Title: etg u1.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.5 * 247.5 35.4 36 0.7 * 241.5 33.0SR 36-450.3 *244.5 35.5 36 0.0 *244.5 32.9MAIN 36-45 0.5 247.5 35.4 36 0.7 248.5 32.7SR 36-45 0.3 244.5 35.5 36 0.0 244.5 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 12.7 227.0 17.1 36 15.2 242.5 13.5SR 45-36 12.3 213.5 17.6 45 14.8 240.0 13.6MAIN 45-36 12.7 242.5 16.5 36 15.2 242.5 13.5SR 45-36 12.5 242.5 16.5 45 14.8 242.0 13.5010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250