Title: Installasjonsmanualer.pdf
Firmware Version: Relay Card V1.4 [1] . Customize Output Relay [2] . Conﬁ gure Input Signal [3] . Customize Normal Open or Normal Close [0] . Quittion to contacts R1~R6.Please Enter Your Choice >Having completed the configuration, shift SW2 to the ON position to activate the settings. The default settings can be restored by setting SW2 to OFF.Customize Output Relay2. Press ‘2’ to configure the input signal.The input signal can be used either to shut down the UPS or to test the batteries. The delay preceding shutdown of the UPS can be set up to 9999 seconds maximum.3. Press ‘3’ to configure NO or NC operation of each relay.Relay Selected Event [1] . Relay 1: Summary Alarm [2] . Relay 2: Power Fail [3] . Relay 3: Battery Low [4] . Relay 4: On by-pass [5] . Relay 5: Overload [6] . Relay 6: Overtemperature [0] . Back to Previous MenuShift SW2 to the ON position to activate the settings.If SW2 is returned to the OFF position, SW1 can be used to check the NO or NC position of all the relays.