Title: 2 etg del2.pdf
RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 8.1Cable ID: D2038 Date / Time: 10/10/2013 12:19:00 PM Headroom 13.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]147 232 15 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.0 75.8 34.3 36 14.1 98.0 29.4SR 12-36 13.8 75.8 34.3 36 14.7 98.0 29.4MAIN 12-36 13.1 98.3 32.4 36 14.1 98.0 29.4SR 12-36 14.1 98.3 32.4 36 14.7 98.0 29.410080604020NEXT (dB)