Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Installing a Reinforced Protective Earth (PER) ConductorThe procedure for adding the PER to the Canalis interface is described in the instruction sheet S1A32783 available on the Schneider Electric website.Sealing KitThe top plate of the switchboard must be cut out to enable the installation of a KTB••••TT01 sealing kit. The sealing kit includes a drilling and cut out template, illustrated here:The procedure for installing the sealing kit is described in the instruction sheet AAV32049, available on the Schneider Electric website.50QGH3492101-01 11/2018Switchboard ConnectionsAdapting the Canalis InterfaceThe size of the Canalis interface is defined by the type of the main circuit breaker installed in the switchboard.The following graphic shows how the heights of the Canalis interface (J) and the run components (K) are defined:The following table gives the heights of the run components that can be connected to a Canalis interface of a given height: