Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
Thermoelectric tripping device is supplied with a mounting plate for self-assembly. The tripping device shall be fastened with two self-tapping screws to the flange of the fire damper, so as not to block the rotation of the blades.Electric actuators – electrical specificationActuator typeLocation of the damper isolation partitionBelimo BFL series - Belimo BFN series - Belimo BF series - Belimo serii BE - Belimo serii BLE - Belimo serii BEE - Belimo serii BENOpen isolation partition – actuator indication: 90 Closed isolation partition – actuator indication: 0Open isolation partition – actuator indication: 0 Closed isolation partition – actuator indication: 90Technical specificationsPower supplyBF 24, BF24-T, BF24- TN AC 24V 50/60Hz DC 24VBF230, BF230-T, BF230-TNAC 220-240V 50/60 HzPower demand:for spring tensioning7 W8,5 Wfor spring holding Sizing (apparent power) Appliance class2 W 10 VA III3 W 11 VA II