Title: +038=360.000-LC007T_06-Coadis line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
Internal automatic overload protection as standard on winding."DFS" motor fault output using a photocoupler for potential alarm feedback via a Konnex protocol communication bus (via the V3000 controller).Mounted on antivibration mounts.230V/1Ph/50 Hz power supply (60Hz compatible).Note: The minimum voltage required for start-up of the motor is 2V.Oru Asynchronous motor5 factory-cabled speeds connected and available at theterminal for customised adjustment.Sealed, tropicalised, with protected shaft.Permanent capacitor.Ball bearingsInternal automatic overload protection as standard on winding.Resilient mounts.230V/1Ph/50 Hz power supply (60Hz compatible).High efficiency and power factor.uFan(s)Balanced centrifugal impeller (& 282 mm) with airfoil blades. o Polymer impeller.Singlepoint mounting system with foolproofing device.Electrics boxLarge ABS electrics box, with a hinge to keep it open and screw closure.Protection rating 1P20.