Title: Kabelspesifikasjoner AutroSafe.pdf
Long parallel PowerLoop cable runs may introduce cross-talk between PowerLoops, thus it is recommended to avoid such long parallel runs. The permissible length of parallel PowerLoop cable runs will depend on the quality of the cable shield. Segregation of parallel PowerLoop cable runs by 30cm (1 feet) will increase permissible parallel length significantly. Contact Autronica for design-advice for applications with long parallel Powerloop cable runs.Maximum resistance (Ω) / capacitance (F) Maximum loop resistance depends on load.