Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,2 23,8 4,4 498,00Remote: 36 28,5 23,8 4,7 499,00Worst Value: Local: 36 28,1 23,8 4,3 499,00Remote: 36 28,5 23,8 4,7 499,00PS-ACRF: Pass Worst Margin: Local: 45 66,3 54,3 12,0 2,20Worst Value: Local: 45 19,5 7,2 12,3 500,00Remote: 12 66,1 54,3 11,8 2,20Remote: 45 19,3 7,2 12,1 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:10Signature:______________________ Page: 109Copper Certification ReportCable Label: 521.002-UD-102 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:40:48 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software: