Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 30.11.2020 10:31SPĆNDINGUln: ___V Ulpe: ___V Unpe: ___V f: ___HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 30.11.2020 10:31Tallberg Elektro A/S Tlf.22796640Side:10GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.6969707071717272737374747575TEST RAPPORTResultatZ-LINEZ: 0.87ΩIsc: 263A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 30.11.2020 10:31Zs(rcd)Z: 0.88ΩIsc: 261A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 30.11.2020 10:34RCD II: 28.5mAUci: 0.1V t: 42.1ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 30.11.2020 11:53 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254V