Title: 2 etg del2.pdf
Cable ID: D2024 Date / Time: 10/10/2013 11:58:23 AM Headroom 11.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]97 153 10 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.2 84.5 33.5 36 13.7 84.5 30.5SR 12-36 11.2 88.0 33.2 36 13.8 67.5 32.1MAIN 12-36 11.4 98.0 32.4 36 13.9 98.0 29.4SR 12-36 11.2 98.0 32.4 36 13.8 98.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.6 98.0 18.8 36 23.8 3.5 44.7