Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]31.1 135 2 4.72Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.7 470.0 29.8 36 5.9 474.0 26.9SR 12-36 7.4 460.0 30.0 36 7.5 497.0 26.4MAIN 36-78 6.8 474.0 29.7 36 6.1 497.0 26.4SR 12-36 7.5 498.0 29.3 36 7.5 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.4 476.0 11.7 45 20.1 500.0 8.3SR 78-45 19.5 476.0 11.7 45 20.6 500.0 8.3MAIN 45-78 19.8 500.0 11.3 45 20.1 500.0 8.3