Title: +038=744.004-UN003T_02-Montering og vedlikehold av Teknoware armaturer Nortek FDV.pdf
all the tests and results are recorded in the logbook of the emergency lighting system, and when asked, presented to the authoritiesThe life time of the battery is ca. 4 years, and of the super capacitor ca. 10 years, in normal conditions. The backup power source must be replaced, when the luminaire is no longer working during the required duration, of 1 or 3 hours. The luminaire, or the light source of the luminaire must be replaced, when the luminaire no longer meets the requirements set to it. For example, the EN 1838 standard requires a min. 2 cd/m2 surface brightness on all green areas, in the pictogram of exit lights. It is recommended to perform a yearly surface brightness sampling measurement on exit lights, beginning from the fifth year of operation, or if the surface brightness is visibly diminished.b) Second segment containing one position: MODE OF OPERATION:0 1non-maintained emergency luminaire maintained emergency luminairec) Third segment containing four positions: FACILITIES.