Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
■ 3.5. Attachment The unit should be installed and fixed on level ground. The sealing of supports should be performed using means suited to the type of flooring (not supplied). - Floor mountingSee annex 3Do not use wooden rafters as a mounting rail. Use a concrete base capable of bearing the load and the vibrations. Use pegs suited to the materials used with an appropriate seal length.■ 3.6. Access to connection points3 - INSTALLATIONSee annex 4■ 3.1. Unpacking Before unpacking, check that the packaging has not been damaged in any way and that the exterior is in good condition.■ 3.7. Refrigeration connections To ensure the quality of our products, the unit’s refrigeration circuit is dry charged. It is delivered pressurized with nitrogen.