Title: Data tester Smestad skole - Detaljert.pdf
601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 68,4 57,3 11,1 2,20Remote: 45-12 68,5 57,3 11,2 2,20Worst Value: Local: 12-45 22,9 10,7 12,2 470,00Remote: 45-12 23,4 10,7 12,7 470,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,3 23,8 3,5 500,00Remote: 36 28,4 23,8 4,6 498,00Worst Value: Local: 36 27,3 23,8 3,5 500,00Remote: 36 28,4 23,8 4,6 499,00PS-ACRF: Pass Worst Margin: Local: 12 73,3 61,2 12,1 1,00Worst Value: Local: 45 21,2 7,6 13,6 479,00Remote: 45 71,8 61,2 10,6 1,00Remote: 45 21,6 7,6 14,0 477,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:06Signature:______________________ Page: 81Copper Certification Report