Title: Tappevann - KV.pdf.pdf
0,518,11,85,91,8101,73,84,81,615,71,625,991,01,621,11,63,61,62,22,71,64,60,20,10,10,14,90,20,90,48,80,83,11,60,00,2K factor0.1430.4850.4851.0000.4800.4800.4850.4850.4850.4850.4910.4911.0000.2440.4881.0000.488dp Hst [kPa]0,14,80,10,33,10,10,117,00,12,00,52,50,10,32,20,30,31,50,10,00,30,20,2pt [kPa]304,8303,9303,3285,2283,2272,6270,6168,9165,4163,8162,3146,6145,2136,3168,977,976,355,253,650,048,648,448,948,747,242,7396,9396,7396,2393,9393,4388,5388,5389,1388,8380,0379,2376,1374,2374,0qv [%]WarningsHigh dpLocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje