Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Small to medium installationsTrafo min. 50VA+18V19VAC ±15%0VGNDL+24V =NControl24VDC ±20%0VL NSensors:Actuators:Electro-mechanical and proximity switches, photoelectric barriers Relays, lamps, displays, small valves with < 0.5A switching currentSuitable for PCD2.Mxxxx ModulesPCD2. E1xx, E5xx, E6xx, A2xx, A4xx, B1xx, G4xx PCD2.W1xx, W2xx, W3xx, W4xx, W5xx, W6xx PCD2. H1xx*), H2xx*), H3xx*) PCD7.D2xx*)) These modules must be connected to a smoothed 24 VDC supplyHardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-24Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsPower supply, earthing scheme, cable layout3.7.2Internal power supplyC D V 4 2g n u s e p SiPCD2+24 VGNDPTC39VLED 24VDCDCVoltage monitor 5VPCD-Bus+5VCLR0V3DCDC+V (16...24V)Capacity of internal power supplyFrom the base units, the following currents are available for the plug-in modules: