Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Carefully lift the unit (without the frame) using the four suspension brackets (or the four corners), inserting it into the false ceiling. If the "T" bar cannot be removed the unit may need to be tilted (this operation may only be carried out with false ceilings with a minimum height of 300 mm) (See fig. 20).Water connectionsTo make water connections to the heat exchanger or the valves use threaded joints and suitable materials that can ensure perfect tightness. The unit is provided with inlet and outlet female connections for both 2 and 4 pipe models. An air bleed valve is also provided (See fig. 26), which can be adjusted using a 8 mm wrench..Models200 300 400 200* 300* 400*Connections dimension (Ø) 3/4" 3/4" 3/4" 1/2" 1/2" 1/2"Models500 600 700 700 *Connections dimension (Ø) 1" 1" 1" 3/4"Hot water circuits, four-pipe versionElectrical connectionsIMPORTANT: • The unit must be installed in compliance with the national standardson plant installation.