Title: Pos. 12A Kjolebenker ProffG2_Bruksanvisning.pdf
the application limits before proceeding. HOW TO CHANGE A PARAMETER VALUE address) with a detailed description of the fault. Model XR02CX, format 32 x 74 x 50 mm, is a digital thermostat with off cycle defrost designed for Anti short cycle delay enabled (AC parameter) Flashing Measurement unit On blinking). 2. Released the keys, then push again the SET+ Measurement unit On In case of failure or faulty operation send the instrument back to the distributor or to “Dixell S.p.A.” (see Push and immediately release the SET key or wait about 5s to return to normal visualisation. 2. Dripping in progress Flashing provided with 1 NTC probe input and one configurable digital input. The instrument is fully configurable 2. Select the required parameter. Press the “SET” key to display its value This manual is part of the product and should be kept near the instrument for easy and quick refrigeration applications at normal temperature. It provides a relay output to drive the compressor. It is also Consider the maximum