Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
If the bolted tap-off unit is dismantled and reassembled at installation or for maintenance, the torque of 100 N•m must be checked with a torque wrench.QGH3492101-01 11/201859Tap-off Units60QGH3492101-01 11/2018Canalis KTSpecific ComponentsQGH3492101-01 11/2018Installation of Specific ComponentsChapter 6 Installation of Specific ComponentsWhat Is in This Chapter?This chapter contains the following topics:TopicInstallation of Expansion UnitsInstallation of Fire-Barrier KitQGH3492101-01 11/2018Page626561Specific ComponentsInstallation of Expansion UnitsIntroductionThe expansion unit controls and absorbs the expansion of run components. Expansion units have the following features:  The expansion unit is 1 m in length and must be fitted horizontally.  The expansion unit is equipped with flexible conductor joints and a sliding case at its centre. Theseabsorb the relative movements of the section that the expansion unit is installed in.