Title: +038=433.000-NI003._03-Testrapport Elektriske Anlegg  Plan7 DM3.E7=433.07.05.docx
Kurs Kontinuitet Ω MΩ Jordfeilbyter mA Jordfeilbryter mS KW 01 28,5 20 KW 20 28,5 12 KW 21 28,5 11 KW 22 28,5 17 KW 23 28,0 16 KW 24 0,25 1000 27,0 24 KW 25 0,25 1000 28,5 11 KW 26 0,28 1000 28,5 24 KW 27 0,28 1000 28,5 82 KW 28 0,31 1000 27,0 242 KW 29 0,32 1000 28,5 12 KW 30 0,39 1000 28,5 11 KW 31 0,18 1000 27,0 267 KW 32 0,18 1000 27,0 52 KW 33 0,16 1000 28,5 20 KW 34 0,15 1000 28,5 12 KW 35 0,12 1000 28,5 19 KW 36 0,20 1000 27,0 57 KW 37 1000 28,5 21 KW 38 0,23 1000 27,0 56 KW 39 0,09 1000 28,5 14 KW 40 0,15 1000 27,0 241 KW 41 28,5 12 KW 42 28,5 21 KW 50 0,02 2,44 25,5 29 KW 51 0,01 93 22,5 69 KW 52 0,01 2,6 24,0 19 KW 53 0,01 99,3 27,0 39 KW 54 0,07 756 27,0 59 KW 55 27,0 123 KW 70 28,5 21 KW 71 27,0 62 KW 72 28,5 17 KW 73 27,0 62 KW 74 27,0 41 KW 75 27,0 82 KONTINUITET LEDENDE DELER LOKASJON (NORD / SØR / KORRIDOR) AKSE Kontinuitet Ω KULVERT S 14 0,04 VENTILASJON S 15 0,02 HIMMLING S 15 0,02 KULVERT S 15 0,05 VENTILASJON S 16 0,01 AGGREGAT S 16 0,01 KULVERT N 16 0,01 AGGREGAT N 16 0,01 HIMLING N 16