Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
For the rules for locating and aligning the neutral conductor, consult the instruction sheet AAV32038 available on the Schneider Electric website.The position of the neutral conductor is indicated by a slot which is located on the opposite side of the run component to the neutral conductor.Check the alignment of the neutral conductors by checking that the slots are aligned on the same side.Correct alignment.Incorrect alignment.NOTE: The mismatch protection of Canalis KT system does not allow the assembly of two run components if the neutral conductors are not on the same side.QGH3492101-01 11/201815Preparation and OrganizationChecking the Labels on the Run ComponentsThe labels on the run components provide information about the phase order, polarity, and the dimensions.A Commercial reference B Product description C Product dimensions D Polarity E Product rating F Standard specifications (IEC / EN) G Phase order