Title: 2 etg del2.pdf
[Pair 12] [Pair 45] [Pair 45] [Pair 45]246 376 14 11.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]7.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.6 246.0 35.5 36 7.9 246.5 32.8SR 12-36 7.8 148.0 39.1 12 8.7 249.5 32.7MAIN 12-36 6.6 246.0 35.5 36 7.9 246.5 32.8SR 12-36 8.4 249.5 35.4 12 8.7 249.5 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 7.9 87.0 25.4 45 10.4 83.5 22.8SR 78-45 8.0 87.0 25.4 78 10.9 87.0 22.4MAIN 78-45 8.4 104.0 23.8 45 16.6 220.0 14.3SR 78-45 8.4 105.0 23.8 36 18.7 250.0 13.2010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 12.7 41.8 36.3 36 12.4 20.1 42.7