Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Attach KTB0000YS1 bar supports on the flexible links or connection bars. The number of KTB0000YS1 bar supports to be used depends on the length of the flexible links or connection bars. The distance between the KTB0000YS1 bar supports depends on the rated short-time withstand current Icw of the equipment (seepage48).10Check for proper clearances between the active conductors and the switchboard.Procedure for Connection Using a Protective CoverThe procedure for connection to switchboards using a KTB••••CR• protective cover is described in the instruction sheet AAV17625, available on the Schneider Electric website.StepAction1Check that the weight of the components does not rest on the switchboard (seepage22).2Check the phase order of the components in the installation, the end feed unit, and the switchboard (seepage15).3If the protective earth conductor (PE) must be connected to neutral conductor (N) to create a PEN, use the PEN link delivered with the end feed unit (seepage47).4