Title: +038=249.001-#####._05-Lydtest plan 10 og 11 Pareto - Flere rom - Multiconsult.pdf
Apparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation between roomsClient: Description:Probea AS Luftlyd horisontaltDate of test:4/27/2020Object:Møterom 10-101 - Møterom 10-103Source room:Receiving room:Condition:Condition:Type:Type:Location:Location:Frequency range according to theArea of common partition:11,24m²curve of shifted reference values (ISO 717-1)Source room volume:Receiving room volume:66m³  B d70FrequencyR',f1/3 octave'R,[Hz]50[dB]18,3x e d ni60638010012516020025031517,921,529,733,638,137,941,043,8n o i t c u d e r d n u o st n e r a p p A504040042,250042,763042,080038,8100045,030125049,7160049,0200050,2250050,420315052,9400053,4500055,7106312525050010002000Hz 4000Frequency, f, Hz