Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
R+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 05.11.2020 12:27SPĆNDINGU12: 234V U1pe: 234V U2pe: 0V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 05.11.2020 12:27Z-LINEZ: 0.64ΩIsc: 358A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 136A Isc(0.76%): 272A Isc(1.15%): 411ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 05.11.2020 12:28Zs(rcd)Z: 0.43ΩIsc: 531A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 05.11.2020 12:31Tallberg Elektro A/S Tlf.22796640Side:11GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.777778787979808081818282TEST RAPPORTResultatRCD II: 28.5mAUci: 0.1V t: 105.1ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF030 16C2/003 06.11.2020 13:18R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩ