Title: økernvn 94.pdf
50 MHz75100LinkWare Version 7.4Cable ID: T4034 Date / Time: 09/11/2013 10:02:12 Headroom 12.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]126 199 14 5.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.6 80.5 33.9 36 14.7 80.8 30.8SR 12-36 13.1 80.5 33.9 36 15.5 75.3 31.3MAIN 12-36 13.5 96.3 32.6 36 15.7 98.5 29.4SR 12-36 14.0 96.3 32.6 36 16.0 96.3 29.610080604020NEXT (dB)