Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
xx7 and RIOs: the firmware reads in the values according to the configuration (I/O Builder or network configurator).Watchdog: This module can interact with the watchdog, if it is used on base address 240. In this case, the last input with address 255 cannot be used. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD3 components.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-53Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W2x0Temperature measurement with Pt 1000In the temperature range -50 °C to +200 °C, the following formulae can be used for working to an accuracy of ± 1 % (± 1.5 °C). Repeating accuracy is significantly higher.T[° C]=DV 2.08 - (0.509 • 10-³ • DV)261.8T = temperature in ° CDV = digital value (0 … 1023)Example 1: digital value DV = 562temperature T in °C?6T[° C]=562 2.08 - (0.509 • 10-³ • 562)261,8= 51.5 °CDV =