Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Uln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF012 C16/2 16.06.2020 09:40Tallberg Elektro A/S Tlf.22796640Side:2GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.1515161617171818191920202121TEST RAPPORTResultatR ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF012 C16/2 16.06.2020 09:43SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF013 C12/2 16.06.2020 09:40R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF013 C12/2 16.06.2020 09:43SPĆNDINGUln: 231V Ulpe: 231V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF020 C63/4 16.06.2020 08:40SPĆNDINGU12: 401V U13: 400V U23: 401V f: 50.0Hz : 1.2.3DM1-3. Plan 9 / DM3.E6.433.09.03 / XF020 C63/4 16.06.2020 09:51R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩ