Title: 40 Bender Datablad.pdf.pdf
Rated residual operating current I∆n1 (prewarning) Function selectable per channel off, <, >, I/O Cut-off frequency adjustable for personnel, plant and fire protection Preset function for I∆n2 and I/O Hysteresis Factor for additional CT Common alarm relay for all channels Alarm relay per channel Start-up delay 0…99 s Response delay tv, adjustable 0…999 sOperating time atI∆n = 1 x I∆n2: ≤ 180 ms I∆n = 5 x I∆n2: ≤ 30msDisplays, memoryAnalysis of the harmonics (I∆, DC, THF) History memory 300 data records Data logger for 300 data records/ channel Internal clock Password Language English, German, French, Swedish Backlit graphics LC display 7-segment display and LED lineonly in conjunction with RCMS4xx-D, MK2430 or COM465IPResidual current monitors LINETRAXX® RCMS460-D/-L – RCMS490-D/-L