Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Specific points about the layout:  Check that the floors, walls and ceilings where supports are to be positioned are strong enough tohandle the weight. Floors, walls, and ceilings should be made of metal or concrete. Check that there is no other equipment in the way of the run (HVAC, plumbing, or others).Identifying the Locations of Missing LinksMissing links are gaps in sections of straight lengths of run components. They are sometimes introduced to ease the installation process and to optimize the system according to on-site constraints. Be aware of these missing links and their locations on-site.For long runs, it is often difficult to plan the dimensions of the missing links. In these cases, the run components to fill the missing links are ordered at the end of the installation after the gaps to be filled have been measured.Pre-Installation Check