Title: Pos. 12A Kjolebenker ProffG2_Bruksanvisning.pdf
which can be applied to each relay (see Technical Data). Model XR01CX, format 32 x 74 x50 mm format is a single stage temperature controller suitable for Push the SET key for more than 2 seconds to change the Set point value; 1. HOW TO CHANGE THE SETPOINT Fit the probe where it is not accessible by the End User. The instrument must not be opened. provided with 1 NTC probe input and one configurable digital input. The instrument is fully configurable Push and immediately release the SET key, the set point will be showed; 1. HIDDEN MENU 1. Enter the Programming mode by pressing the SET+ address) with a detailed description of the fault. pushed till the L2 message is displayed. differential the compressor is started and To change the parameter’s value operate as follows: key for more than 2 seconds and a manual defrost will start Push the DEF NOTE2: the set value is stored even when the procedure is exited by waiting the time-out to expire. Ensure that the wires for probes, loads and the power supply are