Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
PCD2.W325 +10 V0 V10 VClassic 4095 2047 0Digital valuesxx7 4095 2047 0Simatic 27684 13842 0Connection concept for voltage and current inputsThe voltage and current input signals are connected directly to the 14-pole terminal block (I0…I6 and COM). To minimize the amount of interference coupled into the module via the transmission lines, connection should be made according to the principle explained below.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-62Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W3x5The diagram shows a typical wiring layout for: ●voltage inputs with the PCD2.W305 and .W325 modules or ● current inputs for the PCD2.W315 module ●If shielded cables are used, the shield should be continued to an external earthingbar.131211109876542310COME6COME5COME4COME3COME2COME1COME0m c 0 2. x a m6Earthing barBlock diagram