Title: +038=370.001-RD001._01-Siemens Differanstrykk væske QBE3000-D6.pdf
Printed circuit board · Pressure connections G⅛“, external threaded with unscrewed fittings for copper pipe, 6 mm diameterFixing bracket, enclosed loose, with sensor · Plug DIN 175301-803-A unattachedDifferential Pressure Sensor QBE3000-D.. / QBE3100-D..CE1N1922en 2018-11-19AccessoriesInstructionsMountingRecommended measuresImportant noteRemote mountingSiemens Building TechnologiesAQB2002 Mounting kit for remote mounting with 1 mcopper capillary line, both ends prefabri- cated ready for connection. Thread adapters and terminal nuts made of brass. Pressure connection with G⅛“ or G½“ outer threading.Mounting instructions are enclosed with the differential pressure sensor.It can be connected directly with G1/8" screwed fittings. Special precautions must be taken on site when mounting the sensors to ensure airtight screw connections.