Title: +038=370.002-RP011T_01-Siemens Trykkføler vann QBE2003-P10.pdf
Nominal pressureRelative pressure as in "Type summary" (measurement of difference from ambient pressure)Max. admissible pressure/ Rupture pressure3 x scale end value of measuring range 0…1 to 0…4 bar 2.5 x scale end value of measuring range 0...6 to 0...60 barMediaAdmissible temperature of mediumNeutral and slightly corrosive liquids and gases (suited for use with oil-contacting media) − 1 5 ...+ 1 2 5 °CMaintenanceMaintenance-freeMounting positionOptionalProtection standardIP 65 to EN 60529Protection classIII according to EN 60730Electric connectionPlug DIN EN 175301-803-A, Cable diameter 6-8 mmScrewed fittingExternal thread G ½", inside thread M5*)Temperature HumidityO p e r a t i o n − 3 0 ...+ 85 °C Insensitive to CondensationStorage − 5 0 ...+ 1 0 0 °C Insensitive to CondensationPressure sensors QBE2x03-P...A6V10432494_en--_d 2019-06-04Directives and standardsMaterialsEle ConformityWeightInternal diagram QBE2003…QBE2103…Siemens