Title: +038=534.001-RA001._02-Porttelefon Siedle Systemanvisning.pdf
ANG 600-0 Access line rectifier in switch panel housing with 230 V AC switching contact. Admissible switching output: • Light bulbs max. 1300 W • Fluorescent lamps max. 800 W • Twin fluorescent lamps max. 1200 W • Parallel compensated fluorescent lamps max. 400 W Operating voltage: 100–240 V AC, +/-10 %, 50/60 Hz Operating current: 0.5–1 A Output voltage: 48 V DC Output current: 800 mA Fusing: primary thermal fuse, secondary short circuit proof Contact type: changeover switch max. 250 V AC, 6 A Protection system: IP 20 Ambient temperature: 0 °C to +40 °C Horizontal pitch (HP): 6 Dimensions (mm) W x H x D: 107 x 89 x 60Distribution components – Active/passive system expansion