Title: 310-Vannmåler vannbehandling.PDF
| Water MeteringM 100i Multi-jet Meter ARTIST esens communication interface— Multi-jet wet-dial meter for cold water— Nominal size Q3 2.5 to 25 m3/h — Ultra-reliable interface for communication modules— EC type examination certiﬁ cation (MID) up to R160H/R80V— conText® marking systemPerformance characteristics acc. to MID approval for horizontal installation mm Nominal size inches Q3 m3/h m3/h Q4 l/h Q2 l/h Q1 H Q3/ Q1 Q3/ Q1 V °C MAT bar MAP m3/h barDN20 ¾25 132 1 ¼15 ½ 2.5 3.125 25 1625 1 6.3 7.875 63 394 5 40 252.5 3.125 25 1610 12,5 100 63Continuous ﬂ ow Overload ﬂ owrate Transitional ﬂ owrate Minimum ﬂ owrate Measuring rangeR160 R80 30 16Maximum water temperature Maximum working presssure Flow capacity at 1 bar pressure loss Pressure loss class Flow proﬁ le sensitivity class Climatic environment Mechanical environment Electromagnetice environment8.5 0.636.8 0.44.1 0.634.1 0.6313.1 0.63∆pU0, D0 closed spaces, 5°C to 55°C M1 E1Installation position