Title: økernvn 94.pdf
MAIN 12-78 20.7 64.5 30.3 12 21.1 61.0 28.6SR 12-36 16.1 77.0 27.6 36 17.4 63.0 28.1MAIN 36-78 26.6 220.0 7.7 36 28.9 241.0 2.9SR 12-36 22.8 248.0 4.9 36 22.6 247.5 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.8 221.0 10.6SR 45 5.5 223.5 10.5MAIN 36 4.8 221.0 10.6SR 45 5.5 223.5 10.5010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94