Title: økernvn 94.pdf
Cable ID: T3075 Date / Time: 09/12/2013 03:41:34 Headroom 11.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]96 152 11 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.3 95.5 32.6 36 14.6 85.3 30.4SR 12-36 11.3 95.5 32.6 36 13.2 95.5 29.6MAIN 12-36 12.3 95.5 32.6 12 14.8 99.3 29.4SR 12-36 11.3 95.5 32.6 36 13.2 95.5 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 22.3 99.5 18.7 36 24.8 99.5 15.7