Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
2 wire shielded cable Proper section (minimum 0.5mm², maximum 2.5 mm²) Compliant with local laws and regulations in forceConnection of devices to channels configured as outputCh xAUX -AUX +42InstallationInstallation manualConnection of devices to channels configured as inputCh xAUX -AUX +5.13IFMLAN internal module wiringThe screw terminals of the IFMLAN module (paragraph 3.8 - [F]) are not available for any type of connection. For future use5.14IFMEXT internal module wiringThe IFMEXT module provides 7 terminals for the connection of signalling, activation and control devices linked to the apparatus of the fire extinguishment system.3 input terminals:PRESSOS. (paragraph 3.10 - [C]) - STOP-EXT (paragraph 3.10 - [D]) - MAN-EXT (paragraph 3.10 - [E])4 output terminals:VALVE (paragraph 3.10 - [F]) - HOLD (paragraph 3.10 - [G]) - PRE-EXT (paragraph 3.10 - [H]) - RELEASED (paragraph 3.10 - [I])