Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF004 Date / Time: 27-02-2020 19:43:22 Headroom 8.5 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]15.0 66 2 2.48Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]34.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.6 454.0 30.0 36 8.3 462.0 26.8SR 36-45 8.5 462.0 29.6 45 8.9 292.0 31.6MAIN 12-36 9.5 500.0 27.8 36 8.8 500.0 25.0SR 36-45 8.5 462.0 29.6 36 9.4 462.0 26.810080604020NEXT (dB)