Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 45-36 17.5 468.0 11.8 45 19.8 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 29.5 111.5 22.4 45 30.0 109.0 20.3SR 45-78 27.7 108.0 23.0 45 28.8 104.0 21.0MAIN 36-45 41.3 500.0 -12.4 36 41.8 500.0 -15.3SR 36-45 37.1 488.0 -11.6 36 39.0 497.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.6 475.0 8.0SR 12 5.4 478.0 8.0MAIN 45 6.6 475.0 8.0SR 12 5.4 478.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00420.6 m60Insertion Loss (dB)504030201000250 MHz500