Title: 2 etg del2.pdf
MAIN 36-45 8.7 249.0 4.8 36 8.8 248.0 2.2SR 36-78 13.6 238.5 5.8 78 15.0 246.0 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.4 13.8 20.3SR 45 2.3 12.3 20.6MAIN 45 8.7 224.5 10.5SR 36 3.4 247.5 10.1010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94