Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 21,0 10,4 10,6 488,00Remote: 45-12 21,2 10,4 10,8 491,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 31,2 27,6 3,6 388,00Remote: 36 32,6 29,2 3,4 347,00Worst Value: Local: 36 27,5 23,8 3,7 499,00Remote: 45 27,6 23,8 3,8 500,00PS-ACRF: Pass Worst Margin: Local: 12 65,6 54,3 11,3 2,20Worst Value: Local: 12 19,3 7,2 12,1 500,00Remote: 12 65,6 54,3 11,3 2,20Remote: 12 19,7 7,2 12,5 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:16Signature:______________________ Page: 146Copper Certification ReportCable Label: 521.002-UD-45 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:21:56 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: