Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 23,1 11,2 11,9 448,00Remote: 12-45 23,2 11,0 12,2 456,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,4 25,4 2,0 447,00Remote: 45 29,2 23,8 5,4 499,00Worst Value: Local: 36 26,1 23,8 2,3 500,00Remote: 45 29,2 23,8 5,4 499,00PS-ACRF: Pass Worst Margin: Local: 12 71,6 61,2 10,4 1,00Worst Value: Local: 45 21,1 8,0 13,1 454,00Remote: 45 71,1 61,2 9,9 1,00Remote: 45 21,2 8,0 13,2 454,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:59Signature:______________________ Page: 34Copper Certification ReportCable Label: 521.002-UD-153 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:42:03 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: