Title: Sprinklerhode våt.pdf
The Series LFIl Residential Sprinklers have been designed with heat sensi- tivity and water distribution charac- teristics proven to help in the control of residential fires and to improve the chance for occupants to escape or be evacuated.Dry Pipe System ApplicationThe Series LFIl Residential Pendent and Recessed Pendent Sprinklers offers a laboratory approved option for designing dry pipe residential sprinkler systems, whereas, most residential sprinklers are laboratory approved for wet systems only.Through extensive testing, it has been determined that the number of design sprinklers (hydraulic design area) for the Series LFIl Residential Pendent and Recessed Pendent Sprinklers (TY2234) need not be increased over the number of design sprinklers (hydraulic design area) as specified for wet pipe sprinkler systems, as is accustomed for density/ area sprinkler systems designed per NFPA 13.