Title: Sprinklerhode stående_hengende.pdf
The recessed version of the Series TY-FRB Pendent Sprinkler, where applicable, is intended for use in areas with a finished ceiling. This recessedThe owner is responsible for main- taining their fire protection system and devices in proper operating con- dition. Contact the installing contrac- tor or product manufacturer with any questions. Sprinkler Identification Number (SIN) TY313     Upright 56K, 1/2 in NPT TY323    Pendent 56K, 1/2 in NPT Technical Data Approvals Refer to Table ADischarge Coefficient K=5.6 GPM/psi½ (80,6 LPM/bar½)Temperature Rating Refer to Table AFinishes Sprinkler: Refer to Table BRecessed Escutcheon: White Coated, Black Coated, Chrome Plated, or Brass Plated