Title: +038=242.003-QZ001T_02-FR Brannplate Protecta - Teknisk Datablad.pdf
1200mm hey Gjennomforinger Rorstruper Brannmotstand < @40mm PVC-U 8 PVC-C 50 x 1.8mm (1 lag) El 120 UV, CIU, UIC, C/C < @40mm PE. ABS & SAN+PVC 50 x 1.8mm (1 lag) EI120 UV, C/U, UIC, C/IC < @40mm PP 50 x 1.8mm (1 lag) E1120 UV, C/U, UIC, CIC ©241-110mm PVC-U 8 PVC-C 50 x 3.6mm (2 lag) | E120U/C, C/C 8 EI%0 UIC, CICE 120 U/C, C/C & EI 90 U/C, CIC EI90 U, CIU, UIC, CIC©41-110mm PE, ABS & SAN+PVC 50 x 3.6mm (2 lag) 241-110mm PP 50 x 3.6mm (2 lag)©125mm PVC-U & PVC-C 50 x 5.4mm (3 lag) E 120 U/C, C/C & EI 90 U/C, CIC ©125mm PE, ABS & SAN+PVC 50 x 5.4mm (3 lag) E 120 U/C, CIC & EI 90 U/C, CIC @125mm PP 50 x 5.4mm (3 lag) E 120 U/C, C/C & EI 90 U/C, CIC 2160mm PVC-U & PVC-C 50 x 7.2mm (4 lag) E 120 U/C, C/C 8 EI 90 U/C, CIC & 3 @160mm PE, ABS & SAN+PVC 50 x 7.2mm (4 lag) E 120 U/C, C/C 8 EI 90 U/C, C/C Alle gjennomforinger og apninger ma fuges @160mm PP 50 x 7.2mm (4 lag) E 120 U/C, C/IC & EI90 U/C, CICmed FR Akryl pabeqqe sider