Title: økernvn 94.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]22.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.4 * 247.0 35.4 36 0.4 * 248.5 32.7SR 12-36 6.7 245.0 35.5 36 6.6 222.0 33.6MAIN 36-45 0.4 247.0 35.4 36 0.4 248.5 32.7SR 36-78 6.7 249.0 35.4 36 6.7 249.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.1 116.0 22.9 36 18.7 112.5 20.2SR 36-12 15.9 116.0 22.9 12 18.3 108.5 20.5MAIN 12-36 17.0 231.0 16.9 12 19.5 231.5 13.9SR 36-12 16.8 231.0 16.9 12 18.4 223.5 14.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250