Title: V20-03-02 VVS-anlegg plan 3 - DM3.pdf
LD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/s42 mm +c 2586 42 mm +c 2586LD010T Maks:120 m³/h Kjøling: 345 W 0.027 L/s Varme: 265 W 0.006 L/sOpp/ned 370.101: DN 100mm 370.101: DN 100mmLD010T Maks:120 m³/h Kjøling: 345 W 0.027 L/s Varme: 265 W 0.006 L/sLD010T Maks:120 m³/h Kjøling: 345 W 0.027 L/s Varme: 265 W 0.006 L/sLD010T Maks:120 m³/h Kjøling: 100 W 0.008 L/s Varme: 265 W 0.006 L/sLD010T Maks:120 m³/h Kjøling: 100 W 0.008 L/s Varme: 265 W 0.006 L/s3452Romregulering - Plan 03ProduktPlan 03 WISE RTA 03 WISE IAQ 03 WISE IORE 03 WISE RTS 03 WISE director (trådløs router)ProduktBørverdiomstiller CO2-, RH- og temperaturgiver Input Output Radio Extender Temperaturgiver Wise Director router67LD022T Maks:100 m³/h Kjøling: 0 W 0.000 L/s Varme: 120 W 0.006 L/sLD022T Maks:100 m³/h Kjøling: 200 W 0.016 L/s Varme: 120 W 0.003 L/sLD022T Maks:100 m³/h Kjøling: 200 W 0.016 L/s Varme: 120 W 0.003 L/s