Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.8 495.0 29.3 36 6.6 500.0 26.4SR 12-36 9.1 500.0 29.2 36 9.0 500.0 26.4MAIN 12-36 7.8 495.0 29.3 36 6.6 500.0 26.4SR 12-36 9.1 500.0 29.2 36 9.0 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.2 500.0 11.3 45 19.4 499.0 8.3SR 78-45 17.1 499.0 11.3 45 19.3 499.0 8.3MAIN 78-45 17.2 500.0 11.3 45 19.4 499.0 8.3SR 78-45 17.1 499.0 11.3 45 19.3 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.6 29.8 40.9 45 19.9 29.8 38.5SR 36-45 17.1 27.0 42.0 45 18.4 27.0 39.6MAIN 12-36 30.4 495.0 -12.1 36 29.4 500.0 -15.3SR 12-36 31.8 500.0 -12.4 36 31.8 500.0 -15.30804000250 MHzACR-N (dB)