Title: Hardware Installation Guide.pdf
Network addressing of devices shall not make use of public domain name servers.Panic hardware must be UL 305/ULC-S132 Listed.5.1PowerThe standby power system for the HVAC system may be supplied by an engine driven generator alone. Use of a standby battery is not required.All external interconnecting power sources must be UL/ULC Listed access control/proprietary burglary power limited power supplies. AC supply lines shall not be routed in the same conduit or harness as low voltage lines.5.1.1UL/ULC Certified Power SuppliesFor the UL certification, the power supply that must be used is the LNL-AL400ULX or LNL-AL600ULX-4CB6 with additional hardware mounted in LNL-CTX or LNL-CTX-6 enclosures. Other power supplies will be certified for use at a future date.For the ULC Certification, hardware must be mounted in LNL-CTX or LNL-CTX-6 enclosures. All power supplies must be UL, ULC, or cUL Listed for security applications, and power-limited.Output4 hr. of Stand-by & 5 minutes of Alarm