Title: SysAQ R32 100HP.pdf
The indoor heat exchanger is consisting of stainless steel plates insulated with synthetic foam. It is protected by an antifreeze electric heater to ensure a good protection against freezing at low ambient temperature when the unit is switched off.OUTDOOR HEAT EXCHANGER The outdoor heat exchanger has a highly optimized design enables a refrigerant charge reduction of 40%. It is a finned coil constructed withseamless copper tubes mechanically expanded into aluminium fins. The fins of the heat pump versions (H) are covered with an hydrophylic blue coating to facilitate water droplets drain. The condenser can be equipped, as an option, with a protection grid to prevent shocks.FAN MOTORSThe AC fans are axial type, 800 mm diameter, IP54 grade and equipped with a thermal overload protection. They are also fitted with protection grids on top.ELECTRONIC CONTROL