Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 23,1 10,2 12,9 500,00Remote: 12-45 23,2 10,2 13,0 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 30,9 27,4 3,5 392,00Remote: 36 28,5 23,8 4,7 499,00Worst Value: Local: 36 27,6 23,8 3,8 500,00Remote: 36 28,5 23,8 4,7 499,00PS-ACRF: Pass Worst Margin: Local: 12 66,0 54,3 11,7 2,20Worst Value: Local: 45 20,5 7,2 13,3 500,00Remote: 36 72,4 61,2 11,2 1,00Remote: 12 20,6 7,2 13,4 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:10Signature:______________________ Page: 108Copper Certification ReportCable Label: 521.002-UD-101 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:39:51 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: