Title: etg u1.pdf
107 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]21.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 249.5 35.4 36 1.2 250.0 32.7SR 12-36 8.6 176.5 37.8 12 8.6 154.5 36.2MAIN 36-45 0.9 249.5 35.4 36 1.2 250.0 32.7SR 12-36 9.0 238.0 35.7 36 8.8 241.0 33.010080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.1 244.5 16.4 36 16.9 118.0 19.8SR 36-45 15.4 244.5 16.4 36 16.8 121.5 19.5MAIN 45-36 15.1 244.5 16.4 36 17.1 244.5 13.4SR 36-45 15.4 244.5 16.4 45 17.7 247.5 13.3010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)