Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
power requirement: -during spring tensioning -during sustaining3 W5 W2,5 Wsizing (apparent power)6,5 VA5,5 VAprotection classIIIIIprotection degreeIP 54auxiliary switch:point of activation250 VAC /5,0 (2,5) A 5(cid:176) , 80(cid:176)torque: - motor5 Nmspring4 Nmrotation angle100˚ (-5˚...+95˚)cable connection:actuator (length. 0,9 m)auxiliary switch0,75 mm2 0,75 mm2running time : (90°C)motor< 40-75 sreturn spring< 20 sambient temperature30˚C...+50°CTechnical data239-024-20-S2 (239TA-024-20-S2) 239-230-20-S2 (239TA-230-20-S2)Supply24 VAC (50/60Hz) ± 20%230 VAC (50/60 Hz) ± 15%power requirement: -during spring tensioning -during sustaining6,5 W9,0 Wsizing (apparent power)8,5 VA10,0 VAprotection classIIIIIprotection degreeIP 54auxiliary switch:250 VAC /5,0 (2,5) Apoint of activation5°, 80°torque: - motor20 Nmspring15 Nmrotation angle100˚ (-5˚...+95˚)cable connection:actuator (length. 0,9 m)