Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
MAIN 45-36 13.9 3.1 55.3 45 13.1 2.0 56.2SR 36-45 13.9 3.1 55.3 45 13.4 2.1 55.7MAIN 45-36 17.0 472.0 11.8 45 19.1 500.0 8.3SR 36-45 16.9 472.0 11.8 45 18.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 24.1 92.0 25.6 45 24.1 86.5 24.0SR 36-45 25.3 85.8 26.7 36 24.9 91.3 23.2MAIN 12-45 38.2 496.0 -12.1 36 38.5 495.0 -14.9SR 36-78 39.3 490.0 -11.7 36 40.0 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.1 473.0 8.0SR 12 5.1 473.0 8.0MAIN 12 6.1 473.0 8.0SR 12 5.1 473.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASS