Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
30…+5 V +15…30 V for source operationcounter output (switches when count is 0 or 65,535) 5…500 mA(max. current leakage 1 mA) (min. load resistance 48 Ω in voltage range 5…24 V).Voltage range: Circuit type:Voltage drop: Output delay:5…32 V smoothed, max. 10% ripple Electrically coupled, not short circuit protected, positive switching typically 2 V at 500 mA < 10 µs, (longer for inductive load because ofprotective diode).Power supply External supply Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Operational conditions Ambient temperatureNoise immunity: Programming:5…32 VDC, (for supply of CCO output only) max. 90 mA0 mACCO output load current0…+55°C without forced ventilationOperation: Storage: -25…+85°C EC mark according to EN 50 081-1 and EN 50 082-2 Based on Saia PCD® user program and pre-programmed function blocks (FB). There are other FBs for use in the RIO head station.6-111PCD3.H100