Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
2 wire shielded cable Typical impedance 12Ohm Maximum length 1000m (between two successive control panels) Compliant with local laws and regulations in forceThe connection must be a loop connection and must respect the direction of the wiring: the terminals on the terminal board of PORT-B must be connected with their counterparts on the terminal board of PORT-A of the next control panel; whereas, the terminals on the terminal board of PORT-A must be connected to their counterparts on the terminal board of PORT-B of the previous control panel.Port-APort-BPort-APort-B1 -2D-3D+1 -2D-3D+1 -2D-3D+1 -2D-3D+Port-APort-B1 -2D-3D+1 -2D-3D+5.9IFM4R internal module wiringCables:2/3 wire shielded cable Proper section (minimum 0.5mm², maximum 2.5 mm²) Compliant with local laws and regulations in forceEach connection to this output must be completed in accordance with the instructions in paragraph 5.5.1.