Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
26.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.4 499.0 29.3 36 7.3 474.0 26.9SR 36-45 7.9 500.0 29.2 36 7.4 500.0 26.4MAIN 36-45 7.4 499.0 29.3 36 7.4 500.0 26.4SR 36-45 7.9 500.0 29.2 36 7.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.9 5.0 51.3 45 17.2 38.8 30.5SR 78-45 16.8 416.0 12.9 45 16.6 466.0 8.9MAIN 45-78 17.3 468.0 11.8 45 17.6 498.0 8.3SR 78-45 17.0 472.0 11.8 45 16.7 471.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.6 43.3 36.3 45 23.4 43.5 33.8SR 36-45 21.8 42.8 36.4 36 23.2 63.5 28.6MAIN 36-45 33.9 499.0 -12.3 36 34.6 500.0 -15.3SR 36-45 34.4 500.0 -12.4 36 34.6 500.0 -15.30804000250 MHzACR-N (dB)