Title: +135.01=564.001-XS020T_01-Montasje 5202AB13_bma_d-e-blinds_Norsk.pdf
press the bus terminal block (C2) down to the stop. - press the sheathing of the cut-off insulation bus line projecting >3mm into the open clamping slot (C4). If a fur- ther bus line shall be connected break out the closed clamp- ing slot with a screw-driver and press it into the clamping slot as described above. Press the single bus wires into the recess below the bus terminal block and snap on the cover (C1)Connecting bus cables (figure 5) - The bus terminal block (D2) can be used with single coreconductors Ø 0.6…0.8 mm.Remove approx. 5 mm of insulation from the conductor (D1) and plug it into the bus terminal block (D2) (red = +, grey = -)Remove approx. 5 mm of insulation from the conductor (D1) and plug it into the bus terminal block (D2) (red = +, grey = -)Disconnecting bus cables (figure 5) - Unplug the bus terminal block (D2) and remove the bus cableconductor (D2.4) while simultaneously wiggling it.Connecting/disconnecting mains and load circuit: see figure 6