Title: økernvn 94.pdf
100002550 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 7.4Cable ID: T4083 Date / Time: 09/11/2013 12:23:57 Headroom 13.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]138 220 16 6.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.0 92.0 32.9 36 14.7 99.0 29.4SR 12-36 13.2 92.0 32.9 36 15.4 92.0 29.9MAIN 12-36 13.2 99.0 32.4 36 14.7 99.0 29.4SR 12-36 13.2 92.0 32.9 36 15.7 99.0 29.410080604020NEXT (dB)