Title: 1 etg del 2.pdf
Cable ID: D1034 Date / Time: 10/17/2013 11:55:48 AM Headroom 11.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]94 149 10 3.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.7 83.5 33.6 36 13.3 94.0 29.7SR 12-36 13.4 83.5 33.6 36 14.2 94.0 29.7MAIN 12-36 11.7 94.0 32.7 36 13.3 94.0 29.7SR 12-36 13.5 94.0 32.7 36 14.2 94.0 29.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.4 100.0 18.6 36 24.7 3.8 44.1