Title: +175=324.001_KA001_Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.Produktinformasjon.pdf
The valves are combined with the valve actuators without a spring return or with valve actuators with a spring return. The actuator is mounted directly on the valve and fastened with either a nut or screws. The actuator is connected with the valve spindle automatically. When the system is commis- sioned, the actuator moves out and the connector closes automatically when it reaches the lower valve seat. The stroke of the valve is also detected by the actuator, and no further adjustments are required. Therefore the force on the seat is always the same and the smallest amount of leakage is ensured. With the SUT actuators, the characteristic can be set to linear or quadratic as required. The combination of AVM105S and DN 50 F200 cannot be set to equal-percentage.Additional technical dataSAUTER slide rule for valve sizingP100013496Technical manual on control units7 000477 001Parameters, fitting notes, control, general informationApplicable EN, DIN, AD, TRD and UVV regulationsFitting instructions: