Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
2Check the phase order of the components in the installation, the end feed unit, and the switchboard (seepage15).3If the protective earth conductor (PE) must be connected to neutral conductor (N) to create a PEN, use the PEN link delivered with the end feed unit (seepage47).4Cut out the top plate of the switchboard to enable the installation of the end feed unit flange.5Attach the end feed unit to the switchboard.6Determine the number of connection bars according to the rating (seepage47).7Connect the end feed unit to the connection bars with bolts and tighten the bolts to a torque of 60 N•m.8Check that the enclosure of the end feed unit (PE or PER) is correctly connected to the earth of the switchboard.9