Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Site 1/ Building 1/ Storey 11 / Waiting room1 / Room summaryWaiting room1Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Waiting room1) Perpendicular illuminance (adaptive) [Ix] 241 (= 200) 106 326 0.44 0.33 Height: 0.000 m, Wall zone: 0.100 m # Luminaire ®d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 6 iGuzzini illuminazione - Q510 Laser Blade XS - Downlight HC 23.1W 1452 231 62.9 Total via all luminaires 8712 138.6 62.9Lighting power density: 4.70 W/m? (Floor area of room 29.52 m? ), Lighting power density: 5.08 W/m? = 2.11 W/m?#100 Ix (Area of working plane 27.26 m?)Consumption: 270 kWh/a of maximum 1050 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels. The results are informative. The energy consumption of a building results from the sum of all consumptions in the rooms.