Title: økernvn 94.pdf
RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: T3077 Date / Time: 09/13/2013 08:11:17 Headroom 6.9 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]82 126 5 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.9 240.5 35.6 36 6.9 241.5 33.0SR 36-78 7.0 189.0 37.3 36 8.5 189.0 34.7MAIN 36-78 6.9 240.5 35.6 36 6.9 241.5 33.0SR 36-78 8.8 249.0 35.4 78 9.6 248.5 32.710080604020NEXT (dB)