Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD2 compo- nents.6Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-64Saia-Burgess Controls Ltd.Input/output (I/O) modulesAnalogue output modules6.10 Analogue output modulesPCD2.W400 PCD2.W410 PCD2.W600 PCD2.W6104 analogue outputs 8 bit, 0...10 V 4 analogue outputs 8 Bit, 0 … 10 V, 0 … 20 mA, 4 … 20 mA *) 4 analogue outputs 12 bit, 0...10 V 4 analogue outputs 12 Bit, 0 … 10 V, 0 … 20 mA, 4 … 20 mA, Pt/Ni 1000 *)) jumper selectableI/O modules and I/O terminal blocks may only be plugged in and removed when the PCD and the external +24 V are disconnected from the power supply.6Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-65Saia-Burgess Controls Ltd.Input/output (I/O) modules