Title: 370.011 OE501 Siemens UC50 Kalkulator.pdf
Environment class Mechanical class Electromagnetically class *) according 2004/22/EG directive Ambient humidity Storage temperature Max. Height Ambient temperature Housing degree of prot. Safety class line 110 / 230 V AC line 24 V AC/DC Response threshold f. T Temperature diff. T Temperature meas. range Sensors Type Temperature sensors length Battery Power supplyPower inputA (EN 1434) M1 E1) *)< 93 % r. h. at 25°C without condensation - 20 to 60°C 2000 m above MSL 5 to 55°C IP 54 to EN 60529II per EN 61558 III per EN 61558 0.2 K 3 K to 120 K 0...180°C Pt500 or Pt100 per EN 60751 max. 10 m 3.6V DC Lithium 230/110V AC 50/60Hz 24V AC/DC 50/60Hz < 0.8WInstallation5/29Pulse input Pulse length Pulse frequency Pulse wire lengthIB/IC per EN1434 min. 10ms max. 50Hz max. 20m (recommended)3InstallationDefine mounting place (hot or cold side) and the pulse value of the flow sensor.