Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]24.1 105 2 3.81Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 10.3 483.0 28.6 36 10.1 476.0 26.1SR 36-45 5.6 481.0 28.7 36 6.3 484.0 25.7MAIN 12-45 10.3 483.0 28.6 36 10.9 500.0 25.0SR 36-45 6.1 496.0 28.0 36 6.8 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.1 3.8 53.8 45 13.5 2.5 54.3SR 78-45 15.1 3.8 53.8 45 13.5 2.6 53.9MAIN 45-78 15.8 500.0 11.3 45 17.5 500.0 8.3SR 78-45 15.6 500.0 11.3 45 17.0 499.0 8.30100806040200250 MHzACR-F (dB)