Title: +038=370.002-RP011T_01-Siemens Trykkføler vann QBE2003-P10.pdf
Mounting notesPressure measurement with liquidsPressure measurement with condensing gasesImportant noteDisposalSiemensThe pressure sensors operate on the piezo-resistive measuring principle. The ceramic or stainless steel diaphram*) (thick-film hybrid technology) acquires the pressure through direct contact with the medium. The measurement is converted electronically into a linear output signal of DC 0...10 V or DC 4…20 mA.) Applies to QBE2003-P10, QBE2003-P16, QBE2003-P25, QBE2103-P10, QBE2103-P16, andQBE2103-P25The pressure sensor consists of: • • •Sensor hood with DIN EN 175301-803-A plug-in connection Piezo-resistive measuring element integrated in the stainless steel case Pressure connection external thread G ½" and inside thread M5*) for use with accessory AQB2001**) Plug DIN EN 175301-803-A (plugged in)No changes or adjustments are possible.) The following types do not have M5 inside threads:QBE2003-P10, QBE2003-P16, QBE2003-P25, QBE2103-P10, QBE2103-P16, and QBE2103-P25