Title: økernvn 94.pdf
RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: T3089 Date / Time: 09/12/2013 03:53:05 Headroom 12.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]109 172 12 4.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.9 87.5 33.3 36 15.0 87.5 30.3SR 12-36 12.4 87.5 33.3 36 14.2 78.5 31.0MAIN 12-36 13.2 93.8 32.8 36 15.3 93.8 29.8SR 12-36 12.5 93.8 32.8 36 14.6 99.3 29.410080604020NEXT (dB)