Title: økernvn 94.pdf
250MHz60RL @ Remote (dB)50403020100050100150200250MHzLinkWare Version 7.4Cable ID: D4202 Date / Time: 09/09/2013 02:50:30 Headroom 1.6 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 36]48 75 5 2.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]25.7 249.0 30.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 3.5 208.5 36.6 45 5.0 230.0 33.3SR 36-45 1.6 244.5 35.5 45 1.7 244.0 32.9MAIN 45-78 3.6 243.5 35.5 45 5.0 244.0 32.9SR 36-45 1.7 250.0 35.3 45 1.7 244.0 32.910080604020NEXT (dB)