Title: økernvn 94.pdf
SR 36-45 14.9 158.0 20.2 36 19.5 234.0 13.8010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.9 20.6 44.8 36 11.5 20.6 42.4SR 12-36 9.9 20.5 44.8 36 11.3 20.5 42.4MAIN 36-45 16.9 248.0 4.9 36 16.5 248.0 2.2SR 36-45 16.0 248.0 4.9 36 15.7 247.5 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.0 14.8 20.2SR 45 4.9 14.8 20.2MAIN 36 7.9 185.5 11.3SR 36 8.5 250.0 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040206040