Title: økernvn 94.pdf
40202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3413 Date / Time: 09/11/2013 06:22:57 Headroom 6.4 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]119 182 6 5.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]19.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.4 232.0 35.9 36 7.0 209.5 34.0SR 36-78 6.5 113.5 40.9 36 6.7 206.0 34.1MAIN 36-78 6.4 232.0 35.9 36 7.3 246.5 32.8SR 12-36 6.7 212.0 36.5 36 7.1 237.5 33.110080604020NEXT (dB)