Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 17.3 480.0 11.6 45 17.2 3.9 50.5MAIN 78-45 17.1 490.0 11.4 45 18.6 500.0 8.3SR 78-45 17.3 500.0 11.3 45 17.6 473.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 27.7 64.8 30.8 12 29.0 65.0 28.3SR 12-45 24.5 69.8 29.8 12 26.1 75.0 26.2MAIN 36-45 35.7 496.0 -12.1 36 36.1 500.0 -15.3SR 36-45 33.2 497.0 -12.2 36 34.4 497.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.8 486.0 8.0SR 12 6.4 490.0 8.0MAIN 45 8.8 486.0 8.0SR 12 6.4 490.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS