Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.0 143 2 4.99Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.4 45.5 47.4 36 10.9 485.0 26.7SR 36-45 9.5 500.0 29.2 36 8.9 500.0 26.4MAIN 36-78 10.4 485.0 29.5 36 11.0 488.0 26.6SR 36-45 9.5 500.0 29.2 36 8.9 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.4 412.0 12.9 45 13.9 2.6 53.9SR 78-45 14.4 430.0 12.6 45 13.8 2.6 53.9MAIN 45-78 15.1 468.0 11.8 45 16.4 498.0 8.3SR 78-45 15.2 480.0 11.6 45 16.1 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.1 45.8 35.6 45 20.1 45.8 33.1