Title: 40 Bender brukermanual.pdf.pdf
"RESET" button: to acknowledge alarm and fault messages Down button: to change parameters, scroll"SET" button: to set the BMS address "ENTER" button: to confirm parameter changesAlarm-LEDs "1…12“ light up if an insulation fault has been detected in the relevant measuring channel or flash if there is a fault with the measuring current transformer.Digital display for device address and error codes.RCMS460-490_D00067_03_M_XXEN/12.2017Operation6.3 Working in operating modeStandard display6.3.1 In operating mode, you will see a bar graph on the RCMS460…-D display. For each of the 12 measuring channels, it shows what percentage of the set alarm value IΔn2 (alarm) and IΔn1 (prewarning) has been reached. For digital inputs 100 % = 1 and 0 % = 0.100%50%0%k 1 2 3 4 5 6 7 8 9 10 11 12Channel disabled (height = 1 graduation m Channel enabled Channel enabled, current is flowing (height ≥ 2 graduation mThe RCMS…-L shows its BMS bus address (e.g. 02). Only the green "Power ON" LED is lit.