Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Scale: 1:75The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 67Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 ZSite 1/ Building 1/ Storey 10 / Toilet 1 / Room summaryToilet 1Clearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Toilet 1) Perpendicular illuminance (adaptive) [Ix] 279 (= 200) 264 287 0.95 0.92 Height: 0.000 m, Wall zone: 0.200 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 1 iGuzzini illuminazione - Q510 Laser Blade XS - Downlight HC 23.1W 1452 231 62.9 Total via all luminaires 1452 231 62.9Lighting power density: 12.31 W/m? (Floor area of room 1.88 m? ), Lighting power density: 24.58 W/m? = 8.80 W/m2/100 Ix (Area of working plane 0.94 m?)Consumption: 19 kWh/a of maximum 100 kWh/a