Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
4. Connect the CAN drive bars of each cabinet together using the CAN wire (supplied with each cabinet).5.Install the necessary modules and proceed with the installation of the control panel.5.1.2 Mounting the PRCABSP kitThis kit allows the control panel to be mounted 5cm away from the wall and must be mounted before mounting the Previdia Max control panel.1. Assemblethe kit by attachingthe distancing bracket (paragraph 3.2 - [A]) to the support bracket (paragraph 3.2 - [B]) by means of the interlocking dovetails (paragraph 3.2 - [D]).2. Attach the assembled structure to the wall by means of the holes on the support (paragraph 3.2 - [C]).2. Attach the assembled structure to the wall by means of the holes on the support (paragraph 3.2 - [C]).3. Mount the cabinet to the distancing bracket by inserting the threaded rivets (paragraph 3.2 - [E]) through the holes on the back of the enclosure (paragraph 3.1 - [G]), then secure it in place using the supplied nuts.5.1.3 Mounting a PRCABRK kit