Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
Note: 24 V connection through safety transformer.Switch with at least 3 mm gap between contacts (in disconnected state) is required for disconnecting the actuator BFT230-T from the mains.Possible parallel connection of further drives. Check the power consumption.Figure 9. Connection diagram for BELIMO BF24-T(-ST), BF230-T actuators.In order to separate the system from the supply network, it should be equipped with a device disconnecting the phase wires, with gap between contacts equal to at least 3 mm.Possible parallel connection of several actuators. In such a case watch the power consumption.Figure 10. Connection diagram for BELIMO BLF230-T actuator.Connect through separating safety transformer.BLF24-T-ST: Version with plug-in connectors for connecting with the power supply and communication device BKN230-24.Possible parallel connection of several actuators. In such a case watch the power consumption.Figure 11. Connection diagram for BELIMO BLF24-T and BELIMO BLF24-T-ST.