Title: 36 UPK_ATK (NO0416).pdf.pdf
HURTIGVALG, UPK-HATK-H KammerUPK-Hm³/hDim.Ansl.Dim.25 dB(A) 30 dB(A) 35 dB(A)160B600 x 600133169238160S600 x 600126234353200B600 x 600209299418200S600 x 600201324436250B600 x 600338504648250S600 x 600346594756315B600 x 6004757741415315S600 x 6008109471098400*B600 x 600106013021600400*S600 x 600101912531540Tabell 3, tabellen viser luftmengde ved oppgitt lydeffektnivå og 50 Pa totaltrykktap. * = Ø400 er uten spjeld / kapasitet ved oppgitt lydnivå44HURTIGVALGATK kammerUPK-Rm³/hDim.Ansl.B x H25 dB(A) 30 dB(A) 35 dB(A)125B200x10068119180125S200x10086133184125LS200x10068119184160B300x100126256160S300x100126187263160LS300x100130212281160B400x100137198295160S400x100126205295160LS400x100133202320200B500x100252360454200S500x100216284