Title: økernvn 94.pdf
Cable ID: D3201 Date / Time: 09/11/2013 03:05:38 Headroom 12.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]59 94 7 2.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.1 99.8 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.4 78.3 34.1 36 16.7 39.5 35.9SR 12-36 12.4 78.3 34.1 36 14.0 84.5 30.5MAIN 12-36 16.8 84.0 33.5 36 17.2 84.5 30.5SR 12-36 13.3 99.8 32.3 36 14.7 100.0 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 25.4 5.5 43.8 12 25.7 4.0 43.6