Title: +038=543.001-OU003T_07-Dørkontroller Lenel 1320-produktdatablad.pdf
12 to 24Vdc ±10%, 550mA maximum (plus reader current) 12Vdc @ 550mA (plus reader current) maximum, 22.5 BTUs 24Vdc @ 330mA (plus reader current) maximum, 27.0 BTUsOutputs6 outputs, Form-C contacts: Normally Open (NO) Contact: 5A @ 30 Vdc, Normally Closed (NC) Contact: 3A @ 30 VdcInputs8 unsupervised/supervised, standard EOL: 1k/1k ohm, 1% 1/4 watt 2 unsupervised, dedicated for cabinet tamper and UPS fault monitoringReader Interface