Title: Differansetrykkføler sirk.pumpe loft.pdf
0…1.0 bar / 0…2.5 bar (= L/H) 0…4.0 bar / 0…6.0 bar (= L/H) 0…10 Vdc < 8 mA or 4…20 mA < 500 Ω < 2,5 % of full scale < 0,5 % of full scale / 10 K ± 0,03 bar/year manual, by a push button -20…+70 C -20…+100 °C IP5416 bar+ connection 7,5 bar 18,0 bar̶ connection 5,0 bar 12,0 bar3. Press the zeroing button until the indicator light illuminates.3. Press the zeroing button until the indicator light illuminates.4. Release the zeroing button.Materialswetting parts casebrass, ceramics plastics (polycarbonate)The indicator light turns off, when the zeroing was suc- cessful. The indicator light flashes, if the device is faulty.Wiring: 1 2 3 424 Vac/dc supply 0 V 0…10 Vdc output 4…20 mA output+Ordering guide: ModelVPEL 1.0/2.5Product number 1134060VPEL 1.0/2.5-N 1134061VPEL 4.0/6.01134070VPEL 4.0/6.0-N 1134071Description