Title: Data tester Smestad skole - Detaljert.pdf
Overall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 35,2 68,0 183,0 10,0 6,4Limit 100,0 - 555,0 50,0 25,0Margin 64,8 - 372,0 40,0 18,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 2,20Worst Value: Local: 45 15,2 43,7 28,5 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 19,6 12,4 7,2 145,00Remote: 78 21,0 14,2 6,8 94,75Worst Value: Local: 12 16,1 8,6 7,5 345,00Remote: 36 15,4 8,0 7,4 471,00dB -2020600Local