Title: 2 etg del2.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.5 * 245.5 35.5 36 0.3 * 245.0 32.9SR 36-450.8 *245.5 35.5 36 1.1 245.0 32.9MAIN 36-45 0.5 245.5 35.5 36 0.3 245.5 32.8SR 36-45 0.8 247.5 35.4 36 1.1 245.0 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.0 62.5 28.3 36 15.0 62.5 25.3SR 36-45 13.3 62.5 28.3 45 15.0 55.0 26.4MAIN 45-12 18.0 198.0 18.3 45 20.7 196.0 15.3SR 45-12 17.4 195.0 18.4 45 21.9 249.5 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250