Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.10.03-UF034 Date / Time: 27-02-2020 21:55:56 Headroom 8.1 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]18.5 80 1 2.91Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.0 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.8 410.0 31.1 36 8.5 461.0 26.9SR 36-45 8.1 473.0 29.1 36 7.4 461.0 26.9MAIN 36-45 9.6 496.0 28.0 36 8.7 494.0 25.3SR 36-78 8.2 488.0 28.4 36 8.4 500.0 25.010080604020NEXT (dB)