Title: +038=433.002-FS002. Tavlebyggeren FDV.pdf
Rated switching capacity according to IEC/EN 60947-2 (max operational voltage)Terminal capacitiesB, C, D, K, S, ZV ACV ACV ACV ACAs requiredkAkAkAkAkARated voltage according to IEC/EN 60898-1Thickness of busbar materialOperationsTerminal protectionMechanicalRated operational voltage60 (per pole)Mounting width per poleSimilar to illustrationPvidPvidRated operational current for speciﬁed heat dissipation8010105 (UL1077)3lifespanALifespanEnclosure heightDirection of incoming supply00IP20, IP40 (when ﬁtted)IcnV DCHeat dissipation per pole, current-dependent0.8 … 2UeUeMounting positionRated service short-circuit breaking capacity according to IEC/EN 60898-1240/41545Breaking capacity according to UL13.6IEC/EN 60715 top-hat railMountingInEquipment heat dissipation, current-dependent1 x 25IEC/EN 60947-2IEC/EN 60898mmmmmmmmRated switching capacity according to IEC/EN 60898-1