Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 36-45 7.9 478.0 29.7 36 8.6 480.0 26.8SR 12-45 9.7 483.0 29.6 36 9.5 485.0 26.7MAIN 36-45 8.0 480.0 29.6 36 9.0 500.0 26.4SR 12-45 10.0 497.0 29.3 36 9.7 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.8 3.9 53.5 45 13.7 3.8 50.8SR 45-78 14.7 411.0 13.0 45 13.6 2.6 53.9MAIN 78-45 15.1 464.0 11.9 45 15.5 498.0 8.3SR 45-78 15.0 464.0 11.9 45 15.2 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.6 25.6 42.6 45 20.8 25.6 40.2SR 36-45 18.0 30.8 40.5 45 19.6 30.8 38.1MAIN 36-45 29.4 480.0 -11.1 36 31.0 500.0 -15.3SR 12-45 31.5 497.0 -12.2 36 31.5 496.0 -15.00804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.7 496.0 8.0SR 12 7.7 490.0 8.0MAIN 12 7.7 496.0 8.0SR 12 7.7 490.0 8.040010080250 MHzRL (dB)