Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
SIKRING I: 16ASTIKRING T: 35msIsc _lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 064 GODKJENT* 12.03.2020 14:52SPENDINGUln: 233VUlpe: 233VUnpe: 0Vf: 50.0HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 064 GODKJENT* 12.03.2020 13:37ZLINE GODKJENTZ: 0.62QIsc: 372ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 064 GODKJENT* 12.03.2020 13:39Zs (rcd) GODKJENTZ: 0.59QIsc: 390ASikringstype: CSIKRING I: 16ASIKRING T: 3b5msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 064 GODKJENT * 12:03:2020 12:54KONTINUITET GODKJENTR: 0.3QGrenseverdi:R ISCO GODKJENTR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 065 GODKJENT * 11.03.2020 10:10TEST RAPPORTNr. ResultatSPENDINGUln: 234VUlpe: 234VUnpe: 0Vf: 50.0HzR IS0 GODKJENTR: >200MQ Um: 262VUiso: 250V