Title: 2 etg del2.pdf
Cable ID: D2010 Date / Time: 10/10/2013 10:57:36 AM Headroom 6.0 dB (NEXT 12-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]156 237 8 7.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]15.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.3 94.0 42.3 78 7.9 93.8 39.8SR 12-45 6.0 195.0 37.1 12 6.2 195.5 34.5MAIN 36-78 7.7 247.5 35.4 78 8.1 247.5 32.8SR 12-45 6.0 195.0 37.1 12 7.1 250.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.6 106.0 23.7 12 17.2 122.0 19.5