Title: 40 Bender brukermanual.pdf.pdf
Rated insulation voltage....................................................................................................................................... 250 V Overvoltage category/pollution degree....................................................................................................................III/3 Rated impulse voltage ............................................................................................................................................. 4 kV Basic insulation between:............................................................................... (A1, A2), (k1, l…k12, R, T/R, T, A, B) - (C11, C12, C14), (C21, C22, C24), (11,14), (21,24), (31,34), (41,44), (51,54), (61,64), (71,74), (81,84), (91,94),(101,104), (111,114), (121,124) Basic insulation between: ............................................. (11, 14) - (21, 24) - (31, 34) - (41, 44) - (51, 54) - (61, 64) Voltage test acc. to IEC 61010-1