Title: økernvn 94.pdf
Measurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3065 Date / Time: 09/12/2013 03:17:56 Headroom 12.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]191 302 20 8.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.2 91.0 33.0 36 14.3 91.0 30.0SR 12-36 12.9 17.0 44.8 12 15.7 17.0 41.8MAIN 12-36 12.2 91.0 33.0 36 14.7 99.5 29.3SR 12-36 13.9 96.3 32.6 36 15.8 97.8 29.510080604020