Title: 1 etg del 2.pdf
Cable ID: T1181 Date / Time: 10/21/2013 12:27:44 PM Headroom 14.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]136 216 15 5.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.5 67.5 35.1 36 16.1 88.8 30.2SR 12-36 19.6 55.3 36.5 36 20.2 96.0 29.6MAIN 12-36 15.0 96.3 32.6 36 16.2 96.0 29.6SR 36-78 21.5 96.3 32.6 36 20.2 96.0 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.2 95.8 19.0 45 25.5 77.5 17.8