Title: TFP510_06_2015.pdf
TY3735 Horizontal Sidewall with Top of Deflector-to-Ceiling Distance of 4 to 12 inches (100 to 300 mm) with Standard Escutcheon (Figure 8)without Escutcheon (Figure 6)with Deep Escutcheon (Figure 9)without Escutcheon (Figure 10)Temperature RatingBulb Color CodeNatural BrassChrome PlatedWhite PolyesterNatural BrassFinish Chrome PlatedWhite PolyesterNatural BrassChrome PlatedWhite Polyester135°F (57°C) 155°F (68°C) 175°F (79°C) 200°F (93°C) 286°F (141°C)Orange Red Yellow Green Blue1, 21, 21*, 2*Notes: 1. Listed by Underwriters Laboratories, Inc. (maximum order length of 48 inches) 2. Listed by Underwriters Laboratories for use in Canada (maximum order length of 48 inches) * Light and Ordinary Hazard occupancies onlyTABLE A 3/4 INCH NPT SERIES DS-1 QUICK RESPONSE, STANDARD COVERAGE DRY-TYPE SPRINKLERS LABORATORY LISTINGS AND APPROVALS1 Inch NPT (and ISO 7-R 1)TY3235 Pendentwith Recessed Escutcheon (Figure 4)TY3235 Pendent