Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
27.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.2 500.0 29.2 36 6.8 500.0 26.4SR 36-45 6.9 499.0 29.3 36 7.2 500.0 26.4MAIN 12-36 7.2 500.0 29.2 36 6.8 500.0 26.4SR 36-45 6.9 499.0 29.3 36 7.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.6 451.0 12.2 45 21.4 500.0 8.3SR 45-78 20.8 451.0 12.2 45 20.9 500.0 8.3MAIN 78-45 20.8 458.0 12.0 45 21.4 500.0 8.3SR 45-78 20.9 454.0 12.1 45 20.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.7 49.0 34.7 45 20.8 49.0 32.2SR 36-45 21.8 49.3 34.6 45 23.3 49.3 32.1MAIN 12-36 34.9 500.0 -12.4 36 34.6 500.0 -15.3SR 36-45 34.6 499.0 -12.3 36 35.0 500.0 -15.30804000250 MHzACR-N (dB)