Title: 32 Pumper modbuss teknisk data.pdf.pdf
191Limit exceeded, sensor 2215Soft pressure buildup timeout240Lubricate bearings (specific service information)241 Motor phase failure242Automatic motor model recognition failed11. Modbus RTU commissioning, step-by-step guidesIf the sensor configuration is changed, restart the CIM module or CIU unit to ensure a correct scaling of the sensor value.11.1 Hardware setup, CIM 200StepAction1Install CIM 200 in the Grundfos pump according to the pump documentation.2Complete the pump configuration, for example sensor configuration and local mode. This can be done either on the pump control panel, via Grundfos GO Remote or Grundfos PC Tool E-Products.3Select the Modbus slave address (1-247).4Select the bit rate of the Modbus slave.5Select parity and stop bits of the Modbus slave, even parity with 1 stop bit or no parity with 2 stop bits.6If necessary, set line termination.7Connect the necessary cables from CIM 200 to the Modbus network.8