Title: +135.01=315.002-UZ001T_02-Manual320.pdf
Ultimately, the user or attendant must exercise due diligence to ensure that the delivery of warm water is at a stable, safe temperature. This is particularly important in such healthcare procedures as supervised bathing of patients unable to respond immediately to unsafe temperatures.Fluctuating or reduced flow rate a. Check filters and inlet / outlet fittings for flow restriction(check isolators are fully open).b. Ensure that minimum flow rate is sufficient for supplyconditions.Care is required when making any adujustments to flow or temperature, make sure that the temperature is suitable and has stabilised.c. Ensure that dynamic inlet pressures are nominallybalanced.d. Ensure that inlet temperature differentials are sufficient.SpecificationNo flow from mixing valve outlet a. Check inlet isolators are fully open.Pressuresb. Check filters and inlet / outlet fittings for blockage.Minimum Dynamic Supply Pressure: 0.1 bar (10 kPa)c. Hot or cold supply failure.