Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 36]22.0 95 1 3.38Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]31.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.2 476.0 29.0 36 9.3 472.0 26.3SR 36-45 9.6 476.0 29.0 45 10.0 481.0 25.9MAIN 36-78 10.0 496.0 28.0 36 9.5 494.0 25.3SR 36-45 10.3 497.0 28.0 36 10.5 495.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.3 3.4 54.7 45 14.0 12.3 40.5SR 45-78 14.3 3.4 54.7 45 14.0 12.0 40.7MAIN 36-45 17.0 479.0 11.6 45 18.3 500.0 8.3SR 45-36 17.1 479.0 11.6 45 18.8 500.0 8.30100806040200250 MHzACR-F (dB)