Title: Data tester Smestad skole - Detaljert.pdf
Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 36,2 68,0 188,0 10,0 6,4Limit 100,0 - 555,0 50,0 25,0Margin 63,8 - 367,0 40,0 18,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,7 3,1 2,4 2,95Worst Value: Local: 36 15,8 43,7 27,9 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 15,9 8,0 7,9 491,00Remote: 12 13,4 8,0 5,4 476,00Worst Value: Local: 78 15,9 8,0 7,9 491,00Remote: 12 13,4 8,0 5,4 476,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,0 26,8 2,2 494,00