Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
100BASE-TX 10GBASE-T ATM-155 TR-16 Active100BASE-T4 ATM-25 100VG-AnyLan TR-16 Passive60402000250 MHzProject: F13 3 ETGUntitled1Test Summary: PASSModel: DSX-5000 Main S/N: 2552117 Remote S/N: 2552311 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00424.2 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD11 Date / Time: 05/19/2022 11:40:41 AM Headroom 9.1 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 12] [Pair 36] [Pair 36] [Pair 36]