Title: +038=30.001-NI003._24-V20-U1-01 VVS-anlegg plan U1 - DM1.pdf
Space 9-116-47310.001: MA 75 UK = 32880Se tegning V20--001Space 9-116-93SQ001T Ø250 SQ001T Ø250MA 110MA 135SZ001T Ø250 SZ001T Ø250Trafo-1 U2-101-1Trafo-2 U2-101-2Space 9-116-96Space 9-116-94MA 110Opp 370.101: DN 100 370.101: DN 100360.002: ø500 UK=2750DN 65 UK = 2814 DN 65 UK = 2814 42 mm UK = 2831 42 mm UK = 2831SK001T Ø400SZ001T Ø400SZ001T Ø200 SZ001T Ø200Space 9-116-85Fordelerskap 6xKV + 4xVV, siklemikk til rom med slukø160 UK=2760 ø160 UK=2760ST007T-160-200 200 m³/h+U1 = 370.101 - OE 901 +U1 = 320.102 - OE 901ø250 UK=2625 ø160 UK=2670 ø160 UK=2450 ø250 UK=2625ST0014T-400 1680 m³/hCu 15 UK = 3242 Cu 28 UK = 3236 Cu 28 UK = 3236Space Cu 18 UK = 3041 9-116-56 Cu 18 UK = 3041 Cu 15 UK = 3043ST007T-160-200 200 m³/hGarderobe-1 U1-409-1Space 9-116-118SF001T-160 160 m³/h= 320.102,360.002,370.101 - LD001T 220 m³/h Kjøling: 695 W 0.055 L/s Varme: 1145 W 0.027 L/sSZ001T Ø250SZ001T Ø250Cu 28 UK = 86 Cu 28 UK = 2836 Cu 15 UK = 2843