Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,9 26,7 3,2 498,00Worst Value: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,9 26,7 3,2 498,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 68,4 57,3 11,1 2,20Remote: 12-45 68,4 57,3 11,1 2,20Worst Value: Local: 12-45 22,3 10,4 11,9 489,00Remote: 12-36 22,4 10,3 12,1 497,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,8 25,5 2,3 446,00Remote: 36 27,6 23,8 3,8 498,00Worst Value: Local: 36 26,6 23,9 2,7 496,00Remote: 36 27,6 23,8 3,8 498,00PS-ACRF: Pass Worst Margin: Local: 12 67,7 56,3 11,4 1,75Worst Value: Local: 12 19,8 7,3 12,5 494,00