Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
Maximum water type heat exchanger flow rate with low pressure hydraulic module (l/s)High pressure3,63,93,94,24,44,66,97,17,37,58DYNACIAT LG360390450480520600EvaporatorMinimum system water volume, air conditioning application (litres)287,5325360382,5430480Min/max water type heat exchanger flow rate without hydraulic module (l/s)0,8 / 14,40,9 / 16,61 / 18,30,8 / 16,10,9 / 18,31 / 20,2Low pressure7,57,68,68,613,614Maximum water type heat exchanger flow rate with low pressure hydraulic module (l/s)High pressure11,812,512,812,513,0513,3CondenserMinimum system water volume, air conditioning application (litres)342,5390430457,5515575Min/max water type heat exchanger flow rate without hydraulic module (l/s)0,5/13,050,5/150,6/16,660,5/16,380,5/18,80,6/20,5Low pressure11,412,513,212,613,614Maximum water type heat exchanger flow rate with low pressure hydraulic module (l/s)