Title: Instructions manual - THGT fan.pdf
2.4 Fan should be located in position, and assembled with any accessory equipment supplied, on relevant mounting, anti-vibration mountings, safety protection guards, on a solid level base to avoid any distortion and misalignment and with correct air direction as shown on nameplate. Fan should then be leveled on any anti-vibration mountings. Note: high pressure fans may require subsequent adjustment to anti-vibration mountings due to fan reaction to operation pressure. Note: ensure bolts are tightened in accordance with Installers chosen supplier, or refer typical information in Annex 2: Typical bolt fixing torque2.5 When installed correctly, fan duct connections with any flexible connectors, safety guards can be assembled. Flexible connectors mustbe taught to ensure no disruption to air flow, especially on inlet to fan.2.6 When installed correctly, fan electrical connections, earth connections, any sensor connections can be made. Only the specific motor,