Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Switching cabinet components with high field intensity, e.g. transformers or frequency inverters, should be shielded with separator plates with a good ground `connection.Switching cabinet components with high field intensity, e.g. transformers or frequency inverters, should be shielded with separator plates with a good ground `connection.Surge protection for long distances or external linesWhere lines are laid outside the building, or over longer distances, suitable surge protection measures should be applied. For bus lines in particular, theseWhere lines are laid outside the building, or over longer distances, suitable surge protection measures should be applied. For bus lines in particular, thesemeasures are essential. ● With lines laid outside, the shield must have adequate current-carrying capacityand be earthed at both ends.The surge conductors should be installed at the input to the switching cabinet.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-252-3