Title: økernvn 94.pdf
MAIN 12-36 10.3 32.0 39.7 12 11.9 22.4 41.5SR 12-36 9.0 32.0 39.7 12 11.1 31.8 37.3MAIN 36-45 16.9 249.5 4.7 36 16.8 249.5 2.1SR 36-45 17.0 249.5 4.7 36 16.2 247.5 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.7 12.8 20.5SR 45 3.2 12.8 20.5MAIN 36 6.4 236.5 10.3SR 36 6.4 226.0 10.5010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94