Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 16.3 466.0 11.9 45 16.5 3.3 52.0MAIN 78-45 16.8 493.0 11.4 45 17.8 500.0 8.3SR 78-45 16.6 500.0 11.3 45 16.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 26.1 55.0 33.1 36 27.1 55.5 30.5SR 36-45 23.6 55.3 33.1 36 23.8 66.0 28.1MAIN 36-45 35.2 497.0 -12.2 36 35.0 497.0 -15.1SR 36-45 35.4 498.0 -12.3 36 35.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.1 79.3 15.0SR 12 5.6 496.0 8.0MAIN 45 8.5 447.0 8.0SR 12 5.6 496.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS