Title: etg u1.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 249.5 35.4 36 1.1 240.0 33.0SR 12-360.2 *215.5 36.4 36 0.0 *244.0 32.9MAIN 36-45 0.9 249.5 35.4 36 1.3 249.5 32.7SR 12-36 0.3 240.5 35.6 36 0.0 244.0 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.8 250.0 16.2 36 18.9 249.5 13.2SR 36-45 17.3 235.0 16.8 36 18.6 191.5 15.5MAIN 45-36 16.8 250.0 16.2 36 18.9 249.5 13.2SR 36-45 17.3 250.0 16.2 45 19.0 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250