Title: økernvn 94.pdf
100150200250MHzLinkWare Version 7.4Cable ID: T3401 Date / Time: 09/11/2013 06:16:58 Headroom 5.8 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]173 265 10 8.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]14.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.0 207.0 36.7 78 9.8 207.0 34.1SR 36-78 5.8 71.3 44.2 36 7.7 71.5 41.7MAIN 12-36 9.3 239.5 35.6 36 10.0 245.5 32.8SR 12-36 7.8 249.5 35.4 36 8.5 249.5 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)