Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
ual and on the TCS Support site (www.sbc-support.com + getting started). the firmware reads in the values according to the configuration (I/O Builder) Watchdog: This module cannot be used on the base address 240 (or 496 for the PCD2.M17x), because it would interact with the watchdog, and would cause a malfunction. For details, please refer to the “Watchdog” section, which describes the correct use of the watchdog in conjunction with PCD2 components.5-71PCD2.W3x0Formulae for temperature measurement For Ni 1000 (PCD2.W340) Validity: Temperature range - 50 … + 210 °C Computational error:± 0.5 °CT= - 188.5 +260 • DV 26164.676 • 10-6 • (DV - 2784)2For Pt 1000 (PCD2.W340) Validity: Temperature range - 50 … +400 °C Computational error:± 1.5 °CT= - 366.5 +450 • DV 2474+ 18.291 • 10-6 • (DV - 2821)2