Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 30.11.2020 09:19RCD II: 28.5mAUci: 0.1V t: 31.8ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 30.11.2020 11:56 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 27.11.2020 11:56R LOW OhmR: 0.13ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 27.11.2020 11:56Tallberg Elektro A/S Tlf.22796640Side:23GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.160160161161162162163163164164165165166166TEST RAPPORTResultat KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF040 16C2/003 30.11.2020 09:08SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF040 16C2/003 30.11.2020 09:08