Title: etg u1.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]234 372 27 10.2234 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.2 * 242.5 35.6 36 0.6 * 240.0 33.0SR 36-450.6 *244.5 35.5 36 0.7 *241.5 33.0MAIN 36-45 0.2 248.5 35.4 36 0.6 240.0 33.0SR 36-45 0.6 244.5 35.5 36 0.7 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.7 195.5 18.4 36 18.7 168.5 16.7SR 45-36 16.8 208.5 17.8 45 17.5 219.5 14.4MAIN 45-36 17.7 243.0 16.5 45 18.8 224.5 14.2