Title: Eurotester sluttmålinger =433.205.pdf
GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr. 778899101011111212ResultatSimployer / =433.205 / SIKRING4 31.01.2022 09:55:58RCD II: 27.0mAUci: 0.1V t: >300ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING5 31.01.2022 09:56:15RCD II: 27.0mAUci: 0.4V t: 41.9ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING6 31.01.2022 09:56:32RCD II: 24.0mAUci: 0.1V t: 20.2ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING7 31.01.2022 09:00:14Z-LINEZ: 0.69ΩIsc: 254A Sikringstype: B SIKRING I: 16A SIKRING T: 35ms Isc_lim: 80.0A Isc(0.38%): 127A Isc(0.76%): 254A Isc(1.15%): 384ASimployer / =433.205 / SIKRING7 31.01.2022 09:00:36RCD II: 19.5mAUci: 0.2V t: 30.9ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING7 31.01.2022 09:00:46R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩTEST RAPPORTSide:2GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT