Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
67 8 9CAN out top string connectionCAN in top string connection CAN out bottom string connection CAN in bottom string connectionTable 11: Technical featuresLocationMax. voltage limit (V) Current limit (A) Size (mm) Weight (kg) Transport size (mm)C&I connection unitMounted at the top of the battery rack (bottom possi- ble) 500 150 440x230x90 7 560x380x200Cable kit Linking connection unit to battery packs500 150© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL20 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guideTransport weight (kg) Installation Standards PN DescriptionC&I connection unit 9 19 inch cantilever mount IEC 61000, IEC 61439 XSTS2K125PR1 XST C&I Con-box 2-string K125ACable kitAmphenols and DB9XSTS2CKU XST C&I Con-box cable kit4.3 Battery rack