Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Connect the “CRC” cable ref. “E” in the box to connector J5 (remote) ref. “D”.Grouping connection (fig. 40a) The communication card must be inserted into the special connector “communication J8” provided on the card. For more information refer to the manual provided with the grouping kit.Grouping configuration of several units (fig. 40b) Connect the units in daisy chain configuration (white and blue cables in parallel) for grouping. Refer to the figure below.Window (1WS) and presence (1ECO) control (cid:11)(cid:192)(cid:74)(cid:17)(cid:3)(cid:23)(cid:19)(cid:70)(cid:12) The window and presence contacts must be connected to the terminal block ref. 33 fig. 40 according to the diagram.Fault codes: In the case of failure and with the unit ON, the red LED on the board starts flashing according to the fault code: 0.5 seconds ON and 0.5 seconds OFF followed by 5 seconds OFF.The fault code table is shown below:Fault CodeDescriptionResettable2Air temperature sensorYes3Changeover sensorYes