Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Reception activity - receiving data from devices on loop ATXARedTransmission activity - transmitting data to devices on loop ARXBGreenReception activity - receiving data from devices on loop BTXBRedTransmission activity - transmitting data to devices on loop BIFM2L module - technical specificationsPower supply voltage19-30 Vsupplied by IFM24160 moduleOperating temperaturefrom -5°C to +40°CMaximum number of devices managed by a loop240stand-by35mAConsumption @ 27.6Vmaximum50mAMaximum voltage on Loop-A0.5AMaximum voltage on Loop-B0.5A3.8IFMLAN, internal Ethernet moduleThe IFMLAN module provides the Previdia Max with communication ports:USB Host • Mini USB • Ethernet • RS485 • RS232Connecting the Ethernet port establishes a second connection between the control panel and the network for access to the advanced TCP-IP functions (sending of event-related e-mails, communications via SIA-IP, video verification and browser-accessible Web server).