Title: TESEO.pdf
7.2. Check that the se3.rvice3. valve3. placed between the compressor room and the line is closed.7.3. Start the compressor and fill the tank up to the maximum pressure. if a compressor is not available, use nitro-gen tanks and/or small portable compressors.7.4. open the valve and fill the system up to 1 bar approx. (15 psi); close the valve and check that no leaks are de-tected in the system.7.5. Incre3.ase3. the3. pre3.ssure3. of the system slowly until you reach the maximum pressure. keep this pressure forabout 1 hour. Test the system when the pressure is 1.5 times higher than the working pressure.7.6. inspect the system again and check that no leaks or other unusual deformations are visible in the joints.7.7. Empty the system.