Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Kontor 3 / Visual task area 1/ Perpendicular illuminance (adaptive)Visual task area 1/ Perpendicular illuminance (adaptive)Surface Result Average Min Max Min/average Min/maxVisual task area 1 Perpendicular illuminance (adaptive) [Ix] 566 434 635 0.77 0.68 Surrounding area: 0.500 mSurrounding area 1 Perpendicular illuminance (adaptive) [Ix] 513 386 608 0.75 0.63Background area 1 Perpendicular illuminance (adaptive) [Ix] 289 193 343 0.67 0.56Wall zone: 0.100 mDIALux Page 21Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Kontor 3 / Visual task area 1/ Perpendicular iluminance (adaptive)False colors [Ix]500295Scale: 1:25Value grid [Ix]612 607T T631+Scale: 1:25The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 22