Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 6 Perpendicular illuminance (adaptive) [Ix] 491 (= 500) 418 532 0.85 0.79 Surrounding area: 0.500 m 2 Surrounding area 6 Perpendicular illuminance (adaplive) [Ix] 394 (z 300) 295 485 0.75 0.61 3 Background area 5 Perpendicular illuminance (adaptive) [Ix] 210 (= 100) 158 258 0.75 0.61 Wall zone: 0.500 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 3 iGuzzini illuminazione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 114.3HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 8436 73.8 114.3Lighting power density: 5.43 W/m? (Floor area of room 13.59 m?) Consumption: 90 - 140 kWh/a of maximum 500 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.