Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Connect the PEN link between the protective earth conductor (PE) and the neutral conductor (N) of the end feed unit by using the bolts delivered with the link.Flexible LinksThe number of flexible links required for the connection of the transformer to the end feed unit depends on the rating of the busbar trunking system.KTA rating (A)1000 to 16002000 to 250032004000–5000–KTC rating (A)1350 to 16002000 to 2500320040005000–6300Number of flexible linksCopper Bars2 (100×5)3 (100×5)4 (100×5)5 (100×5)6 (100×5)6 (120×5)8 (120×5)Cross section (mm2)1000150020002500300036004800QGH3492101-01 11/201839Transformer ConnectionsConnection to Dry-Type TransformersIntroductionThe Canalis KT system can be connected to dry-type transformers using either an edgewise or a flatwise arrangement. The incoming run component can either be from the side or the centre.Examples of connection arrangements:Edgewise with side incomer: