Title: Hardware Installation Guide.pdf
1. Wire the supervised alarm inputs.2. Wire the upstream host communication.3. Wire the relay outputs.4. Wire the downstream TTL interface for the keypads and/or card readers.5. Wire the Power Fault and Cabinet Tamper Monitors.6. Wire the power input.80.1Wiring80.1.1Supervised Alarm InputsThe Dual Reader Interface Module contains eight (8) supervised inputs that can be used for door position monitoring, REX exit push button monitoring, and alarm control.These inputs are connected using the IN1, IN2, IN3, IN4, IN5, IN6, IN7, and IN8 inputs. The standard wiring configuration is as follows:revision 6 — 391LNL-1320 Dual Reader Interface ModuleInputs 1-4 are for Door #1, Inputs 5-8 for Door #2DRI Alarm Input Contact WiringDoor 1 Door ContactIn 1Door 1 REXIn 2Door 1 Aux 1In 3Door 1 Aux 2In 4Door 2 Door ContactIn 5Door 2 REXIn 6Door 2 Aux 1In 7Door 2 Aux 2In 8TMPCabinet Tamper Power FailureGNDPFLGNDDoor Contact