Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 8.8 332.0 8.8SR 12 7.1 493.0 8.0MAIN 45 8.8 452.0 8.0SR 12 7.1 493.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00432.3 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1