Title: Bytesteinen 1 - =514.202-FS001.pdf
Cable ID: 521.202-UD055 Date / Time: 30/03/2021 11:06:17 Headroom 7.5 dB (NEXT 3,6-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]19.7 100 6 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]29.9 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 7.5 211.0 34.4 7,8 9.1 227.5 30.9SR 3,6-4,5 9.0 127.5 38.1 3,6 8.8 127.5 35.3MAIN 3,6-7,8 8.0 233.5 33.6 7,8 9.1 233.5 30.7SR 3,6-4,5 9.3 221.0 34.0 1,2 10.5 245.0 30.3