Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uln: 235V Ulpe: 235V Unpe: 0V f: 49.9HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF086 16C2/003 26.11.2020 14:01Z-LINEZ: 0.58ΩIsc: 396A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF086 16C2/003 26.11.2020 14:01Tallberg Elektro A/S Tlf.22796640Side:37GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.256256257257258258259259260260261261262262TEST RAPPORTResultatZs(rcd)Z: 0.58ΩIsc: 396A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF086 16C2/003 26.11.2020 14:03RCD II: 28.5mAUci: 0.3V t: 24.9ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF086 16C2/003 27.11.2020 11:41R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF086 16C2/003 27.11.2020 11:41KONTINUITET R: 0.3ΩGrenseverdi: 0.7Ω