Title: +175=737.001_KR001_Flytskjema for kuldekrets.Tegning.pdf
W9 EvaporatorHeat pump 1 Refrigerant:R134a Evaporating temp.: -3°C Condensing temp.:62°C Suction gas superheat.:10K Liquid subcooling: 10K Heating capacity:178.8kW Power input: 59.8kWHeat pump 2 Refrigerant:R134a Evaporating temp.: -3°C Condensing temp.:72°C Suction gas superheat.:10K Liquid subcooling:10K Heating capacity:159kW Power input: 62.4kWChiller Refrigerant:R134a Evaporating temp.: 2°C Condensing temp.:47°C Suction gas superheat.:10K Liquid subcooling: 0K Cooling capacity:171kW Power input: 58.4kW=+Page3Pagesh / ³ m 6 . 9 3. lG . t EC ° 5 / C ° 0 1:r el l ih C3