Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 38,6 68,0 200,0 11,0 6,9Limit 100,0 - 555,0 50,0 25,0Margin 61,4 - 355,0 39,0 18,1Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,1 2,4 2,95Worst Value: Local: 36 16,5 43,5 27,0 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 22,6 18,4 4,2 33,00Remote: 78 22,9 16,5 6,4 56,75Worst Value: Local: 78 15,4 8,0 7,4 485,00Remote: 12 17,2 8,5 8,7 355,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 30,3 26,7 3,6 500,00Remote: 36-45 30,0 26,7 3,3 499,00Worst Value: Local: 36-45 30,3 26,7 3,6 500,00Remote: 36-45 30,0 26,7 3,3 499,00dB 060