Title: økernvn 94.pdf
50 MHz75100LinkWare Version 7.4Cable ID: T4006 Date / Time: 09/11/2013 09:45:05 Headroom 4.6 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]227 348 14 10.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.8 84.5 43.0 36 7.9 84.5 40.5SR 36-78 4.6 228.5 36.0 78 5.6 228.5 33.4MAIN 45-78 8.5 245.5 35.5 78 9.1 245.0 32.9SR 36-78 4.6 228.5 36.0 78 5.6 228.5 33.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)