Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 25.8 84.3 26.9 36 24.5 99.3 21.8SR 36-45 24.3 84.0 27.0 36 24.0 84.0 24.5MAIN 36-78 39.6 499.0 -12.3 36 38.2 499.0 -15.2SR 36-78 40.1 493.0 -11.9 36 39.7 494.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.2 498.0 8.0SR 12 5.8 447.0 8.0MAIN 12 6.2 498.0 8.0SR 12 5.8 447.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00423.6 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)