Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]29.9 130 2 4.40Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.0 499.0 29.3 36 6.1 499.0 26.4SR 36-45 7.8 471.0 29.8 36 7.4 498.0 26.4MAIN 36-45 7.0 499.0 29.3 36 6.1 499.0 26.4SR 36-45 7.9 499.0 29.3 36 7.4 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.7 7.6 47.6 45 21.1 500.0 8.3SR 45-78 19.7 16.8 40.8 45 20.8 499.0 8.3MAIN 78-45 20.4 500.0 11.3 45 21.1 500.0 8.3SR 45-78 20.7 500.0 11.3 45 20.8 499.0 8.30100806040200250 MHzACR-F (dB)