Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 25,0 12,1 12,9 400,00Remote: 12-36 25,1 12,7 12,4 376,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,9 23,8 3,1 498,00Remote: 36 28,7 23,8 4,9 499,00Worst Value: Local: 36 26,9 23,8 3,1 498,00Remote: 36 28,7 23,8 4,9 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,8 61,2 11,6 1,00Worst Value: Local: 12 22,5 8,7 13,8 419,00Remote: 12 72,1 61,2 10,9 1,00Remote: 12 22,5 8,7 13,8 419,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:57Signature:______________________ Page: 19Copper Certification ReportCable Label: 521.002-UD-021 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 14:06:09 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein