Title: Hardware Installation Guide.pdf
3. Connect the reader to the access control panel according to the following figure(s). Tape or cap the unused wires singly.Wiring with reader interface modules:Use the following tables to wire the LenelProx LPSL-6820 with either the single or dual reader interface module. Since the current requirements for these readers range from 40 to 120 mA, this means that the readers can be powered from the reader interface modules.Wiring the LPSP-6820 and the LNL-1300From LNL-1300To LPSP-6820 ReaderTypical Software SettingsReader TerminalPinWire ColorDescriptionReader Type = Wiegand/ProxKeypad = No KeypadGNDBZRBlackYellowGroundBeeperLED Mode = 1-Wire LED ControlLEDBrownLEDTB4CLK D1WhiteData 1DAT D0GreenData 0V0Red5 - 12 VDCWiring the LPSP-6820 and the LNL-1300-UFrom LNL-1300-UTo LPSP-6820 ReaderTypical Software SettingsReader TerminalsPinWire ColorDescriptionReader Type = Wiegand/ProxGNDBlackGroundKeypad = No Keypad