Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Burst protection: (IEC 801-4) Temperature error Internal current consumption:(from +5 V bus)± 1 kV, with unshielded cables ± 2 kV, with shielded cables 0.3 % (across temperature range 0 … +55 °C) max. 200 mA5-93PCD2.W5x0Internal current consumption: (from V+ bus) External current consumption: Terminals:0 mA 0 mA Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²As the current consumption of this module is considerable, when using a number of them in the same system, the total load for all modules must be taken into consideration..TerminalsBus connectorDC-DC converterBasic moduleJumper: inputs unipolar (U)Substitution moduleJumper U/B 0 and U/B 1 on substitution moduleU/B0 U/B1Jumper: inputs bipolar (B)9876543210Screw terminalsA1+A1A0+A0E1+E1E0+E0+ must not be connected