Title: økernvn 94.pdf
200250MHzLinkWare Version 7.4Cable ID: T3402 Date / Time: 09/13/2013 08:30:55 Headroom 7.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]269 412 16 12.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]5.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.5 191.5 37.2 12 9.1 223.5 33.5SR 36-78 7.1 220.5 36.2 36 8.0 250.0 32.7MAIN 36-78 9.3 250.0 35.3 36 9.8 250.0 32.7SR 36-78 7.1 249.5 35.4 36 8.0 250.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)