Title: EDM_AQAR32_01-S-2GB.pdf
Water volume Antifreeze heater COIL Number Frontal surface Number of rows FAN NumberSTDECHPFWater flow Water pressure drop Water flow Water pressure dropAir flow Rotational speed Power input each fan Air flow Rotational speed Power input each fan Air flow Rotational speed Power input each fan Static pressurem³/h kPa m³/h kPa l W1 / Plate 8.7 31.8 9.3 36.3 6.0 30m21 4.2 21m³/h 21 200 Rpm 870 2.1 kW m³/h 21 200 Rpm 780 kW 1.1 m³/h 21 200 Rpm 940 1.60 kW 85 Pa10.6 46.7 10.7 48.1 6.0 301 4.2 21 21 200 870 2.1 21 200 780 1.1 21 200 940 1.60 8512.2 33.0 12.5 34.4 8.4 2 x 302 5.6 22 30 000 690 1.0 30 000 620 0.6 30 000 940 1.90 18013.2 38.2 13.9 42.8 8.4 2 x 302 5.6 22 30 000 690 1.0 30 000 620 0.6 30 000 940 1.90 180WATER CONNECTIONSEvaporatorDesuperheaterType Inlet diameter Outlet diameter Type Inlet diameter Outlet diameterinch inchinch inchMale gas threaded 2'' 2'' Male gas threaded 1''1/4 1''1/42'' 2''1''1/4 1''1/42'' 2''1''1/4 1''1/42'' 2''