Title: Ahlsell.pdf
Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]9.5 47 1 5.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]37.0 499.0 43.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 8.3 212.5 36.5 7,8 8.2 212.5 33.9SR 1,2-3,6 6.3 304.0 33.8 3,6 7.8 303.0 31.3MAIN 3,6-4,5 10.1 488.0 27.0 3,6 11.4 486.0 24.2SR 1,2-3,6 9.9 461.0 27.8 3,6 11.9 485.0 24.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 16.7 91.5 25.0 4,5 18.3 59.0 25.8SR 7,8-4,5 16.7 91.5 25.0 4,5 18.1 89.5 22.2MAIN 7,8-4,5 19.4 494.0 10.3 4,5 21.1 447.0 8.2