Title: 2 etg del2.pdf
Cable ID: D2041 Date / Time: 10/10/2013 12:20:29 PM Headroom 6.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]170 261 10 7.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]14.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.5 204.0 36.8 36 8.7 204.0 34.2SR 12-36 6.1 166.5 38.2 36 6.7 167.0 35.6MAIN 36-78 7.6 250.0 35.3 78 8.7 250.0 32.7SR 12-36 7.2 244.0 35.5 12 7.3 250.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.4 197.5 18.3 45 17.5 3.6 50.0