Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Uln: 235V Ulpe: 232V Unpe: 3V f: 50.0HzOBJEKT / Plan 10 / FUSE042 07.02.2020 12:44SPÆNDINGUln: 228V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE042 07.02.2020 12:45Z-LINEZ: 1.32ΩIsc: 174A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE042 07.02.2020 12:45Zs(rcd)Z: 1.12ΩIsc: 205A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE042 07.02.2020 12:46RCD II: 28.5mAUci: 0.1V t: 22.1ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE042 07.02.2020 12:50TEST RAPPORTSide:14GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.878788888989909091919292Resultat R LOW OhmR: 0.42ΩR+: 0.4Ω R-: 0.4Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE042 10.02.2020 09:05SPÆNDINGUln: 225V Ulpe: 226V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE042 10.02.2020 09:05Z-LINEZ: 0.89Ω