Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Setup timeout: This timeout can be increased up to 60 sec (value is 60) and up to “∞ “ ( value is -1 ). Using the intermediate values 0 to 2 is injudicious because we have not enough reaction time to stay in the setup menu.Configuration page 2Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-57Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsE-display with PCD7.D3100E nano-browserPCD system page 13Reference of the PCD2.M5PCD type HW version Hardware version of the PCD2 FW version Firmware version of the PCD2 Prod. date Back NextRead only Read only Read only Production date of the PCD2 (year & week) Read only Read only Back to the root menu Read only Go to the PCD system page 2PCD system page 2Status of the PCD2: RUN / HALT Serial Number of the PCD2PCD Status Read only Read only Serial Nr. Program name: Name of the PG5 Program ( can be cut at end) Read only S-bus Address Back NextRead/ write