Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]16.8 73 1 2.70Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.4 448.0 30.3 36 8.8 468.0 26.5SR 36-45 8.2 405.0 31.2 36 8.8 467.0 26.6MAIN 36-45 10.5 497.0 28.0 36 9.4 496.0 25.2SR 36-45 9.7 493.0 28.2 36 9.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.9 3.9 53.5 45 14.1 3.9 50.5SR 78-45 14.9 3.9 53.5 45 14.1 5.9 46.9MAIN 36-45 15.7 473.0 11.7 45 17.9 459.0 9.0