Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 29.9 181.0 13.6 12 31.7 180.0 11.1SR 12-45 32.6 181.0 13.6 12 33.7 181.0 11.0MAIN 36-45 39.9 481.0 -11.1 36 40.3 498.0 -15.1SR 36-45 40.7 500.0 -12.4 36 40.5 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 5.5 482.0 8.0SR 12 5.7 482.0 8.0MAIN 12 5.5 482.0 8.0SR 12 5.7 482.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00415.0 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100