Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]32.3 141 3 4.88Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.8 477.0 29.7 36 8.1 477.0 26.8SR 36-45 8.2 462.0 30.0 36 7.8 491.0 26.6MAIN 36-45 8.2 499.0 29.3 36 8.5 499.0 26.4SR 36-45 8.4 492.0 29.4 36 7.8 491.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.4 17.8 40.3 45 14.9 9.6 42.6SR 78-45 16.0 354.0 14.3 45 14.9 4.5 49.2MAIN 78-36 17.5 473.0 11.7 45 18.8 486.0 8.5SR 36-78 17.2 472.0 11.8 78 18.6 473.0 8.70100806040200250 MHzACR-F (dB)