Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.0 112 1 3.97Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.9 464.0 29.6 36 8.4 465.0 26.7SR 12-36 8.9 466.0 29.5 36 10.0 461.0 26.9MAIN 12-36 7.9 497.0 28.0 36 9.3 499.0 25.0SR 12-36 9.5 498.0 27.9 36 10.5 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.1 7.1 48.2 45 20.0 500.0 8.3SR 45-78 19.1 6.5 49.0 45 20.2 4.9 48.5MAIN 36-45 19.8 500.0 11.3 45 20.0 500.0 8.3SR 45-36 19.9 500.0 11.3 45 20.7 500.0 8.30100806040200250 MHzACR-F (dB)