Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.122122123123124124125125126126127127TEST RAPPORTResultatRCD II: 28.5mAUci: 0.1V t: 22.1ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF037 16C2/003 05.11.2020 11:13KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF037 16C2/003 05.11.2020 11:25R LOW OhmR: 0.27ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF038 16C2/003 28.10.2020 14:09SPĆNDINGU12: 234V U1pe: 0V U2pe: 235V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF038 16C2/003 28.10.2020 14:10Z-LINEZ: 0.65ΩIsc: 355A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 135A Isc(0.76%): 270A Isc(1.15%): 408ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF038 16C2/003 28.10.2020 14:10Zs(rcd)Z: 0.57ΩIsc: 402A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A