Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.03.03-UF063 Date / Time: 19-06-2020 09:45:50 Headroom 4.6 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 36] [Pair 12] [Pair 45]6.3 27 0 1.30Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]36.4 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 4.7 422.0 30.8 36 5.6 463.0 26.8SR 36-45 4.6 462.0 29.6 36 5.6 463.0 26.8MAIN 36-45 4.9 479.0 28.8 36 5.9 479.0 26.0SR 36-45 5.3 480.0 28.8 36 7.0 500.0 25.010080604020NEXT (dB)