Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: D4166 Date / Time: 09/09/2013 02:06:18 Headroom 3.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]81 127 7 3.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.5 188.0 37.4 12 7.6 220.5 33.6SR 12-36 3.1 200.0 36.9 12 3.3 219.5 33.6MAIN 12-36 6.5 220.5 36.2 78 7.8 247.0 32.8SR 12-45 3.6 219.0 36.3 12 3.3 219.5 33.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.5 176.5 19.3 36 17.2 164.5 16.9