Title: +038=360.012-#####._06-BA-ESR NI-DV Controller Nicotra Gebhardt - Operating Instruction.pdf
Product name NI-DV-1005 NI-DV-1007 NI-DV-1011 NI-DV-3016 NI-DV-3024 NI-DV-3030 NI-DV-3040 NI-DV-3055 NI-DV-3065 NI-DV-3075 NI-DV-3110 NI-DV-3150 Table 2-1 All 3x400V versions can also be connected to 3x230V. The power output (kW) will, however, be limited to max. 58% (1/√3) of the rated power output at 3x400V.CautionWith enclosure sizes H3 ... H5, NI-DV operating and motor parameters are set for connection to a supply voltage of 3x400V. If these types are connected to a 3x230V power supply, operating and motor parameters must therefore be changed for optimum operation. Motor parameters can be changed by the installer via the hand terminal (OJ- DV Hterm), OJ-Drives-Tool or OJ-DV PCTool. Configuration parameters can only be changed by the manufacturer.DE-6/36BA-ESR_NI-DV 1.0 – 11/2015English2.10. Rating plateNI-DV is equipped with a silver-coloured rating plate. See the example in fig. 2-1 and explanation in table 2-2. Check that the information specified on the rating plate is as expected.