Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
26.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 500.0 29.2 36 7.4 500.0 26.4SR 12-36 8.5 500.0 29.2 36 7.8 500.0 26.4MAIN 12-36 8.0 500.0 29.2 36 7.4 500.0 26.4SR 12-36 8.5 500.0 29.2 36 7.8 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.3 451.0 12.2 45 19.2 499.0 8.3SR 78-45 18.4 459.0 12.0 45 18.9 499.0 8.3MAIN 78-45 18.5 463.0 11.9 45 19.2 499.0 8.3SR 78-45 18.4 459.0 12.0 45 18.9 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.1 45.8 35.6 36 20.2 45.8 33.1SR 36-45 20.5 42.8 36.4 45 21.9 42.8 34.0MAIN 12-36 34.7 500.0 -12.4 36 34.2 500.0 -15.3SR 12-36 35.2 500.0 -12.4 36 34.6 500.0 -15.30804000250 MHzACR-N (dB)