Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]38.2 497.0 41.5Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.0 398.0 31.4 36 6.3 477.0 26.1SR 12-45 5.8 464.0 29.6 36 5.7 476.0 26.1MAIN 36-78 7.8 494.0 28.1 36 6.3 477.0 26.1SR 36-45 6.1 477.0 28.9 36 5.7 476.0 26.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.4 3.5 54.4 45 14.2 2.6 53.9SR 78-45 15.3 3.5 54.4 45 14.3 2.5 54.3MAIN 45-78 16.9 499.0 11.3 45 16.4 500.0 8.3SR 78-45 17.0 499.0 11.3 45 16.0 498.0 8.30100806040200250 MHzACR-F (dB)N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.0 3.5 61.0 45 20.3 4.1 57.6SR 36-45 21.2 3.6 60.8 36 21.1 3.6 58.0MAIN 36-78 45.0 495.0 -12.1 36 44.6 498.0 -15.1