Title: Data tester Smestad skole - Detaljert.pdf
dB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,3 25,3 4,0 450,00Remote: 36 28,7 23,8 4,9 498,00Worst Value: Local: 36 27,9 23,8 4,1 498,00Remote: 36 28,7 23,8 4,9 498,00PS-ACRF: Pass Worst Margin: Local: 12 73,3 61,2 12,1 1,00Worst Value: Local: 45 20,6 7,9 12,7 460,00Remote: 12 73,2 61,2 12,0 1,00Remote: 36 20,4 7,4 13,0 488,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:16Signature:______________________ Page: 151Copper Certification ReportCable Label: 521.002-UD-51 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:25:16 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: