Title: 4. Leieavtaler.pdf
21. The automatic sprinkler systems should be fed from an adequate and reliable dedicated water supply based on the final hydraulic calculations of the automatic sprinkler systems. Most likely this will need to be comprised of a fire pump and suction tank for the sprinkler system.The fire pump and suction tank installations should be installed in accordance with FM Global Property Loss Prevention Data Sheets 3-7, Fire Protection Pumps and Data Sheet 3-2, Water Tan/cs for Fire Protection. Ideally the fire pump and tank should be located a minimum of 15 m away from the main building to eliminate any fire exposure. Ensure all components (including fire pump, fire pump controller, fire pump engine and suction tank) are FM Approved. Send details of the proposed water supply installation to FM Global for review, prior to ordering or installing any components.