Title: +038=453.003-LZ001. Defrost Snow Nexans leggeanvisning.pdf
Installation of cold leads Conductors in the cold lead of SNOWMAT/DEFROST SNOW are made of copper, and have a cross section area of 1 mm². During operation the cold lead will dissipate a little heat, and therefore the cold leads shall be separated and not gathered in a cluster. A maximum of three cold leads should be put in direct contact with each other. Any cold lead going through an insulated wall shall not be in contact with any other cold lead.Further the following apply for larger elements, with output 2700 W and 3400 W: •If installing three or more elements, the cold leads must be sepa- rated with minimum 1 cm distance.