Title: 2 etg del2.pdf
50 MHz75100LinkWare Version 8.1Cable ID: T2075 Date / Time: 10/11/2013 07:48:43 AM Headroom 13.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]201 320 24 8.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.7 77.8 34.1 36 15.6 95.8 29.6SR 12-36 14.2 56.8 36.3 12 15.9 56.8 33.3MAIN 12-36 13.9 95.8 32.6 36 15.6 95.8 29.6SR 12-36 14.8 95.8 32.6 36 15.9 95.5 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)