Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
fast-blow (S) 4 A fuseWatchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD2 components.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-23Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.A4606.4.3 PCD2.A460, 16 digital outputs for 0.5 A each, with ribbon connectorApplicationLow cost output module with 16 transistor outputs 5..500 mA, with short-circuit protection. The individual circuits are electrically connected; the voltage range is 10 … 32 VDC.Technical dataNumber of outputs: Output current: