Title: FEBDOK Døli pleie og omsorgshjem 19.04.16.pdf
7,000 / 2497,6 A4,000 / 1427,2 A:Anleggets adresse:Beregningsresultater for anlegget: Døli Pleie og OmsorgshjemDato:19.04.2016 15:12:11Sørum Elektriske ASFordeling HOVEDTAVLE PLAN UNEK 400:2014400 V TN-C-SSørumsandvegen 931921 SØRUMSANDVer.5.5.06Side1(15)Tel: 63825575Dato.29.04.2015av42BeregningsresultaterKurs nr.F11Kombinert vernIk [kA]cos phiî [kA]Kabel t=k²S²/I² [s]t utkobling [s]Ik3p max7,3000,8010,7169,7550,040Ik3p max ende6,8420,8110,02411,1050,040Ik3p min4,9770,907,19220,9860,058Ik2p max6,3210,809,27813,0110,040Ik2p max ende5,9260,818,68214,8030,040Ik2p min4,3110,906,23027,9710,058Ik1p max3,5000,805,13842,4360,058Ik1p max ende3,2490,824,74649,2460,058Ik1p min3,1400,914,53452,7240,058Ij max3,5000,805,13816,2290,058Ij max ende3,2490,824,74618,8340,058Ij min3,1400,914,53420,1640,058