Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.03.03-UF014 Date / Time: 06-05-2020 15:53:36 Headroom 7.5 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]16.4 71 1 2.66Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.6 461.0 29.7 36 8.8 461.0 26.9SR 36-45 7.5 468.0 29.4 36 7.9 461.0 26.9MAIN 36-45 9.4 498.0 27.9 36 9.3 497.0 25.1SR 36-45 7.5 468.0 29.4 36 9.1 498.0 25.110080604020NEXT (dB)