Title: Data tester Smestad skole - Detaljert.pdf
1000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 31,1 27,4 3,7 392,00Remote: 45 27,9 23,8 4,1 500,00Worst Value: Local: 36 27,7 23,8 3,9 500,00Remote: 45 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 19,3 7,3 12,0 497,00Worst Value: Local: 45 19,3 7,3 12,0 497,00Remote: 45 73,0 61,2 11,8 1,00Remote: 45 19,4 7,2 12,2 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 49Copper Certification ReportCable Label: 521.002-UD-148 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:56:44 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: