Title: økernvn 94.pdf
75100LinkWare Version 7.4Cable ID: D4103 Date / Time: 09/09/2013 10:43:05 Headroom -1.9 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]37 58 4 1.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]26.6 245.0 30.3Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 -0.7 245.5 35.5 36 0.8 244.5 32.9SR 36-45 -1.9 246.0 35.5 36 -0.4 245.5 32.8MAIN 36-45 -0.7 245.5 35.5 36 0.8 244.5 32.9SR 36-45 -1.9 246.0 35.5 36 -0.4 245.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)