Title: Sprinklerhode våt (1).pdf
(a) For coverage area dimensions less than or between those indicated, use the minimum required flow for the next highest coverage area for which hydraulic design criteria are stated.Requirement is based on minimum flow in GPM (LPM) from each sprinkler. The associated residual pressures are calculated using the nominal K-factor. Refer to Hydraulic Design under the Design Criteria section.For NFPA 13 residential applications, the greater of 0.1 gpmVft2 over the design area of the flow in accordance with the criteria in this table must be used.11/4 to 13/4inches belowbottom ofbeam.()©TABLE AWET PIPE SYSTEMSERIES LFIl RESIDENTIAL PENDENT AND RECESSED PENDENT SPRINKLERS (TY2234) NFPA 13D, 13R, AND 13 HYDRAULIC DESIGN CRITERIADRY PIPE TEM Minimum Flow and Residual Pressure(®: ©)