Title: Samsvar Hea5.pdf
il 4 ¢ ityL=e S = W4 ] iI YyL.05.10.21Clearance height: 2.600 m, Reflection faclors: Ceiling 70.0%, Walls 48.4%, Floor 20.0%, Light loss factor: 0.80EN 124641Surface Result1 Visual task area 7 Perpendicular illuminance (adaptive) [Ix] |539 (= 500) Surrounding area: 0.500 m2 Surrounding area 7 Perpendicular illuminance (adaptive) [Ix] |463 (z 300)3 Background area 6 Perpendicular illuminance (adaptive) [Ix] |333 (= 100) Wall zone: 0.500 mAverage (Target) Min Max Min/average Min/max388 615 0.72 0.63261 619 0.56 0.42220 409 0.66 0.54@ ELECTRONOVADronning Mauds gate 1-3 BREEAM HEA 5 - Interne og eksterne lysnivaer 05.10.21Oversikt over krav til belysning - Utdrag fra tabell 1B - Lyskultur/ NS EN 12464-2011, 5.1