Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
60RL @ Remote (dB)504030201050000250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.03.03-UF048 Date / Time: 06-05-2020 16:37:26 Headroom 5.7 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 36]29.2 127 2 4.41Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]27.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 11.1 477.0 29.7 36 10.9 498.0 26.4SR 36-45 5.7 499.0 29.3 36 7.0 497.0 26.4MAIN 36-78 11.2 493.0 29.4 36 10.9 498.0 26.4SR 36-45 5.8 500.0 29.2 36 7.0 497.0 26.410080604020NEXT (dB)