Title: Simployer - Data testrapport =514.204-FS001.pdf
[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]22.0 113 8 5.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]28.8 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 7.5 167.0 36.1 3,6 8.8 166.5 33.2SR 1,2-3,6 7.4 151.5 36.9 3,6 8.1 197.0 32.0MAIN 1,2-3,6 7.6 207.5 34.5 3,6 9.5 239.5 30.5SR 1,2-3,6 8.0 243.5 33.3 3,6 9.3 238.5 30.5PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 16.5 3.5 52.4 4,5 16.7 3.5 49.4SR 4,5-7,8 16.5 3.5 52.4 4,5 16.7 3.5 49.4MAIN 7,8-4,5 20.4 250.0 15.3 4,5 22.6 250.0 12.3SR 4,5-7,8 20.7 250.0 15.3 7,8 22.6 249.5 12.3PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 12.7 4.5 57.8 3,6 11.9 4.8 54.8SR 3,6-4,5 12.6 4.5 57.8 3,6 12.0 4.5 55.3