Title: 2 etg del2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]260 411 28 11.2260 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.4 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 3.0 234.5 35.8 36 2.3 235.0 33.2SR 36-45 1.7 249.5 35.4 36 1.9 240.0 33.0MAIN 36-45 3.2 246.5 35.4 36 2.3 235.0 33.2SR 36-45 1.7 250.0 35.3 36 2.0 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 14.3 217.0 17.5 45 16.4 219.0 14.4SR 45-12 15.0 219.0 17.4 45 15.9 215.5 14.5MAIN 45-12 14.3 221.0 17.3 45 16.4 219.0 14.4