Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Uiso: 250VGrenseverdi:IMQR LOW Ohm GODKJENTR: 0.07QR+: 0.1QR: 0.1QGrenseverdi: 1.0QSPENDINGUln: 235VUlpe: 235VUnpe: 0Vf£: 50.0HzGODKJENTZs (rcd) GODKJENTZ: 0.57QIsc: 403ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AZLINE GODKJENT| Z: 0.62QIsc: 3727Sikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AKONTINUITET GODKJENTR: 0.1QGrenseverdi:1.0QTEST RAPPORTNr. ResultatR ISO GODKJENTR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQ132 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 034 GODKJENT * i 12.03.2020' 13:28 R LOW Ohm GODKJENT R: 0.19Q R+: 0.2Q R-: 0.2QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 034 GODKJENT* 12.03.2020 13:34ZLINE GODKJENTZ: 0.70QIsc: 328ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 034 GODKJENT * 12.03.2020 13¢36RCD I . GODKJENTI: 28.5mAUci: 0.3Vt: 18.1msIdn: 30mAtype: ACHN\,