Title: 2 etg del2.pdf
PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.6 22.4 19.3SR 36 3.8 12.6 20.5MAIN 36 9.7 238.5 10.2SR 36 8.5 226.0 10.560500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94Cable ID: T2192 Date / Time: 10/10/2013 03:25:47 PM Headroom 1.2 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%