Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
SR 36-78 34.7 499.0 -12.3 36 35.2 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 8.1 482.0 8.0SR 36 9.1 26.4 18.9MAIN 36 8.1 482.0 8.0SR 36 9.9 414.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-51 TR-4100BASE-TX 10GBASE-T ATM-155 TR-16 Active100BASE-T4 ATM-25 100VG-AnyLan TR-16 Passive60402000250 MHzProject: F13 3 ETGUntitled1Test Summary: PASSModel: DSX-5000 Main S/N: 2552117 Remote S/N: 2552311 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00436.6 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0