Title: V20-08-01 VVS-anlegg plan 8 - DM1.pdf
LD018T Maks:210 m³/h Kjøling: 580 W 0.046 L/s Varme: 700 W 0.017 L/sLD018T Maks:210 m³/h Kjøling: 580 W 0.046 L/s Varme: 700 W 0.017 L/s141516LD021T Maks:210 m³/h Kjøling: 580 W 0.046 L/sLD021T Maks:210 m³/h Kjøling: 580 W 0.046 L/sLD018T Q: 100 m³/h Varme: 740 W 0.018 L/sLD018T Q: 100 m³/h Varme: 740 W 0.018 L/sSTAD Dim:10/09 StengtSTAD Dim:10/09 StengtA22 mm +c 3435STAP/STAD DN 20SF002T-12522mm320.102: 18 mm +c 3520 320.102: 18 mm +c 3520IT lager 8-001SK001T Ø125 Q:50 m³/hST008T-125 50 m³/hPatcherom 8-531ø125 UK=3434Fancoil, 2kW tilkobles prosesskjølingÅpent landskap 8-002ADN25 0,017 l/sWISE RTAWISE IAQSF002T-200SF002T-200SF002T-200ø200 UK=3374WISE RTSSF002T-200ø200 UK=3374ø160 UK=3420ø200 UK=34008 3 4 3 = K U 5 2 1 øNed 310.003: MA 110mm 370.102: 54mm 370.102: 54mm 320.101: 28mm 320.101: 28mm310.302: Cu 22mm 310.201: Cu 22mm 310.101: Cu 28mm 310.001: MA 110mm0 6 : 1Eks. trapp 8-530-s0 0 1 : 1SF002T-125