Title: Tegning tank.pdf
THERMOMETER G 172"G1/2"MANOMETERMANOMETER G 1/2" 0-25 bar, Vent Valve Reg0 3165C - 1/4"NPTDN500MANNLOCHT 1 POHLED P l IR |VNEISI NATER 2.} kbmpnnenlnn min 120 ym RAL 9010,31t RAL 6019 VNITRNI NATER TRYSKARI SA 22/1die DiN 55 928£ RIG RN 2%, LN 2% - {SPDIE 100% }MAGNETBAREVNA DEFEXTOSKOPIE -POVRCHOV AT Pi MATERIAL AROVANT& 2 i: i—“_“HAG DRAT G351ENISO 14 341SHESNY PLYN M21ENISO 14 175POD TAVIDLEM | DRAT S2 - EN 156TAVIDLO SA AB 167 AC HS - EN 760RUCKE Ti6 W3Si1 - EN IS0 636, ELECTRODA E 424 3 42H5 - ENISO 2560-A KOEFICENT SVAROVEHO SPOJE _ v= 0,85PROVEDENI SVARU A PRIPRAVA SYAR PLOCH VIZ JEDNOTLIVE SVAROVACT nAvoDxV PROVEDENI SVARD OLE EN 1S0 5817 1FiATEST DOKLADOVAT DLE EN 10 204PREJIMKA DLE RICHTLINE 97/23/G, AD2000-H, HODUL G PREJIMKA OD AD Juy KXATEGORIE NADOBY W 0BJEM 32000 PRACOVNI PRETLAK 185 bar ZKUSEBNT PRETLAK 23 bar TESNOSTNT PRETLAK 6 bar PRACOVNI MEDIUM PROPAN, BUTAN, EN 589 V¥POCTOVA TEPLOTA ) C PRACOVNi TEPLOTA 407240 *C