Title: Instructions manual - THGT fan.pdf
Users electrical supply, air duty, and any relevant data, for example if speed control is required must be considered.Guidance on area ventilation rates for ATEX may be found in IEC EN 60079-10-1All fan data applicable to “Standard Air” with ambient air / ducted air temperature within range, -20°C to +40°C unless stated otherwise, and for ATEX refer IEC EN 60079.1.2.3 Safe ventilation:Ensure adequate ventilation available to fan and motor. Working ambient temperature for fan equipment should not be exceeded, typically this will be within -20°C to +40°C, unless stated otherwise.1.2.4 Safe operation:Ensure any fan / motor temperature protection devices are fitted and operating correctly, especially for all ATEX Ex e motored products, and all ATEX Ex d motored products speed controlled by VSD Frequency Inverter.