Title: 1 etg del 2.pdf
MAIN 36-45 18.6 247.0 5.0 36 18.4 242.5 2.8SR 36-45 18.1 247.0 5.0 36 17.9 247.0 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.1 23.5 19.1SR 36 4.0 23.4 19.2MAIN 36 8.3 240.5 10.2SR 36 8.9 241.0 10.260500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94