Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 20,8 10,3 10,5 497,00Remote: 12-45 21,0 10,3 10,7 497,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,9 3,2 496,00Remote: 36 28,7 23,8 4,9 499,00Worst Value: Local: 36 27,1 23,9 3,2 496,00Remote: 36 28,7 23,8 4,9 499,00PS-ACRF: Pass Worst Margin: Local: 45 19,3 7,2 12,1 499,00Worst Value: Local: 45 19,3 7,2 12,1 499,00Remote: 45 19,6 7,2 12,4 500,00Remote: 45 19,6 7,2 12,4 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:08Signature:______________________ Page: 97Copper Certification ReportCable Label: 521.002-UD-106 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:30:58 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: