Title: isover_fireprotect_produktdokumentasjon_spfr_010-0202_2016_no_-_gyldig_til_07_2021.pdf
Foretaksnummer NO 982 930 057 MVASPFR 010-0202 ISOVER FireProtect 150/150F Side 12 av 16Tabell A.8: Design Steel Temperature (TKritisk) 650oC: Design table for ISOVER Fire Protect 150 mineral wool boards for fire protection on steel to Standard Fire Exposure. Design values from ENV 13381-4:2007 numerical regression. Regression constants multiplied with factor kMOD = 0,996 to satisfy prEN 13381- 4:2009 Section 13.5.1 Criteria for acceptability.Open and closed steel sectionsCritical steel temperature:F/A3060Multiple R R20,999348650 oC Fire Resistance time in minutes 900,998696150120180ao = 0kMOD = 0,996210240502020202020253540602020202020305060702020202025405070802020202035506080902020202540607080100202020305060801102020203550708012020202035507013020202040607014020202540608015020202550608016020