Title: Eurotester sluttmålinger =433.205.pdf
Bruker:Bøifot elektro AS Bytesteinen 1, 6517 Kristiansund NInstrument dataType:EUROTEST COMBOModell:MI 3125BNr. 11ResultatSimployer / =433.205 / SIKRING1 31.01.2022 08:17:56R ISOR: 680MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩ22Simployer / =433.205 / SIKRING1 31.01.2022 08:18:21R ISOR: 622MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩ33Simployer / =433.205 / SIKRING1 31.01.2022 08:18:27R ISOR: 184.4MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩ44Simployer / =433.205 / SIKRING1 31.01.2022 08:18:36R ISOR: 368MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩ55Simployer / =433.205 / SIKRING2 31.01.2022 09:54:55RCD II: 27.0mAUci: 0.1V t: 123.7ms Idn: 30mA type: AC Ulim: 50V66Simployer / =433.205 / SIKRING3 31.01.2022 09:55:40RCD II: 27.0mAUci: 0.2V t: 281.8ms Idn: 30mA type: AC Ulim: 50VTEST RAPPORTTeststed:Bytesteinen 1 6517 Kristiansund NSer.Nr.:15360352Produsent:Metrel d.d.Side:1Rapport opprettet28.02.2022GODKJENTGODKJENTGODKJENTGODKJENT