Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 38,4 68,0 199,0 10,0 6,8Limit 100,0 - 555,0 50,0 25,0Margin 61,6 - 356,0 40,0 18,2Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,1 2,4 2,95Worst Value: Local: 36 16,5 43,7 27,2 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 25,4 18,1 7,3 37,75Remote: 78 13,4 9,7 3,7 272,00Worst Value: Local: 12 16,4 8,7 7,7 338,00Remote: 78 13,4 9,7 3,7 272,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):