Title: økernvn 94.pdf
Cable ID: D3096 Date / Time: 09/11/2013 02:26:54 Headroom 0.9 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]94 149 10 4.094 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]22.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 213.0 36.5 12 8.3 213.0 33.9SR 36-450.9 *247.5 35.4 36 1.7 244.5 32.9MAIN 45-78 8.4 248.5 35.4 45 8.4 237.5 33.1SR 36-45 0.9 247.5 35.4 36 1.7 248.0 32.8100806040