Title: Bruksanvisning_1436854.pdf
StörungursacheThe detector should be positioned according to spatial conditions and requirements (fig. 1, (1) working area (2) head-on to detector (3) diagonally to detector).The detector should be positioned according to spatial conditions and requirements (fig. 1, (1) working area (2) head-on to detector (3) diagonally to detector).Switch off the power supply at the mains before installing the product.Beleuchtung schaltet nicht ein, bzw. Beleuchtung schaltet aus bei Anwesenheit und DunkelheitLichtwert zu tief eingestellt  Beleuchtung wurde manuell ausgeschaltet  Person nicht im Erfassungsbereich  Hindernis(se) stören Erfassung - Nachlaufzeit zu kurz eingestelltThe detectors are designed for recessed mounting (fig. 2), surface mounting (fig. 3) or (with accessories) recessed ceiling mounting (fig. 4). Install the mounting plate as per the relevant illustration. Connect the detector according to the wiring diagram(fig. 5) and snap it into place in the mounting plate. (5)