Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
GND (Strang A-) MP-Bus Signalleitung (18V in/out) MFT-Parametriergerät (MP-Bus intern) MFT-Parametriergerät Detektion (Input 10 kOhm, Z5V1) Masse-Anschluss MFT-Parametriergerät GNDSteckplatz A1PCD7.F1801 t r o P, 4 x10 11 12 13 14 15 16 17 18 1910, (0) - 11, (1) MP 12, (2) ,MFT’ 13, (3) ,IN’ 14, (4) GND 15, (5) -GND (Strang A-) MP-Bus Signalleitung (18V in/out) MFT-Parametriergerät (MP-Bus intern) MFT-Parametriergerät Detektion (Input 10 kOhm, Z5V1) Masse-Anschluss MFT-Parametriergerät GNDThere are the following parameterization devices of BELIMO®: Manual Control UnitMFT-HWith its own power supply/batteriesPC-ToolMFT-PWith the adapter ZIP-RS232Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-255-15Saia-Burgess Controls Ltd.Supply option Common supply for control and drivePCD2D /D -WD- + + +L+NController24 VDC ±20%L N–Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-25Communication interfaces