Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD2 components.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-35Input/output (I/O) modulesPCD2.A2506.5.4 PCD2.A250, 8 relays with make contacts, without contact protectionApplicationThe module contains 8 relays with normally-open contacts for direct or alternating current up to 2 A, 48 VAC. The module is especially suited wherever AC switching circuits with infrequent switching have to be controlled. For space reasons, there is no integrated contact protection.Technical dataNumber of outputs: Type of relay (typical): Operating mode: Switching capacity: *) (contact lifetime)4 + 4 make contacts with shared terminal RE 030024, SCHRACK > 12 V, > 100 mA 2 A, 48 VAC AC1 1 A, 48 VAC AC11 2 A, 50 VDC DC1 1 A, 24 VDC DC11