Title: +038=370.001-NT014._01-Statico_NO_low.pdf
= -12,9 °C0,01510,02070,02670,03330,04010,04760,05540,06390,07270,07740,082340 %= -20,9 °C0,02110,02720,03380,04080,04810,05610,06440,07310,08260,08730,092450 %= -33,2 °C0,02880,03550,04250,05000,05770,06600,07470,08390,09350,09850,1036Tabell 4: vs ca. vannvolum*** for varmeanlegg i forhold til installert varmeeffekt Qtsmax | tr Eldre radiatorer°Cvs liter/kW90 | 7014,080 | 6016,570 | 5520,170 | 5020,660 | 4027,950 | 4036,640 | 3035| 28Nye radiatorervs liter/kW9,010,112,111,915,120,1Konvektorervs liter/kW6,57,08,47,99,613,4Ventilasjonssystemervs liter/kW5,86,17,26,67,610,8Gulvvarmevs liter/kW10,311,413,313,115,820,329,137,8) MEG = Mono-Ethylene Glycol **) MPG = Mono-Propylene Glycol ***) vannvolum = energikilde + distribusjonsnett + varmeavgivere