Title: Hardware Installation Guide.pdf
Primary power: - - - -12 to 24 VDC + 10% 12 VDC @ 700 mA (includes reader current) nominal 24 VDC@ 350 mA (includes reader current) nominal 28.7 BTU/hourOutputs: Form-C contacts: Relay 1 and 2 (K1 and K2): 5 A @ 30 VDCInputs: - -Two (2) supervised, End of Line resistors, 1k/1k ohm, 1% 1/4 watt standard One (1) unsupervised, dedicated for external (cabinet) tamperReader Interface: -Reader power: voltage 12 VDC +/-10% (optional 5 VDC +/-5% jumper selectable, current 400 mA maximum to 50°C, derate to 300 mA for 70°C) Reader LED output: open collector type switching (sinking) 10 mA each Buzzer output: open collector type switching (sinking) 10 mA each Reader data inputs: 2-wire RS-485, Wiegand, Clock and Data Does not support Bioscrypt readers or the LNL-CK keypad- - -Upstream communication: RS-485, 2-wire. 2400 to 38400 bps -Does not support encryptionDownstream communication: Does not support RS-485 -- -Cable requirements: - -