Title: økernvn 94.pdf
SR 36-45 13.1 49.8 30.3 45 15.8 42.8 28.6MAIN 45-36 18.3 204.5 18.0 36 20.9 235.5 13.7SR 36-45 19.6 235.5 16.7 45 19.9 222.5 14.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.8 10.5 51.8 36 8.6 10.5 49.4SR 12-36 7.1 10.5 51.8 12 9.1 10.5 49.4MAIN 36-45 10.7 250.0 4.7 36 10.7 249.0 2.1SR 36-45 10.6 250.0 4.7 36 10.7 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.5 22.6 19.2SR 36 3.5 22.6 19.2MAIN 36 7.5 214.0 10.7SR 45 8.6 249.0 10.0010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active