Title: 32 Pumper modbuss teknisk data.pdf.pdf
Controls the state of relay 3. 0: Closed 1: Open Only MGE model H and later.Controls the state of relay 4. 0: Closed 1: Open Only MGE model H and later.Sets the maximum flow limit, FLOWLIMIT. It must be enabled in register 00101, bit 5. The value is set in 0.01 m3/h. If enabled, the FLOWLIMIT is active in all control modes. If disabled, the maximum flow limit will only be active in FLOWADAPT control mode. Read actual value in register 00345 Only available on MAGNA3 and MGE model H and later.Sets the real-time clock in the pump in unix format (seconds since 01-01-1970). Only available on MAGNA3 and MGE model H and later.Sets the proportional gain, Kp. The scale is 0.1. Only available on MAGNA3 and MGE model H and later.Sets the integral action time, Ti. The scale is 0.1 s. Only available on MAGNA3 and MGE model H and later.Selection of Direct/Inverse control. 0: Inverse control 1: Direct control Only available on MAGNA3 and MGE model H and later.9.6 Pump status register block