Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
5x pressure rangeVacuum30 microns (0.03 mm Hg); short termMedia compatibilityAll media compatible with 17-4PH stainless steel, including ammoniaOutput signal0.5 VDC to 4.5 VDC, 0 VDC to 10 VDC, or 4 mA to 20 mAP499 Series Electronic Pressure Transducers Product/Technical Bulletin9P499 Series Electronic Pressure Transducers (Part 2 of 2 )Supply voltage0.5 VDC to 4.5 VDC ratiometric output5.0 ±0.25 VDC, Safety Extra-Low Voltage (SELV) or Class 24 mA to 20 mA output9 VDC to 30 VDC, SELV or Class 20 VDC to 10 VDC output12 VDC to 30 VDC, SELV or Class 2Direct-mount pressure connections1/8in. -27 NPT External Thread (Style 49), 1/4 in. SAE 45 Flare Internal Thread (7/16-20 UNF) with Depressor (Style 47)Temperature and humidityStorageOperating40F to 257F (-40C to 125C)40F to 185F (-40C to 85C)Compensated range4 toF 185F (-20C to 85C)Humidity0 to 100% RHLinearity±0.25% Full Span Best Fit Straight LineAccuracy