Title: Ventilmotor kjølebatterier 36.01 og .02 - AVM115.pdf
The upper section of the housing with the cover and indicator knob contains the synchronous motor with capacitor. The lower section of the housing contains the maintenance-free gear unit and the gear-release knob.Auxiliary change-over contacts: • Switch rating max. 230 V VAC, current min. 20 mA at 20 V • Switch rating max. 4...30 V VDC, current 1...100 mAPower consumptionTypeRunning time [s]StatusActive power P [W]Apparent power S [VA]AVM105F10030Operation2.45.4AVM105F120120Operation2.05.0AVM105F122120Operation1.61.7AVM115F120120Operation2.05.0AVM115F122120Operation1.61.7Outdoor installationThe actuators must also be protected from the weather if they are installed outside the building.DisposalWhen disposing of the product, observe the currently applicable local laws. More information on materials can be found in the Declaration on materials and the environment for this product.Connection diagram2-Pt.F..0 = 230V~