Title: økernvn 94.pdf
Cable ID: D3067 Date / Time: 09/12/2013 10:15:17 Headroom 13.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]178 283 20 7.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.8 93.3 32.8 36 15.7 93.3 29.8SR 12-36 13.4 75.0 34.4 36 15.2 84.3 30.5MAIN 12-36 14.0 97.0 32.5 36 15.7 97.0 29.5SR 12-36 13.5 91.5 32.9 36 15.9 99.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.5 66.5 22.2 45 21.8 56.5 20.6