Title: 1 etg del 2.pdf
Cable ID: T1279 Date / Time: 10/21/2013 01:29:22 PM Headroom 11.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]69 110 8 2.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.6 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.3 75.0 34.4 36 13.2 88.8 30.2SR 12-36 11.2 98.5 32.4 36 12.8 98.5 29.4MAIN 12-36 11.7 98.5 32.4 36 13.2 98.5 29.4SR 12-36 11.2 98.5 32.4 36 12.8 98.5 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 22.4 4.0 46.6 36 23.7 3.3 45.4