Title: 2 etg del2.pdf
SR 12-36 9.9 30.5 40.3 12 11.7 22.1 41.6MAIN 12-36 16.8 249.5 4.7 36 16.6 249.0 2.1SR 36-45 17.2 248.5 4.8 36 16.9 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.3 36.5 18.2SR 45 2.7 15.9 20.0MAIN 36 7.9 227.5 10.4SR 36 5.4 250.0 10.060500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94