Title: 1 etg del 2.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.2 28.3 41.2 36 7.1 243.5 2.7SR 12-36 5.8 20.4 44.9 36 6.2 239.5 3.1MAIN 36-45 7.9 249.5 4.7 36 7.3 246.5 2.4SR 36-45 6.9 249.5 4.7 36 6.4 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.5 5.3 21.0SR 45 4.1 5.3 21.0MAIN 45 8.2 238.5 10.2SR 36 6.7 234.5 10.360500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1