Title: Hardware Installation Guide.pdf
2. Wire the power input.3. Wire the downstream device communication.4. Cycle power to the device.116.1Wiring116.1.1Unsupervised Alarm Inputs: Power Fault and Cabinet Tamper MonitorsOn the wireless reader gateway, there are two unsupervised alarm inputs that can be used for power fault and cabinet tamper monitoring. These inputs are connected using the Input 2 (IN2) and Input 1 (IN1) contact terminals on the wireless reader gateway board.Input 2 and Input 1 are both simple N/C (normally closed) contact closure monitors.Wire the Input 2 and Input 1 contacts using twisted pair cable, 30 ohms maximum. (No EOL resistors are required.)Note:If either of these inputs is not used, a shorting wire should be installed.Unsupervised Alarm Input Wiring.CABINET TAMPERGNDIN 2POWER FAULTGNDIN 1116.1.2Upstream Host Communication