Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
m i =l - n i i | ] T § Y | | X Surface Result Average Min Max Min/average Min/max Visual task area 7 Perpendicular illuminance (adaptive) [Ix] 539 388 615 0.72 0.63 Surrounding area: 0.500 m Surrounding area 7 Perpendicular illuminance (adaptive) [Ix] 463 261 619 0.56 0.42 Background area 6 Perpendicular illuminance (adaptive) [Ix] 333 220 409 0.66 0.54Wall zone: 0.500 mDIALuxPage 40Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Mote 6_2 / Visual task area 7 / Perpendicular illuminance (adaptive)False colors [Ix]500295Scale: 1:25Value grid [Ix]566 563 560 560 562 T585 581 577 577 580 T605 601 597 597 599{505 {801 4567 4597 ¢615) 611 607 607 _ 611 T614 610 ,606 606 610 T605 599 596 596 600 T581 578 | 575 575 578 T551 548 545 545 548 T516 511 509 509 513 T 467 468 466 466 467 e, + 7 e, 7422 421 420 420 422 T388) ,389 (388) (388),389(39, KScale: 1:25