Title: +038=453.003-LZ001. Defrost Snow Nexans leggeanvisning.pdf
Base: The base should be made of compressed and levelled quarry dust/ paver sand, asphalt or similar, free of sharp edges that can damage the cable. The base should be dimensioned to fit the expected load. Do not place the heating cable(s) directly on to insulation.Installation in asphalt: The heating cable mat or cable is placed and attached to the area you want to keep snow- and ice-free. Cover the heating cable(s) manually with a 2-3 cm layer of asphalt and let it cool down to approximately 40°Cbeforeanytruckorconstructionvehicleisusedontheinstallation site. If the product is put in a driveway with a slope, this could imply a danger of the base sliding. Thus, a manual installation is required. The topcoveroftheinstallationshouldbeminimum5cmofasphaltAG B8 or equivalent. Always measure insulation and conductor resistance before connecting the installation. The SNOWMAT heating cable mat canbecoveredinasphaltwithtemperatureuptoamaximumof160°C/ 350°F.