Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Perform such work only after reading and understanding all the instructions contained in the tablebelow. Turn off all power supplying this equipment before working on or inside equipment.  Always use a properly rated voltage sensing device to confirm power is off.  Beware of potential hazards and take adequate safety precautions.Failure to follow these instructions will result in death or serious injury.Tests Before EnergizingCarry out the following tests before energizing the busbar trunking system. You can record the test results in the check-list provided (seepage71).All the operations described below are given for indication only. Under no circumstances can they be used to substitute the installation company’s own procedures and engage Schneider Electric’s responsibility.StepTestDescription1Support and alignment check