Title: +038=433.002-FS025._02-Eaton Tavlebyggeren Produktblad.pdf
Is the panel builder's responsibility. The speciﬁcations for the switchgear must be observed.10.13 Mechanical functionThe device meets the requirements, provided the information in the instruction leaﬂet (IL) is observed.Technical data ETIM 7.0 Low-voltage industrial components (EG000017) / Power circuit-breaker for trafo/generator/installation protection (EC000228)01/04/2019Eaton 147397 ED2018 V51.0 EN3 / 9Electric engineering, automation, process control engineering / Low-voltage switch technology / Circuit breaker (LV < 1 kV) / Circuit breaker for power transformer, generator and system protection (ecl@ss10.0.1-27-37-04-09 [AJZ716013])Rated permanent current IuA160Rated voltageV690 - 690Rated short-circuit breaking capacity lcu at 400 V, 50 HzkA50Overload release current settingA80 - 160Adjustment range short-term delayed short-circuit releaseA160 - 1600Adjustment range undelayed short-circuit releaseA1920 - 1920Integrated earth fault protectionNo