Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 78] [Pair 45] [Pair 45] [Pair 45]35.5 155 3 5.34Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]25.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.1 473.0 29.8 45 7.9 472.0 26.9SR 36-45 8.6 499.0 29.3 36 9.2 476.0 26.9MAIN 36-45 8.2 496.0 29.3 45 8.0 496.0 26.5SR 36-45 8.6 499.0 29.3 36 9.3 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.3 435.0 12.5 45 14.5 2.5 54.3SR 78-45 15.1 435.0 12.5 45 14.4 2.6 53.9MAIN 78-45 15.7 500.0 11.3 45 16.1 487.0 8.5SR 45-78 15.9 495.0 11.3 78 16.2 493.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.1 49.8 34.5 45 21.2 42.8 34.0