Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
I/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24 V are disconnected from the power supply.5-18PCD2.E5005.3.1PCD2.E500, 6 digital inputs for 115 - 230 VACApplicationModule with 6 electrically isolated inputs for alternating current. The inputs are set up for source operation and have one common “COM” terminal. Only the positive half-wave of the alternating current is used.Technical dataNumber of inputs6 electrically isolated from the CPU,Source operation, all inputs to the module in the same phaseInput voltageInput current115/230 V 50/60 Hz, sinusoidal (80 to 250 VAC) 115 VAC: 230 VAC:5 … 6 mA (wattless current) 10 … 12 mA (wattless current)Input delay switch-on: switch-off: LED Resistance to interference acc. to IEC 801-4Electrical isolation voltage Electrical isolation resistance Optocoupler isolation voltage