Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
33.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.1 470.0 29.3 36 6.6 469.0 26.5SR 36-45 5.5 415.0 31.0 36 7.2 450.0 27.4MAIN 36-45 6.3 477.0 28.9 36 7.4 495.0 25.2SR 36-45 7.0 495.0 28.1 36 7.8 491.0 25.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.8 6.9 48.5 45 17.3 167.5 17.8SR 45-78 17.8 6.9 48.5 45 17.3 82.0 24.0MAIN 36-45 19.3 484.0 11.5 36 21.1 480.0 8.6SR 36-45 19.3 471.0 11.8 36 19.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 31.9 167.5 15.1 12 31.4 167.5 12.5SR 12-36 32.3 179.0 13.8 36 32.2 178.0 11.3MAIN 36-45 39.6 494.0 -12.0 36 40.1 495.0 -14.9SR 36-45 39.6 495.0 -12.1 36 41.1 499.0 -15.20804000250 MHzACR-N (dB)