Title: ECY-303_SP.pdf
equipmentUniversal Inputs (UI)GeneralInput Type Universal; software configurable Input Resolution 16-bit analog to digital converterPower Supply Output 18VDC; 80mA maximumProtection Auto-reset fuse for 24VACprotectionContactType Dry contactCounterType Dry contactMaximum Frequency 1Hz maximum Minimum Duty Cycle 500 ms On / 500 ms Off0 to 10VDCRange 0 to 10VDC (40kΩ inputimpedance)ECY-3030 to 5VDCRange 0 to 5VDC (high input impedance)0 to 20mARange 0 to 20mA, 249Ω externalresistor wired in parallelResistance/ThermistorRange 0 to 350 KΩSupported Thermistor Types Any that operate in this rangePre-configured Temperature Sensor Types:Thermistor 10KΩ Type 2, 3 (10KΩ @ 77ºF;25ºC)Platinum Pt1000 (1KΩ @ 32ºF; 0ºC)Nickel RTD Ni1000 (1KΩ @ 32ºF; 0ºC)RTD Ni1000 (1KΩ @ 69.8ºF; 21ºC)Universal Outputs (UO)GeneralOutput Type Universal; software configurableOutput Resolution Converter 10-bit digital to analogConverter