Title: 1 etg del 2.pdf
244 386 26 10.5244 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.4 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.5 * 245.5 35.5 36 0.9 * 230.5 33.3SR 36-450.0 *248.0 35.4 36 1.1 241.5 33.0MAIN 36-45 0.5 250.0 35.3 36 1.0 250.0 32.7SR 36-45 0.0 248.0 35.4 36 1.2 248.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 19.5 166.5 19.8 12 21.0 124.0 19.3SR 36-12 19.7 165.5 19.8 36 21.3 124.0 19.3MAIN 45-12 20.4 244.0 16.4 12 21.2 248.0 13.3SR 45-12 20.2 245.0 16.4 12 21.7 246.5 13.4010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz