Title: økernvn 94.pdf
RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 7.4Cable ID: D4049 Date / Time: 09/10/2013 12:53:35 Headroom 13.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]229 363 26 9.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.6 97.0 32.5 36 15.4 96.8 29.5SR 12-36 14.6 74.0 34.5 36 16.3 87.0 30.3MAIN 12-36 13.7 99.8 32.3 36 15.4 98.0 29.4SR 12-36 15.4 99.8 32.3 36 16.3 99.8 29.310080604020NEXT (dB)