Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
On request the Skystar cassettes are available with electric control panel reachable from below and with the electric board that can be placed in a remote position. In this case the units are supplied with an electronic connecting control panel, fitted to the bottom side on the 4 smallest sizes and to the lateral side on the 3 biggest sizes. The electronic control panel is connected to the fan motor, to the condensate pump and to the condensate level control. A 6 m wire is also supplied with integral plug-in connections to connect the unit with the remote electric board that can be installed in a suitable and comfortable position, where the power and system connections can be made easily. This feature is not available for units with electric heater or infra- red remote control.14SkyStarON-OFF valves with thermoelectric actuatorValVe with MicroMetric lockshield ValVe3 ways2 waysValVe with siMplified kit3 ways2 waysTechnical data:Valves characteristicsRated pressure: