Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.187187188188189189190190191191192192TEST RAPPORTResultatSPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF045 16C2/003 15.12.2020 10:35 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF046 16C2/003 30.11.2020 09:29RCD II: 28.5mAUci: 0.2V t: 28.3ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF046 16C2/003 30.11.2020 09:30SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF046 16C2/003 30.11.2020 09:30Z-LINEZ: 0.56ΩIsc: 408A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF046 16C2/003 30.11.2020 09:31Zs(rcd)Z: 0.55ΩIsc: 415A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A