Title: etg u1.pdf
Cable ID: D0109 Date / Time: 10/21/2013 03:22:38 PM Headroom 13.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]121 191 12 5.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.3 97.8 32.5 36 15.5 97.8 29.5SR 12-36 18.6 43.3 38.3 36 20.5 43.3 35.3MAIN 12-36 13.3 97.8 32.5 36 15.5 98.0 29.4SR 12-36 19.9 97.8 32.5 12 21.3 97.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 23.9 84.3 20.1 12 24.9 84.3 17.1