Title: økernvn 94.pdf
MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3410 Date / Time: 09/11/2013 06:21:24 Headroom 7.1 dB (NEXT 12-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]130 198 7 5.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]18.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.0 243.0 35.5 36 8.7 221.5 33.6SR 12-45 7.1 160.5 38.5 36 8.5 242.0 32.9MAIN 36-78 8.0 243.0 35.5 36 8.9 242.5 32.9SR 36-78 7.7 239.0 35.7 36 8.5 242.0 32.910080604020NEXT (dB)