Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]25.0 108 1 3.84Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.5 479.0 28.8 36 9.5 477.0 26.1SR 36-45 7.8 461.0 29.7 36 7.3 482.0 25.8MAIN 36-45 9.5 479.0 28.8 36 9.8 496.0 25.2SR 36-45 8.0 499.0 27.9 36 7.8 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.9 3.8 53.8 45 14.5 2.6 53.9SR 78-45 14.9 3.8 53.8 45 14.6 3.5 51.4MAIN 78-45 15.8 500.0 11.3 45 16.7 500.0 8.3SR 45-78 16.1 500.0 11.3 45 17.0 494.0 8.40100806040200250 MHzACR-F (dB)