Title: 1 etg del 2.pdf
[Pair 12] [Pair 45] [Pair 45] [Pair 45]147 224 7 6.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]16.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.5 233.5 35.8 36 7.9 25.0 49.1SR 12-36 5.9 229.5 35.9 12 6.2 229.5 33.3MAIN 12-36 6.5 233.5 35.8 36 8.2 233.5 33.2SR 12-36 5.9 229.5 35.9 12 6.2 229.5 33.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 15.1 135.0 21.6 36 16.6 36.8 29.9SR 12-36 14.5 135.0 21.6 36 16.2 135.0 18.6MAIN 12-45 18.4 250.0 16.2 45 18.6 250.0 13.2SR 12-45 19.1 249.5 16.2 12 19.2 250.0 13.2010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 11.8 25.0 42.6 36 12.7 24.9 40.3