Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
26.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.1 457.0 30.1 36 6.2 499.0 26.4SR 12-36 8.3 488.0 29.5 36 8.0 495.0 26.5MAIN 12-36 6.3 499.0 29.3 36 6.2 499.0 26.4SR 12-36 8.4 495.0 29.3 36 8.0 495.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.6 411.0 13.0 45 19.6 500.0 8.3SR 45-78 18.6 410.0 13.0 45 20.0 470.0 8.8MAIN 78-45 19.0 453.0 12.1 45 19.6 500.0 8.3SR 78-45 19.0 448.0 12.2 45 20.0 470.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.8 41.3 36.9 45 20.6 41.3 34.4SR 36-45 20.9 41.3 36.9 45 23.0 41.3 34.4MAIN 12-36 32.7 499.0 -12.3 36 32.6 499.0 -15.2SR 12-36 34.7 495.0 -12.1 36 34.7 500.0 -15.30804000250 MHzACR-N (dB)