Title: 360.001 - Tilluft.pdf
7.41.5 +0.03.03.90.0 +0.05.46.0 +0.0 2.76.0 +0.0 2.75.10.5 +0.0Lp [dB]11,63. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasjeNodeType57 T-BRANCHDUCT58 SUPPLYDUCT59 PLUGDUCT60 PLUG219 TAPDUCTJOINTProductTCPU-315-315MAGID-C1-315FKV-315 CoolingMAGID-C1-315ESU-315MAGID-C1-315ESU-315MAGIO-RC-*MAGID-C1-315NPU_SE-*0,1Size315/315315315315315315315315315315L [m]0,10,20,23,823qv [m³/h]300300300120012001200v [m/s]1,11,11,14,34,34,3dpt [Pa]0,8 Sound in:Attenuation: Addition:Dividing:0,0 Sound in:Attenuation: Addition:3,1 Sound in:Attenuation: Addition:Total Lw:Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:6,3 Sound in:2,7 Sound in:Attenuation: Addition:Sound in:63 [dB]37.90.0 +0.03.034.90.0 +0.034.912.0 +0.022.934.90.0 +0.041.30.0 +0.035.635.60.4 +25.7