Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
PCD2.W11x, analogue inputs, 4 channels, 12 bit resolutionfor resistive temperature sensors Pt/Ni 100, 1000High-speed, convenient module for recording absolute temperatures in the range -50 … +150 °C or +350 °C (W114) using a resistive temperature sensor. (2-wire connection with zero adjustment) The temperature curves are linearized in the module itself. The resolution is 12 bits.Module overviewPCD2.W110PCD2.W111PCD2.W112PCD2.W113PCD2.W1144 analogue inputs for temperature measurement with Pt 100 probes (IEC 751) 4 analogue inputs for temperature measurement with Ni 100 probes (DIN 43 760) 4 analogue inputs for temperature measurement with Pt 1000 probes (IEC 751) 4 analogue inputs for temperature measurement with Ni 1000 probes (DIN 43 760) 4 analogue inputs for temperature measurement with Pt 100 probes (IEC 751)Technical dataNumber of channels Galvanic separation Resolution (digital representation) Measuring principle Conversion time Time between 2 measurements Temperature error: