Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 16.4 4.3 52.7 45 16.9 3.9 50.5MAIN 78-45 17.5 497.0 11.3 78 18.9 500.0 8.3SR 78-45 17.9 500.0 11.3 36 18.5 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 45-78 24.4 118.5 21.4 45 26.3 111.5 19.9SR 36-78 26.5 120.0 21.2 36 27.8 126.0 17.8MAIN 12-36 39.5 499.0 -12.3 36 39.9 499.0 -15.2SR 36-45 38.5 496.0 -12.1 36 39.3 495.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.2 500.0 8.0SR 12 6.3 474.0 8.0MAIN 45 7.2 500.0 8.0SR 12 6.3 474.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS