Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 27.11.2020 11:55KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 27.11.2020 10:53SPĆNDINGUln: 236V Ulpe: 236V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 27.11.2020 10:53Z-LINEZ: 0.16ΩIsc: 1.45kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 27.11.2020 10:54Zs(rcd)Z: 0.17ΩIsc: 1.35kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 27.11.2020 10:54RCD II: 27.0mAUci: 0.2V t: 147.4ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 30.11.2020 12:00 (ELEKTRIKER)Tallberg Elektro A/S Tlf.22796640Side:45GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.311311312312313313