Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 45-78 29.5 137.5 18.8 78 30.7 138.5 16.1SR 36-78 31.4 140.0 18.4 36 31.6 140.0 15.9MAIN 36-45 40.5 482.0 -11.2 36 41.9 495.0 -14.9SR 36-45 42.3 495.0 -12.1 36 42.9 495.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 6.2 366.0 8.4SR 36 7.2 482.0 8.0MAIN 36 6.2 366.0 8.4SR 36 7.2 482.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-51 TR-4100BASE-TX 10GBASE-T ATM-155 TR-16 Active100BASE-T4 ATM-25 100VG-AnyLan TR-16 Passive60402000250 MHzProject: F13 3 ETGUntitled1Test Summary: PASSModel: DSX-5000 Main S/N: 2552117 Remote S/N: 2552311 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00416.4 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)80