Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
120120121121TEST RAPPORTResultatZ-LINEZ: 0.63ΩIsc: 366A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF036 16C2/003 19.11.2020 09:15Zs(rcd)Z: 0.48ΩIsc: 479A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF036 16C2/003 19.11.2020 10:41KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF037 16C2/003 05.11.2020 09:51SPĆNDINGU12: 233V U1pe: 233V U2pe: 0V f: 50.1HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF037 16C2/003 05.11.2020 09:51Z-LINEZ: 0.62ΩIsc: 370A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 140A Isc(0.76%): 281A Isc(1.15%): 425ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF037 16C2/003 05.11.2020 09:51Zs(rcd)Z: 0.59ΩIsc: 390A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF037 16C2/003 05.11.2020 09:52Tallberg Elektro A/S Tlf.22796640Side:18GODKJENT