Title: 32 Pumper modbuss teknisk data.pdf.pdf
Confirm that the GENIbus LED is permanently green and that the Modbus LED is either off, if no master is actively polling the slave, or flashing green, indicating error-free communication.CIU 200 is now ready to be accessed via the Modbus network.11.3 Hardware setup, CIM 260 data connectionStepAction1Install CIM 260 in the Grundfos product according to the product documentation.2Fit an antenna to the CIM module SMA connector. See section 6.1.1 Fitting a cellular antenna.3Insert the SIM card in CIM 260. See section 6.1.2 Inserting the SIM card.4Power on the Grundfos product.5Observe that LED2 turns permanently green. See section 6.2 Status LEDs.6Observe that LED1 blinks yellow and changes to yellow pulsing after approximately 30 seconds, indicating that the cellular network connection is working. See section 6.2 Status LEDs.7