Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 56,0 68,0 292,0 17,0 9,7Limit 100,0 - 555,0 50,0 25,0Margin 44,0 - 263,0 33,0 15,3Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 1,1 3,0 1,9 2,80Worst Value: Local: 45 24,4 43,7 19,3 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 25,5 18,6 6,9 30,70Remote: 78 17,1 14,5 2,6 89,25Worst Value: Local: 12 18,0 8,0 10,0 428,00Remote: 78 16,8 8,0 8,8 446,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):