Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The tap-off unit with automatic clamping system can be clamped in two stable positions:  Disconnected position: the tap-off unit is not connected to the mains. It can remain clamped in thisdisconnected position before being plugged into the run component. Connected position: the tap-off unit is connected to the mains.QGH3492101-01 11/201857Tap-off UnitsInstallation of Bolted Tap-Off UnitsIntroductionTap-off units are used to connect loads or secondary runs. They comply with installation standards and regulations (IEC 60364) irrespective of the earthing system (TT, TNS, TNC, or IT).Bolted tap-off units can be plugged into and removed from the run component when the run component is not energized.The bolted tap-off units from the Canalis KS systems are compatible for use with the Canalis KT system.DANGER HAZARD OF ELECTRIC SHOCK, EXPLOSION OR ARC FLASH