Title: FDV-DOKUMENTASJON.pdf
Limit: 0.90MZ: 0.33L-PE,N-PEUln: 239VXl: 0.04R: 0.35Xl: 0.06SYS.: TN/TTSYS.: TN/TTSYS.: TN/TTSYS.: TN/TTSYS.: TN/TTINSULATIONPage:2Fuse I: 32AFuse I: 32AVOLTAGEΩΩΩΩΩΩΩΩΩΩΩΩ:::Um: 530VNoResultsIscMaxLN: 694At: 258.6msUc: 0.0VIdn: 30mAUlim: 50VIsc: 482ARnpe: >30.0MCONTINUITY6Ulim: 50VUlim: 50V88PASSPASSPASSPASSRnpe: >30.0MUlpe: 238VIscMinLN: 375Atype:type:Elektro Nettverk Service asUm: 532VRlpe: >30.0MPASSXl: 0.02R-: 0.1Um: 533VUm: 533VTripout timeTripout timePage:3t: 93.7msIscMaxLN: 622AUc: 0.1VTRMSUiso: 500VUiso: 500VPASS*PASS*Fuse Type: BZ: 0.39SYS.: ITIscStd: 592AR200mAFuse T: 0.4sIsc_lim: 160.0At: 247.0msR: 0.39MUL.: x1MUL.: x1R: 0.18f: 50.05HzTEST REPORTZ-LINERCDRCDUnpe: 0V02.09.2020 11:25 (459)41119 / U1 / PLASS 341119 / U1 / PLASS 3NPELimit: 0.90MLimit: 0.90ML-PE,N-PEL-PE,N-PEUln: 239VUm: 529V