Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
R LOW Ohm GODKJENTR: 0.09QRt: 0.1QR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT * 12.03.2020 13:46SPENDINGUln: 235V Ulpe: 236V Unpe: 0V f: 50.1Hz 113 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT* 12.03.2020 13:46 Z-LINE GODKJENT Z: 0.58Q Isc: 394A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc lim: 160.0A 114 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT * 12.03.2020 13:47 Zs (red) GODKJENT Z: 0.52Q Isc: 444ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0A11ﬂDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT * 12.03.2020 13:50RCD I a GODKJENTI: 28.5mAUciy: 1e5Yt: 14.6nsIdn: 30mAtype: ACON,Ulim: 25V‘1161Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 031 GODKJENT* 12.03.2020 14:57KONTINUITET GODKJENTR: 0.1QGrenseverdi:1.0QTEST RAPPORTResultatR ISO GODKJENTR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQ