Title: 26 Manual for takslukvakt.pdf.pdf
For more info on Alarm’s, see chapter 7.5 diagnostics The parameters for the Temp modes, can be parametrized in the config file, see Appendix 13. Appending on the application, 1 or 2 set points can be selected, see below.Hysteresis = 1C° Setpoint 1= 4 C°Hysteresis = 1C° Setpoint 1= 4 C° Setpoint 2 =2 C°REV. 02 - MARCH 2021 - BLÜCHER® CONNECTED ROOF 177.4 Measurement values7.4.1 Water Level10 mm10 mm10 mm6 mm 3 mm54321Water level is measured in increments from sensor pin 1 to 5, corresponding to 0-42mm water level. Water level information is updated every 30 minutes, or if the water level values change.7.4.2 Temperature Temperature values are updated every 30 minutes. Should the temperature change more than +/-4 degrees from last update, the temperature will be updated more frequently.7.5 Diagnostics There are two types of diagnostics, Roof diagnostics and Monitor systems diagnostics: See detail in chapter 7.5.1 and 7.5.2