Title: Ahlsell.pdf
80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 11 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 01:10:09 PM Operator: Pam Headroom 10.0 dB (NEXT 3,6-7,8) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 4,5] [Pair 4,5] [Pair 3,6]21.1 103 1 3.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]32.8 500.0 43.8Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 10.0 284.0 34.4 3,6 11.2 163.5 35.8SR 3,6-7,8 11.8 3.4 65.0 3,6 12.9 4.1 61.6