Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Trapperom hall) Perpendicular illuminance (adaptive) [Ix] 280 (= 100) 131 386 0.47 0.34Height: 0.000 m, Wall zone: 0.100 m# Luminaire O(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 5 iGuzzini illuminazione S.p.A - QA85+QB22_B66J iN60 LED: Down LO 1824 16.7 109.5plateDALIGeneral LightLED WarmL 119615W 2400Im -3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 9120 83.5 109.2Lighting power density: 7.94 W/m? (Floor area of room 10.52 m? ), Lighting power density: 9.05 W/m? = 3.23 W/m2/100 Ix (Area of working plane 9.22 m?)Consumption: 92 kWh/a of maximum 400 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 77