Title: 1 etg del 2.pdf
0501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: D1057 Date / Time: 10/17/2013 12:09:14 PM Headroom 2.3 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]275 436 31 11.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 2.3 242.5 35.6 36 2.3 249.5 32.7SR 36-78 9.5 250.0 35.3 78 9.9 241.5 33.0MAIN 36-45 2.3 249.5 35.4 36 2.3 249.5 32.7