Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 11:41RCD II: 28.5mAUci: 0.1V t: 105.3ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 11:43Tallberg Elektro A/S Tlf.22796640Side:7GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.4949505051515252535354545555TEST RAPPORTResultatZ-LINEZ: 0.59ΩIsc: 387A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 11:43Zs(rcd)Z: 0.53ΩIsc: 438A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 11:43RCD tt: 61.6msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 11:43RCD UbUc: 0.0V Rl: 2Ω Idn: 30mA type: AC Ulim: 25V