Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
f: 50.0HzZs (rcd) GODKJENTZ: 0.52QIsc: 4437Sikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AZLINE GODKJENTZ: 0.58QIsc: 398ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AGODKJENTGODKJENTI: 28.5mAUci: 0.2Vt: 87.7msIdn: 30mAtype: ACHN,Ulim: 25VKONTINUITET GODKJENTR: 0.0QGrenseverdi: 1.0QNr.TEST RAPPORTResultatR ISO GODKJENTR: >200MQ Um: 262VUiso: 250VGrenseverdi:1MQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT * 2R1082020, Se3iNI0R LOW Ohm GODKJENTR: 0.09QRt: 0.1QR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT * 12.03.2020 13:46SPENDING