Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 17.6 482.0 11.6 45 17.4 91.0 23.1MAIN 78-45 17.5 500.0 11.3 78 18.5 482.0 8.6SR 45-78 17.9 500.0 11.3 45 17.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.8 61.0 31.7 36 24.6 65.0 28.3SR 12-36 21.8 88.0 26.3 36 23.4 88.0 23.7MAIN 36-45 37.4 496.0 -12.1 36 37.0 496.0 -15.0SR 36-45 34.4 494.0 -12.0 36 35.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.9 495.0 8.0SR 12 6.5 496.0 8.0MAIN 45 6.9 495.0 8.0SR 12 6.5 496.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS