Title: økernvn 94.pdf
MAIN 12-36 7.2 15.1 48.1 36 7.1 242.5 2.8SR 12-36 6.4 8.1 54.2 36 6.7 180.5 9.5MAIN 36-45 8.0 249.5 4.7 36 7.3 249.5 2.1SR 36-45 7.6 250.0 4.7 36 6.9 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.8 9.3 21.0SR 45 4.4 5.3 21.0MAIN 45 8.0 225.0 10.5SR 36 6.3 241.5 10.206050050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94