Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Average: 361 Ix, Min: 25.1 Ix, Max: 699 Ix, Min/average: 0.070, Min/max: 0.036 Height: 1.250 mFalse colors [Ix]17 26 39 58 87 131 196 295 500 666 IxScale: 1:50Value grid [Ix]Scale: 1: 50The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 98Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 11 / Waiting room 2 / Room summaryWaiting room 2Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Waiting room 2) Perpendicular illuminance (adaptive) [Ix] 301 (= 200) 183 407 0.61 0.45 Height: 0.100 m, Wall zone: 0.200 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 4 iGuzzini illuminazione - Q510 Laser Blade XS - Downlight HC 23.1W 1452 231 62.9 Total via all luminaires 5808 924 62.9