Title: etg u1.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.8 52.8 33.2 12 14.8 45.5 32.7SR 12-78 19.0 57.3 32.0 12 17.1 45.5 32.7MAIN 36-45 22.6 249.5 4.7 36 22.6 250.0 2.0SR 12-36 29.8 238.0 5.9 36 29.8 241.0 2.9010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.4 30.1 18.6SR 36 4.2 30.1 18.6MAIN 45 6.9 235.0 10.3SR 36 7.2 249.5 10.060500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1