Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
1. Align the 6 holes on the module frame (paragraph 3.4 - [H]) with the 6 holes on the cabinet front-plate or repeater enclosure (paragraph 3.3 - [D]).2. Secure the module in place by fastening the supplied screws into the aligned holes.2. Secure the module in place by fastening the supplied screws into the aligned holes.3. Connect the CAN BUS wire ([A] supplied):if the module is mounted in the upper aperture, the CAN BUS wire must be connected between the module port ([B], paragraph 3.4 - [N], paragraph 3.5 - [D], paragraph 3.10 - [N]) and the CAN bar port ([C], paragraph 3.1 - [P])if the module is mounted in the lower aperture and another module is mounted in the upper aperture, the CAN BUS wire must be connected between module port ([D], paragraph 3.4 - [N], paragraph 3.5 - [D], paragraph 3.10 - [N]) and the appropriate port on the upper module ([E], paragraph 3.4 - [O], paragraph 3.5 - [E], paragraph 3.10 - [O])F