Title: +135.01=370.003-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Power pack AC/DC 24 V ● Protection class ● Power supply ● Frequency ● Maximum power consumption ● Terminals ● For connecting line ● Backup time in the event of power failureIII (SELV) AC 12...36 V or DC 12...42 V 50/60 Hz or DC 0.8 VA 2x1.5 mm² Ø 5...6 mm >20 minutesCommunicationPulse module WZU-P2Pulse outputs ● Number of outputs per module ● Standard pulses – Pulse value– Pulse length – Period duration2 For energy, volume and tariff register 1 kWh, 10 kWh, 1 MJ, 10 MJ, 100 MJ, 0.1 m3, 1 m3 per pulse 100 ms conducting >200 msPulse for operating states– Pulse duration for "Ready" – Pulse duration for "Fault" – Period durationFast pulses– Pulse length – Max. pulse frequencyFast pulses– Pulse length – Max. pulse frequency0.1…0.25 ms conducting Constantly non-conducting 500 ms If 1 pulse module is fitted 2…100 ms in increments of 1 ms 33 Hz If 2 pulse modules are fitted 5…100 ms in increments of 5 ms 33 Hz39 CE2N5324en 2018-08-1840 Building Technologies