Title: 360.001 - Tilluft.pdf
0.0 +0.09.70.0 +0.013.313.30.6 +8.114.014.01.5 +8.113.81.5 +0.01.5Lp [dB]10,1LocationLevel2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeTypeProductDUCTMAGID-C1-31565 FLOWDAMPER LEO-0-315DUCTMAGID-C1-315BEND-90MAGIB-C3-90-315DUCTMAGID-C1-315SILENCERLKR-315-1200DUCTMAGID-C1-315FIREDAMPER FKR-EU/DE/315/ZXXDUCTMAGID-C1-315BEND-90MAGIB-C3-90-315315315315315315315315315315315SizeSound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]1,312004,312004,30,412004,312004,30,112004,312004,30,212004,312004,30,212004,312004,3470,9 Sound in:Attenuation: Addition:22,0 Sound in:Addition:0,3 Sound in:Attenuation: Addition:2,8 Sound in:Attenuation: Addition:0,1 Sound in:Attenuation: Addition:11,0 Sound in:Attenuation:0,2 Sound in:Attenuation: Addition:4,8 Sound in:Addition: