Title: etg u1.pdf
MAIN 36-45 20.5 246.0 5.1 36 20.2 246.0 2.4SR 36-78 28.0 246.0 5.1 36 28.1 245.5 2.5010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.9 32.0 18.5SR 36 5.1 32.0 18.5MAIN 36 6.7 180.0 11.4SR 36 5.9 248.5 10.060500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 ETG.U1 økernveien 2410.flwSite: OKERNVEIEN 94