Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-45 15.4 498.0 11.3 45 16.5 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.2 45.3 35.7 45 21.1 45.5 33.2SR 36-45 19.6 45.3 35.7 45 21.1 45.3 33.2MAIN 36-45 36.1 494.0 -12.0 36 36.2 500.0 -15.3SR 12-45 36.1 499.0 -12.3 36 36.4 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.7 478.0 8.0SR 12 7.2 492.0 8.0MAIN 45 6.7 478.0 8.0SR 12 7.2 492.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00433.2 m60Insertion Loss (dB)504030201000250 MHz500