Title: DOCA0005EN-12.pdf
NOTE: only applies to the iEM3265 / iEM3465 / iEM3565113114Communications via BACnetiEM3000 series user manualObject ID Units Default COVObject name / descriptionFor iEM32 65, the unit is A,54For iEM34 65, the unit is mV,1AI54 - CT SecondaryNOTE: only applies to the iEM3265 / iEM3465 / iEM3565For iEM35 65, the unit is uV/kA/ HzAI55 - VT connection type55—10 = Direct connection, not VTs1 = 3PH3W (2VTs)2 = 3PH4W (3VTs)Communications settings informationThe following AI objects display information about the meter’s communications settings.NOTE: You can access the meter’s communications configuration information over BACnet communications. However, you must use the front panel to configure the meter’s settings.Object ID Units Default COVObject name / description00—1AI00 - BACnet MAC Address01—1AI01 - BACnet Baud RateDigital input and output setting informationThe following AI objects display information about the meter’s I/O settings.