Title: +135.01=370.001-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Function description The analog module (WZU-AM) converts the measured value from the meter to an analog signal. Each module has 2 channels with functions that can be configured independently. The service software configures the unit (selection of measured value and output range). The output signal is refreshed at 4-second intervals.NOTICEThe analog module can be plugged into either of the 2 slots and 2 modules can be used concurrently.Power supply The module must be powered via an external power pack (e.g. WZU-NE24). The 2 cables of the power pack are interchangeable. The 2 analog modules can be powered by the same power pack. The module(s) and the meter can be connected to the same power outlet if the meter is mains-powered (AC/DC 24 V). In this case, the wires must be bridged on module WZU-AM; the plug-in terminals on the meter’s power pack are not suited for that purpose. If a meter is used with an analog module, a D-cell is required – if battery-powered.