Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]24.6 106 1 3.77Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.3 418.0 30.9 45 8.5 442.0 27.6SR 12-45 9.8 467.0 29.4 45 10.1 466.0 26.6MAIN 12-45 10.2 500.0 27.8 36 9.6 490.0 25.5SR 12-45 9.8 467.0 29.4 36 10.8 491.0 25.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.4 3.9 53.5 45 14.7 2.9 53.1SR 78-45 15.4 3.9 53.5 45 14.6 2.4 54.7MAIN 36-45 15.9 477.0 11.7 45 16.8 492.0 8.4SR 45-36 16.2 477.0 11.7 45 17.7 498.0 8.30100806040200250 MHzACR-F (dB)