Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
Table 23: Location and environmental requirements Ambient temperature range Recommended operating range Maximum relative humidity Maximum altitude0-30°C (5-40°C for converter) 20-25°C 95 %, non-condensing 2,000 mThe total cooling requirements must be calculated considering: • Cooling requirements for each battery rack according to Table 24 • Cooling requirements for each PCS according to Table 25Table 24: Cooling requirements for battery rackBattery technologyGEN 1 GEN 2 GEN 3 GEN 4Maximum initial cooling requirement per battery rack at 1C (kW) 25 % load 0.15 0.15 0.16 0.2350 % load 0.29 0.31 0.34 0.6175 % load 0.52 0.56 0.64 1.25100 % load 0.84 0.92 1.05 2.14Table 25: Cooling requirements for PCS MediumxStorage PCS 50 Medium xStorage PCS 100 Medium xStorage PCS 150 Medium0.81.72.5Maximum cooling requirement per PCS (kW) 1.71.22.32.33.44.53.55.06.7xStorage PCS 200 Medium2.54.26.39.5