Title: økernvn 94.pdf
Cable ID: T3047 Date / Time: 09/12/2013 02:54:14 Headroom 0.8 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]270 428 30 11.6270 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 248.0 35.4 36 0.9 * 248.0 32.8SR 36-450.8 *249.0 35.4 36 1.0 *243.0 32.9MAIN 36-45 1.3 248.0 35.4 36 0.9 248.0 32.8SR 36-45 0.8 249.0 35.4 36 1.1 249.5 32.710080