Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]26.0 113 2 3.95Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.2 412.0 31.1 45 10.2 412.0 28.3SR 12-45 9.2 411.0 31.1 36 9.1 500.0 25.0MAIN 36-45 10.6 495.0 28.1 36 10.6 500.0 25.0SR 36-45 10.4 500.0 27.8 36 9.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.3 3.9 53.5 45 13.5 2.6 53.9SR 78-45 14.3 3.8 53.8 45 13.6 2.6 53.9MAIN 45-78 15.9 500.0 11.3 45 17.1 500.0 8.3