Title: Hydrauliske beregninger sprinkler Kontorer plan 3 78m².pdf
545861585759627668626465666769707172k-factor C-factor Height[m]120195.4120195.4120195.4120196.1120195.4120200.6120200.6120200.6120200.6120204.5120200.6120200.6120200.6120204.5120204.5120204.5120204.5120204.5120204.5120204.5120204.580.0120204.2120204.5120204.5120204.5120204.5120204.5120204.5120204.5120204.5120204.5120204.5120204.580.0120204.2120204.580.0120204.280.0120204.2120204.580.0120204.2120204.5qv [l/min]292.9286.56.5422.0292.9333.118.544.9558.4666.5108.165.8398.910.4158.0168.4170.72.3170.8173.192.892.8265.957.9400.6342.7323.8342.7194.3206.3259.765.5164.984.480.580.577.7182.165.7116.4v [m/s]0.50.50.10.80.50.60.10.11.01.20.30.20.70.31.21.34.90.04.91.32.61.82.01.63.0