Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
31.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.0 468.0 29.4 36 6.6 467.0 26.6SR 36-45 4.7 463.0 29.6 45 6.3 463.0 26.8MAIN 36-45 6.9 495.0 28.1 36 7.6 500.0 25.0SR 36-45 5.8 496.0 28.0 36 7.0 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.8 5.4 50.6 45 17.3 26.3 33.9SR 78-45 17.7 5.0 51.3 45 17.3 17.8 37.3MAIN 36-78 18.2 468.0 11.8 78 19.8 485.0 8.5SR 78-36 18.1 468.0 11.8 36 19.1 468.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 29.7 150.0 17.2 36 31.1 150.0 14.6SR 12-36 26.7 96.0 24.9 36 25.9 95.8 22.4MAIN 36-45 36.8 495.0 -12.1 36 37.7 500.0 -15.3SR 36-45 35.6 496.0 -12.1 36 37.1 500.0 -15.30804000250 MHzACR-N (dB)