Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
To avoid reflections, each segment must be terminated at the line ends. According to the Profibus standard, this cannot be done on the device. The PCD7.T160 termination boxes or standard 9-pole Profibus DP D-Sub connectors are suitable for this.Details can be found in manual 26 / 765 "Profibus DP".D-Sub 9 pole pin allocationC Socket Connection type D-Sub 9-pole (female) signal RTS / CNTR-P PGND RxD / TxD-N RxD / TxD-P DP GND DP +5 VPin no 4 Threaded bolts 8 A (green) 3 B (red) 5 6Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-255-29Saia-Burgess Controls Ltd.Input/output (I/O) modulesOverview6Input/output (I/O) modules6.1Module overviewThe summary below shows the available digital and analogue I/O modules, counters etc. for the PCD2 series: TypeDescriptionPageDes- igna- tionNo. I/ Os or mods.Input/ output signal rangeDigital input modules PCD2.E110 PCD2.E111 PCD2.E112 PCD2.E116 PCD2.E1608 I 8 I 8 I 8 I 16 IPCD2.E16116 IPCD2.E165