Title: Våtventil Brukermanual.pdf
monitors, and those in the affected area that the valve is back in service . Provide test results, if required, to the authority having jurisdiction .I-751.VDS_11WATER FLOW ALARM TESTPerform the water flow alarm test on a frequency required by national standards . In addition, the authority having jurisdiction in the area may require these tests on a more frequent basis . Verify these requirements by contacting the authority having jurisdiction in the affected area .1 . Notify the authority having jurisdiction, remote station alarm moni- tors, and anyone in the affected area that the water flow alarm test will be performed .4 . Close the system test valve (13) after proper operation of all alarmsis verified .5 .Verify that all alarms stopped sounding, that the alarm line drained properly, and that remote station alarms reset properly .2 .Verify that the alarm line ball valve (11) is open .6 . Push in the plunger of the restricted orifice/alarm line drain (7), as