Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
6. Compare the calculated output voltage (Step 4) and the measured output voltage (Step 5). If the measured output voltage differs greatly from the calculated output voltage, replace the transducer. It is normal for the transducer reading to differNote: somewhat from pressure gauge readings due to voltmeter and gauge tolerances, and other factors.0 VDC to 10 VDC versions To verify that the transducer is working properly:1. With the transducer in place and the controlled system pressure stabilized, measure the pressure at the transducer with an accurate and reliable gauge. This is the measured pressure (P).1. With the transducer in place and the controlled system pressure stabilized, measure the pressure at the transducer with an accurate and reliable gauge. This is the measured pressure (P).2. Determine the maximum (Pmax) and minimum (Pmin) pressure values for the transducer’s pressure range. (See Table 6.)