Title: 2 etg del2.pdf
Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94Cable ID: D2229 Date / Time: 10/10/2013 02:24:07 PM Headroom 12.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 45]67 106 8 2.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.7 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.6 39.0 39.0 36 15.8 93.0 29.8SR 12-36 12.9 39.0 39.0 36 14.5 92.8 29.8MAIN 12-36 15.2 97.8 32.5 36 15.8 97.8 29.5SR 12-36 12.9 97.8 32.5 36 14.5 97.8 29.510080604020NEXT (dB)