Title: +038=433.002-FS016._02-Eaton Tavlebyggeren Produktdatablad.pdf
Rated short-circuit breaking capacity Icu IEC 60947-2 at 400 VkA0Voltage typeACFrequencyHz50 - 60Current limiting class3Suitable for ﬂush-mounted installationNoConcurrently switching N-neutralNoOver voltage category3Pollution degree2Additional equipment possibleYesWidth in number of modular spacings4Built-in depthmm70.5Degree of protection (IP)IP20Ambient temperature during operating°C25 - 55Connectable conductor cross section multi-wiredmm²1 - 25Connectable conductor cross section solid-coremm²1 - 2504/01/2019Eaton Industries GmbH http://www.eaton.eu © 03/2019 by Eaton Industries GmbH Eaton 264985 ED2019 V54.0 EN1 / 1DATASHEET - NDRBM-10/2/C/003-Felectronic residual current circuit-breaker/miniature circuit-breaker, 10A, 30mA, miniature circuit-breaker trip curve: C, 2pole, residual current circuit-breaker trip characteristic: FPart no. Catalog No.NdRBM-10/2/C/003-F 300489Delivery program Basic function