Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
30.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.2 477.0 28.9 36 7.3 471.0 26.4SR 36-45 5.4 453.0 30.1 36 6.6 491.0 25.4MAIN 36-45 7.8 497.0 28.0 36 8.2 500.0 25.0SR 36-45 5.5 488.0 28.4 36 6.7 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.3 4.5 52.2 45 16.2 3.8 50.8SR 45-78 16.3 4.5 52.2 45 16.2 3.8 50.8MAIN 36-78 17.7 490.0 11.4 78 18.3 490.0 8.4SR 78-36 17.7 490.0 11.4 45 18.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 25.5 81.3 27.5 12 27.1 81.3 25.0SR 36-45 27.5 81.8 27.4 45 27.6 81.8 24.9MAIN 36-45 36.6 497.0 -12.2 36 37.4 500.0 -15.3SR 36-45 34.5 492.0 -11.9 36 35.8 496.0 -15.00804000250 MHzACR-N (dB)