Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Nr.778899101011111212ResultatSPÆNDINGUln: 234V Ulpe: 234V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE025 07.02.2020 13:08Z-LINEZ: 1.07ΩIsc: 214A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE025 10.02.2020 08:56Zs(rcd)Z: 0.83ΩIsc: 277A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE025 06.02.2020 11:50R LOW OhmR: 0.22ΩR+: 0.1Ω R-: 0.3Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE025 10.02.2020 08:56RCD II: 28.5mAUci: 0.2V t: 12.1ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE026 10.02.2020 09:01Z-LINEZ: 0.75ΩIsc: 307A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE026 06.02.2020 09:14TEST RAPPORTSide:2GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.131314141515161617171818Resultat R LOW OhmR: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0Ω