Title: økernvn 94.pdf
Cable ID: T4072 Date / Time: 09/11/2013 10:57:53 Headroom 0.1 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]184 292 21 8.0184 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.3 * 250.0 35.3 36 0.7 * 250.0 32.7SR 36-450.1 *242.5 35.6 36 0.5 *250.0 32.7MAIN 36-45 0.3 250.0 35.3 36 0.7 250.0 32.7SR 36-45 0.1 250.0 35.3 36 0.5 250.0 32.7100