Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
3 / E.433.11.01 TNS / Sikring 03611.03.2020 10:23SPENDINGUln: 234VUlpe: 235VUnpe: 0OVf: 49.9HzR ISOR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQGODKJENT*GODKJENT| Dronning M.g.13 / E.433.11.01 TNS / Sikring 03711.03.2020 10:58SPENDINGUln: 234VUlpe: 234VUnpe: 0Vf: 50.0HzR ISOR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQGODKJENT*GODKJENTDronning M.g.13 / E.433.11.01 TNS / Sikring 03811.03..2020 10:18SPENDINGUln: 236VUlpe: 236VUnpe: 0Vf: 49.9HzGODKJENT *TEST RAPPORTR IS0 GODKJENTR:>200MQ Um: 263VUiso: 250VGrenseverdi:1MQDronning M.g.13 / E.433.11.01 TNS / Sikring 03912.03.2020 14:04SPENDINGUln: 233VUlpe: 233VUnpe: 0Vf: 50.0HzGODKJENT*Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 039 GODKJENT* 12.03.2020Z:ZLINE GODKJENT0.52QIsc: 442A14:05Sikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 039 GODKJENT * 12.03.2020