Title: økernvn 94.pdf
227 359 25 10.0227 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.1 240.0 35.6 36 1.2 243.0 32.9SR 36-450.8 *246.0 35.5 36 1.2 246.0 32.8MAIN 36-45 1.1 249.0 35.4 36 1.2 246.0 32.8SR 36-45 0.8 246.0 35.5 36 1.2 246.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 9.5 240.0 16.6 36 12.3 240.0 13.6SR 45-36 9.7 249.0 16.3 45 12.1 240.0 13.6MAIN 45-36 9.5 247.5 16.3 36 12.4 247.5 13.3SR 45-36 9.7 249.0 16.3 45 12.1 245.0 13.4010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz