Title: økernvn 94.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.3 46.5 34.9 36 13.4 20.6 42.4SR 12-36 10.0 20.5 44.8 36 11.1 20.4 42.5MAIN 12-36 17.8 247.0 5.0 36 18.1 249.0 2.1SR 36-45 14.7 248.5 4.8 36 15.2 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 2.4 22.1 19.3SR 36 3.1 15.1 20.1MAIN 45 5.8 142.5 12.5SR 45 7.0 232.0 10.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4