Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
If a key (or Input 0 / Input 1) is activated for longer than the defined "hold time", the module will switch to hold operation. The smallest value that can be set for the hold time is 1 (1/10 second), i.e. the module will switch directly into hold mode.In hold mode, the output (blinds up/down) stays on for the defined "move time". The module resets the output at the end of this time. The movement can be stopped by activating an input. The processing of these times may be affected by accesses by the Saia PCD®. The hold function can also be activated via the FBox.Input> hold-timeOutputshort move-time move-timeStopping the movementIf an output is switched to hold mode, this will stop as soon as a new input pulse is detected, regardless of which key (direction) is pressed.Input> hold-timeInput Ø oder 1Outputmove-time6-50PCD3.A860