Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]117 186 14 5.1117 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]20.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.8 238.5 35.7 36 7.2 230.0 33.3SR 36-450.7 *242.0 35.6 36 1.0 *249.5 32.7MAIN 36-45 7.8 238.5 35.7 36 7.2 230.0 33.3SR 36-45 0.7 248.0 35.4 36 1.0 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 16.4 176.0 19.3 12 17.8 168.0 16.7SR 36-12 16.5 172.5 19.5 12 18.2 164.0 16.9MAIN 45-12 17.4 228.5 17.0 12 19.8 234.0 13.8SR 45-12 17.7 228.5 17.0 45 19.6 228.5 14.0010080604020050100150MHzACR-F (dB)200250010080