Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
[Pair 12] [Pair 12] [Pair 12]29.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.9 474.0 29.1 36 9.3 455.0 27.2SR 36-45 8.6 465.0 29.5 36 9.2 465.0 26.7MAIN 36-45 9.1 494.0 28.1 36 10.0 500.0 25.0SR 36-45 10.1 499.0 27.9 36 10.7 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.6 5.0 51.3 45 14.0 2.6 53.9SR 45-78 15.6 5.0 51.3 45 14.0 2.9 53.1MAIN 36-45 16.8 468.0 11.8 45 18.0 500.0 8.3SR 36-45 16.7 474.0 11.7 45 18.0 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 26.8 78.8 28.0 36 27.2 84.0 24.5SR 12-45 28.3 76.0 28.5 12 29.7 76.0 26.0MAIN 36-45 37.3 499.0 -12.3 36 38.7 500.0 -15.3SR 36-45 38.0 499.0 -12.3 36 39.4 500.0 -15.30804000250 MHz