Title: 1 etg del 2.pdf
Wire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]21.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.8 * 249.0 35.4 36 0.8 * 245.5 32.8SR 12-36 2.8 205.5 36.7 36 4.7 245.0 32.9MAIN 36-45 0.8 249.0 35.4 36 0.8 249.0 32.7SR 12-36 3.0 230.0 35.9 36 4.7 245.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.4 185.0 18.8 36 16.7 185.0 15.8SR 36-45 16.6 185.0 18.8 36 17.5 185.5 15.8MAIN 45-36 16.5 249.5 16.2 36 17.5 234.0 13.8SR 36-45 16.8 249.5 16.2 45 18.2 249.5 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250