Title: DM1-3 plan 05 lysberegningsrapport.pdf
≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 1300 kWh/aPΦ50.0 W4996 lmCheckLuminous efficacy99.9 lm/W50201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M4 SummaryGround area: 10.74 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.520 m | Mounting height: 2.850 m51201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M4 SummaryResultsSymbolCalculatedVisual task areasĒ Task Area782 lxg1 Task Area0.90Ē Surrounding area473 lxg1 Surrounding area0.46Ē Background area190 lxg1 Background area0.40Consumption valuesConsumption[56 - 89] kWh/aLighting power densityRoom4.30 W/m²Utilisation profile: Offices, Conference and meeting roomsLuminaire listpcs.Manufacturer Article No.Article name2IGUZZINIQ509Laser Blade XS - Downlight HC 23.1WTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 400 kWh/aPΦ23.1 W1452 lmCheck