Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]21.3 93 2 3.34Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.6 479.0 28.8 36 8.0 467.0 26.6SR 36-45 6.7 468.0 29.4 36 7.2 468.0 26.5MAIN 36-45 8.9 490.0 28.3 36 9.0 500.0 25.0SR 36-45 7.0 496.0 28.0 36 7.3 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.9 6.5 49.0 45 17.6 3.8 50.8SR 78-45 17.8 5.0 51.3 45 17.6 3.8 50.8MAIN 78-45 18.1 498.0 11.3 78 19.2 500.0 8.3SR 78-45 18.0 498.0 11.3 45 19.2 498.0 8.30100806040200250 MHzACR-F (dB)