Title: +175=737.001_IK001_Brukermanual for Refra varmepumpe.Produktinformasjon.pdf
°C °C kW kW kW - kW °C kg/s kW °C kg/s dB(A)+32°C max, -25°C min Fluids gr.2-HFC, HCFC (R134a/R404A/R507A/R407A/R407C/R407 etc.) R134a (CF3CH2F), fluid gr.2 253,6 m3/h (306,0 m3/h @60 Hz) 2 1 Stepless power control 2 With frequency invertor 6GE-40Y Bitzer Semi-Hermetic compressor 73,9 A, 380/420 V-3~/50 Hz 304,0 1691100349, 1691100350 POE, BSE32(Standard) / R134a tc>70°C: BSE55 (Option) With oil separator, filter and sight glass 18,5 l, Oil prefilling 0,6, PED III/B+C1Heat pump 1 (-3/+62°C)Heat pump 1 (-3/+72°C)Chiller (+2/+47°C)3,0 +62,0 178,8 - 59,8 2,99 180,0 +50,0/+60,0 4,303 120,0 +3,0 / 0,0 9,6083,0 +72,0 159,0 - 62,4 2,55 160,0 +60,0/+70,0 3,820 98,0 +3,0 / 0,0 7,847+2,0 +47,0 - 189,6 58,4 3,25 230,0 +40,0/+45,0 11,01 172,0 +10,0 / +5,0 8,130≤ 61,0