Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-45 13.3 496.0 11.3 78 14.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.1 40.3 37.2 45 18.5 40.5 34.7SR 36-45 19.0 40.3 37.2 36 19.4 43.8 33.7MAIN 36-45 35.6 500.0 -12.4 36 35.2 499.0 -15.2SR 36-78 34.8 483.0 -11.3 36 36.1 494.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.4 499.0 8.0SR 45 7.0 451.0 8.0MAIN 12 6.4 499.0 8.0SR 45 7.0 451.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00434.4 m60Insertion Loss (dB)504030201000250 MHz500