Title: økernvn 94.pdf
LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: D4132 Date / Time: 09/10/2013 02:26:29 Headroom 12.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]61 97 7 2.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.0 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.1 96.5 32.6 36 14.0 91.3 30.0SR 12-36 12.2 91.0 33.0 36 13.5 91.3 30.0MAIN 12-36 12.1 96.5 32.6 36 14.0 97.0 29.5SR 12-36 12.5 96.5 32.6 36 13.9 96.8 29.510080604020NEXT (dB)