Title: +038=370.002-LB004._02-Opera DMN 9034 Tørrkjøler CIAT - produktdatablad.pdf
THERMAL PERFORMANCES FOR 1 UNITThermal capacity Exchange area (Thermal margin) Fluid Inlet/outlet temperature Flow in inlet Pressure drops Ambient air Altitude Temperature220 kW 583 m2 (-5,0%) MEG 30% 42 / 36 °C 34,03 m3/h (0,009453 m3/s) 28,7 kPa0 m 28 °CSOUND LEVEL FOR 1 UNIT (No options - For X units, add 10logX)Sound pressure level : 59.1 dBA at 10 meters from unit, in the bundle axis, in free field, directivity 2, tolerance +/-2 dB. Sound pressure level: reference 2 * 10E-5 Pa, tolerance +/-2 dB. Calculated according to Lp = Lw - 10 x log S Sound pressure levels depend on installation conditions and are given for information only. We remind you that only sound power levels are certified and reliable values. Sound power spectrum (ISO 3744) : Frequencies (Hz) Sound power dB(A)