Title: 1 etg del 2.pdf
Cable ID: T1093 Date / Time: 10/17/2013 03:08:42 PM Headroom 13.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]302 479 34 13.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]4.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.9 71.5 34.7 36 16.1 97.3 29.5SR 12-36 13.8 99.8 32.3 36 14.5 99.8 29.3MAIN 12-36 14.2 99.8 32.3 36 16.2 99.8 29.3SR 12-36 13.8 99.8 32.3 36 14.5 99.8 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.5 44.0 25.7 36 22.8 47.0 22.2