Title: Aggregatkjøring.pdf.pdf
Motor protectionTotal power(2 x 3.50 kW) 7.00kWSpeed (nominal)1950RPMSystemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.002-3/Unit no. 20Date 18.06.2021Page 31/40Total current, Amp.(2 x 5.60 A) 11.20AVoltage3x400VConsumed power from mains power supply, including speed control3.16kWHeating coil, FluidAir flow14400m³/hPressure drop19PaAir temperature before/after13.7/21.0°CAir relative humidity before/after61/38%Capacity34.99kWFace velocity2.11m/sFluid typeWaterFluid temperature inlet/outlet40.0/25.0°CFluid flow rate0.57l/sFluid pressure drop8.9kPaFluid velocity0.48m/sCoil volume17.5Connection sideService sideConnection size inlet/outlet1 1/4" / 1 1/4"Tube materialCuFin materialAl