Title: økernvn 94.pdf
MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: D3409 Date / Time: 09/11/2013 03:27:37 Headroom 6.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]130 199 7 5.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]18.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.1 249.5 35.4 36 7.3 249.5 32.7SR 36-78 7.6 246.0 35.5 78 9.0 243.5 32.9MAIN 36-78 6.1 249.5 35.4 36 7.3 249.5 32.7SR 36-78 7.6 246.0 35.5 78 9.0 243.5 32.910080604020NEXT (dB)