Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 36] [Pair 36] [Pair 45]23.1 100 1 3.47Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.8 450.0 30.2 36 7.1 455.0 27.2SR 36-45 7.1 470.0 29.3 36 7.4 454.0 27.2MAIN 36-45 8.7 500.0 27.8 36 7.2 500.0 25.0SR 36-45 7.4 500.0 27.8 36 7.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.8 20.4 39.1 45 21.9 20.4 36.1SR 45-78 19.8 20.4 39.1 45 21.9 16.0 38.2MAIN 78-45 20.9 496.0 11.3 45 22.3 500.0 8.3