Title: 1 etg del 2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]146 232 17 6.1146 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.0 * 243.0 35.5 36 0.7 * 243.0 32.9SR 36-450.7 *248.0 35.4 36 0.8 *248.0 32.8MAIN 36-45 1.0 248.0 35.4 36 0.7 243.0 32.9SR 36-45 0.7 248.0 35.4 36 0.8 248.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 12.1 2.4 56.7 45 14.7 2.3 54.1SR 45-36 12.1 2.4 56.7 45 14.7 2.3 54.1MAIN 45-36 16.9 236.0 16.7 45 19.2 239.0 13.6SR 45-36 17.4 247.5 16.3 45 18.8 236.0 13.7010080604020050100150MHzACR-F (dB)20025001008060