Title: +038=534.001-RA001._02-Porttelefon Siedle Systemanvisning.pdf
o) The COM 611-… code lock module is always available for making calls (direct dial via numeric code). Together with the EC 602-… entrance controller, additional con- trol functions (e.g. access control) can be carried out for this door station.Where there are more than 20 backlit call buttons, an additional 12 V AC supply for instance TR 603-… must be installed due to the current consumption. To use the additional supply, remove the jumpers on the SATLM… connection board from b1/c1 to b/c and connect the terminals b/c of the call buttons directly to the additional supply. • Supply limits ATLC/NG 670-… (For detailed information, see page 19, 24)12910.4 Siedle Steel Display call module (Digital call)SACMDoor release (Tö) 12 V AC/DC min. 20 OhmV1V2SATLMS1S2S3S4D1D2DbDaSDRMcvbvDevice requirementSiedle Steel SACM 673-... SATLM 670-... SDRM 612-...Remarksg)130cbNL1TR 603-...C A V 0 3 2W6W5W4W3ZWA 640-...n)PRINL1ANG 600-...C A V 0 3 2