Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 11.06.2020 16:28RCD II: 28.5mAUci: 0.1V t: 27.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 11.06.2020 16:35Zs(rcd)Z: 0.64ΩIsc: 360A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 12.06.2020 09:36Tallberg Elektro A/S Tlf.22796640Side:33GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.225225226226227227228228229229230230231231232232TEST RAPPORTResultatRCD UbUc: 0.1V Rl: 2Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 12.06.2020 12:08R LOW OhmR: 0.29ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 12.06.2020 12:08KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF045 C16/2 10.06.2020 11:25R ISOR: >200MΩ Um: 263V