Title: økernvn 94.pdf
250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: T3398 Date / Time: 09/13/2013 08:28:07 Headroom 14.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]258 392 12 11.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]5.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 18.3 52.0 37.0 36 19.6 52.0 34.0SR 12-36 14.0 49.5 37.3 78 14.5 79.3 31.0MAIN 12-78 20.3 96.8 32.5 78 21.1 94.0 29.7SR 36-78 14.2 79.5 33.9 78 14.5 81.8 30.7