Title: Data tester Smestad skole - Detaljert.pdf
Overall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 36,2 68,0 188,0 10,0 6,3Limit 100,0 - 555,0 50,0 25,0Margin 63,8 - 367,0 40,0 18,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,7 3,1 2,4 2,95Worst Value: Local: 36 15,9 43,8 27,9 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 17,4 12,8 4,6 131,50Remote: 12 17,7 12,8 4,9 131,50Worst Value: Local: 12 17,4 12,8 4,6 131,50Remote: 78 13,1 8,0 5,1 472,00dB -2020600Local