Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
0100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 25.2 68.8 30.0 36 24.2 64.0 28.5SR 36-78 23.8 68.5 30.0 36 24.6 63.8 28.6MAIN 36-45 39.5 500.0 -12.4 36 40.4 500.0 -15.3SR 36-45 39.1 500.0 -12.4 36 40.9 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 7.1 499.0 8.0SR 36 7.3 397.0 8.0MAIN 36 7.1 499.0 8.0SR 36 7.3 397.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-51 TR-4100BASE-TX 10GBASE-T ATM-155 TR-16 Active100BASE-T4 ATM-25 100VG-AnyLan TR-16 Passive60402000250 MHzProject: F13 3 ETGUntitled1Test Summary: PASSModel: DSX-5000 Main S/N: 2552117 Remote S/N: 2552311 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00424.2 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100