Title: 40 Bender brukermanual.pdf.pdf
1. The currently measured value is multiplied by the appropriate factor. 2. The specified offset value is added.Displayed by a formula:Response value = (currently measured value x factor) + OffsetExit 1.Factor: 2.Offset: 3.PRESET3 30 mA56RCMS460-490_D00067_03_M_XXEN/12.2017Operation1. Factor (for PRESET) Set the multiplication factor for the latest measured value. Setting range: 1…99 %, resolution of setting 1 %. Recommended setting (factory setting): Factor 32. Offset (for PRESET) Set the offset value that is to be added to the product of the "current measu- red value x factor". Setting range: 0…20 A, resolution of setting:Setting range 0…20 mA 25…50 mA 60…200 mA 250…500 mA 600 mA… 2 A 2.5 A…5 A 6 A…20 AResolution of setting 1 mA 5 mA 10 mA 50 mA 100 mA 0.5 A 1.0 ARecommended setting (factory setting): Offset 30 mA3. PRESETWARNING