Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
[Pair 45] [Pair 45] [Pair 45]28.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.3 491.0 29.4 36 9.5 500.0 26.4SR 12-36 7.6 474.0 29.7 36 7.6 474.0 26.9MAIN 12-36 9.3 491.0 29.4 36 9.5 500.0 26.4SR 12-36 7.9 499.0 29.3 36 7.8 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.1 6.1 49.5 45 19.7 5.0 48.3SR 45-78 18.1 6.1 49.5 45 19.7 4.9 48.5MAIN 78-45 21.3 500.0 11.3 45 20.5 500.0 8.3SR 45-36 21.6 498.0 11.3 45 20.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.5 58.5 32.3 36 20.1 58.3 29.8SR 45-78 20.4 58.8 32.2 45 19.9 58.5 29.8MAIN 36-45 38.1 500.0 -12.4 36 38.3 500.0 -15.3SR 12-36 36.6 499.0 -12.3 36 36.6 500.0 -15.30804000250 MHz