Title: 2 etg del2.pdf
002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 8.1Cable ID: D2071 Date / Time: 10/10/2013 12:54:50 PM Headroom 13.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]198 314 23 8.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.1 82.5 33.7 12 15.6 82.5 30.7SR 12-36 13.4 82.5 33.7 36 15.3 89.3 30.1MAIN 12-36 13.5 89.0 33.1 36 15.9 97.3 29.5SR 12-36 13.4 89.3 33.1 36 15.6 99.0 29.4