Title: TFP340_03_2007.pdf
The 11.2 K-factor, Model ELO-231 (TY5111, TY5211 & TY5811) Sprin- klers are to be installed in accordance with NFPA 13 standard sprinkler posi- tion and area/density flow calculation requirements for light, ordinary, or ex- tra hazard occupancies, as well as high piled storage occupancies (solid piled, palletized, rack storage, bin box, and shelf storage including but not lim- ited to Class I-IV and Group A plastics) with a minimum residual (flowing) pressure of 7 psi (0,5 bar) for wet or dry pipe systems.Finishes Refer to Table AFM Approval RequirementsPhysical Characteristics Frame . . . . . . . . . . . . . Bronze Seal Disc . . . . . . . . . . Copper Cap . . . . . . . . . . . . . . Bronze Strut Assembly . . . Solder, Bronze, . . . . . . . . . . . . Stainless Steel Compression Screw . . . . . Bronze Deflector . . . . . . . . . . . . Bronze Helper Spring . . . . Stainless Steel Ejector Spring . . . . . . . . . Nickel Strut Clip . . . . . . Stainless Steel