Title: Hardware Installation Guide.pdf
1. Position the reader at the desired mounting height on the metal door frame. Observe ADA height requirements. Drill two 7/64 (0.109)-inch holes for the reader, and one clearance hole for the cable.1. Position the reader at the desired mounting height on the metal door frame. Observe ADA height requirements. Drill two 7/64 (0.109)-inch holes for the reader, and one clearance hole for the cable.Holes locationrevision 6 — 4753. Connect the reader to the access control panel according to the following figure. Tape or cap the unused wires singly.Wiring diagram (Wiegand)CUTREADERREADER INTERFACE MODULEReceive (Orange )Transmit (Violet )Hold (Blue)Beeper (Yellow )BuzzerLED (Brown)LEDData1 (W hite)Data1Data0 (Green)Data0Ground (Black)Ground5-12 VDC (Red)PowerShield (Drain)Chassis GroundEARTH GROUND4. Use a regulated linear power supply, between 5 volts (50 mA peak) and 12 volts DC (80 mA peak).