Title: 40 Bender brukermanual.pdf.pdf
The devices are suitable for the following installation methods:   Distribution panels according to DIN 43871 or   DIN rail mounting according to IEC 60715 or   Screw mounting using M4 screws. Mount the measuring current transformers in accordance with the notes in the "Transformer installation“ technical information. When connecting the measu- ring current transformers, it is essential that you observe the maximum cable lengths, the conductor cross section and that you use shielded cables.22RCMS460-490_D00067_03_M_XXEN/12.2017Installation and connection4.3.1 Dimension diagram RCMS460-…4.3.2 Dimension diagram RCMS490-…Dimensions in mmRCMS460-490_D00067_03_M_XXEN/12.201723Installation and connection4.4 Connection4.4.1 Wiring diagram RCMS460-…24RCMS460-490_D00067_03_M_XXEN/12.2017Installation and connectionLegend to wiring diagram RCMS460-…A1, A2Connection of supply voltage US (see ordering informa- tion):we recommend the use of 6 A fuses.k1, l … k12, l