Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
18.2 78 0 2.79Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]32.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.3 455.0 30.0 36 7.2 462.0 26.8SR 12-36 8.7 454.0 30.0 36 9.1 467.0 26.6MAIN 12-36 8.1 495.0 28.1 36 8.2 500.0 25.0SR 12-36 8.8 500.0 27.8 36 9.3 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.7 7.4 47.9 45 22.2 6.5 46.0SR 45-78 20.7 7.4 47.9 45 22.4 7.6 44.6MAIN 12-36 21.6 470.0 11.8 36 22.8 470.0 8.8SR 36-12 21.7 470.0 11.8 36 22.9 472.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 27.6 129.0 19.9 36 29.5 129.0 17.3SR 36-45 26.6 129.0 19.9 36 28.5 128.5 17.4