Title: 2 etg del2.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 8.5 53.8 36 9.0 232.0 3.8SR 12-36 6.9 64.0 30.4 36 8.2 207.0 6.5MAIN 36-45 9.5 249.5 4.7 36 9.1 249.5 2.1SR 36-45 9.3 246.0 5.1 36 8.6 245.5 2.5010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.8 19.8 19.5SR 45 3.8 10.9 20.8MAIN 36 7.5 185.0 11.3SR 45 8.8 225.0 10.560500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.