Title: +038=320.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Nettserverhåndbok.pdf
directly a certain power output at the exchanger. The valve works temperature- and pressure - independento Control signal range  0.5 – 10 VDC  2 – 10 VDC o Invert control signal no: no inversion → 0V = valve closed / 10V = valve open  yes: inversion → 10V = valve closed / 0V = valve openo Control signal characteristics equal percentage: equal-percentage characteristic curve   This selection is not available when 'Power control' is selected. For power controllinear: linear characteristic curvethe characteristic is always linearSettings – Delta-T- ManagerThis function can be used in order to prevent an increase in the volumetric flow when levels fail to reach a set supply/return differential temperature.  The valve will not be openedfurther in such cases, even with an increasing control signalLimitation functiono -: Delta-T limitation switched off o Delta-T- Manager: Simple Delta-T limitation switched