Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
The two pulse inputs are identically constructed and can be individually set up to receive pulses from water meters with max. 1 Hz or pulses from electricity meters with max. 3 Hz.Configuration for correct pulse value has been carried out from the factory based on order information or is configured by means of METERTOOL. See paragraph 3.6 concerning configuration of VA (FF-codes and VB (GG- codes).MULTICAL 801 registers the accumulated consumption of the meters connected to VA and VB and saves the counter values every month and every year on target date. In order to facilitate the identification during data reading it is also possible to save the meter numbers of the two meters connected to VA and VB. Programming is carried out with METERTOOL.The registration, which can both be read from the display (selecting a suitable DDD-code) and via data communication, includes the following as well as date indication of yearly and monthly data:Type of registrationCounter valueIdentification