Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 25Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Kontor 5/ Visual task area 3 / Perpendicular illuminance (adaptive)Visual task area 3 / Perpendicular illuminance (adaptive)Surface Result Average Min Max Min/average Min/maxVisual task area 3 Perpendicular illuminance (adaptive) [Ix] 578 395 669 0.68 0.59 Surrounding area: 0.500 mSurrounding area 3 Perpendicular illuminance (adaptive) [Ix] 422 290 535 0.69 0.54Background area 3 Perpendicular illuminance (adaptive) [Ix] 235 121 350 0.51 0.35Wall zone: 0.500 mDIALux Page 26Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Kontor 5 / Visual task area 3 / Perpendicular iluminance (adaptive)False colors [Ix]666500295Scale: 1:50Value grid [Ix]395)431443 486500Scale: 1:50