Title: 563-Beckhoff-buskobler BK1150.pdf
The BK1150 "Compact" Bus Coupler works in an identical way to the BK1120 and supplements this series with an inexpensive DIN rail mounting coupler. The IP 20 housing of the BK1150 is around 5 mm narrower than that of the BK1120.The Bus Terminals on the BK1150 can be parameterised via ADS by the KS2000 software; the KS2000 plug is omitted. Alternatively, the controller (PLC, IPC) can configure the Bus Terminals via PLC function blocks.System dataEtherCAT | BK1150Number of I/O stations65,535Number of I/O pointsdepending on controllerData transfer mediumIndustrial Ethernet cable, screened, min. CAT 5Max. cable length100 m (100BASE-TX)Data transfer rates100 MbaudData transfer timetyp. 0.01 ms in the case of 10 modules for 32 bit inputs and outputs each (without K-bus run-time)Technical dataBK1150Number of Bus Terminals64 (255 with K-bus extension)Max. number of bytes fieldbus1,024 byte input and 1,024 byte outputConfiguration possibilityvia KS2000 or EtherCAT (ADS)