Title: 40 Bender brukermanual.pdf.pdf
5. . Delay on release t(off) If the condition that triggered the alarm does not exist anymore, the RCMS… terminates its alarm once the release delay has elapsed. Setting range: 0…999 s. Resolution of settings: the same as for response delay t(on).6. Cutoff frequency Set the characteristics for the frequency response of residual current measu- rement IΔn and current measurement I.Param.Objective50 HzPlant protection: Only evaluates the fundamental compo- nent of the current measurement.60 HzPlant protection: Only evaluates the fundamental compo- nent of the current measurement.IECPersonnel protection in accordance with IEC 60990 (touch current for let-go): Above 200 Hz (approx.), the set response value increases corresponding to the frequency-dependent threshold according to IEC 60990.NoneFire protection: Response factor remains the same over the entire frequency range.