Title: økernvn 94.pdf
Cable ID: T4003 Date / Time: 09/11/2013 09:43:01 Headroom 5.5 dB (NEXT 12-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]257 396 17 12.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.9 224.5 36.1 36 7.5 224.0 33.5SR 12-45 5.5 219.5 36.3 45 6.4 220.0 33.6MAIN 36-78 5.9 224.5 36.1 36 7.5 224.0 33.5SR 12-45 5.5 220.0 36.2 45 6.4 220.0 33.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 16.7 127.5 22.1 12 18.1 250.0 13.2