Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]38.8 168 2 5.74Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]24.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.7 500.0 29.2 45 8.5 500.0 26.4SR 36-45 8.8 500.0 29.2 36 8.7 500.0 26.4MAIN 36-45 8.7 500.0 29.2 45 8.5 500.0 26.4SR 36-45 8.8 500.0 29.2 36 8.7 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.2 369.0 13.9 45 14.4 3.9 50.5SR 45-78 14.5 369.0 13.9 45 14.3 2.6 53.9MAIN 78-36 16.6 492.0 11.4 45 16.0 416.0 9.9SR 78-36 16.2 487.0 11.5 78 16.0 418.0 9.80100806040200250 MHzACR-F (dB)