Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
R: 0.11QRt: 0.1QR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 040 GODKJENT* 121103812020 13536RCD T . GODKJENTI: 28.5mAUci: 0.3Vt: 18.1msIdn: 30mAtype: ACO\,Ulim: 25VDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 040 GODKJENT* 12.03.2020 13:34ZLINE GODKJENTZ: 0.70QIsc: 328ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 040 GODKJENT* 12.03.2020 13:35Zs (recd) GODKJENTZ: 0.69QIsc: 331ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0ANr. ResultatR ISOR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQSPENDINGUln: 234VUlpe: 234VUnpe: 0Vf: 50.1HzZLINEZ: 0.24QIsc: 950ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc _lim: 160.0AZs (rcd)Z: 0.17QIsc: 1.35kASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AI a27.0mAUci: 0.0Vt: 127.4msIdn: 30mAtype: ACH\,Ulim: 25VKONTINUITETR: 0.1QGrenseverdi: