Title: +038=249.001-#####._01-10203518-01-RIA-NOT-007 Lydmålinger Collier_rev01.pdf
dB C100-5000 = dB Ctr,100-5000 =311dBdBName of test institute:Multic onsultNo. of te st re port:7Date:09.02.2022Signature:HGA10203518-RIA-NOT-00722. februar 2022 / Revisjon 00Side 15 av 30Dronning Mauds gate 1-3multiconsult.noKontrollmålinger av lydisolasjon plan 5, akse 0-8Vedlegg 2.8Apparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation betw een roomsClient: Desc ription:Dronning Maugs gt. 1- 3 Lydisolasjon fra korridor til kontor 5- 118Date of test:09.02.2022Object:Kontor med dør (glass og gipsvegg)Source room: korridorReceiving room: 5- 118Condition:Condition:Type:Type:Location:Location:Frequency range ac cording to theArea of common partition:10,00m²curve of shifted reference values (ISO 717- 1)Source room volume:Receiving room volume:49m³→ ⎯ B d65FrequencyR'f1/3 octave'R[Hz]50[dB]18,7, x e d ni55638010012516020025015,2