Title: V20-05-02 VVS-anlegg plan 5 - DM3-1.pdf
LD018T Maks:200 m³/h Kjøling: 350 W 0.028 L/s Varme: 300 W 0.007 L/s+05 = 320.102 - OE 054 0.120 L/sSTAP/STAD DN20320.102: 54mm 320.102: 54mmLD018T Maks:200 m³/h Kjøling: 350 W 0.028 L/s Varme: 300 W 0.007 L/sLD018T Maks:160 m³/h Kjøling: 300 W 0.024 L/s Varme: 280 W 0.007 L/sLD018T Maks:160 m³/h Kjøling: 300 W 0.024 L/s Varme: 280 W 0.007 L/s370.101: DN 100mm 370.101: DN 100mmSTAP/STAD DN32+05 = 370.101 - OE 054 0.370 L/sLD018T Maks:190 m³/h Kjøling: 300 W 0.024 L/s Varme: 410 W 0.009 L/sLD018T Maks:190 m³/h Kjøling: 300 W 0.024 L/s Varme: 410 W 0.009 L/sLD018T Maks:150 m³/h Kjøling: 300 W 0.024 L/s Varme: 410 W 0.009 L/sLD018T Maks:150 m³/h Kjøling: 300 W 0.024 L/s Varme: 410 W 0.009 L/sLD018T Maks:220 m³/h Kjøling: 450 W 0.037 L/s Varme: 410 W 0.010 L/sLD018T Maks:220 m³/h Kjøling: 450 W 0.037 L/sLD018T Maks:220 m³/h Kjøling: 450 W 0.037 L/s Varme: 410 W 0.010 L/sLD018T Maks:220 m³/h Kjøling: 450 W 0.037 L/sSTAP/STAD DN40370.101: DN 100mm 370.101: DN 100mm