Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]13.3 58 1 2.15Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]34.9 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.5 471.0 29.2 36 6.5 469.0 26.5SR 36-45 6.5 471.0 29.2 36 8.0 461.0 26.9MAIN 36-45 7.1 497.0 28.0 36 7.1 495.0 25.2SR 36-45 7.3 497.0 28.0 36 8.2 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.4 7.6 47.6 45 20.3 5.0 48.3SR 45-78 18.4 7.6 47.6 45 20.3 5.0 48.3MAIN 12-36 22.4 470.0 11.8 36 23.7 469.0 8.8SR 36-12 22.7 470.0 11.8 36 24.8 499.0 8.30100806040200250 MHzACR-F (dB)