Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
RCD II: 28.5mAUci: 0.0V t: 107.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM1.E5.433.09.04 / XF046 C16/2 15.06.2020 11:35SPĆNDINGUln: 231V Ulpe: 231V Unpe: 0V f: 50.0HzTallberg Elektro A/S Tlf.22796640Side:13GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr. 9393949495959696979798989999TEST RAPPORTResultatDM1-3. Plan 9 / DM1.E5.433.09.04 / XF046 C16/2 15.06.2020 11:35Z-LINEZ: 0.31ΩIsc: 746A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF046 C16/2 15.06.2020 11:36Zs(rcd)Z: 0.26ΩIsc: 873A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF046 C16/2 15.06.2020 11:36SPĆNDINGUln: 230V Ulpe: 230V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF046 C16/2 15.06.2020 13:09R LOW OhmR: 0.11ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0Ω