Title: Simployer - Data testrapport =514.204-FS001.pdf
LinkWare™ PC Version 10.4Cable ID: 521.204-UD47 Date / Time: 28/01/2022 12:58:27 Headroom 7.4 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]55.8 286 20 10.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 8.7 217.0 34.2 3,6 10.4 217.0 31.2SR 1,2-3,6 7.4 151.0 36.9 3,6 8.7 151.0 34.0MAIN 1,2-3,6 8.7 217.0 34.2 3,6 11.2 250.0 30.2SR 1,2-3,6 9.0 225.0 33.9 3,6 11.0 248.0 30.2