Title: DM1-3 plan 05 lysberegningsrapport.pdf
PΦ23.1 W1452 lmCheckLuminous efficacy62.9 lm/W108201104 DM1-3 McKinseyBuilding 1 · Storey 1 · TR/P8 SummaryGround area: 9.54 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.850 m | Mounting height: 2.850 m109201104 DM1-3 McKinseyBuilding 1 · Storey 1 · TR/P8 SummaryResultsSymbolCalculatedVisual task areasĒ Task Area737 lxg1 Task Area0.67Ē Surrounding area290 lxg1 Surrounding area0.17Ē Background areag1 Background areaConsumption valuesConsumption89 kWh/aLighting power densityRoom4.84 W/m²Utilisation profile: Offices, Conference and meeting roomsLuminaire listpcs.Manufacturer Article No.Article name2IGUZZINIQ509Laser Blade XS - Downlight HC 23.1WTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 350 kWh/aPΦ23.1 W1452 lmCheckLuminous efficacy62.9 lm/W110201104 DM1-3 McKinsey