Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
I/O modules and I/O terminal blocks may only be plugged in and removed when the PCD and the external +24 V are disconnected from the power supply.6Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-60Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W3x56.9.1 PCD2.W3x5, analogue inputs, electrically isolated, 7 channels,12 bit resolutionApplicationHigh-speed input modules for general use, electrically isolated from the CPU, with 7 channels, each with 12 bit resolution. Different variants for voltage 0..10 V, -10 V...+10 V and current 0..20 mA are available.Module overviewresolution *)PCD2.W305:Voltage 0..10 V2.5 mVPCD2.W315: PCD2.W325: *) Resolution = value of least significant bit(LSB)Current 0...20 mA Voltage -10..10 V5 μA 5 mVTechnical data6Input ranges: Galvanic separation:see module overview 500 V, electrical isolation of outputs to PCD, channels themselves not separated