Title: Data tester Smestad skole - Detaljert.pdf
Margin 76,3 - 432,0 43,0 20,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,3 3,0 2,7 1,60Worst Value: Local: 45 10,4 43,4 33,0 493,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 17,5 12,2 5,3 150,50Remote: 12 14,0 8,0 6,0 470,00Worst Value: Local: 12 15,7 8,0 7,7 469,00Remote: 12 14,0 8,0 6,0 470,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,7 26,7 3,0 498,00Worst Value: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,7 26,7 3,0 498,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 68,8 57,3 11,5 2,20