Title: Data tester Smestad skole - Detaljert.pdf
1200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 67,5 57,3 10,2 2,20Remote: 12-45 67,5 57,3 10,2 2,20Worst Value: Local: 12-45 22,4 11,2 11,2 445,00Remote: 45-12 22,9 11,2 11,7 444,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,5 25,5 4,0 446,00Remote: 36 29,0 23,8 5,2 499,00Worst Value: Local: 36 28,0 23,8 4,2 499,00Remote: 36 29,0 23,8 5,2 499,00PS-ACRF: Pass Worst Margin: Local: 45 71,1 60,0 11,1 1,15Worst Value: Local: 45 21,7 8,1 13,6 452,00Remote: 12 71,4 60,0 11,4 1,15Remote: 12 22,1 8,6 13,5 428,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:17Signature:______________________ Page: 153Copper Certification Report