Title: Hardware Installation Guide.pdf
04Pin 15 (Green/Yellow)Connected to Earth GroundNote: Do not use Power Ground as a substitute for Earth Groundrevision 6 — 587Biometric ReadersPigtail from reader588 — revision 6Wiring of V-Pass FX with Series 2 LNL-1300Network Identification Number MUST be set to 0.9-24 VDC Power Supply (DC- must tie into Signal Ground)Single Reader Interface ModuleSignal Ground (Black/Red)GNDBZRRS-485 + (Blue)LEDCLK/D1RS-485- (Blue/Black)DATA/D0VOGreen/YellowTie to Earth GroundTYPICAL SOFTWARE SETTINGS (Note: Software version 5.12.12 or higher required for Series 2 single reader interface module.) 1. Reader Type = (Bioscrypt RS-485)Hardware Installation GuideWiring of V-Pass FX with LNL-2220, 2210 or Series 2 LNL-1320Network Identification Number MUST be set to 0.9-24 VDC Power Supply (DC- must tie into Signal Ground)Reader Interface ModuleVOLEDPigtail from reader2 r e d a e RBZRCLK/D1DATA/D0RS-485 + (Blue)RS-485- (Blue/Black)GND