Title: 32 Pumper modbuss teknisk data.pdf.pdf
It is possible to have connection to the webserver simultaneously with a connection to a Modbus TCP master. It is possible to have connection to more Modbus TCP masters simultaneously, for example to have connection to PC Tool CIM/CIU while connected to another Modbus TCP master.3211.6 CIU 500 Modbus TCP communication setupStepAction1Check that both CIU 500 unit and the E-pump are powered off.2Remove the front cover of CIU 500.3Select position 1 at the CIM 500 module protocol rotary switch. See section 7.2 Setting the Industrial Ethernet protocol.4Connect the GENIbus cable from CIU 500 to the E-pump. See the "CIU, Communication Interface Unit installation and operating instructions" or see the CIU quick guide.5Power on CIU 500 and the E-pump, and observe LED2 turn permanently green and LED1 remaining off.6Connect one of the CIU 500 Ethernet ports (RJ45) to a PC using an Ethernet cable.7