Title: Kabelspesifikasjoner AutroSafe.pdf
116-P-ASIFGCABLESPEC/CGB Rev. D, 2015-04-09 | Autronica Fire and Security AS | Tel.: +47 73 58 25 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 1(3)Cable Specifications – AutroSafe and AutroprimeCablingAl_Com Fire Detection Loops AutroprimeLow Current Detectors and I/O UnitsDetection Loop current setting (mA) 100 150 200 250Max cable resistance (Ω) 105 58 35 21Maximum capacitance (µF)0,5 0,5 0,5 0,5Cable length (m) for AWG 20 (0,5mm²) 1500 829 500 300Cable length (m) for AWG 18 (0,75mm²) 2250 1243 750 450Cable length (m) for AWG 17 (1,0mm²) 3000 1657 1000 600Cable length (m) for AWG 15 (1,5mm²) 4500 2486 1500 900Cable length (m) for AWG 13 (2,5mm²) 7500 4143 2500 1500CablingAl_Com Fire Detection Loops AutroprimeHigh Current Detectors and I/O UnitsDetection Loop current setting (mA) 100 150 200 250 300 350 400Max cable resistance (Ω) 112 78 55 40 30 23 18Maximum capacitance (µF) 0,5 0,5 0,5 0,5 0,5 0,5 0,5