Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]20.1 87 1 3.16Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.2 468.0 29.4 45 9.0 469.0 26.5SR 36-45 6.3 462.0 29.6 36 7.3 462.0 26.8MAIN 36-45 8.8 480.0 28.8 36 9.9 499.0 25.0SR 36-45 7.1 498.0 27.9 36 7.8 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.6 118.5 23.8 45 14.4 2.6 53.9SR 36-45 15.6 142.5 22.2 45 14.5 2.6 53.9MAIN 36-45 17.3 467.0 11.8 45 19.7 479.0 8.6