Title: økernvn 94.pdf
MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3422 Date / Time: 09/11/2013 03:43:39 Headroom 5.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]144 220 8 6.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.2 247.5 35.4 78 6.3 247.5 32.8SR 36-78 8.1 201.5 36.9 36 7.9 199.5 34.3MAIN 36-78 5.2 247.5 35.4 78 6.3 247.5 32.8SR 36-78 9.3 250.0 35.3 36 7.9 199.5 34.310080604020NEXT (dB)