Title: Aggregatkjøring.pdf.pdf
(2 x 3.50 kW) 7.00; 3x400; (2 x 5. 60) 11.20kW/V/ASound break out57 dB(A)Power supply3x400V + N + PE 50 HzConsumed current25.4 AFilter Supply / ExtractF7 - ePM1 60% / F7 - ePM1 60%Heating, water35.0 kW ; 13.7/21.0°CWater circuit 40/25°C ; 8.9 kPa ; 0.57 l/s ; 1 1/4" / 1 1/4" Pipe connectionsEnergyDimensioningAverageFans [kWh/year 8760 hours]Heat Recovery (Wet / Dry)82.4 % / 82 %82.4 % / 82 %SFPv, clean filters including speed control1.42 kW/(m³/s)1.42 kW/(m³/s)49790 kWhSFPe with dimensional filter press. incl. speed contr.1.56 kW/(m³/s)1.56 kW/(m³/s)54662 kWh2018Ecodesign approvedYesSystemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Unit no. 20Date 18.06.2021Page 21/400 2.o nt in U2 - n e g n e d n a r b.o n n oi ta o u Qt1 2 0 2 6 0 8 1 e a D..te n e g n e d n a r B