Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
I (Ø+1): O (Ø+1):Inputs 0 + 1 + Uext error Outputs 0 + 1Four-pole connector:O Ø Skylight 0 / blind motor up O 1Skylight 1 / blind motor downSix-pole connector:I Ø (pin 5) – GND (pin 6)I 1 (pin3) – GND (pin4)Uext (pin 1) – GND (pin 2)external switch for Input 0 (skylight 0 / blind motor up) external switch for Input 1 (skylight 1 / blind motor down) external supply + 24 VDCThe GND connections are fitted to the circuit board.6-48PCD3.A860Block diagramBusIn LEDIn LEDLEDLEDOØaInterface(CPLD)RelaisOØbO1aPCD3 I/O BusMicroControllerRelaisO1b+24VSwitchGNDInp. FilterIØPowerSwitchGNDSupply+5VInp. FilterI1+3.3VGNDSummary of functionsFunctionKeys / inputs:FBoxShade moduleFully up/down Slat movement up/down ----- ----- -----Fully up/down Slat movement up/down (variable) Stop all movements Reset module and reinitialise Block keys and inputsLight moduleOn/off per channel (2x) ----- -----