Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
Switch off mains power to shut down completely.7.4. SETTING MENU7.4-1 Standby modeFunction DescriptionOPVOutput voltage selectionOPFOutput frequency selectionMODEWork mode selectSTYAuto bypass enable disable7.4-21 secSettings[208] = 208 V [220] = 220 V [230] = 230 V [240] = 240 V[050] = 50 Hz [060] = 60 Hz[UPS] = Normal [ECO] = ECO mode [CVF] = Converter mode[000] = disable [001] = enable7. OPERATING MODESDefault settings[230][050][UPS][000]ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0015H S I L G N E168. VISUAL AND AUDIBLE WARNING SIGNALS8.1. ALARM INDICATION (ITYS 1-3 kVA)Battery replace or battery disconnectOverload alarmLow battery mode Icon Iconwill ﬂ ash every second will ﬂ ash every secondFault mode (over temperature)The following table shows the description of the LCD display string:WarningCodeSite fail09Fan fail10Battery over voltage (over charged)11Battery low12Charge fail13DC-DC temperature high21