Title: økernvn 94.pdf
40202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3408 Date / Time: 09/13/2013 08:34:37 Headroom 7.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]187 286 10 8.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]13.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.3 249.0 35.4 78 7.7 229.0 33.3SR 36-78 7.7 238.5 35.7 12 8.4 211.5 33.9MAIN 36-78 7.3 249.0 35.4 36 7.8 249.0 32.7SR 36-78 7.7 247.5 35.4 36 8.5 247.0 32.810080604020NEXT (dB)