Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Uci: 0.1V t: 222.9ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 525V Rnpe: >30.0MΩ Um: 514VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 2 10.03.2022 13:39 (TomekElektriker)KONTINUITET: R200mA LPER: 0.16ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 3 10.03.2022 11:33 (TomekElektriker)TALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:3GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.12121313TEST RAPPORTResultat SPENNING TRMS Uln: 234V Ulpe: 234V Unpe: 1V f: 50.06HzSYS.: TN/TTZ-LINEZ: 0.42ΩIsc: 549A R: 0.42Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 28.5mAUci: 0.1V t: 12.3ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 529V Rnpe: >30.0MΩ Um: 514VUiso: 500V Grenseverdi: 1MΩ