Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
20.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 499.0 29.3 36 8.8 499.0 26.4SR 36-78 10.0 473.0 29.8 36 8.6 496.0 26.5MAIN 12-36 8.0 499.0 29.3 36 8.8 499.0 26.4SR 12-36 10.4 496.0 29.3 36 8.6 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.5 402.0 13.2 45 18.9 465.0 8.9SR 78-45 18.2 402.0 13.2 45 19.1 461.0 9.0MAIN 45-78 19.3 460.0 12.0 45 18.9 465.0 8.9SR 78-45 18.8 455.0 12.1 45 19.2 470.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.4 22.3 44.2 36 18.1 22.3 41.8SR 36-45 16.6 22.3 44.2 36 18.4 22.3 41.8MAIN 12-36 28.8 499.0 -12.3 36 29.6 499.0 -15.2SR 36-45 31.2 500.0 -12.4 36 29.3 496.0 -15.00804000250 MHzACR-N (dB)