Title: Aggregatkjøring.pdf.pdf
Commissioning DataSupplyExtractPressure drop clean filters5151Fans absorbed power clean filtersAlternative working pointsDim.Airflow, Supply, m³/h14400Airflow, Extract, m³/h14400External pressure drop, Supply250External pressure, Extract250SFPv, kW/(m³/s)1.42SFPe, kW/(m³/s)1.56Efficiency, Heat exchanger (wet), %82.4Efficiency, Heat exchanger (dry), %82Heating coil, Output, kW35.0Fluid flow rate, l/s0.57Fluid pressure drop, kPa8.9Sound data dB(A)Supply air77Outdoor air63Exhaust air79Extract air63Sound break out57Operation hours8760Operational hours yearly8760Systemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Unit no. 20Date 18.06.2021Page 23/40UnitPakWAverage14400144001.421.5682.48235.00.578.9Quotation no. Project Plant no.