Title: bn303_cgb.pdf
Application include: • Fire alarm push buttons • Flame, heat or beam detectors with relay contactsFunction BS1.1 ONS1.2 OFFS1.3 OFFS1.4 OFFFunction: Pre Alarm condition signaling input.Number of addresses: 1Application include: • Manual input for Pre Alarm • Pre Alarm input from a detector with relay outputFunction CS1.1 OFFS1.2 ONS1.3 OFFS1.4 OFFFunction: Fault condition signalling input.Number of addresses: 1Application include: • Monitoring of associated equipment for faults • Monitoring of detectors with relay contactsAutronica Fire and Security AS | Tel.: +47 90 90 55 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 6Single Monitored Input Unit – BN-303Function DS1.1 ONS1.2 ONS1.3 OFFS1.4 OFFFunction: Uncommitted input.Number of addresses: 1