Title: +135.01=744.001-UP001T_03-O80 LED brukermanual.pdf
Fuses and RCDs (Residual Current Device) It is recommended that MCBs (Miniature Circuit Breaker) with Type-C operation characteristics are used for lighting circuits. Information on the number of luminaires/ ballasts/drivers that can be connected to one MCB can be found on our WEB- product pages. On a lighting circuit you must not combine inductive loads (magnetic ballast) and electronic devices. The luminaire standard (IEC/EN 60598) allows a maximum earth leakage current of 3.5mA from one luminaire. Electronic devices generate a higher earth current than old conventional equipment. You should therefore use an RCD that is prepared for electronic loads. The RCD has to be time delayed and to withstand high inrush currents without tripping.