Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
26.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.5 489.0 29.5 36 7.3 500.0 26.4SR 12-45 9.0 464.0 29.9 36 8.6 500.0 26.4MAIN 36-45 8.5 489.0 29.5 36 7.3 500.0 26.4SR 12-45 9.4 486.0 29.5 36 8.6 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.6 435.0 12.5 45 17.9 28.8 33.1SR 45-78 17.6 434.0 12.5 45 17.9 30.4 32.6MAIN 78-45 18.0 493.0 11.4 45 19.1 500.0 8.3SR 45-78 18.2 497.0 11.3 45 18.7 471.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.6 43.3 36.3 45 25.1 43.3 33.8SR 36-45 20.5 49.8 34.5 45 22.0 49.5 32.1MAIN 36-45 35.5 496.0 -12.1 36 34.4 500.0 -15.3SR 36-45 36.6 500.0 -12.4 36 35.7 500.0 -15.30804000250 MHzACR-N (dB)