Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
For example, output CCO should be switched off after 200,000 count signals.0200'000200'0003392655366553665536Counter FlagReset EnableCCOCPU-Zähler43210ProgrammingProgramming examples for the PCD3.H100 can be found on the TCS Support site www.sbc-support.com.xx7 and RIOs: the firmware reads in the values according to the configuration (I/O Builder or network configurator).Watchdog: This module can interact with the watchdog, if it is used on base address 240. In this case, the last input with address 255 cannot be used. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD3 components.6-115PCD3.H1106.17.2PCD3.H110, counting module up to 100 kHzApplication