Title: 2 etg del2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]299 472 32 12.9299 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.4 244.0 35.5 36 1.0 * 245.0 32.9SR 36-450.8 *249.5 35.4 36 0.8 *247.5 32.8MAIN 36-45 1.4 244.0 35.5 36 1.0 246.5 32.8SR 36-45 0.8 250.0 35.3 36 0.8 250.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 7.6 45.5 31.0 36 10.5 40.8 29.0SR 45-36 7.5 46.8 30.8 45 10.6 45.5 28.0MAIN 36-45 14.7 247.5 16.3 45 17.3 250.0 13.2