Title: +038=453.003-LZ001. Defrost Snow Nexans leggeanvisning.pdf
DEFROST SNOW The heating cable has a linear ouput of 28 W/m and is preferably attached to the surface with a C-C distance of 10 to 8 cm (distance between cable loops), resulting in an area output ranging from 280 to 350W/m².Theheatingcablecanbeheldinplacebyusingattach- ment bands or cable ties. It is also possible to attach the heating cable element to reinforcement bars, preferably along longitudinal bars.Applicable for both products Always measure insulation and conductor resistance before and imme- diately after covering the cables. If there are diverting values from the nominal value, the product should be replaced or repaired. The product shall be supplied via a ground fault interrupter (GFCI/RCD).If you are installing more than three products remember to separate the cold leads from each other. A maximum of three cold leads can be put next to each other.