Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Special care must be taken when positioning supports below run components dedicated to tap-off units, when the run components are installed flatwise:  Supports should not be positioned in front of outlets or future tap-off units  Spacers must be added between supports and run components to compensate for the asymmetry oftheir lateral profiles due to the extra size of the tap-off unit outletsFailure to follow these instructions can result in equipment damage.For KT••••EB•• run components, supports must be installed under the sheet metal enclosure. No spacers are required.For KT••••ED•• and KT••••EH•• run components, spacers must be installed on supports to compensate for the gap so that the base of the component is parallel to the supports.The gap to be compensated depends on:  Whether the run component is installed with the neutral at the top or at the bottom.  Whether the support is installed under the upper hood profile of the tap-off unit outlet (A) or the sheetmetal enclosure (B).