Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 063 GODKJENT* 12.03.2020 12:54KONTINUITET GODKJENTR: 0.3QGrenseverdi:1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 063 GODKJENT* 12.03.2020 13:02R LOW Ohm GODKJENTR: 0.15QR+: 0.1QR: 0.1QGrenseverdi: 1.0Q224Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 063 GODKJENT *12403.2020 13:38Zs (rcd) GODKJENTZ: 0.57QIsc: 403ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc _lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 063 GODKJENT* | 12.03.2020 13:40RCD I a GODKJENTI: 28.5mAUci: 0.5Vt: 12.8msIdn: 30mAtype: ACH\,Ulim: 25VR ISO GODKJENTR: 19.95MQ Um: 262VUiso: 250VGrenseverdi:MQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 064 GODKJENT* 12.03.2020 14:36TEST RAPPORTResultatR LOW Ohm GODKJENTR: 0.11QR+: 0.1QR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 064 GODKJENT* 12.08.2020: 13:37 ’ZLINE GODKJENTZ: 0.60QIsc: 383ASikringstype: C