Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
26.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.0 498.0 29.3 36 9.0 498.0 26.4SR 36-45 6.6 477.0 29.7 36 7.0 476.0 26.9MAIN 36-45 9.0 498.0 29.3 36 9.0 498.0 26.4SR 36-45 6.8 495.0 29.3 36 7.1 491.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.2 402.0 13.2 45 17.7 15.3 38.6SR 45-78 17.4 402.0 13.2 45 17.7 30.1 32.7MAIN 78-45 17.3 449.0 12.2 45 18.2 499.0 8.3SR 45-78 17.5 449.0 12.2 45 18.2 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.5 42.5 36.5 36 23.0 45.3 33.2SR 36-78 24.2 44.8 35.9 36 24.8 92.8 22.9MAIN 36-45 35.8 498.0 -12.3 36 36.2 498.0 -15.1SR 36-45 33.4 495.0 -12.1 36 34.4 495.0 -14.90804000250 MHzACR-N (dB)