Title: Ahlsell.pdf
Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505095Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 3,6] [Pair 4,5] [Pair 4,5] [Pair 3,6]34.2 166 3 5.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-4,5 10.4 465.0 29.9 4,5 10.9 486.0 26.7SR 3,6-7,8 7.7 154.0 38.8 3,6 9.2 319.0 30.8MAIN 1,2-4,5 10.4 465.0 29.9 4,5 10.9 486.0 26.7SR 3,6-4,5 9.1 499.0 29.3 3,6 9.4 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 16.9 35.0 34.4 4,5 18.9 6.0 46.7SR 4,5-7,8 16.8 499.0 11.3 4,5 18.8 4.3 49.7