Title: Hardware Installation Guide.pdf
V-Smart Enrollment Kit114.3InstallationUse the following information to install V-series readers (for either enrollment or access verification). Software option SWG-1402 is required in order for these readers to function with the OnGuard software.114.3.1Reader Power RequirementsThe Bioscrypt readers (V-Smart, V-Pass FX, V-Station) require an Earth ground connection to dissipate ESD (electrostatic discharge).Important:Do not use power ground as a substitute for Earth ground.Sensor damage is often a result of ESD. Be sure that every unit that is installed has a connection to Earth ground using pin 15 of the pigtail. Pin 15 should be connected to an Earth ground such as a cold water copper pipe or building ground using a 14-18 AWG single conductor. In addition to the Earth ground connection, the ridge-lock should be used consistently during finger placement to ensure a safe path to discharge the electrostatic. The sensor should NOT be the first point of contact.114.3.2Enrollment Readers