Title: DOCA0005EN-12.pdf
Set the Device ID for this device. Make sure the Device ID is unique in your BACnet network.Com.ProtectionCom.ProtectionEnableDisableProtects selected settings and resets from configuration via communications.ContrastContrast1-9Increase or decrease the value to increase or decrease the display contrast.PasswordPassword0-9999Sets the password for accessing the meter configuration screens and resets.Reset ConfigReset Config—Settings are reset to their defaults, except for Password. Meter restarts.46DOCA0005EN-12Communications via ModbusChapter 5 Communications via ModbusModbus communication overviewModbus RTU protocol is available on the iEM3150, iEM3155, iEM3250, iEM3255, iEM3350, iEM3355, iEM3455, and iEM3555.The information in this section assumes that you have an advanced understanding of Modbus communications, your communications network and the power system that your meter is connected to.