Title: Data tester Smestad skole - Detaljert.pdf
Limit 100,0 - 555,0 50,0 25,0Margin 50,7 - 300,0 37,0 16,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 2,05Worst Value: Local: 45 21,0 43,8 22,8 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 15,1 8,0 7,1 500,00Remote: 12 25,6 18,8 6,8 27,10Worst Value: Local: 12 15,1 8,0 7,1 500,00Remote: 78 16,2 8,0 8,2 492,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,1 26,7 2,4 497,00Remote: 36-45 30,1 26,7 3,4 500,00Worst Value: Local: 36-45 29,1 26,7 2,4 497,00Remote: 36-45 30,1 26,7 3,4 500,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):