Title: 563.X0X-RY001 SLASXCX - temperatur og CO2 sensor.pdf
High impact ABS plasticIP 30TouchscreenLCD61 mm (2.4 in), color, backlit, capacitive, 240x300px Setpoint: 0-10Vdc. Temperature, humidity or fan speed selectable Timeout override: Display timeout** Lockout override: Touchscreen/button lockout** 52mm (2.05 in), segmented with 3 buttons Setpoint: 0-10Vdc. Temperature, humidity or fan speed selectable Timeout override: Display timeout** Lockout override: Touchscreen/button lockout**CO2 SensorSetpoints***Sensor typeNon-dispersive infrared (NDIR), diffusion samplingOutput range0 to 2000/5000 ppm (selectable)Accuracy±30 ppm ±3% of measured valueRepeatability±20 ppm ±1% of measured valueResponse time <60 seconds for 90% step changeTemperature setpointHumidity setpoint Fan speed setpoint0 to 10V output Scale: 10 to 35 °C (50 to 95 °F) / 0 to 50 °C (32 to 122 °F) 0 to 10V output Scale: 0 to 100% RH 0 to 10V output Off 0V, Auto 1.5V, Low 3.3V, Med. 6.7V, High 10.0VVOC SensorOverrideSensor typeOutput rangeSolid state