Title: Luftport - frico_ar3500-no.pdf
Pressure drop [kPa] - 6,0 - 3,0 - 7,0Water temperature: 55/35 °C Room temperature: +18 °COutput *2[kW] 6,9 4,5 10,2 6,6 15,0 9,7Outlet air temp. [°C] 28,3 31,4 28,8 32,0 29,1 32,4Water flow [l/s] 0,08 0,06 0,12 0,08 0,18 0,12Pressure drop [kPa] 3,0 1,0 2,0 1,0 6,0 3,013Output charts water AR3500AR3500WLL Special coilTypeFan positionAR3510WLL max min AR3515WLL max min AR3520WLL max minAirflow[m3/h] 1900 950 2600 1300 3800 1900Supply water temperature:55 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 Output Return water Water temp. flow [°C] [l/s] 0,08 26,8 0,03 23,4 0,10 25,1 0,04 22,1 0,15 25,5 0,07 22,3[kW] 9,0 4,5 12,3 6,1 18,0 9,0Pressure drop [kPa] 1,0 0,3 1,0 0,3 1,0 0,4Water temperature: 55/35 °C Room temperature: +18 °COutput *2[kW] 12,5 7,6 18,4 11,0 26,4 15,8Outlet air temp. [°C] 37,5 41,6 39,0 43,0 38,6 42,6Water flow [l/s] 0,15 0,09 0,22 0,13 0,32 0,19Pressure drop [kPa] 3,0 1,0 4,0 2,0 4,0 2,0TypeFan position