Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
1000 VAC, 1 min. 2.5 kV Electrical isolation of outputs to the Saia PCD®. The channels are not isolated from each otherInternal current consumption: (from +5 V bus)1 … 24 mA typ. 12 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption:max. 40 mA (all inputs=1) at 24 VDC, (source operation), max. 18 mA (sink operation)Terminals:Plug-in 10-pole spring terminal block (4 405 4954 0) or pluggable 10-pole screw terminal block (4 405 4955 0), both for wires up to 2.5 mm²6-20PCD3.E61xLEDs and connection terminalsLED 0...7Terminal 0Terminal0–L–L1234567Description LabelAddress LabelE6 1 00 1 2 3 4 5 6 7 8 9E0 E1 E2 E3 E4 E5 E6 E7 L ––V 4 2+nEe c r u o SnE–V 4 2+k n Si0 1 6 E . 3 D C PC D V 4 2s t u p t u O 8Terminal 9Input circuits and terminal designationDepending on external wiring, this module may be used for source or sink operation.Source operation (positive logic):+5V6k611k+5VE1