Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Attach KTB0000YS1 bar supports on the flexible links or connection bars. The number of KTB0000YS1 bar supports to be used depends on the length of the flexible links or connection bars. The distance between the KTB0000YS1 bar supports depends on the rated short-time withstand current Icw of the equipment (seepage48).12Check for proper clearances between the active conductors and the switchboard.13Close the protective cover.PEN ConnectionTo connect the protective earth conductor (PE) to the neutral conductor (N) to create a PEN, use the PEN link delivered with the end feed unit:Connect the PEN link between the protective earth conductor (PE) and the neutral conductor (N) of the end feed unit by using the bolts delivered with the link.Flexible LinksThe number of flexible links or connection bars required for the connection of the switchboard to the end feed unit depends on the rating of the busbar trunking system.KTA rating (A)1000 to 16002000 to 250032004000–5000–