Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF023 Date / Time: 27-02-2020 20:12:55 Headroom 6.5 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]5.6 24 0 1.23Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]38.2 500.0 41.6Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.4 471.0 29.2 36 7.0 471.0 26.4SR 36-45 6.5 472.0 29.2 45 6.4 350.0 29.9MAIN 36-45 7.4 471.0 29.2 36 7.1 472.0 26.3SR 36-45 6.5 472.0 29.2 36 6.8 472.0 26.310080604020NEXT (dB)