Title: 1 etg del 2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]212 338 25 9.1212 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 1.1 235.5 35.8 36 0.9 * 246.5 32.8SR 36-78 5.6 229.0 36.0 36 6.8 227.5 33.4MAIN 36-45 1.3 249.5 35.4 36 0.9 246.5 32.8SR 36-78 5.6 248.0 35.4 36 7.2 248.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.7 190.5 18.6 36 19.6 241.5 13.5SR 36-12 17.1 190.5 18.6 36 19.7 233.5 13.8MAIN 12-36 19.0 241.5 16.5 36 19.6 241.5 13.5SR 36-12 18.4 241.5 16.5 36 19.7 238.0 13.7010080604020050100150MHzACR-F (dB)2002500100806040