Title: økernvn 94.pdf
MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: D4183 Date / Time: 09/10/2013 06:30:09 Headroom 7.3 dB (NEXT 45-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]102 158 7 4.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]20.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.7 180.5 37.7 36 9.2 209.5 34.0SR 45-78 7.3 229.0 36.0 78 8.2 229.5 33.3MAIN 12-36 8.8 213.0 36.5 78 9.5 236.0 33.1SR 45-78 7.3 229.5 35.9 78 8.2 229.5 33.310080604020NEXT (dB)