Title: økernvn 94.pdf
MAIN 36-45 24.2 242.5 5.4 36 23.4 245.0 2.5SR 36-45 20.7 250.0 4.7 36 21.4 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.4 24.4 19.1SR 45 2.1 24.4 19.1MAIN 36 9.3 220.5 10.6SR 36 5.6 175.5 11.6010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94