Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
DIALux Page 72Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Trapperom / Room summaryTrapperomClearance height: 2.900 m, Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Trapperom) Perpendicular illuminance (adaptive) [Ix] 190 (= 100) 92.1 269 0.48 0.34 Height: 0.000 m, Wall zone: 0.100 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 3 iGuzzini illuminazione - Q879 Laser Blade XS - Ceiling HC 10W 738 10.0 73.8 7 iGuzzini illuminazione S.p.A - MI59 (1.0 M)+MXK3+MXMO0_LX43 610 144 42.4Underscore15: flexible strip - 5m - LED blanco - 14.4W 1220Im (1.0 m) - 3000K - Ledstrip Top surface low linear profile - L 1000 - Opal diffuser screen L 1000Total via all luminaires 6484 130.8 49.6