Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
Temperature SEtpoint. COMPRESSOR diFferential. Relay compressor tripping differential. The compressor stops on reaching the Setpoint value (as indicated by the adjustment probe), and restarts at temperature value equal to the Setpoint plus the value of the differential. Note: the value 0 cannot be assumed Higher SEt. Maximum possible setpoint valuediFHSERANGE -50…990.1...30.050…230LEVEL*1&21&2U.M. °C/°F°C/°F°C/°F10LSE OSP Offset Set Point. Temperature Value to be added to the Set-Point if reduced set is enabled