Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
PCD2.K106 PCD3.K1x6 PCD3.K010 Max. 6 PCD3.C200PCD2.C2000/ C1000* 756895PCD2.K106 PCD3.K1x6 PCD2.K010* *In preparationHardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-10Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsPCD2 CPUs3.4.4 Expansion housingsThe PCD2.C2000/C1000 expansion housing provides space for 8/4 additional I/O modules and can be expanded to provide up to 64 sockets. The dimensions of the housing match those of the PCD2.M5_ base unit. The sockets are numbered clock- wise from the left, from 0 to 7. The expansion housings with sockets 8 to 15 etc. are also numbered clockwise. They are connected to each other and to the base unit with 26-wire expansion cables or connectors:3PCD2.K010 Connector for mounting side-by-sideInternal supply to PCD2.C2000/C1000 module holdersC D V 4 2 y p p u SlPTCDC39V4400 µFLED 24VDCDCDCVoltage- monitor 5V und V+PCD-Bus+5VCLR0VV+ (16,2V)