Title: økernvn 94.pdf
181 287 20 7.8181 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.0 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.8 * 244.5 35.5 36 0.7 * 240.5 33.0SR 36-450.9 *244.5 35.5 36 0.9 *231.5 33.3MAIN 36-45 0.8 244.5 35.5 36 0.7 246.5 32.8SR 36-45 0.9 248.5 35.4 36 0.9 246.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 15.6 101.5 24.1 12 17.8 101.5 21.1SR 45-12 15.0 97.0 24.5 45 17.7 97.5 21.4MAIN 45-12 17.6 249.5 16.2 12 20.1 249.5 13.2SR 45-12 17.1 249.5 16.2 45 19.0 249.5 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz