Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
■ 5.3. Replacing the compressor In the event of replacing an AJ² compressor, please refer to annex 6.■ 5.4. Searching for leaks and regular checks Perform a search for leaks once a year, or according to local regulations. Use the appropriate equipment to empty or refill the system (recovery machine, goggles, gloves, etc.)■ 5.5. Electrical checks Always check the electrical connections of screwed down components. Tighten if necessary. Check the following on a regular basis: - the safety and control components, - the condition of the electrical and refrigeration connections(retightening, oxidation, etc.),the operating conditions, - the compressor fixings on its base, - the cowling attachments (no vibrations), - the operation of the crankcase heater.