Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]7.5 33 1 1.44Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]37.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.4 487.0 28.5 36 7.6 489.0 25.5SR 12-45 8.0 499.0 27.9 36 8.9 489.0 25.5MAIN 36-45 7.4 487.0 28.5 36 7.6 489.0 25.5SR 12-45 8.1 500.0 27.8 36 8.9 489.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.8 3.4 54.7 45 14.0 2.6 53.9SR 45-78 14.8 3.4 54.7 45 13.9 2.1 55.7MAIN 12-45 17.6 493.0 11.4 45 16.4 483.0 8.6SR 36-45 17.3 483.0 11.6 45 16.3 476.0 8.70100806040200250 MHzACR-F (dB)