Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF041 C16/2 12.06.2020 12:03R LOW OhmR: 0.20ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 10.06.2020 11:24R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 11.06.2020 15:30SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.1HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 11.06.2020 16:15Zs(rcd)Z: 0.47ΩIsc: 488A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 11.06.2020 16:15RCD II: 28.5mAUci: 0.3V t: 102.3ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF042 C16/2 12.06.2020 09:16Tallberg Elektro A/S Tlf.22796640Side:30GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.205205206206207207208208209209210210211211TEST RAPPORTResultatZ-LINE