Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.4 114 1 3.86Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.6 459.0 29.8 36 7.0 455.0 27.2SR 12-36 8.0 451.0 30.2 36 7.9 451.0 27.4MAIN 36-78 8.9 500.0 27.8 36 7.7 496.0 25.2SR 12-36 8.7 496.0 28.0 36 8.4 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.3 7.1 48.2 45 21.9 7.4 44.9SR 45-78 20.3 7.4 47.9 45 21.9 7.1 45.2MAIN 36-12 21.4 479.0 11.6 36 23.7 498.0 8.3SR 12-36 21.4 479.0 11.6 36 22.7 479.0 8.60100806040200250 MHzACR-F (dB)