Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.0 113 2 3.98Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 459.0 29.8 36 6.9 460.0 26.9SR 36-45 8.5 466.0 29.5 36 8.3 474.0 26.2MAIN 12-36 7.1 459.0 29.8 36 7.6 478.0 26.0SR 36-45 9.3 497.0 28.0 36 9.3 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.6 496.0 11.3 45 17.6 47.8 28.7SR 45-78 16.9 496.0 11.3 45 17.5 9.8 42.5MAIN 78-45 16.6 496.0 11.3 45 18.1 496.0 8.3SR 45-78 16.9 496.0 11.3 45 18.2 496.0 8.30100806040200250 MHzACR-F (dB)