Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 36-78 15.7 415.0 12.9 45 15.0 17.8 37.3SR 78-36 15.7 415.0 12.9 45 14.9 8.9 43.3MAIN 36-78 16.0 429.0 12.6 78 16.2 415.0 9.9SR 78-36 15.9 429.0 12.6 45 16.4 416.0 9.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.9 31.8 40.1 12 18.4 31.8 37.7SR 12-36 23.3 31.0 40.4 36 22.4 30.8 38.1MAIN 12-45 31.0 498.0 -12.3 45 31.3 500.0 -15.3SR 36-45 31.4 500.0 -12.4 36 31.9 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.0 500.0 8.0SR 12 6.0 500.0 8.0MAIN 12 6.0 500.0 8.0SR 12 6.0 500.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS