Title: 360.001 - Tilluft.pdf
LKR-800-500-8098-*DUCTLKR-800-500-8098-*221 TAPMAGIO-RC-*DUCTFIREDAMPER FKRS-EU/200/ZXXDUCTBEND-45MAGIB-C4-*-*Size160800x600800x600800x800800x800200200200200200Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]0,03,296004,20,696004,23002,70,03002,73002,70,33002,73002,734Sound in:Attenuation: Addition:0,7 Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:Dividing:11,3 Sound in:0,0 Sound in:Attenuation: Addition:1,8 Sound in:Addition:0,1 Sound in:Attenuation: Addition:0,7 Sound in:Attenuation: Addition:63 [dB]43.50.0 +0.047.02.1 +34.345.30.2 +31.215.629.629.60.0 +11.429.6+32.434.20.0 +11.434.20.0 +11.4125 [dB]38.80.0 +0.042.61.4 +33.241.80.9 +27.315.625.525.50.0 +10.325.6+19.426.60.0 +10.326.60.0 +10.3250 [dB]36.00.0 +0.040.61.0 +32.2