Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Current mode: Operating resistance: Resolution range 0 … 20 mA: Resolution range 4 … 20 mA:< 600 Ω 12 Bit; 4.88 µA per LSB 11.7 Bit; 4.88 µA per LSBGeneral details Current consumption at I/O bus +5V: Current consumption at I/O bus V+: Temperature range:max. 40 mA no load 0…55 °CExternal power supply (The same power supply can be used as for the Saia PCD® without losing the galvanic separation of the inputs/outputs.) Operating voltage: Current consumption:24 V ±4 V smoothed max. 2.5 W (depending on output load)Terminals:Plug-in 14-pole screw clamps (PCD3.W525; item no: 4 405 4998 0) for cables up to 1.5 mm²6-102Analogue manual control modules6.14Analogue manual control modulesPCD3.W800Analogue output module with 4 output channels, 0…+10 V, 10 Bit resolution3 outputs with manual operation, 1 output withoutGalvanic separation of outputs to Saia PCD®, channels themselves not separated