Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
CONDENSATE COLLECTION TRAY High density ABS polystyrene foam condensate tray, shaped in order to optimize the air diffusion, fire retardant rating B1 to DIN 4102.AIR FILTER Synthetic washable filter, easily removable.CONDENSATE PUMP Float switch centrifugal pump with 650 mm of maximum head, integral to the unit and wired to the control panel on the outside of the casing.VALVE SET Two or three way valves for ON/OFF operation, with pipe mounting kit and thermostatic actuator.29SkyStarEUROVENT Certificationwww.eurovent-certification.comTechnical features2 pipe units. The following standard rating conditions are used:COOLING Entering air temperature: + 27°C d.b., + 19°C w.b. Water temperature:+ 7/12°CHEATING Entering air temperature: + 20°C Water temperature: + 50°C water flow rate as for the cooling conditionsMODEL Inverter Power Speed Air flow Cooling total emission (E) Cooling sensible emission (E) Heating (E) Water flowP Cooling (E) P Heating (E)