Title: +135.01=370.001-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Hourly archive1 hour45 days1 hourDaily archive1 day65 days1 hourMonthly archive1 month15 months1 hourYearly archive1 year15 years1 hour/24 hours) For measuring periods of less than 1 hour, the highest value from the maximum values as calculated within 1 hour applies The data is recorded with their values and time stamps. The service software configures and reads out the data via the optical interface.NOTICEData transmission is in a manufacturer-specific format.23 CE2N5324en 2018-08-18Type summary24 Building TechnologiesValue set for data to be recordedMeter readings at the end of the period for...Energy Tariff register 1, 2, 3 Volume Operating time *) Fault duration *) Pulse input 1 Pulse input 2 *) Depending on configuration: Hours or daysInstantaneous values at the end of the period for...Power Flow rate Temperature heat side Temperature cold side Temperature difference Indication of errorsMaximum for...