Title: 1 etg del 2.pdf
Cable ID: D1009 Date / Time: 10/21/2013 12:39:47 PM Headroom 8.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]141 216 8 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.8 228.5 36.0 78 9.4 229.0 33.3SR 12-36 8.7 227.5 36.0 78 8.3 221.5 33.6MAIN 36-78 8.8 228.5 36.0 78 9.4 229.0 33.3SR 12-36 8.7 227.5 36.0 78 8.3 221.5 33.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.4 164.5 19.9 12 15.1 2.4 53.7