Title: +038=433.002-FS058._04-Eaton Tavlebyggeren Produktblad.pdf
Rated impulse withstand voltage UimpkV4Rated short-circuit breaking capacity Icn EN 60898 at 230 VkA10Rated short-circuit breaking capacity Icn EN 60898 at 400 VkA10Rated short-circuit breaking capacity Icu IEC 60947-2 at 230 VkA15Rated short-circuit breaking capacity Icu IEC 60947-2 at 400 VkA15Voltage typeACFrequencyHz50 - 60Current limiting class3Suitable for ﬂush-mounted installationNoConcurrently switching N-neutralYesOver voltage category3Pollution degree2Additional equipment possibleYesWidth in number of modular spacings4Built-in depthmm70.5Degree of protection (IP)IP20Ambient temperature during operating°C25 - 75Connectable conductor cross section multi-wiredmm²1 - 25Connectable conductor cross section solid-coremm²1 - 2503/07/2019Eaton 279067 ED2019 V53.0 EN2 / 8Characteristics2 t Let-through energy I According to IEC/EN 6089803/07/2019Eaton 279067 ED2019 V53.0 EN3 / 803/07/2019