Title: etg u1.pdf
002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 8.1Cable ID: D0016 Date / Time: 10/21/2013 02:51:54 PM Headroom 1.1 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]159 252 18 6.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.1 248.0 35.4 36 1.6 231.0 33.3SR 12-36 7.7 202.0 36.9 36 8.4 243.0 32.9MAIN 36-45 1.1 248.0 35.4 36 1.6 248.0 32.8SR 12-36 8.4 243.0 35.5 36 8.4 243.0 32.9