Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Definition of input signalsfor 5 VDC PCD2.E616for 24 VDC PCD2.E610, PCD2E611for 48 VDC PCD2.E6137 VDC 5 VDC2.5 VDC130 VDC 24 VDC15 VDC160 VDC 48 VDC30 VDC11 VDC 0 VDC5 VDC 0 VDC10 VDC 0 VDC0007 VDC30 VDC60 VDCfor 115 – 230 VAC PCD2.E500250 VAC180 VAC40 VAC0 VAC0Installation instructionsFor reasons of safety it is not permissible to connect low voltages (up to 50 V) and higher voltages (50 … 250 V) to the same module.If a Saia PCD® module is connected to a higher voltage (50 … 250 V), approved components for this voltage must be used for all elements that are electrically con- nected to the system.Using higher voltage (50 … 250 V), all connections to the relay contacts must be connected on the same circuit, i.e. in such a way that they are all protected against one AC phase by one common fuse. Each load circuit may also be protected individually.