Title: 32 Pumper modbuss teknisk data.pdf.pdf
Selecting the Modbus address: MODBUSADDR <1-247> Default value is 231.To verify the APN settings after completion, use the SMS command "APNSETTINGS". The command "APNSTATUS" can verify if the APN connection is working.The connection states have the following meaning:To verify the SCADA settings after completion, use the SMS command "SCADA".– "Detached": Trying to locate APN connection service.– "Attached": APN connection service located.– "Context active": IP address has been assigned, ready for aclient to establish a socket connection.– "Connected": A client has established a socket connection. The system is ready for TCP/IP data exchange, or already exchanging data.For details about the use of SMS commands, see "CIM 260 SMS commands", which you can download from Grundfos Product Center.349 0 2 27 0 9 44 0 M T1. CIU 260 locates the APN service. The connection state changes from "Detached" to "Attached".