Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 30.11.2020 09:49RCD II: 28.5mAUci: 0.1V t: 107.7ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 30.11.2020 09:50SPĆNDINGUln: 233V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 30.11.2020 09:50Z-LINEZ: 0.48ΩIsc: 476A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 30.11.2020 09:51Tallberg Elektro A/S Tlf.22796640Side:5GODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.3434353536363737383839394040TEST RAPPORTResultatZs(rcd)Z: 0.45ΩIsc: 506A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 30.11.2020 11:52 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 253V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩ