Title: +038=310.000-NI024T_01-Innreg. protokoll OAR.xlsx
1.5 - Ventilasjonsanlegg - 360.002 0.6 0.56 5.36 2.5 DN40 1.071429 Pumpe 1,9 meter. 360.003 0.18 0.15 9.62 0.6 D40 1.2 Pumpe 1,2 meter. 360.004 - 360.005 0.126 0.12 6.4 1.9 DN20 1.05 Pumpe 1,5 meter 360.006 0.13 0.12 4.3 2.2 DN20 1.083333 Pumpe 1,4 meter 360.007 0.13 0.12 6.85 1.9 DN 20 1.083333 Pumpe 1,5 meter 360.008 0.127 0.12 4.6 2.2 DN20 1.058333 Pumpe 1,7 meter 360.009 0.31 0.27 10.9 1 DN40 1.148148 Pumpe 2 meter 360.010 0.29 0.26 4.62 2.5 DN25 1.115385 Pumpe 1,7 meter 360.011 0.3 0.26 4.34 2.5 DN25 1.153846 Pumpe 1,7 meter 360.012 0.55 0.51 4.14 3 DN32 1.078431 Pumpe 3,6 meter 360.013 0.61 0.54 5.9 2.5 DN40 1.12963 Pumpe 3,0 meter 360.014 0.33 0.3 6.03 2.5 DN25 1.1 Pumpe 2,5 meter 360.015 0.3 0.27 6.5 2.2 DN25 1.111111 Pumpe 1,1 meter 360.016 0.39 0.33 5.46 2 DN40 1.181818 Pumpe 3,36 meter 360.017 0.29 0.25 3.13 2 DN40 1.16 Pumpe 2 meter 360.018 0.37 0.34 6.3 2 DN32 1.088235 Pumpe 2 meter 360.019 0.47 0.43 6.6 3 DN25 1.093023 Pumpe 2,2 meter 360.020 0.15 0.13 9.22 1.9 DN20 1.153846 Pumpe 1,2 meter