Title: +038=30.001-NI003._29-V20-04-02 VVS-anlegg plan 4 - DM3.pdf
XCSnitt 1 - Aggregat 360.004, 1:50400x1400 UK=2414LF400x1400 UK=1952For rør-, shunt- og ventildetaljer se: Oppleggskjema varme V62--01 Systemskjema varme og kjøling V67--01 Oppleggskjema kjøling V67--02 Rørtilkoblinger, shuntopplegg og pumper skal vises på as-built tegning.600x1400LF600x700 UK=1167600x1400 UK=1167600x1400 UK=1167600x1400600x700 UK=261Plan 04600x1400 UK=261600x1400 UK=261600x1400 UK=261Plan 0415.77 m344-421 4-130Lager Kontor515.77 m101234567LD018T Maks:150 m³/h Kjøling: 235 W 0.019 L/s Varme: 130 W 0.003 L/sLD018T Maks:135 m³/h Kjøling: 645 W 0.051 L/s Varme: 185 W 0.005 L/s8LD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/sLD018T Maks:140 m³/h Kjøling: 330 W 0.026 L/s Varme: 260 W 0.006 L/s