Title: Sirkulasjonspumper.pdf
Utskrift fra Grundfos Product Center [2021.21.005]VerdiTPED 65-210/2 S-A-F-A-BQQE-JDB99132830 100 57126073547632910 omdr/min11.66 l/s 170 kPa 210 dm 127 mm BQQE ISO9906:2012 3B2 ACast iron EN-GJL-250 ASTM class 35 Cast iron EN-GJL-200 ASTM class 30 A20 .. 50 °C 16 bar 16 bar / 120 °C DIN DN 65 PN 16 360 mm FF215 F Vann -25 .. 120 °C 20 °C 998.2 kg/m³ 1 mm²/s20 .. 50 °C 16 bar 16 bar / 120 °C DIN DN 65 PN 16 360 mm FF215 F Vann -25 .. 120 °C 20 °C 998.2 kg/m³ 1 mm²/s100LA IE5 3 kW 50 Hz 3 x 380-500 V 5.80-4.80 A 0.91-0.86 360-4000 omdr/min 90.7% 90.7 % 2 IP55 F ELEC 98971269HMI300 - Advanced FM300 - Advanced Built-in0.70 121 kg 145 kg 0.68 m³ 99137334Firmanavn: Grundfos Laget av: Telefon:Aleksander StortjønnliDato:23.08.2021H [kPa]TPED 65-210/2, 3*500 V260110 %Q = 11.66 l/s H = 170 kPa n = 99 % / 2881 rpm Pumpemedie = Vann Væsketemperatur under drift = 20 °C Massetetthet = 998.2 kg/m³240220100 %20018016014012010080604020020 %