Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]44.0 190 2 6.26Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]22.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.8 462.0 30.0 36 7.2 500.0 26.4SR 12-36 7.0 498.0 29.3 36 8.1 500.0 26.4MAIN 36-78 8.2 500.0 29.2 36 7.2 500.0 26.4SR 12-36 7.0 498.0 29.3 36 8.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 21.0 500.0 11.3 45 21.3 416.0 9.9SR 45-78 21.3 450.0 12.2 45 20.8 500.0 8.3MAIN 78-45 21.0 500.0 11.3 45 21.6 500.0 8.3SR 45-78 21.4 500.0 11.3 45 20.8 500.0 8.30100806040200250 MHzACR-F (dB)