Title: Eurotester målerestultat.pdf
Bytesteinen 1 / =433.202 / SIKRING41 30.03.2021 14:55:41R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩTestet av: Andreas PedersenSide:15GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr. 9696979798989999100100101101102102TEST RAPPORTResultatBytesteinen 1 / =433.202 / SIKRING41 30.03.2021 14:55:53R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING41 30.03.2021 14:56:06R LOW OhmR: 0.38ΩR+: 0.4Ω R-: 0.4Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING42 30.03.2021 15:06:45RCD II: 24.0mAUc: 8.9V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING44 30.03.2021 14:59:00Z-LINEZ: 0.56ΩIsc: 414A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 157A Isc(0.76%): 314A Isc(1.15%): 476ABytesteinen 1 / =433.202 / SIKRING44 30.03.2021 14:59:17RCD II: 21.0mAUc: 9.8V Idn: 30mA type: AC Ulim: 50V