Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.0 112 1 3.96Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.2 463.0 29.6 36 7.7 464.0 26.7SR 36-78 9.8 429.0 30.7 36 9.1 500.0 25.0MAIN 12-36 8.6 500.0 27.8 36 8.6 500.0 25.0SR 12-36 10.2 500.0 27.8 36 9.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.6 6.5 49.0 45 20.8 5.9 46.9SR 78-45 18.5 5.9 49.9 45 20.6 498.0 8.3MAIN 45-36 21.3 498.0 11.3 45 21.1 498.0 8.3SR 36-45 21.1 498.0 11.3 45 20.6 498.0 8.30100806040200250 MHzACR-F (dB)