Title: +175=325.001_JP001_Igangkjøringsprotokoller på sirkulasjonspumper V.2017.08.28.Protokoll.pdf
LT-471 B2 KAUNAS, LITHUANIA TECE 370837 322 258 WWW.ENSOBALTIC.COMEENSL]ENGINEERING SOLUTIONSPRESTARTup checklistCIRCULATION PUMPSCommissioning report No. )0 (; Date: _ (8} /OZ z&\Service partner:LName of |nsmlatloh. Nitedal Doli Address: Vargveien 1, 1488 Hakadal, Operational Manager: Audrius DaniulisPhone/e-mail: +370 676 19634 / audrius.daniulis@ensoprojects.comRequired flow (designed): 34 m¥hRequired head (designed): 12mWater temperature; 60 °C Fluid: Water Operation mode: Open loop / delta TPump nam type IL 50/120-2,2/2Product No. : 2120875Marking in the system: 320.010-JP404Nom. flow; Nom. Pressure: 11.2mMax. Liquid temp. : -25..140 °C Head max: 14.8mCheck expansion joints installed: ok Check vibration damper installed: ok Check air locks are avoided (suction side): ok Check for pipes adequate support: ok Check mechanical seal for leaks: ok{ 'llrrtc'Real setpount (head pressure) 11.5mFlow at preseted setpoint (all valves opened): 35.2m3/h