Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Colliers Plan 5 / DM3.E2=433.05.02 / XF028 C16/2/003 / Mal 1 10.03.2022 11:27 (TomekElektriker)SPENNING TRMS Uln: 234V Ulpe: 234V Unpe: 1V f: 49.97HzSYS.: TN/TTZ-LINEZ: 0.47ΩIsc: 487A R: 0.47Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ATALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:16GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr.474748484949TEST RAPPORTResultatRCD: UtlřsningsstrřmI: 27.0mAUci: 0.0V t: 258.2ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 529V Rnpe: >30.0MΩ Um: 514VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF028 C16/2/003 / Mal 1 10.03.2022 13:43 (TomekElektriker)KONTINUITET: R200mA LPER: 0.14ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF028 C16/2/003 / Mal 2 10.03.2022 11:37 (TomekElektriker)SPENNING TRMS Uln: 232V Ulpe: 1V Unpe: 233V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.38Ω