Title: økernvn 94.pdf
MAIN 12-36 7.8 18.1 46.2 12 9.6 18.1 43.8SR 12-36 7.6 18.1 46.2 12 9.4 18.1 43.8MAIN 36-45 14.8 250.0 4.7 36 14.3 250.0 2.0SR 36-45 14.7 250.0 4.7 36 14.4 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.3 19.8 19.5SR 36 4.3 24.9 19.0MAIN 45 8.5 249.0 10.0SR 45 7.9 232.0 10.3010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94