Title: 40 Bender brukermanual.pdf.pdf
6.6.7.3 This function enables you to test communication between the RCMS… and other BMS equipment. To do this, the RCMS… sends an alarm message via the BMS bus until the "Test communication“ function is exited. A connected evaluating device (COM460IP, CP700, MK2430, MK800, TM…) must indicate this alarm.Channel disabledExit 1.Chan.: --74RCMS460-490_D00067_03_M_XXEN/12.20171. Use the  button to go to the measuring channel setting. Press the "↵" button.2. Use the Up/Down buttons to select a measuring channel. Press "↵" to confirm your selection. An alarm message is sent to the BMS bus. This is indicated by the alarm display . Depending on the function set for the measuring channel, an alarm (residual current, overcurrent, undercurrent) is output or a digital input is indicated.