Title: +175=324.001_KA001_Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.Produktinformasjon.pdf
10.1Right of amendment reserved © 2015 Fr. Sauter AGProduct data sheetDN 15…50MV 506008AVM 105,115,105S,115SMV 506065AVM 125SMV 506066AVF 124,124SMV 505851AVF 125SMV 506067AVM 321SP 100011900Declaration on materials and the environmentMD 56.115Fitting positionThe control unit can be fitted in any position, but the hanging position is not recommended. Conden- sate, drops of water, etc. must be prevented from entering the actuator. When the actuator is mounted on the valve, make sure the plug is not twisted on the seat (this can damage the sealing surface). When insulating the valve, it may only be insulated up to the connecting clip of the actuator. To increase the functional reliability of the valves, the system should conform to DIN/EN 14336 (heat- ing systems in buildings). DIN/EN 14336 states, amongst other things, that the system has to be flushed through before being put into service.