Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
instrument must enter defrosting (if the temperature measured by the evaporator allows this operation). y = yes; n = no. ALARMS Allow you to select if the parameters HAL and LAL will have absolute (Att=0) or relative (Att=1) value. Alarm Fan differential. Alarm differential. Higher ALarm. Maximum temperature alarm. Temperature value (in relative value) which if exceeded in an upward direction triggers the activation of the alarm signal. Lower ALarm. Minimum temperature alarm. Temperature value (in relative value), which if exceeded in a downward direction, triggers the activation of the alarm signal. Power-on Alarm Override. Alarm exclusion time after instrument switch on, after a power failure. defrost Alarm Override. Temperature alarm exclusion time after defrost. Alarm signaling delay after digital input disabling (door close). Alarm is only for high-low temperature alarms. time out door Open. Alarm activation delay time open door. temperature Alarm Override. Temperature alarm signal delay time. External