Title: 91290FDV Campus F13 433.04 West elektro.pdf
Rated operational voltageOvervoltage category/pollution degreeRated insulation voltageUse in unearthed supply systemsSwitching capacity Rated short-circuit making capacity240 V400/415 V440 V 50/60 Hz525 V 50/60 Hz690 V 50/60 HRated short-circuit breaking capacity Icn07/23/2019In = IuAUimpVVUeV ACUeV DCUiVVIcmIcmkAIcmkAIcmkAIcmkAIckAIcnEaton 110283 ED2019 V58.0 ENWith XFI earth-fault release: - NZM1, N1, NZM2, N2: vertical and 90° in all directions with plug-in unit - NZM1, N1, NZM2, N2: vertical, 90° right/left with withdrawable unit: - NZM3, N3: vertical, 90° right/left - NZM4, N4: vertical with remote operator: - NZM2, N(S)2, NZM3, N(S)3, NZM4, N(S)4: vertical and 90° in all directionsas requiredIn the operating controls area: IP20 (basic degree of protection)With insulating surround: IP40 With door coupling rotary handle: IP66Tunnel terminal: IP10 Phase isolator and strip terminal: IP00Temperature dependency, Derating160