Title: 1 Pos. HFPD 4000x1500x480 (1).PDF
12525015039015003152250 0 0 10 0 0 10 0 50 0 0 20 0 0 20 0 0 40 8 4SECTION A-A SCALE 1 : 14Airflow Rate Calculation DataKitchen Block Size Hood Type Simultaneity factor3950x800 Next to a Wall 0.7Appliance ListQ-tyAppliance TypePower, kW1 1 2Tilting frying pan Industrial cooktop Steam convection oven40 16 36General Notes:All dimensions are in millimetres - Recommended hood hanging height 2000- 2100 mm from finished floor - Verify building entry conditions and limitations for access upon approval - Nuventas will not accept claims for problems that result from sub-standard installation - Airflow rate calculations are based on EN 16282 detailed calculations method and are provided as an accurate reference. The contractor is responsible for balancing and fine-adjusting the airflow rates on-site Exhaust Hood Details: 4000x1500x480 2 Cyclonic 8 N/A Exhaust No Grease box LED IP65, min. 500lx None 4x 315 4x 250 4x 125