Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]198 315 23 8.6198 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.4 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.0 * 242.5 35.6 36 0.8 * 242.5 32.9SR 36-450.4 *249.0 35.4 36 0.6 *247.5 32.8MAIN 36-45 1.0 249.0 35.4 36 0.8 242.5 32.9SR 36-45 0.4 249.0 35.4 36 0.6 247.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 14.9 93.5 24.8 45 17.1 89.3 22.2SR 45-12 14.8 89.3 25.2 45 16.4 88.3 22.3MAIN 45-12 17.4 187.5 18.7 12 19.4 191.5 15.5SR 45-12 17.0 187.5 18.7 45 20.0 188.0 15.7010080604020050100150MHzACR-F (dB)200250010080