Title: 1 etg del 2.pdf
Cable ID: T1133 Date / Time: 10/21/2013 08:01:29 AM Headroom 13.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]207 329 24 8.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.5 97.8 32.5 36 14.8 94.5 29.7SR 12-36 15.2 15.6 45.4 36 16.5 90.0 30.1MAIN 12-36 13.5 97.8 32.5 36 14.8 94.5 29.7SR 12-36 15.2 90.0 33.1 36 16.5 90.3 30.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 21.1 54.0 24.0 36 23.2 3.5 44.7