Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
MAIN 36-45 22.6 58.5 32.3 45 23.9 54.5 30.8SR 36-45 24.1 54.5 33.2 36 24.8 58.3 29.8MAIN 12-36 36.5 499.0 -12.3 36 36.1 500.0 -15.3SR 36-45 37.7 500.0 -12.4 36 37.5 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 9.8 444.0 8.0SR 45 8.6 474.0 8.0MAIN 45 9.8 444.0 8.0SR 45 8.6 474.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: SP1 BANK 4 ETGSMN 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00427.8 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100