Title: +175=324.001_KA001_Ventilmotor kjølebatterier 36.01 og .02 - AVM115.Produktinformasjon.pdf
Product data sheetAVM 105, 115: ActuatorHow energy efficiency is improvedTorque-dependent cut-off facility for efficient usage of energyFeatures • Activation of 2-way and 3-way valves of the VUN/BUN, VUD/BUD and VUE/BUE series. For con-trollers with a switching (2-/3-point) output.Synchronous motor with electronic control unit and time-dependent cut-off • Maintenance-free gear unit • Gear unit can be disengaged in order to position the valve by hand (hexagon key provided) • Connection with valve spindle created automatically • Cap nut for valve fitting made of brass • Fitting vertically upright to horizontal, not suspendedTechnical dataPower supplyPower supply 24 V~±20%, 50...60 HzPower supply 230 V~±15%, 50...60 HzParametersActuator stroke1) Response time0...8 mm200 msAmbient conditionsAdmissible ambient temperature–10...55 °CTemperature of mediumMax. 100 °CAdmissible ambient humidity5...95% rh, no condensationFunctionControl2-/3-pointConstructionWeight