Title: +038=360.000-LC008T_04-Major line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
(cid:404)(cid:3)(cid:3)Wire clamps for customer connection (cid:404)(cid:3)(cid:3)Unit opposite side to hydraulic connections (possibility of(cid:404)(cid:3)(cid:3)2 or 4-tube main coil fitted with ½" or ¾" rotary couplings withputting all on the same side optional with NCH)air bleed valve and drain.(cid:404)(cid:3)(cid:3)Additional coil for 4 tubes fitted with ½" rotary couplings with40 mm centre-to-centre distance.(cid:404)(cid:3)(cid:3)Nominal pressure of 16 bar (at 20°C) (cid:404)(cid:3)(cid:3)Test pressure: 24 bar. (cid:404)(cid:3)(cid:3)Max. water T°: 90°C (cid:404)(cid:3)(cid:3)Maximum hot water inlet temperature:4-tube application: 90°C - 2-tube application: 90°C - 2T/2-wire application: 55°C (min. air flow rate: 200 m3/h)Electric heater (cid:404) Single tube 230V single phase 50/60 Hz electrical elementsinserted into the aluminium housing.(cid:404)(cid:3)(cid:3)Two capillary tube temperature limiters with manual and