Title: 2 etg del2.pdf
SR 45-36 11.7 189.0 18.7 45 13.8 201.5 15.1MAIN 45-36 11.8 209.5 17.8 36 14.3 210.0 14.7SR 36-45 12.4 209.5 17.8 45 14.8 234.5 13.8010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 14.5 48.5 36 8.6 14.4 46.3SR 12-36 12.2 14.5 48.5 12 12.9 14.5 46.2MAIN 36-45 10.1 250.0 4.7 36 9.9 250.0 2.0SR 12-36 18.2 250.0 4.7 12 17.1 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.2 9.0 21.0SR 45 1.7 8.9 21.0MAIN 36 7.0 231.0 10.4SR 36 1.9 203.0 10.9010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active