Title: Luftport - frico_ar3500-no.pdf
Supply water temperature: 60 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 Return water Output temp. [°C] 53,7 41,2 51,0 39,6 51,2 38,8Water flow [l/s] 0,44 0,08 0,43 0,09 0,63 0,13[kW] 11,5 5,7 16,0 8,0 23,0 11,5Pressure drop [kPa] 53,0 2,0 20,0 1,0 46,0 3,0Water temperature: 60/40 °C Room temperature: +18 °COutput *2[kW] 8,6 5,6 12,6 8,1 18,3 11,8Outlet air temp. [°C] 30,7 34,5 31,3 35,2 31,6 35,5Water flow [l/s] 0,10 0,07 0,15 0,10 0,22 0,14Pressure drop [kPa] 4,0 2,0 3,0 1,0 8,0 4,0TypeFan positionAR3510W max min AR3515W max min AR3520W max minAirflow[m3/h] 2000 1000 2800 1400 4000 2000Supply water temperature: 55 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 Return water Output temp. [°C] - 44,0 - 42,2 - 41,7Water flow [l/s] - 0,13 - 0,15 - 0,21[kW] - 5,7 - 8,0 - 11,5Pressure drop [kPa] - 6,0 - 3,0 - 7,0Water temperature: 55/35 °C Room temperature: +18 °COutput *2[kW] 6,9 4,5 10,2 6,6 15,0 9,7