Title: 1 etg del 2.pdf
Cable ID: D1003 Date / Time: 10/17/2013 10:35:43 AM Headroom 1.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]98 151 6 4.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]21.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.0 195.0 37.1 36 7.0 226.0 33.4SR 12-36 1.8 191.5 37.2 36 4.0 208.5 34.0MAIN 36-78 6.5 246.5 35.4 36 7.0 246.0 32.8SR 12-36 2.5 242.5 35.6 36 4.5 246.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.3 232.5 16.9 12 16.5 2.8 52.4