Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
[Pair 45] [Pair 45] [Pair 45]22.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.1 498.0 29.3 36 9.2 499.0 26.4SR 12-36 8.9 496.0 29.3 36 9.3 496.0 26.5MAIN 12-36 9.1 498.0 29.3 36 9.2 499.0 26.4SR 12-36 8.9 496.0 29.3 36 9.3 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.2 472.0 11.8 45 19.8 494.0 8.4SR 78-45 19.0 451.0 12.2 45 19.6 500.0 8.3MAIN 78-45 19.7 496.0 11.3 45 19.9 500.0 8.3SR 78-45 19.4 487.0 11.5 45 19.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 17.8 26.9 42.1 36 17.5 26.8 39.7SR 36-45 17.1 26.6 42.2 36 17.5 29.4 38.6MAIN 12-36 31.5 498.0 -12.3 36 31.6 499.0 -15.2SR 12-36 31.5 500.0 -12.4 36 32.0 500.0 -15.30804000250 MHz