Title: 40 Bender Datablad.pdf.pdf
RCMS…-D4/RCMS…-L4 The function of device version RCMS…-D4/RCMS…-L4 corresponds to the function described before. The functions of measuring channels k9…k12 vary from those described before. They are exclusively designed for current measurements with Type A measuring current transformers (measuring range 100 mA…125 A). For that reason, the measuring channels k9…k12 cannot be used in combination with W…AB series measuring current transformers or as digital inputs.Standards The LINETRAXX® RCMS460/490 series complies with the requirements of the device standards: DIN EN 62020 (VDE 0663) and IEC 62020.RCMS460-D…RCMS460-LRCMS490 -D…RCMS490-L…––1…90 121…90 121…90 121…90 1210 mA…10 A 6 mA…20 A10 mA…10 A 6 mA…20 A10 mA…10 A 6 mA…20 A10 mA…10 A 6 mA…20 A100 mA…125 A100 mA…125 A100 mA…125 A100 mA…125 A10…100 %, min. 5 mA 10…100 %, min. 5 mA 10…100 %, min. 5 mA 10…100 %, min. 5 mA2…40 %2…40 %2…40 %2…40 %