Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Mote 6_2Motte 6_2DIALux Page 38Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Mete 6_2 / Results summary, EN 12464/ENTSKMgte 6_2 - 2 1 B —rm T = i e e —— v | S X EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 7 Perpendicular illuminance (adaptive) [Ix] 539 (= 500) 388 615 0.72 0.63 Surrounding area: 0.500 m 2 Surrounding area 7 Perpendicular illuminance (adaptive) [Ix] 463 (= 300) 261 619 0.56 0.42 3 Background area 6 Perpendicular illuminance (adaptive) [Ix] 333 (= 100) 220 409 0.66 0.54Wall zone: 0.500 mThe results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 39Dronning Mauds gate 1310. og 11. etasje8/28/2019Site 1/ Building 1/ Storey 10 / Mate 6_2 / Visual task area 7 / Perpendicular illuminance (adaptive)Visual task area 7 / Perpendicular illuminance (adaptive)