Title: 1 etg del 2.pdf
Cable ID: T1061 Date / Time: 10/17/2013 03:22:56 PM Headroom 9.0 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]237 376 27 10.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.0 226.5 36.0 78 8.7 204.0 34.2SR 36-78 9.0 237.5 35.7 78 9.1 237.5 33.1MAIN 45-78 9.1 241.5 35.6 78 8.8 239.5 33.0SR 36-78 9.0 237.5 35.7 78 9.1 237.5 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 13.9 248.0 16.3 36 15.6 172.0 16.5