Title: Ahlsell.pdf
50000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 26 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/04/2022 07:56:31 AM Operator: Pam Headroom 9.6 dB (NEXT 1,2-3,6) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 3,6] [Pair 4,5] [Pair 4,5] [Pair 3,6]19.7 97 2 4.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]32.9 500.0 43.8Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 12.3 96.5 42.1 3,6 12.4 96.3 39.6SR 1,2-3,6 9.6 319.0 33.1 1,2 10.0 319.0 30.5