Title: Ahlsell.pdf
Cable ID: UD 8 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 01:02:03 PM Operator: Pam Headroom 10.7 dB (NEXT 3,6-7,8) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 4,5] [Pair 4,5] [Pair 3,6]14.7 72 1 5.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]35.2 495.0 43.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 11.5 99.8 41.9 3,6 12.9 92.5 39.9SR 3,6-7,8 10.7 322.0 33.0 3,6 11.5 467.0 24.8MAIN 3,6-4,5 13.4 496.0 26.8 3,6 13.5 496.0 23.9SR 3,6-4,5 11.5 482.0 27.2 3,6 11.5 467.0 24.810080604020NEXT (dB)