Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]36.4 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.5 464.0 29.6 36 6.8 466.0 26.6SR 36-45 3.1 481.0 28.7 36 4.6 481.0 25.9MAIN 36-45 6.1 480.0 28.8 36 7.0 481.0 25.9SR 36-45 3.1 481.0 28.7 36 4.7 482.0 25.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.0 5.0 51.3 45 13.6 2.3 55.2SR 36-45 15.0 4.0 53.2 45 13.6 2.1 55.7MAIN 45-12 16.3 500.0 11.3 45 15.7 500.0 8.3SR 12-45 16.0 500.0 11.3 45 15.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 39.6 423.0 -7.2 45 41.0 423.0 -10.0SR 36-45 37.5 423.0 -7.2 45 39.7 423.0 -10.0MAIN 36-45 41.3 480.0 -11.1 36 42.7 481.0 -14.0