Title: Sprinklerhode våt.pdf
7/16" (11,1 mm)NOMINALMAKEINESCUTCHEONPLATE SEATINGSURFACE3Sealing Assembly4Bulb5CompressionScrew6Deflector®Temperature rating is indicated on Deflector.CROSS SECTIONRAPID RESPONSE SERIES LFIl RESIDENTIAL21/4"(57,2 mm)(41,3 mm)PENDENTFIGURE 127/8" DIA.(73,0 mm)RECESSEDESCUTCHEONRECESSED PENDENTPENDENT AND RECESSED PENDENT SPRINKLERS (TY2234)27/8" DIA.(73,0 mm)7/16+1/8"(11,143,2 mm)FACE OFSPRINKLERFITTINGMOUNTINGSURFACE1/2" (12,7 mm)1/4" (6,4 mm)21/4" DIA.(57,2 mm)MOUNTINGPLATE13/8" (34,9 mm)11/8" (28,6 mm)FIGURE 2 STYLE 20 RECESSED ESCUTCHEON FOR USE WITH THE RAPID RESPONSE SERIES LFIl RESIDENTIAL PENDENT SPRINKLER (TY2234)CLOSURE TY2234TechnicalDataApprovalsUL Listed for use with wet pipe and dry pipe systemsC-UL Listed for use only with wet pipe systemsNSF Certified to NSF/ANSI 61For details on these approvals, refer to the Design Criteria section.