Title: isover_fireprotect_produktdokumentasjon_spfr_010-0202_2016_no_-_gyldig_til_07_2021.pdf
Tabell A.5: Design Steel Temperature 525oC: Design table for ISOVER Fire Protect 150 mineral wool boards for fire protection on steel to Standard Fire Exposure. Design values from ENV 13381-4:2007 numerical regression. Regression constants multiplied with factor kMOD = 0,996 to satisfy prEN 13381-4:2009 Section 13.5.1 Criteria for acceptability.Multiple R0.998433525oCR20.99686830609012015018021024050202020202535405060202020203040506070202020253550607080202020304060708090202020355060801002020253550708011020202540607012020203050608013020203050608014020203550708015020203550701602020356070170202040608018020204060801902025406080200202540608021020255060802202025507080230202550702402025507025020305070Open and closed steel sections ao = 0Critical steel temperature:kMOD = 0,996F/AFire Resistance time in minutesSP Fire Research AS Postadresse Postboks 4767 Sluppen 7465 TrondheimBesøksadresse Tillerbruveien 202 7092 TillerTelefon 464 18 000E-post / web post@spfr.no www.spfr.no