Title: 370.02-SC001 - Siemens VKF41.100 (Stengeventil).pdf
PN 16 to EN1333 1600 kPa (16 bar) refer to "Type summary", page 2 chilled water, low temperature hot water, high temperature hot water, brine, softened water, water with anti-freeze; recommendation: water treatment to VDI2035 -10…120 °C PN 6, PN 10, PN 16 to ISO7005 90° (to end stop) PED 97/23/EC as per article 1, section 2.1.4Medium temperature Flanged connection for pipes Angle of rotation Pressure Equipment Directive Pressure Accessories Fluid group 2:DN 40…50 without CE-marking as per article 3, section 3(sound engineering practice) DN 65…200 category I, with CE-markingEnvironmental compatibilityHousing Shaft Valve disc Shaft sealISO 14001 (Environment) ISO 9001 (Quality) SN 36350 (Environmentally compatible products) RL 2002/95/EG (RoHS) grey cast iron EN-GJL-250 stainless steel 1.4104 stainless steel 1.4016 EPDM O-rings refer to "Dimensions" refer to "Dimensions"Butterfly valves PN6, PN10, PN16CM1N4131en 2013-11-11DimensionsVKF41.. with SAL..T10 and ASK33N SAL..T40 and ASK33N