Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
1 x pluggable 4-pole cage clamp terminal block (4 405 5027 0), for wires up to 2.5 mm², or as above with 4 grouped strands, numbered, 2.5 m long (PCD3.K860)Sensor inputs:1 x pluggable 6-pole cage clamp terminal block (4 405 5028 0), for wires up to 1.0 mm², or as above with 6 grouped strands, numbered, 2.5 m long (PCD3.K861)6-47PCD3.A860LEDs and connection terminalsI ØO ØI 1O 11 A1 ADescription- labelA8 6 06 4 25 3 10 6 8 A . 3 D C PC A V 0 5 2 A 2 1. t u o2 / . p ni2TerminalsPin 1 in frontControl elementsImpulseswitch:The switches can be used to activate the two inputs manually. The keys have the same effect as the external inputs.A = Rest position; the module works via the inputs and via the FBox for the relevant function. 1 = Switch on manually (impulse only)LEDs:The LEDs (red) display the state of the inputs/outputs. I Ø + I 1 are also used to display the Uext error. If Uext is not connected, the two input LEDs flash together.