: 18mm 310.001: MA 75Kompressor i en lyddempende kasse 690x690x690320.101: 18mm 320.101: 18mmPlan 07Sluk 75mm25.07 mProduktPlan 06 WISE RTA 06 WISE IAQ 06 WISE RTS 06 WISE director (trådløs router)RomreguleringProduktBørverdiomstiller CO2-, RH- og temperaturgiver Temperaturgiver Wise Director routerSnitt P7-A 1 : 50Snitt P7-B 1 : 50Snitt P7-C 1 : 501415LD018T Maks:220 m³/h Kjøling: 710 W 0.056 L/s Varme: 330 W 0.008 L/sLD018T Maks:220 m³/h Kjøling: 710 W 0.056 L/s Varme: 330 W 0.008 L/sLD018T Maks:220 m³/h Kjøling: 710 W 0.056 L/s Varme: 330 W 0.008 L/sLD018T Maks:220 m³/h Kjøling: 710 W 0.056 L/s Varme: 330 W 0.008 L/sø200 UK=2678Snitt P7-Aø200 UK=2680370.101: 28 mm +c 2790