Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
1 – e.g. a masonry wall 2 – A building element with fire resistance equal or higher to the building envelope resistance 3 – mcr FID S/... p/P fire damper, BxH.4 – A building element with fire resistance equal or higher to the building envelope resistance. For example, a brick wall. 5 – e.g. mortarInstallation of the mcr WIP fire damper as a multiple damper set (a set of 4) Other configurations of the mcr WIP/… dampers modules can be made, consisting of two or more dampers, while maintaining the minimum distances between the dampers according to the drawing above6.4. ELECTRICAL CONNECTIONSOnce a fire damper has been correctly installed, it is necessary to connect it to the electrical wiring system (using the wiring system’s cables) if the fire damper is equipped with controls or other components that require such connection. Shown below are the wiring diagrams and basic electrical data of the release and control mechanisms supplied together with the mcr WIP type fire dampers.