Title: 360.002 - Avtrekk.pdf
4k [dB]34.60.0 +10.434.624.010.60.1 +10.413.513.521.621.60.0 +21.324.5+8.324.60.0 +21.326.31.5 +3.23.021.80.0 +17.68k [dB]24.80.0 +3.424.914.010.90.1 +3.411.511.514.714.70.0 +14.317.5+5.517.80.0 +14.319.41.5 +0.03.014.90.0 +10.6Lp [dB]27,9LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeProductSizeFIREDAMPER FKR-EU/DE/400/400DUCT40049 T-BRANCHTCPU_DK-*-*0,0 400/315DUCT315BEND-30MAGIB-C4-*-*315DUCT315178 T-BRANCHTCPU_DK-*-*0,0 315/250DUCT250BEND-90MAGIB-C4-*-*250DUCT250L [m]0,20,10,60,51,2Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]18504,12,6 Sound in:Addition:18504,10,1 Sound in:Attenuation: Addition:18504,17,2 Sound in:Attenuation: Addition:Dividing:10003,60,0 Sound in:Attenuation: Addition:10003,60,9 Sound in: