Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 16.3 491.0 11.4 45 16.5 3.4 51.7MAIN 45-78 16.8 497.0 11.3 45 18.2 500.0 8.3SR 78-45 16.3 491.0 11.4 45 17.1 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 24.8 85.5 26.7 45 26.2 85.3 24.2SR 12-45 25.9 68.8 30.0 45 26.1 78.5 25.5MAIN 36-45 37.3 498.0 -12.3 36 36.9 493.0 -14.8SR 36-45 35.2 499.0 -12.3 36 36.0 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.1 79.8 15.0SR 45 5.4 79.8 15.0MAIN 45 9.3 483.0 8.0SR 12 6.9 480.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS