Title: 40 Bender brukermanual.pdf.pdf
RCMS460-490_D00067_03_M_XXEN/12.201743RCMS…-L has a 7-segment LED display. Operation and setting can be carried out via an RCMS…-D or using the following devices: MK2430, MK800, COM460IP or CP700. The harmonics analysis and the preset function can only be carried out in conjunction with an RCMS…-D. Only the BMS bus address can be set directly on the RCMS…-L. The following functions and settings are not included in the RCMS…-L :– Language– Time/date– Data logger– Interface menu– History memory– PasswordSetting the BMS bus address of the RCMS…-L1. Press the "SET" button for approximately two seconds to open the main menu. The BMS bus address flashes.1. Press the "SET" button for approximately two seconds to open the main menu. The BMS bus address flashes.2. Use the arrow buttons ", " to select the required address. 3. Press the Enter button "↵" to confirm this setting. 4. If you wish to exit the setting without making a change, press the "ESC" button.