Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
Sensible emission Air (°C) K K K25-18 26-18.5 28-20 1,06 0,94 0,9 0,78 0,72 0,580,9 0,72 0,5Note:the correction factors are indicative, as they are average values.7Emission of 4 pipe units with enhanced cooling batterySkyStarCooling emission of 2 battery units (4 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.Model SpeedAir flowEWT 5 - LWT 10°C Total emissionWater flowSensible emissionEWT 7 - LWT 12°C Total emissionWater flowSensible emissionEWT 9 - LWT 14°C Total emissionWater flowSensible emissionEWT 12 - LWT 17°C Total Water emission flowSensible emissionSK 26SK 36SK 56SK 66High Med Low High Med Low High Med Low High Med Lowm3/h 710 500 320 880 610 430 1500 970 710 1820 1280 710l/h 812 629 425 940 729 557 1804 1291 1012 2105 1607 1012kW 4,72 3,66 2,47 5,46 4,24 3,24 10,49 7,50 5,89 12,24 9,34 5,89kW 3,29 2,51 1,66 3,86 2,93 2,21 7,25 5,08 3,94 8,57 6,41 3,94l/h 676 526 359 779 607 468 1508 1089 858 1754 1348 858