Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
RCD: UtlřsningsstrřmI: 28.5mAUci: 0.1V t: 12.3ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 529V Rnpe: >30.0MΩ Um: 514VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 3 10.03.2022 13:40 (TomekElektriker)KONTINUITET: R200mA LPER: 0.18ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 4 10.03.2022 11:36 (TomekElektriker)SPENNING TRMS Uln: 233V Ulpe: 233V Unpe: 1V f: 49.98HzSYS.: TN/TTZ-LINEZ: 0.46ΩIsc: 501A R: 0.46Ω Xl: 0.05Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ATALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:4GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr.141415151616TEST RAPPORTResultatRCD: UtlřsningsstrřmI: 27.0mAUci: 0.0V t: 223.1ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 521V Rnpe: >30.0MΩ Um: 515VUiso: 500V Grenseverdi: 1MΩ