Title: 40 Bender brukermanual.pdf.pdf
3. Function Monitoring the measuring channel for overcurrent or undercurrent. Use of the measuring channel as digital input. Unused measuring channels have to be disabled. > < 0/1 off Alarm when the response value is exceeded. Alarm when the value falls below the set response value. Use of the measuring channel as digital input. Measuring channel disabled.Scanning time digital inputs < 3.5 s.Potential-free contact > 250 Ω, LC display indication: "0" Potential-free contact < 100 Ω LC display indication: "1"RCMS460-490_D00067_03_M_XXEN/12.201763Measuring function (selectable)RCMS…-D/-L Channel 1…12RCMS…- D4/-L4, Channel 1…8RCMS…- D4/-L4, Channel 9…12I/IΔn:6 mA…20 A (42…2000 Hz) type A</>/OFF</>/OFF---I:100 mA…125 A (42…2000 Hz)------</>/OFFI/IΔn:10 mA…10 A (0…2000 Hz) type B</>/OFF</>/OFF---1/01/0/OFF1/0/OFF---