Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD33 Date / Time: 28/01/2022 11:15:12 Headroom 10.1 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]55.8 286 20 10.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.2 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 10.3 27.6 49.3 4,5 10.7 27.4 46.7SR 4,5-7,8 10.1 129.0 38.0 3,6 11.2 180.5 32.6MAIN 1,2-3,6 12.3 242.0 33.4 3,6 13.1 226.5 30.9SR 4,5-7,8 11.5 250.0 33.1 7,8 12.1 243.5 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)