Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]30.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.8 451.0 30.2 36 9.9 451.0 27.4SR 36-45 10.5 459.0 29.8 36 10.4 455.0 27.2MAIN 36-45 11.9 500.0 27.8 36 10.3 500.0 25.0SR 36-45 11.5 500.0 27.8 36 11.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 15.9 5.0 51.3 45 14.6 12.0 40.7SR 12-45 15.9 8.9 46.3 45 14.5 2.6 53.9MAIN 78-45 17.0 500.0 11.3 45 17.6 500.0 8.3SR 45-78 17.3 500.0 11.3 45 18.1 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.0 71.5 29.4 36 22.7 76.3 25.9SR 36-45 21.9 67.0 30.3 36 22.3 71.8 26.8MAIN 36-45 40.5 500.0 -12.4 36 39.1 500.0 -15.3