Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF086 16C2/003 30.11.2020 11:58 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 26.11.2020 13:59SPĆNDINGUln: 236V Ulpe: 236V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 26.11.2020 13:59Z-LINEZ: 0.60ΩIsc: 382A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 26.11.2020 14:00Tallberg Elektro A/S Tlf.22796640Side:38GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.263263264264265265266266267267268268269269TEST RAPPORTResultatZs(rcd)Z: 0.60ΩIsc: 381A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 26.11.2020 14:03RCD II: 28.5mA