Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
The PCD2.C2000/C1000 module holders provide the following internal supply cur- rents to the modules plugged in or connected to them:power supplypower consumptionType PCD2.C2000/C1000 1,400 mA 800 mAtypically 2WWhen planning PCD2 systems, it is essential to check that the two internal supplies are not overloaded. This check is especially important when using analogue, counter and positioning modules, as these may have a very large power consumption. It is advisable to use the calculation table at www.sbc-support.ch.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-11Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsExpansion housingsThe PCD2.LIOs are also snapped onto two 35 mm hat rails. LIO module holderDescriptionModule slotsExt. supplyInt. supply I at +5 VPCD2.C2000 (PCD2.C1000)8 (4)for 8 (or 4) I/O modules; acts as I/O bus repeater and provides internal +5V and V+ for a segment of I/O modules24 VDC1,400 mA3