Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 1 Perpendicular illuminance (adaptive) [Ix] 566 (= 500) 434 635 0.77 0.68 Surrounding area: 0.500 m 2 Sunounding area 1 Perpendicular illuminance (adaplive) [Ix] 513 (= 300) 386 608 0.75 0.63 3 Background area 1 Perpendicular illuminance (adaptive) [Ix] 289 (= 100) 193 343 0.67 0.56 Wall zone: 0.100 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 4 iGuzzini illuminazione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 114.3HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 11248 98.4 114.3Lighting power density: 7.13 W/m? (Floor area of room 13.81 m?) Consumption: 170 - 270 kWh/a of maximum 500 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.