Title: Hardware Installation Guide.pdf
Power: 18 AWG, 1 stranded twisted pair RS-485: 24 AWG, 120 ohm impedance, stranded twisted pair with shield, 4000 feet [1219m] maximum Alarm inputs: 1 stranded twisted pair per input, 30 ohms maximum Outputs: As required for the load Reader data (Wiegand, Clock and Data): 6 conductors, 18 AWG stranded, 500 feet [150m] maximum Reader data (RS-485): 24 AWG, 120 ohm impedance, stranded twisted pair with shield, 4000 feet [1219m] maximumMechanical:Dimension: 5 x 8 x 1.25 in. (127 x 203 x 32 mm)- Weight: 7.3 oz. (207 g) nominalEnvironmental: - -Temperature: -10 to +70°C (14 to 158°F) operating, -40 to +85°C (-40 to 185°F) storage Humidity: 10% at 93°C (199°F) non-condensing operating, 10 to 95% at 85°C (185°F) non- condensing storageCertifications: -FCC Part 15revision 6 — 427LNL-1320-U Dual Door Controller ModuleETL294, s319 UL294, 1076 C-Tick N22193 CE marking RoHS Environmental class: Indoor dry- - - - - - WEEE428 — revision 6LNL-8000 STAR MULTIPLEXERHardware Installation Guide