Title: Simployer - Data testrapport =514.204-FS001.pdf
[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]48.9 251 18 8.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]21.2 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 9.9 242.0 33.4 4,5 11.0 46.0 42.9SR 3,6-4,5 7.4 90.5 40.7 1,2 8.4 220.0 31.1MAIN 1,2-3,6 9.9 242.0 33.4 3,6 12.1 242.0 30.4SR 1,2-7,8 8.2 248.5 33.2 1,2 8.8 248.5 30.2PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 16.4 5.0 49.3 4,5 17.5 151.0 16.7SR 7,8-4,5 16.3 5.3 48.9 4,5 17.6 5.0 46.3MAIN 1,2-4,5 18.4 225.5 16.2 4,5 20.9 248.0 12.4SR 1,2-4,5 19.1 226.0 16.2 4,5 21.0 250.0 12.3PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 11.7 4.0 58.9 3,6 13.0 4.0 56.4SR 3,6-4,5 10.9 4.0 58.9 4,5 12.4 4.0 56.4