Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Condensate may be discharged at a maximum height of 200 mm above the unit, as long as the ascending tube is vertical and aligned with the drainage flange. If it is necessary to discharge the condensate from a level above 200 mm, install an auxiliary water discharge pump and float valve. A float valve is recommended to stop the flow switch if there is a fault at the auxiliary pump.Condensate may be discharged at a maximum height of 200 mm above the unit, as long as the ascending tube is vertical and aligned with the drainage flange. If it is necessary to discharge the condensate from a level above 200 mm, install an auxiliary water discharge pump and float valve. A float valve is recommended to stop the flow switch if there is a fault at the auxiliary pump.The condensate pipe must be insulated with a condensation-proof material such as polyurethane, propylene or neoprene of 5 to 10 mm thickness. If more than one unit is installed in the room, the drain system can be made as shown in the drawing fig.23.