Title: 4. Leieavtaler.pdf
FM Global's best advice is to store all ignitable liquids in an external store located at least 15 m away from the main building with the ground sloping away from it. Only when required, transfer small quantities of ignitable liquids into the main building. This will limit the quantity of ignitable liquids within the building and reduce the impact of a potential fire.Although only minor quantities of ignitable liquids are used in the existing facility, please confirm whether ignitable liquids will be utilized and to what extent within the new facility. This should include information from the material safety data sheet, location, quantity, use, containers and storage arrangement. Please confirm if there will be any pipe transfer of ignitable liquids.2015-01-07: Only a few 5 L containers are to be stored in ventilated and dedicated fire rated storage cabinets. Dispensing safeguards are to be implemented.