Title: økernvn 94.pdf
Cable ID: D4151 Date / Time: 09/09/2013 01:16:33 Headroom 0.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]157 241 10 7.5157 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]15.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.5 222.0 36.2 36 9.4 224.0 33.5SR 12-360.6 *234.5 35.8 36 0.5 *245.0 32.9MAIN 12-36 8.5 222.0 36.2 36 9.6 247.5 32.8SR 12-36 0.9 247.5 35.4 36 0.5 249.0 32.710080