Title: 32 Pumper modbuss teknisk data.pdf.pdf
Indicates the current rotational direction of the E-pump as seen from the ventilator side. 0: Clockwise. 1: Counterclockwise.Bit 8: AccessModeIndicates if the E-pump is locally or remotely controlled. 0: Local (a local control source with higher priority controls the E-pump) 1: Remote (controlled by Modbus master).Bit 9: OnOffIndicates if the E-pump is on or off. 0: Off (stopped, the green LED on the E-pump flashes) 1: On (started, the green LED on the E-pump is on). Started does not necessarily indicate rotation, for instance in case of low-flow stop.Bit 10: FaultIndicates if there is a fault or not. 0: No fault 1: Fault (red LED on the E-pump is on).Bit 11: WarningIndicates if there is a warning or not. The E-pump will continue running even if there is a warning. 0: No warning 1: Warning (red LED on the E-pump is on).Bit 12: ForcedToLocalState of the "Forced to local" control option 0: Not forced to local 1: Forced to local. Only available on MAGNA3 and MGE model H and later.