Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]28.1 121 1 4.29Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]28.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.8 477.0 29.7 36 7.1 490.0 26.6SR 12-36 7.9 499.0 29.3 36 9.0 498.0 26.4MAIN 36-45 8.0 498.0 29.3 36 7.2 498.0 26.4SR 12-36 7.9 499.0 29.3 36 9.0 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.2 471.0 11.8 45 19.2 500.0 8.3SR 45-36 18.0 471.0 11.8 36 20.0 471.0 8.8MAIN 36-45 18.7 500.0 11.3 45 19.2 500.0 8.3SR 45-36 18.5 500.0 11.3 45 20.0 499.0 8.30100806040200250 MHzACR-F (dB)