Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
4. Use the equation in Figure 7 to determine the calculated output voltage for the ratiometric transducer. P - (P )min) ](s [V = V 0.1 + 0.8VDCoV = Calculated Output Voltage V = Measured Supply Voltage P = Measured Pressure P = Maximum Pressure Value P = Minimum Pressure Valueo smax minc i r t e m o i t a r _ l d i :G I F4. Measure the voltage between the transducer Output (white) wire and Common (black) wire with a multimeter set to measure DC voltage. (See Figure 3.) This is the measured output voltage.4. Measure the voltage between the transducer Output (white) wire and Common (black) wire with a multimeter set to measure DC voltage. (See Figure 3.) This is the measured output voltage.5. Compare the calculated output voltage (Step 3) and the measured output voltage (Step 4). If the measured output voltage differs greatly from the calculated output voltage, replace the transducer. It is normal for the transducer reading to differ