Title: Kapasitetsmåler Mecon.pdf
300 - 15001130 - 5650X XKM6"/ DN 150 (Ø168,3)1000400 - 20001500 - 7500X XLP8"/ DN 200 (Ø219,1)1500600 - 30002200 - 11000X XLQ8"/ DN 200 (Ø219,1)2000800 - 40003000 - 15000 X XOptional version for sizes 6"/ DN 150 and 8"/ DN 200SHousing tube made of stainless steel * XApproval in processPage 12 / 16www.mecon.deOperating Instructions FO Turbo-Lux 3 FM VdS05/2015 OI_FO_Turbo-Lux 3 FM VdSTechnical Data6 Technical DataMeasuring principleOrifice plate flowmeter with variable flowmeter asindicationInputNominal Size2"/ DN 50 grooved ends (Ø60,3)2½"/ DN 65 grooved ends (Ø76,1)3"/ DN 80 grooved ends (Ø88,9)4"/ DN 100 grooved ends (Ø114,3)6"/ DN 150 grooved ends (Ø165,1)6"/ DN 150 grooved ends (Ø168,3)8"/ DN 200 grooved ends (Ø219,1)Pressure limitPN16Measuring accuracy±2 % of full-scale value (FM)±2.5 % of full-scale value (VdS)Application conditionsTemperature limit+4°C - 50°C (39°F - 122°F)Medium:Water