Title: Data tester Smestad skole - Detaljert.pdf
601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,3 11,3 10,0 440,00Remote: 45-12 21,6 11,3 10,3 442,00Worst Value: Local: 12-45 21,2 11,3 9,9 443,00Remote: 45-12 21,6 11,3 10,3 442,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,8 3,3 499,00Remote: 36 28,8 23,8 5,0 499,00Worst Value: Local: 36 27,1 23,8 3,3 499,00Remote: 36 28,8 23,8 5,0 500,00PS-ACRF: Pass Worst Margin: Local: 45 19,6 8,2 11,4 446,00Worst Value: Local: 45 19,5 8,1 11,4 449,00Remote: 12 19,8 8,3 11,5 442,00Remote: 12 19,7 8,2 11,5 444,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:12Signature:______________________ Page: 119Copper Certification Report