Title: bg201_cgb.pdf
Technical specificationsWeight210 gMaterialsPolycarbonate, sapphire glassColourTransparent / light greySensitivityRef. Table 1Field of viewHorizontal=+/-45°, Vertical=+30°/ -45° (see the Field of view diagram below for additional EN 54-10 information)Voltage:Supplied from detector loopCurrent consumption: Stand by Current consumption: Alarm LED on90 µA 2,1 mACPD certificate0832-CPD-1999Degree of protectionIP66 and 67Working temperature40 to +70°CStorage temperature50 to +70°CHumidity0-96% rh, can withstand 100% condensing humidity for short periods of timeMaintenanceCleaning of windowServiceReplace if faultyApprovalsCable sizeSee web site Maximum cable 2,5mm2 / AWG14Dimensions/ConnectionsConnection Al_Com loopPluggable ConnectorLoop In +Loop In -Loop Out +Loop Out -1 2 3 4PCBField of viewLOOPCONVEN- TIONAL12 IN+ IN/OUT - +4 3 OUT - +RALARM RESISTORJ5J4LOOPCONV.STANDARD LEGACY HIGH SENS. LOW SENS.J5