Title: 40 Bender brukermanual.pdf.pdf
5. Start-up delay t Time delay after the RCMS… is switched on. No alarm messages are generated during this period. This time delay is requi- red if the RCMS…-D and the monitored system are switched on simultaneous- ly. Currents caused by switching actions are ignored. Setting range: 0…99 s. Resolution of settings as follows: Setting range 0…50 ms 60…200 ms 250…500 ms 600 ms …2 s 2.5…5 s 6…20 s 25…50 s 60…99 s Resolution of setting 5 ms 10 ms 50 ms 100 ms 0.5 s 1 s 5 s 10 s5. Start-up delay t Time delay after the RCMS… is switched on. No alarm messages are generated during this period. This time delay is requi- red if the RCMS…-D and the monitored system are switched on simultaneous- ly. Currents caused by switching actions are ignored. Setting range: 0…99 s. Resolution of settings as follows: Setting range 0…50 ms 60…200 ms 250…500 ms 600 ms …2 s 2.5…5 s 6…20 s 25…50 s 60…99 s Resolution of setting 5 ms 10 ms 50 ms 100 ms 0.5 s 1 s 5 s 10 sSettings menu 2: PRESET