Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF035 16C2/003 27.11.2020 11:41R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF035 16C2/003 27.11.2020 11:41Tallberg Elektro A/S Tlf.22796640Side:19GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.132132133133134134135135136136137137138138TEST RAPPORTResultat KONTINUITET R: 0.3ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF036 16C2/003 30.11.2020 11:48SPĆNDINGUln: 236V Ulpe: 236V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF036 16C2/003 30.11.2020 11:49Z-LINEZ: 0.69ΩIsc: 334A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF036 16C2/003 30.11.2020 11:49Zs(rcd)Z: 0.72ΩIsc: 320A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A