Title: økernvn 94.pdf
Cable ID: T4024 Date / Time: 09/11/2013 09:54:58 Headroom 11.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]71 113 8 3.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.8 91.8 32.9 12 16.2 100.0 29.3SR 12-36 11.7 91.8 32.9 12 15.9 100.0 29.3MAIN 12-36 11.8 91.8 32.9 36 13.7 92.0 29.9SR 12-36 11.7 91.8 32.9 36 13.5 92.0 29.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 28.0 7.6 41.0 12 28.7 6.0 40.1