Title: 1 etg del 2.pdf
Cable ID: T1210 Date / Time: 10/17/2013 02:17:45 PM Headroom 11.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]83 133 10 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.5 97.8 32.5 36 14.0 78.3 31.1SR 12-36 11.4 97.8 32.5 36 13.9 97.8 29.5MAIN 12-36 11.5 97.8 32.5 36 14.0 97.8 29.5SR 12-36 11.4 97.8 32.5 36 13.9 97.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 26.5 97.3 18.9 45 26.4 4.5 42.5