Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
2,85,250603/4"1"2,54,550503/4"1"Travel time:Max. glycol content of water:approx. 3 min.50%Auxiliary04-14-24-26-34-3644-54-56-64-662,8503/4"2,5503/4"Valves pressure dropmaximum pressure difference for valve to close Note: 3 way valves with simplified kit and 1” connection have conical seal. ** external thread, flat sealmaximum pressure difference for valve to close Note: 3 way valves with simplified kit and 1” connection have conical seal. ** external thread, flat seal∆p - kPaValve set, 2 or 3 ways, ON-OFF, with thermoelectric actuator. The set includes connection pipes.Note: The main battery lockshield valve connectionis 1/2” female (Kvs 2) for SK0 - SK1 - SK2 - SK3 sizes and 3/4” female (Kvs 3,5) for SK4 - SK5 - SK6 sizes, the auxiliary battery valve connection is 1/2” female (Kvs 2).Note: The maximum pressure drop accrossthe fully open valve should not exceed 25 kPa for cooling operation and 15 kPa for heating operation.Water flow (l/h)15