Title: BNNY-80P DM1-3 Omrapport.pdf
Schedule of Evidence1 of 2 Credits achieved (For full explanation, please refer to Validation Statement)Ene23.doc01Ene23.v01Confirmation of compliance Energy reportEne23.v02CV energy specialistEne23.v03TEK 17 evaluationEne23.v04Passive house evaluationEne23.v05Confirmation air leakage testing and thermographic surveyValidation StatementFirst credit Criterion 1.Calculation method According to Ene23.v01 the calculations have been carried out in accordance with NS 3031 and NS 3701. The calculations have been carried out using the modelling software SIMIEN, which is approved according to NS 3031.Evaluation and calculation of the building’s energy performance has been carried out by a qualified energy specialist (Ene23.v02).Criterion 2. Designed to reduce air leakages According to Ene23.v01 the building is designed to achieve a result from the air leakage test of n50 ≤ 0,6 1/h, which means a reduction of air leakage compared with normal practice according to regulations.