Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]35.3 152 1 5.27Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.6 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.1 421.0 30.9 45 9.4 499.0 26.4SR 36-45 8.1 500.0 29.2 36 8.2 481.0 26.8MAIN 12-45 8.5 499.0 29.3 45 9.4 499.0 26.4SR 36-45 8.1 500.0 29.2 36 8.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.2 4.0 53.2 45 13.8 2.5 54.3SR 36-45 15.2 4.0 53.2 45 13.8 2.3 55.2MAIN 45-78 15.4 500.0 11.3 78 16.2 500.0 8.3SR 78-45 15.2 500.0 11.3 45 16.0 500.0 8.30100806040200250 MHzACR-F (dB)