Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 30.11.2020 10:37RCD II: 28.5mAUci: 0.2V t: 108.2ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 30.11.2020 11:53 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 27.11.2020 11:54R LOW OhmR: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 27.11.2020 11:54KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF029 16C2/003 30.11.2020 10:11SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 49.9HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF029 16C2/003 30.11.2020 10:11Tallberg Elektro A/S Tlf.22796640Side:12GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.8383848485858686878788888989TEST RAPPORTResultatZ-LINE