Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
nom. 24 VDC smoothed or pulsed, reverse voltage protectedVoltage tolerance, dependent on ambient temperature:20°C: 21.5…32 VDC 30°C: 21.9…32 VDC 40°C: 22.3…32 VDC 50°C: 22.8…32 VDCIsolation Withstand voltage - coil contacts Withstand voltage - open contact circuit4 kV (relay details) 1 kV (relay details)Terminals:Plug-in 12-pole spring terminal block (4 405 4936 0), for Ø up to 1.5 mm², or as above with 12 grouped strands, numbered, 2.5 m long (PCD3.K810)The supply to the relay coils is not electrically isolated from the Saia PCD® side. General technical specifications as per CL-EPC-015 Rev. 026-43PCD3.A810LEDs and connection terminals12 1110987654324V GNDA0 ncA0 coA0 noA1 ncA1 coA1 noA2 coA2 no0123Man Auto Man1 A 01 A 01 A 01 A 0Description- LabelA8 1 0LEDsC D V4 2+ –2 11 1green: Automatic yellow: Manual red: Output0 A1 A2 A0 9 8 7 6 5 4 3 13 A2 10 1 8 A 3 D C P.C A V 0 5 2A 6 5/tu o. l