Title: Bytesteinen 1 - =514.202-FS001.pdf
Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]42.0 215 15 7.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]23.3 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 7.1 174.0 35.8 7,8 8.9 172.0 33.0SR 4,5-7,8 7.1 228.0 33.8 4,5 9.1 228.0 30.9MAIN 4,5-7,8 7.8 219.5 34.1 7,8 10.1 233.0 30.7SR 4,5-7,8 7.1 228.0 33.8 4,5 9.1 228.0 30.9PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 13.4 162.0 19.1 4,5 15.0 3.5 49.4SR 7,8-4,5 13.7 162.0 19.1 4,5 15.1 3.1 50.4MAIN 7,8-4,5 14.1 186.0 17.9 4,5 15.8 186.0 14.9