Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 19,9 10,2 9,7 499,00Remote: 45-12 20,1 10,2 9,9 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 30,9 28,2 2,7 372,00Remote: 36 33,1 29,3 3,8 346,00Worst Value: Local: 45 27,0 23,8 3,2 499,00Remote: 45 28,1 23,8 4,3 499,00PS-ACRF: Pass Worst Margin: Local: 12 17,9 7,4 10,5 488,00Worst Value: Local: 12 17,8 7,3 10,5 495,00Remote: 12 71,8 61,2 10,6 1,00Remote: 12 18,1 7,2 10,9 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:17Signature:______________________ Page: 154Copper Certification ReportCable Label: 521.002-UD-22 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:30:46 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: