Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
■ Maintenance operations Specific preventive maintenance operations are required at regular intervals and should be performed by CIAT-approved contractors.List of system start-up checks (non-exhaustive): - Correct siting of unit - Power supply protections - Phases and direction of rotation - Wiring connections on unit - Direction of water flow in unit - Cleanliness of water circuit - Water flow rate at specified value - Pressure in the refrigerant circuit - Direction of rotation of compressors - Water pressure drops and flow rates - Operating readingsThe operating parameters are read and noted on a "CHECK LIST" form to be returned to CIAT.To do this, you must refer to and comply with the instruction manual.take out a maintenance contract with a You must CIAT-approved refrigeration equipment specialist. Such a contract is required even during the warranty period.Drycoolers ■ CIAT OPERA series drycoolers are compatible withDYNACIAT LG units with water cooled condensers.