Title: +038=433.000-NI003._07-Testrapport elektriske anlegg - DM1.E7=433.08.05, Pareto plan 08.pdf
DM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 12:44Tallberg Elektro A/S Tlf.22796640Side:1Rapport opprettet25.11.2020GODKJENTGODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.7788991010111112121313TEST RAPPORTResultat R LOW OhmR: 0.14ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 12:44KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF022 16/2/C/003 19.11.2020 14:23R ISOR: >200MΩ Um: 10VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF025 16/2/C/003 19.11.2020 14:23R ISOR: >200MΩ Um: 10VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF025 16/2/C/003 23.11.2020 10:00SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 8 / DM1.E7.433.08.05 / XF025 16/2/C/003 23.11.2020 10:01Z-LINEZ: 0.60ΩIsc: 386A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A