Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
Insulation tape40 mm35 mm6 Apply heat to the contraction tube to contract it.Contraction tube7 After tube contraction work is completed, wrap it withthe insulation tape to finish.Insulation tapeCAUTIONMake sure that the connection parts are not exposedto outside.Be sure to use insulation tape and a contraction tubemade of approved reinforced insulating materials that have the same level of withstand voltage with the power cable. (Comply with the local regulations on extensions.)WARNING In case of extending the electric wire, please DO NOT use a round-shaped Pressing socket.– Incomplete wire connections can cause electricshock or a fire.360_AirCon_Indoor_IM_ENG_EN.indb 19Step 14 Setting the indoor unit addresses and the installation optionsYou cannot set both of the indoor unit addresses and the installation options in a batch: set both of them respectively.Common steps for setting the addresses and optionsAR-KH00E remote control (for 360 cassette only)