Title: V20-04-01 VVS-anlegg plan 4 - DM1-1.pdf
ø200 UK=2645ø200 UK=2645200x100 UK=2610ø160 UK=2665ø160 UK=2665ø160 UK=2665ø160ø160 UK=2665ø160 UK=2665ø160 UK=2665ø160 UK=2665ø160 UK=2665SF002T-160 150 m³/hSF002T-160 130 m³/hSF002T-160 130 m³/hSF002T-160 130 m³/hSF002T-160 130 m³/h28 mm +c 2675WISE RTA WISE IAQWISE RTA WISE IAQ320.102: 28 mm +c 2770 320.102: 28 mm +c 2770 370.101: 42 mm +c 2770 370.101: 42 mm +c 27700.073 L/s320.102: 54 mm STAP/STAD DN20+04 = 320.102 - OE 045 0.073 L/sLD018T Maks:130 m³/h Kjøling: 225 W 0.018 L/s Varme: 205 W 0.005 L/sLD018T Maks:130 m³/h Kjøling: 225 W 0.018 L/s Varme: 205 W 0.005 L/sLD018T Maks:130 m³/h Kjøling: 225 W 0.018 L/s Varme: 205 W 0.005 L/sLD018T Maks:130 m³/h Kjøling: 225 W 0.018 L/s Varme: 205 W 0.005 L/s89Opp/ned 360.012: ø400 UK=7Ned 360.012 ø630I dekke SZ001T Ø630Opp/ned 370.101: DN 100 370.101: DN 100 310.102: Cu 42 310.202: Cu 35 310.302: Cu 22 310.001: MA 135 310.002: MA 11010Tilkobles eksisterendeSZ001T Ø250Tilkobles fremtidig