Title: 360.001 - Tilluft.pdf
1.5 +0.03.08k [dB]12.80.0 +9.514.41.0 +9.514.90.2 +9.515.81.5 +0.03.011.50.3 +0.011.51.5 +0.03.07.40.0 +0.08.16.0 +0.0 4.26.0 +0.0 4.28.80.5 +0.08.91.5 +0.03.0Lp [dB]15,21. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeTypeDUCT70 SUPPLYDUCT71 PLUGDUCT72 T-BRANCHDUCT73 T-BRANCHDUCT74 SUPPLYProductMAGID-C1-315FKV-315 CoolingMAGID-C1-315ESU-315MAGID-C1-315TCPU-315-315MAGID-C1-315TCPU-315-315MAGID-C1-315FKV-315 CoolingSize315315315315315315/315315315/315315315L [m]0,10,22,81,40,149qv [m³/h]300300600600600600300300v [m/s]1,11,12,12,12,12,11,11,1dpt [Pa]0,0 Sound in:Attenuation: Addition:3,1 Sound in:Attenuation: Addition:Total Lw:Sound in:Attenuation: Addition: