Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
; Clean the pool filter regularly to maintain adequatecirculation.P20 100400010000002828; Check that the area surrounding the unit provides gooddrainage and ventilation.; It is a good idea to clean the heat exchanger to promote good function and energy savings. This is easily done with winter drainage. Flush the heat exchanger using e.g. a garden hose and drain thoroughly.B051806270010 See above example for serial number label.If an error message occurs, consult the error code table below for the possible cause and suggested response.Fault tracing chartOperating disturbanceCauseAction1. The heat pump is in standby mode.1. Press the ON/OFF button.2. The heat pump is in cooling mode.2. Change the operating mode to Heating modeSet pool temperature not reached3. The heat pump is too small for the pool.3. The heat pump is too small for the pool.as set out in Section 3.3. Larger heat pump required.4. The outdoor air temperature is too low.