Title: 40 Bender brukermanual.pdf.pdf
3. Hysteresis If the measured value were to oscillate around the response value, the RCMS… would constantly change from alarm to normal status and back again. If a hysteresis of 20 % is set, the alarm status is not exited until the mea- sured value is 20 % below resp. above the response value. Setting range: 2…40 %, resolution of setting 1%.4. Frequency Select the rated frequency of the monitored current. Only if the setting is cor- rect, can the RCMS… determine the harmonics currents properly. Setting options: DC, 50 Hz, 60 Hz, 400 Hz.RCMS460-490_D00067_03_M_XXEN/12.201755