Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.9 147 2 5.16Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.2 434.0 30.6 45 8.2 500.0 26.4SR 36-45 8.7 456.0 30.1 36 8.8 500.0 26.4MAIN 12-45 8.0 500.0 29.2 45 8.2 500.0 26.4SR 36-45 9.1 497.0 29.3 36 8.8 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-78 14.6 477.0 11.7 45 14.0 2.6 53.9SR 78-36 14.8 477.0 11.7 45 14.2 2.5 54.3MAIN 36-78 14.7 478.0 11.6 78 14.9 481.0 8.6SR 78-45 15.0 497.0 11.3 45 15.3 497.0 8.30100806040200250 MHzACR-F (dB)