Title: økernvn 94.pdf
MAIN 12-36 8.8 13.4 49.4 36 10.3 13.4 47.0SR 12-36 8.6 13.3 49.5 12 10.1 11.8 48.3MAIN 36-45 12.9 249.5 4.7 36 12.9 249.5 2.1SR 36-45 12.2 249.5 4.7 36 12.0 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.6 14.8 20.2SR 45 3.9 8.5 21.0MAIN 36 5.2 171.5 11.7SR 36 6.8 234.5 10.306050050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94