Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
MAIN 45-78 20.4 8.4 46.8 45 22.0 8.4 43.8SR 45-78 20.4 8.4 46.8 45 22.0 8.4 43.8MAIN 45-36 21.4 499.0 11.3 36 23.4 495.0 8.3SR 36-45 21.4 499.0 11.3 45 23.6 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 30.0 186.5 13.0 36 31.7 186.5 10.4SR 12-36 30.4 212.5 10.3 12 32.3 196.0 9.4MAIN 12-36 40.6 496.0 -12.1 36 40.4 497.0 -15.1SR 12-36 40.3 497.0 -12.2 36 41.0 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.8 498.0 8.0SR 45 7.6 497.0 8.0MAIN 45 5.8 498.0 8.0SR 45 7.6 497.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasjeTest Summary: PASS