Title: 91290FDV Campus F13 433.04 West elektro.pdf
Designated Use • The astronomical time switch is used for lighting equipment (roads, external stair- cases, shop windows, entrances etc.)ENFor use only in closed, dry rooms ! Do not use on safety devices, e.g. escape route doors, fi re safety equipment etc. Installation ¾ Install on DIN top hat rails (in accordancewith EN 60715)¾ Disconnect power source ¾ Strip cable by 8 mm (max. 9 mm) ¾ Insert cable at 45° in the open terminal ¾ Only with ﬂ exible wires: Press screwdriverdownwards to open spring terminalDisconnecting the cable ¾ Use the screwdriver to push the load lineconnection opener downwards Connection ¾ Note connection diagramCorrect connection required for smooth zero- cross switching operation Initial start-upYou have two options for the initial start-up: 1. Set language, country, town/city, date, timeas well as summer/winter time (SO-WI)2. Set language, coordinates, date, time as well as summer/winter time (SO-WI)