Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.0 112 1 3.93Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]29.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.2 457.0 29.9 36 8.3 457.0 27.1SR 12-36 8.8 453.0 30.1 36 9.6 454.0 27.2MAIN 12-36 9.3 499.0 27.9 36 8.9 499.0 25.0SR 12-36 9.5 499.0 27.9 36 9.9 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.7 5.9 49.9 45 21.0 5.9 46.9SR 45-78 18.7 5.9 49.9 45 21.1 6.1 46.5MAIN 78-45 21.7 500.0 11.3 45 21.7 500.0 8.3SR 78-45 21.8 494.0 11.4 45 21.9 500.0 8.30100806040200250 MHzACR-F (dB)