Title: 32 Pumper modbuss teknisk data.pdf.pdf
Fig. 18 Example of Ethernet connectionPos. DescriptionDesignation1Industrial Ethernet RJ45 connector 1ETH12Industrial Ethernet RJ45 connector 2ETH23Rotary switch for protocol selectionSW14Data activity LED for connector 1DATA15Link LED for connector 1LINK16Data activity LED for connector 2DATA27Link LED for connector 2LINK28Green and red status LED for Ethernet communicationLED19Green and red status LED for internal communication between the module and the pump.LED21 1 7 45 3 4 65 0 M T3 1 0 11 3 4 75 0 M TThe CIM 500 Ethernet module has a rotary switch for selection of the Industrial Ethernet protocol. See fig. 19.Fig. 19 Selecting the Industrial Ethernet protocolPos. Description0PROFINET IO (default)1Modbus TCP2BACnet IP3EtherNet/IP4GRM IP (requires a contract with Grundfos)5..EReserved, LED1 will be permanently red to indicate an invalid configurationF