Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Technical dataNumber of outputs:3 + 3 make contacts with common terminalType of relay (typical):RE 030024, SCHRACKSwitching capacity: (contact lifetime)2 A, 250 VAC AC1 1 A, 250 VAC AC11 2 A, 50 VDC DC11 1 A, 24 VDC DC110.7 × 106 operations 1.0 × 106 operations 0.3 × 106 operations 3) 0.1 × 106 operations 1)3)Relay coil supply: 2)Voltage tolerance, dependent on ambient temperature:nominal 24 VDC smoothed or pulsed, 8 mA per relay coil 20 °C: 17.0 … 35 VDC 30 °C: 19.5 … 35 VDC 40 °C: 20.5 … 32 VDC 50 °C: 21.5 … 30 VDCOutput delay:typically 5 ms at 24 VDCResistance to interference: acc. to IEC 801-4 Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption:4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 1 … 20 mA typically 10 mA 0 mAmax. 48 mATerminals:Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²