Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
Leading off condensation water Outdoor air is cooled in the evaporator by approximately 5–10 °C. The water vapour then condenses on the evaporator coil fins. If the air humidity is high this can result in many litres of water per hour. To counter this, there are several drainage holes in the base plate to lead off the water. It is important to consider the position of the unit so that the condense water can be led off correctly.!Do not confuse condense water for water leakage!Pipe connectionThe pool heat pump is connected to the pool’s circulation system with the help of the supplied 50 mm union couplings. Screw connections to the heat exchanger must be tightened by hand.A bypass connection should be fitted for easier setting of the correct partial flow to the pool heat pump, as well as to facilitate servicing.Bypass coupling We recommend that a bypass coupling is fitted to all installations in order to adjust the right partial flow to the pool heat pump.