Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
33.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.3 456.0 29.9 36 6.7 449.0 27.4SR 12-36 8.8 442.0 30.4 36 8.6 472.0 26.3MAIN 36-78 9.0 500.0 27.8 36 7.6 494.0 25.3SR 12-36 10.0 494.0 28.1 36 8.9 494.0 25.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.7 6.9 48.5 45 21.2 500.0 8.3SR 45-78 20.7 7.4 47.9 45 22.3 500.0 8.3MAIN 45-36 21.5 500.0 11.3 45 21.2 500.0 8.3SR 36-45 21.3 500.0 11.3 45 22.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 31.3 169.0 14.9 45 32.7 168.5 12.4SR 36-45 31.4 169.0 14.9 45 32.3 168.5 12.4MAIN 12-36 41.6 495.0 -12.1 36 40.2 494.0 -14.9SR 12-36 42.5 494.0 -12.0 36 41.5 494.0 -14.90804000250 MHzACR-N (dB)