Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
OBJEKT / Plan 10 / FUSE033 10.02.2020 13:28SPÆNDINGUln: 228V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE033 10.02.2020 13:28Z-LINEZ: 0.70ΩIsc: 330A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE033 10.02.2020 13:29Zs(rcd)Z: 0.63ΩIsc: 368A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE033 06.02.2020 09:13R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE035 10.02.2020 09:10SPÆNDINGUln: 232V Ulpe: 230V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE035 10.02.2020 09:11TEST RAPPORTSide:7GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.454546464747484849495050ResultatZ-LINEZ: 0.63ΩIsc: 367A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE035 10.02.2020 09:12Zs(rcd)Z: 0.47Ω