Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
MAIN 36 7.0 457.0 8.0SR 45 9.8 121.5 13.2MAIN 36 7.0 457.0 8.0SR 36 9.9 436.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-51 TR-4100BASE-TX 10GBASE-T ATM-155 TR-16 Active100BASE-T4 ATM-25 100VG-AnyLan TR-16 Passive60402000250 MHzProject: F13 3 ETGUntitled1Test Summary: PASSModel: DSX-5000 Main S/N: 2552117 Remote S/N: 2552311 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00415.5 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD15 Date / Time: 05/19/2022 12:22:50 PM Headroom 8.0 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013