Title: økernvn 94.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 17.1 23.0 43.6 36 15.4 22.9 41.2SR 12-36 11.6 23.0 43.6 36 11.4 23.0 41.2MAIN 36-78 26.4 247.0 5.0 12 25.8 249.5 2.1SR 36-45 16.9 250.0 4.7 36 16.6 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 5.0 22.8 19.2SR 36 3.8 22.8 19.2MAIN 45 6.0 214.5 10.7SR 45 7.5 203.5 10.906050050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4