Title: økernvn 94.pdf
Cable ID: D4012 Date / Time: 09/10/2013 10:08:23 Headroom 14.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]148 234 16 6.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 18.9 94.5 32.7 36 19.3 95.0 29.7SR 12-36 14.2 90.8 33.0 36 15.0 99.3 29.4MAIN 36-78 18.9 94.5 32.7 36 19.3 95.0 29.7SR 12-36 14.5 99.5 32.3 36 15.0 99.5 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 24.6 71.3 21.6 36 24.9 69.3 18.8