Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]24.3 105 1 3.70Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.6 455.0 30.0 36 8.6 456.0 27.1SR 12-45 9.1 477.0 28.9 36 8.9 465.0 26.7MAIN 36-45 10.1 493.0 28.2 36 9.4 500.0 25.0SR 12-45 9.1 477.0 28.9 36 9.4 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.9 3.8 53.8 45 14.2 3.3 52.0SR 36-45 14.9 3.8 53.8 45 14.2 2.9 53.1MAIN 36-45 17.2 477.0 11.7 45 18.4 496.0 8.3SR 45-36 17.4 477.0 11.7 45 18.8 500.0 8.30100806040200250 MHzACR-F (dB)