Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]27.6 120 2 4.27Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.7 462.0 29.6 36 8.9 483.0 25.8SR 36-45 7.8 470.0 29.3 45 7.5 469.0 26.5MAIN 36-45 9.5 500.0 27.8 36 9.4 499.0 25.0SR 36-45 7.8 470.0 29.3 45 7.6 470.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.7 4.5 52.2 45 14.4 2.6 53.9SR 36-45 15.7 4.5 52.2 45 14.5 2.6 53.9MAIN 78-45 16.1 500.0 11.3 45 16.7 500.0 8.3SR 45-78 16.4 500.0 11.3 78 17.5 500.0 8.30100806040200250 MHzACR-F (dB)