Title: +038=360.000-LC007T_04-Coadis line 600 Fan-coil CIAT - Manual.pdf
Pull the fan motor assembly bundle towards the interior of the boxUndo the 3 motor retaining screws and remove the motor (Fig. 20, b).To refit, perform the operation in reverse order.5.4. Heat exchange coil A clean coil is crucial to the efficiency of the unit. If necessary, clean the coil with a vacuum cleaner.If the coil must be disassembled on account of a leak: Disconnect the electrical supply to the unit before carrying out any work.(cid:121)(cid:3)(cid:53)(cid:72)(cid:80)(cid:82)(cid:89)(cid:76)(cid:81)(cid:74)(cid:3)(cid:87)(cid:75)(cid:72)(cid:3)(cid:70)(cid:82)(cid:76)(cid:79)(cid:29)Insulate the unit hydraulically from the network and drain the coil. - Disconnect the coil inlets and outlets - Next, follow the same procedure as for disassembling the main pan (Fig. 18) and the fan motor assembly (Fig. 20) (see sections 5.2 Condensate drain pans and 5.3 Fan motor assembly)Undo the 2 screws on the coil retaining clamp (Fig. 21, a) and the coil connectingplate screw (Fig. 21, b).