Title: 40 Produktark nettanalysator 4x-serie.pdf.pdf
1. 1 VArh 2. 10 VArh 3. 100 VArh 4. 1 kVArh 5. 10 kVArh 6. 100 kVArh. 7. 1 MVArh44Pulse Output Duration SettingThe duration during the pulse stays at logic-1 level is entered here.1. Press SET button while PULS DURATION is displayed. 2. Enter the duration in seconds with 0.01 second increments with UP/DOWN buttons. 3. Exit from the menu when selection is complete. 4. When exiting from the menu with the BACK or ESC button, don’t forget to save the changes.Pulse Output Inactive Time SettingThe duration during the pulse stays at logic-0 level is entered here.1. Press SET button while PULSE DUTY is displayed. 2. Enter the inactive time in seconds with 0.01 second increments with UP/DOWN buttons. 3. Exit from the menu when selection is complete. 4. When exiting from the menu with the BACK or ESC button, don’t forget to save the changes.Operating Hours Settings