Title: 32 Pumper modbuss teknisk data.pdf.pdf
Read the holding register at address 00002 "Register Offset" to see if this value is different from 0. If so, write the value 0 to this address to make the slave return to the default used in this functional profile.4. The slave returns data value 0xFFFF (65535).a) The value is unavailable. A data value of0xFFFF does not necessarily indicate an error condition. It means that the value is unavailable from the E-pump.See section 9. Modbus register addresses for available data.b) The E-pump is not configured to show thevalue or lacks a sensor to read the value.See section 9.7 Pump data register block for data values that require a sensor.5. The slave does not change Modbus transmission speed with register 0004.a) Configuration error.Set the transmission speed switches to "Software- defined". Otherwise, the value in register 0004 is ignored by the slave.