Title: etg u1.pdf
Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 2 10/25/2013 07:33:06 AM økernveien 2410.flw9774 ft 69 69 0 0 0Cable ID: D0001 Date / Time: 10/21/2013 02:38:14 PM Headroom 8.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 36]53 86 7 2.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.3 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.1 60.5 35.9 36 11.7 60.5 32.9SR 12-36 8.2 78.8 34.0 36 10.6 96.5 29.6MAIN 12-36 9.6 96.8 32.5 36 11.7 96.8 29.5