Title: Ahlsell.pdf
Cable ID: UD 12 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 01:13:11 PM Operator: Pam Headroom 9.6 dB (NEXT 3,6-7,8) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 4,5] [Pair 4,5] [Pair 3,6]23.4 115 2 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]31.1 491.0 43.3Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 11.7 321.0 33.0 3,6 12.7 26.8 48.6SR 3,6-7,8 9.6 3.8 64.5 3,6 11.1 3.8 62.0MAIN 3,6-4,5 12.7 494.0 26.8 3,6 13.6 494.0 23.9SR 3,6-4,5 12.1 498.0 26.7 3,6 12.1 485.0 24.210080604020NEXT (dB)