Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
61 to 120 m2Anchor pointExpansion unitDirection of expansionTap-off unitQGH3492101-01 11/2018Specific Components63Specific ComponentsExpansion Units on Transformer and Switchboard LinksIn transformer or switchboard links, provide a rigid anchor just before the run component that is connected to the end feed units. Provide for expansion units every 30 m of straight run length (L).Anchor pointExpansion unitDirection ofexpansionExpansion Units Between Two BuildingsThe expansion unit installed between two buildings is used to absorb the forces arising due to the movement of the two buildings relative to each other.Anchor pointExpansion unitAnchoring the Run ComponentsThe run components can be anchored to the supports using accessories as shown:Edgewise assembly:Flatwise assembly:NOTE: Accessories to anchor the run components on the supports are not provided by Schneider Electric.64QGH3492101-01 11/2018Specific ComponentsInstallation of Fire-Barrier Kit