Title: Data tester Smestad skole - Detaljert.pdf
Length (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 65,5 68,0 341,0 19,0 11,6Limit 100,0 - 555,0 50,0 25,0Margin 34,5 - 214,0 31,0 13,4Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 1,4 3,1 1,7 2,95Worst Value: Local: 45 28,4 43,7 15,3 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 20,1 13,5 6,6 113,50Remote: 78 22,4 15,5 6,9 71,50Worst Value: Local: 12 16,4 8,0 8,4 495,00Remote: 36 17,1 8,0 9,1 477,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,1 26,7 2,4 498,00Worst Value: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,1 26,7 2,4 498,00dB 0601200Local250500 MHzdB 0