Title: Simployer - Data testrapport =514.204-FS001.pdf
10.7 54 3 3.210.7 mWire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 4,5] [Pair 4,5] [Pair 4,5]31.4 250.0 35.9Worst Case Margin Worst Case ValueFAIL Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,60.5 *F250.0 33.1 4,5 -1.5 F223.0 31.0SR 1,2-3,65.4 F247.5 33.2 3,6 -3.8 F249.0 30.2MAIN 4,5-7,8 -4.0 221.5 34.0 4,5 -1.5 223.0 31.0SR 1,2-3,6 -5.4 247.5 33.2 3,6 -3.8 249.0 30.2PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 9.6 194.0 17.5 4,5 12.1 194.0 14.5SR 4,5-7,8 10.1 194.0 17.5 7,8 12.4 194.0 14.5MAIN 7,8-4,5 9.9 216.5 16.5 4,5 13.5 245.5 12.5SR 4,5-7,8 10.3 219.5 16.4 7,8 12.8 216.5 13.5PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 0.3 * 3.5 60.0 4,5 2.4 3.5 57.5SR 4,5-7,80.4 * 5.1 56.6 4,5 2.5 6.3 52.2MAIN 4,5-7,8 25.8 222.0 0.4 4,5 28.2 223.0 -2.7