Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 25.0 82.0 27.3 36 25.2 82.0 24.8SR 12-45 26.6 82.5 27.3 45 27.3 82.3 24.8MAIN 36-45 39.3 493.0 -11.9 36 39.0 500.0 -15.3SR 36-45 39.2 493.0 -11.9 36 39.0 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.4 491.0 8.0SR 12 7.8 470.0 8.0MAIN 45 6.4 491.0 8.0SR 12 7.8 470.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00424.3 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)