Title: 1 etg del 2.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.9 16.4 47.3 36 8.3 15.0 45.8SR 12-36 7.4 16.5 47.2 36 9.1 13.8 46.7MAIN 36-45 11.6 250.0 4.7 36 10.6 248.5 2.2SR 12-36 12.2 248.5 4.8 36 11.9 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.5 12.3 20.6SR 45 3.6 12.3 20.6MAIN 36 7.4 234.0 10.3SR 36 7.8 181.0 11.460500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1