Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.205205206206207207208208209209210210211211TEST RAPPORTResultatZ-LINEZ: 0.80ΩIsc: 286A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 12.06.2020 09:19RCD UbUc: 0.1V Rl: 3Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 12.06.2020 09:19RCD tt: 61.9msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 12.06.2020 12:10KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 12.06.2020 12:10R LOW OhmR: 0.29ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 10.06.2020 11:24R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 10.06.2020 11:28SPĆNDINGUln: 234V Ulpe: 233V Unpe: 0V f: 50.0Hz