Title: 2 etg del2.pdf
4020002550 MHz75100100ACR-F @ Remote (dB)80604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: D2163 Date / Time: 10/10/2013 02:14:05 PM Headroom 4.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 36]56 89 6 2.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]25.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 4.3 228.5 36.0 36 4.5 228.5 33.4SR 12-36 5.8 229.0 36.0 12 7.4 217.0 33.7