Title: 2 etg del2.pdf
40202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 8.1Cable ID: D2011 Date / Time: 10/10/2013 10:57:54 AM Headroom 7.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]137 210 8 6.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.2 237.5 35.7 36 8.0 232.5 33.2SR 36-78 7.1 242.5 35.6 78 7.7 242.5 32.9MAIN 36-78 7.2 237.5 35.7 36 8.0 232.5 33.2SR 36-78 7.1 242.5 35.6 78 7.7 242.5 32.910080604020NEXT (dB)