Title: økernvn 94.pdf
100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: D3189 Date / Time: 09/11/2013 03:08:54 Headroom 2.7 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]109 165 5 4.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]20.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 2.7 43.0 47.8 45 5.1 43.3 45.3SR 12-36 3.8 250.0 35.3 36 3.5 247.5 32.8MAIN 36-78 4.6 247.5 35.4 78 6.3 247.5 32.8SR 12-36 3.8 250.0 35.3 36 3.5 250.0 32.710080604020NEXT (dB)