Title: etg u1.pdf
Cable ID: D0205 Date / Time: 10/22/2013 12:22:33 PM Headroom 6.9 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]138 211 8 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.9 238.5 35.7 36 8.5 238.5 33.0SR 12-36 8.4 210.5 36.6 12 8.9 210.5 34.0MAIN 36-78 6.9 238.5 35.7 78 8.5 250.0 32.7SR 12-36 8.4 210.5 36.6 12 8.9 210.5 34.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.5 3.6 53.0 36 15.5 2.6 52.8