Title: 2 etg del2.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.2 12.0 50.5 36 6.0 224.0 4.7SR 12-36 5.6 12.0 50.5 36 5.4 244.5 2.6MAIN 36-45 6.7 249.5 4.7 36 6.1 249.5 2.1SR 36-45 6.4 248.0 4.9 36 5.5 248.0 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.3 20.0 19.5SR 45 4.5 4.0 21.0MAIN 36 7.3 242.0 10.2SR 36 8.2 230.5 10.4010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1