Title: 2 etg del2.pdf
Cable ID: D2083 Date / Time: 10/10/2013 01:11:54 PM Headroom 13.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]223 355 26 9.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.5 65.5 35.3 36 15.3 65.5 32.3SR 12-36 13.7 94.8 32.7 36 14.8 94.8 29.7MAIN 12-36 13.6 94.8 32.7 36 15.7 99.0 29.4SR 12-36 13.7 94.8 32.7 36 14.9 97.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 22.8 20.8 32.3 12 23.7 3.9 43.8