Title: 2 etg del2.pdf
Cable ID: D2046 Date / Time: 10/10/2013 12:33:50 PM Headroom 13.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]219 336 13 10.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]7.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.0 58.3 36.1 78 19.8 58.3 33.1SR 12-36 13.6 97.8 32.5 36 14.8 97.8 29.5MAIN 12-36 20.2 85.8 33.4 78 22.1 98.8 29.4SR 12-36 13.6 97.8 32.5 36 14.8 98.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-78 23.9 6.0 43.1 36 24.6 4.4 42.8