Title: etg u1.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 12.4 50.1 12 8.0 12.4 47.8SR 12-36 6.2 12.4 50.1 12 7.3 12.4 47.8MAIN 36-45 11.9 247.5 4.9 36 11.5 248.5 2.2SR 36-45 11.9 250.0 4.7 36 10.7 244.5 2.6010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.9 7.8 21.0SR 45 4.2 28.3 18.7MAIN 45 8.3 232.5 10.3SR 36 7.2 235.5 10.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1