Title: 4. Leieavtaler.pdf
Data Sheet 5-23, Emergency and Standby Power Systems. Please send specific details on the generators and fuel tanks to FM Global for review.Design and construct fuel storage tanks and tank supports in accordance with FM Global Property Loss Prevention Data Sheet 7-88, Ignitable Liquid Storage Tanks. Install double-wall fuel tanks, provide containment and arrange the fuel system to automatically shut down the flow of fuel on fire detection.2015-01-07: There is no plan at this point to install an Emergency Power Generator.15. Install transformers in accordance with FM Global Property Loss Prevention Data Sheet 5-4, Transformers. Preferably install dry-type transformers, however if this is not possible, install an FM approved or a transformer with FM Approved liquid. Please send details of the proposed electrical supply system to FM Global for review.