Title: Ahlsell.pdf
SR 4,5-7,8 17.2 5.6 57.6 4,5 17.8 5.6 55.3MAIN 3,6-4,5 45.7 481.0 -15.6 3,6 47.1 497.0 -19.7SR 3,6-4,5 43.0 475.0 -15.1 3,6 46.2 497.0 -19.70804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 4,5 8.7 109.0 13.6SR 3,6 5.8 481.0 8.0MAIN 3,6 8.8 456.0 8.0SR 3,6 5.8 481.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Ahlsell Site: Not Set Floor: Not Set Rack: Not Set Untitled1Building: Not Set Room: Not Set Patch: Not SetPage 23Test Summary: PASSRemote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 250509519.7 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)80604020