Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 23,4 11,3 12,1 440,00Remote: 12-36 23,4 10,6 12,8 477,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,8 25,5 3,3 445,00Remote: 45 28,7 23,8 4,9 500,00Worst Value: Local: 36 27,3 23,8 3,5 500,00Remote: 45 28,7 23,8 4,9 500,00PS-ACRF: Pass Worst Margin: Local: 45 68,2 56,3 11,9 1,75Worst Value: Local: 45 21,7 8,3 13,4 443,00Remote: 12 66,4 54,3 12,1 2,20Remote: 36 21,5 7,5 14,0 482,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:55Signature:______________________ Page: 4Copper Certification ReportCable Label: 521.002-ud128 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:16.01.2019 15:55:59 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: