Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
R+: >1999Ω R-: >1999Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Gulv kanal 27.11.2020 11:30R LOW OhmR: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Gulv kanal 27.11.2020 11:49KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Gulv kanal 27.11.2020 11:29R LOW OhmR: 0.06ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Gulv kanal 27.11.2020 11:29R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Kabel bru 27.11.2020 11:30R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Kabel bru 27.11.2020 11:49KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Kabel bru 27.11.2020 11:49R LOW OhmR: 0.14ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Kabel bru 27.11.2020 11:30Tallberg Elektro A/S Tlf.22796640Side:53MISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESMISLYKKESGODKJENTMISLYKKES