Title: økernvn 94.pdf
Cable ID: D4172 Date / Time: 09/09/2013 02:09:51 Headroom 7.5 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]196 301 12 9.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 7.9 236.5 35.7 78 7.9 249.0 32.7SR 36-78 7.5 249.5 35.4 78 8.8 249.5 32.7MAIN 45-78 7.9 236.5 35.7 78 7.9 249.0 32.7SR 36-78 7.5 249.5 35.4 78 8.8 249.5 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 4.4 51.4 45 16.1 78.3 23.3