Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
OBJEKT / Plan 10 / FUSE026 06.02.2020 14:44RCD II: 28.5mAUci: 0.1V t: 82.7ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE026 10.02.2020 08:55SPÆNDINGUln: 228V Ulpe: 228V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE027 06.02.2020 11:49R LOW OhmR: 0.21ΩR+: 0.0Ω R-: 0.4Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE027 10.02.2020 08:58RCD II: 28.5mAUci: 0.1V t: 47.9ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE027 10.02.2020 09:00SPÆNDINGUln: 227V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE027 10.02.2020 09:00Z-LINEZ: 0.69ΩIsc: 332A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATEST RAPPORTSide:3GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTNr. 1919202021212222232324242525ResultatOBJEKT / Plan 10 / FUSE027 10.02.2020 09:00Zs(rcd)Z: 0.45ΩIsc: 511A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A