Title: 32 Pumper modbuss teknisk data.pdf.pdf
For software configuration of CIU 260, which includes setting of SMS functions and SCADA communication parameters, see "CIM 260 SMS commands" which you can download from Grundfos Product Center.6.2 Status LEDsThe CIM 260 module has two LEDs. See fig. 12.Yellow and green status LED1 for cellular communication.Red and green status LED2 for internal communication between CIM 260 and the E-pump.LED1, yellow and green12341 second3 secondsYellowGreenFig. 16 LED1 statusPos. StatusDescription1Flashing yellowSearching for cellular network.2Pulsating yellow, single pulseConnection to the cellular network has been established.3Pulsating green, single pulseCommunication via data connection.4Green, 3 secondsSending or receiving an SMS message.LED2, red and greenStatusDescriptionOffCIM 260 has been switched off.Flashing redNo communication between CIM 260 and the E-pump.Permanently redCIM 260 does not support the connected version of the E-pump.