Title: +038=370.102-RT004T_01-Siemens Tempføler vann QAE2130.010.pdf
In the return at a location where the temperature can be correctly acquiredThe sensor should be installed in an elbow such that the immersion rod or the protec- tion pocket faces the direction of flow. The water must be well mixed where the tem- perature is acquired. This is downstream from the pump or, if the pump is mounted in the return, at least 1.5 m after the mixing point.The sensor should be mounted such that the cable does not enter from the top.With all types of sensors, the immersion length must be a minimum of 60 mm!The sensor must not be covered by lagging.To fit the sensor, a threaded fitting or T-piece G ½ must be welded into the pipe.Mounting positionspermitted:not permitted:Mountingmin. 60 mmG ?ab2 0 Z 1 8 7 1cd1 0 Z 1 8 7 1Note!For sensors with non-sealing threaded nipples G ½, sealing means must be usedwith the threaded connection (e.g. hemp, Teflon tape or similar)Tighten compression fitting AQE2102 on the sensor's immersion rod