Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]11.7 51 1 2.02Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]35.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.0 465.0 29.5 36 6.5 466.0 26.6SR 36-45 5.2 405.0 31.2 36 5.6 406.0 28.4MAIN 36-45 6.0 465.0 29.5 36 8.0 497.0 25.1SR 36-45 6.9 496.0 28.0 36 6.8 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 4.3 52.7 45 14.1 2.9 53.1SR 36-45 14.7 4.0 53.2 45 14.1 2.9 53.1MAIN 45-36 15.9 473.0 11.7 45 17.5 473.0 8.7SR 36-45 15.8 473.0 11.7 45 17.5 473.0 8.70100806040200250 MHzACR-F (dB)