Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
The unit must stand firmly, straight and raised from ground level. Provide a firm and flat surface, for example, a ground stand, a garden slab, concrete bed, Leca blocks or similar. Note that the wooden pallet that the pool pump is resting on for delivery is to be removed during installation.Large amounts of melt and condensation water are discharged during defrosting and operation, which is entirely normal. Consequently, it is important to ensure good drainage and run-off. Up to 10 litres of condensation water per hour can form during operation.700mm m 0 0 5Air intakeThe outdoor section must be placed so that the air supply to the evaporator coil is sufficient. This produces a higher output and improved efficiency.mmm700mmmmPositioning of a horizontal model67InstallationDistance to the pool The pool heat pump is normally installed in connection to the pool’s purification system to minimise pipe routing.