Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Install an air inlet grille with filter inspection port to prevent dust and dirt from entering and fouling the unit heat exchanger. Filter installation also makes the installation of a duct closing damper during shut-down periods unnecessary.Fresh air renewal (See fig. 44) • Remove the precut sheet metal (ref. 14) and install the air controlConditioned air supply to an adjacent room (See fig. 47) • Air supply to an adjacent room requires that the outletdevice by fixing it to the unit frame.Use locally purchased material, suitable for operating temperatures of 60 °C (continuous). Conduits can be of flexible polyester (with spiral core) or corrugated aluminium, externally covered with anti- condensate material (fibre glass of 12 +/- 25 mm thickness).To complete the installation, all non-insulated ducts must be covered with anti-condensate insulation (ex. expanded neoprene, 6 mm thickness).