Title: bn305_cgb.pdf
Cable requirements Al_ComConnects to Al_Com loop only0,1 mA25 to +70 °C10 % - 95 % RH (non-condensing)IP67Autronica loop communication protocol (AL_Com)Max 2.5 mm² single core wiresRefer to specification for AutroSafe or AutroprimeAll connections are made to screw terminals numbered 1-12. Function Terminal AL_Com In (+) 1 AL_Com In (-) 2 AL_Com Out (+) 3 AL_Com Out (-) 4 Input 1 (+) 5 Input 1 (common) 6 Relay 1 contact 7 Relay 1 contact 8 Input 2 (+) 9 Input 2 (common) 10 Relay 2 contact 11 Relay 2 contact 12Maximum input cable length100 mLED connectorsMaximum cable capacitanceSerial impedance ZC MaxResponse time30 nF40mΩ<= 1 secondTerminal J2.1 J2.2 J2.3 J2.4Function LED1 + (LED Activate) LED1 - (LED Activate) LED2 + (LED Fault) LED2 - (LED Fault)Output relay rating1 A 30 VDCOutput relay typeThresholdDry contact, Latching type; keep state on loss of power. No EOL monitoring