Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
0,5/16,380,5/18,80,6/20,5Low pressure11,412,513,212,613,614Maximum water type heat exchanger flow rate with low pressure hydraulic module (l/s)High pressure11,712,412,913,814,414,7(1) Maximum flow rate for a pressure drop of 100 kPa in the plate heat exchanger (2) Maximum flow rate for a machine operating pressure of 20 kPa (unit with low pressure pump) or 50 kPa (high pressure pump).2021Operating range DYNACIAT units have a broad field of application, enabling them to meet a range of heating and cooling requirements in the most varied of climates.Multi-application: air conditioning, heating, industrial processesThe DYNACIAT can be used for all traditional heating and air conditioning applications in sectors as varied as collective housing, hotels, shopping centres and offices.■ Water chiller operating limits - LG heat pump Cooling mode Production of chilled water from -12°C (with low temperature brine option) to +20°C.Heating mode