Title: 360.013 Hybra Modul A 8,00-2,0 +- 22.800 m³h -Datakjøring Fra leverandør.pdf
Ma 8,00-2,0 410 - 255 - 131 1,7 m/s / V1 35 mm / PU T2 (M) / TB2 (M) D1 (M) / L1 (M) SFP1 / 791 SFP2 / 892 A+ A+ GI GI GIPlug fan Volume flow operating mode Designation Number of width and height Pressure loss external / static (Pa) Pressure loss total / dynamic (Pa) Shaft output / performance class Sound p. suction / pressure dB(A) Efficiency total / static (%) System-efficiency total / static (%) System p. consumption V/E (kW) Speed (U/min) / C-factor Differential pressure (dp at Vn) Operating frequency Maximum frequency Motor Size / Number of terminals Energy class / Protection item x Nominal output (kW) Rated current (A) Nominal speed (U/min) Voltage (V) / Frequency (Hz) revision door with dual hinge18.240 m³/h parallel RLM E0-BE 560 2 x 1 290 / 645 682 / 37 2,130 kW / P1 75,8 / 80,6 81,0 / 77,0 73,1 / 69,2 3,850 / 4,740 1.487 / 242 852 Pa 125 Hz 150 Hz220-55 / Default (IE5) / IP55 2 x 4,30 10,00 1.700 3x400 / 50