Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
Heat exchangerTitanium heat exchangerFan motorAC motorCabinetGrey painted steel cabinetNoise level (at 1 m)dB(A)49515354Water connectionmm50 mmm3/h1.52.33.04.5Pressure drop at nominalbar0.050.020.030.08Pressostat breaking value HPbar44 (switch closes again at 32 bar)Pressostat breaking value LPbar1.5 (switch closes again at 3.0 bar)Heightmm575575603603Widthmm79079010001000Depthmm341341403403Weightkg33375359humidity of 70 % and a pool temperature of 26 °C, in accordance with the French pool heat pump standard NF 414.2 Heating capacity should be regarded as guide values for an insulated pool covered at night. The models are primarily designed for use during the period May to September which is a normal pool season.temperature of 26 °C. The operating current may vary depending on the above conditions.79Technical specificationDimensions and connectionsP10/P15290Water outlet Ø500 7 2