Title: DOCA0005EN-12.pdf
SU (summer time) :Bit to 0 if this parameter is not used.iV (validity of received data) :Bit to 0 if this parameter is not valid or not used.Command interfaceCommand interface overviewThe command interface allows you to configure the meter by sending specific command requests using Modbus function 16.Command requestThe following table describes a Modbus command request:Slave Numb erFunctio n CodeRegister AddressCommand blockCommand DescriptionCRC1–247165250 (up to 5374)The command is made of a command number and a set of parameters. See the detailed description of each command in the command list.NOTE: All the reserved parameters can be considered as any value, e.g. 0.CheckingThe following table describes the command block:Command resultThe command result can be obtained by reading registers 5375 and 5376.The following table describes the command result:Register AddressContentSize (Int16)Data (example)5375Requested Command Number12008 (Set Tariff)