Title: Data tester Smestad skole - Detaljert.pdf
17.01.2019 14:06:09 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 68,9 68,0 357,0 19,0 11,4Limit 100,0 - 555,0 50,0 25,0Margin 31,1 - 198,0 31,0 13,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,5 3,1 1,6 3,10Worst Value: Local: 36 28,9 43,6 14,7 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):