Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
BEE24, BEE24-ST AC 24V 50/60Hz DC 24 V40 Nm 50 Nm3x0,75 mm2 6x0,75 mm260 s30 ...+50°Cmax 62 dB (A)BEE230AC 220-240V 50/60 Hz15 Nm 20 Nm3x0,75 mm2 6x0,75 mm230 s30 ...+50°Cmax 62 dB (A)BEN24, BEN24-ST AC 24V 50/60Hz DC 24V15 Nm 20 Nm3x0,75 mm2 6x0,75 mm230 s30 ...+50°Cmax 62 dB (A)BEN230AC 220-240V 50/60 HzPower demand: - for spring tensioning - for spring holding Sizing (apparent power) Appliance class Ingress protection ratingAuxiliary circuit breaker:2,5 W 0,1W 5 VA III IP 54 2xSPDT 3A AC 250V 5°, 80°3,5 W 0,4 W 6 VA II IP 54 2xSPDT 3A AC 250V 5°, 80°3 W 0,1 W 6 VA III IP 54 2xSPDT 3A, AC 250V 5°, 80°4 W 0,4 W 7 VA II IP 54 2xSPDT 3A, AC 250V 5°, 80°activation position [degrees] Torque: - motor Cable connection: - motor (L = 0.9 m) - auxiliary circuit breaker Movement time: (0-90°) - motor Operating temperature range Sound pressure level: - motor25 Nm3x0,75 mm2 6x0,75 mm260s30 ...+55°Cmax 58 dB (A)25 Nm