Title: Hardware Installation Guide.pdf
150 — revision 6Hardware Installation GuideWiring for power, power fault, and cabinet tamperingVIN GND TMP GND FLT GND+ -12 to 24 VDC (wire power with stranded twisted pair, 18 AWG)CABINET TAMPERPOWER FAULT29.6Memory Backup BatteryRemove the factory-installed plastic safety strip from the memory backup battery. This plastic strip prevents the battery from being effectively seated. The battery will not function properly until the plastic strip is removed. When the battery is enabled, event memory is protected.29.7ConfigurationThe IDRC board is configured through jumpers, DIP switches, and web browser.29.7.1Setting Dip SwitchesSet DIP switches as required. The following chart describes the use of each DIP switch.Some switch settings behave differently at power up than they do after initialization. Keep this in mind when changing settings.SwitchSelection:SW1