Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
The circular panel is by default available in exposedFor the recessed installation of the circular panelinstallation.Make inspection holes on the ceiling for easier installation and maintenance, as shown in the following table. (The size of an inspection hole must be at least 450 mm x 450 mm.)Inspection holeRefrigerant pipe1050883A suspended ceiling structure can substitute for theinspection holes.Inspection holeCategoryRecessed installationIntegratedsuspendedExposed installationSquare panel1 eaCircular panel2 eaIndoor unit displayConnection part of the drain hoseø1010 to 1020Inspection holeCeiling opening diameter ø1010 to 1020NOTEThe clearance between the panel and the inspection hole is 15 to 20 mm on a side.I n s t a l l a t i o n P r o c e d u r eSpacing requirementsAA'C' mmIndoor unitA2500 mm or more10 mmA20 mm1500 mm or moreObstructionA : 1500 mm or more(Unit: mm)ModelAC071KN4DKHAC090KN4DKHAC100KN4DKH