Title: 05_ListOfVariables_MemoryOrganisation_Smarteh_v25_V6523.xls
UV lamp maintenance "0" = Ok, "1" = Fault FUTURE USE 241 #31 242 UV lamp replacement 242 243 DI5_IN7_ww signal from water wash MU4:DI5:IN7 status 243 244 DI5_IN8_ww signal from water wash MU4:DI5:IN8 status 244 245 FireAlrDamperOK "0" = Ok, "1" = Fault 245 246 FireAlrDamperAlarm "0" = Ok, "1" = Fault 246 247 ComonAlarm "0" = Ok, "1" = Fault system common alarm (possible to select which alarms are counted to common alarm) 247 MU5 248 MU5-Fire Alarm status 1-On, 0-off new:30.11.2016 (implemented in version 6228) 248 FUTURE USE 249 #32 Future Use 249 #32 250 Future Use 250 251 Future Use 251 252 Future Use 252 AEROLYSE FILTERS 253 Filter#3 Dirty 253 254 Filter#3 Overload 254 255 Filter#4 Dirty 255 256 Filter#4 Overload 256