Title: 365 R›ykmeldere i ventilasjon monteringsveiledning.pdf
NOTE! If the indicator does not move, you should consider a new mounting positioning of the Uniguard or install a booster fan venturi pipe.Venturirör med hjälpfläkt. Venturi pipe with booster fan.With installation of a booster fan venturi pipe a mounting bracket is always used.A booster fan pipe is a standard venturi pipe including a booster fan, which needs separate 24 VAC supply.A booster fan pipe is a standard venturi pipe including a booster fan, which needs separate 24 VAC supply.Resetknapp. Reset button.Electrical installation.Snäpplås. Snap locking.Remove the cover over the printed circuit board by opening the snap locking.Remove the cover over the printed circuit board by opening the snap locking.Enter the cable through one of the Klikseal glands. When using another type of cable gland dismount the ones already installed by first pressing one side through the hole and then the other one (1-2).