Title: Jordfeilautomat 3+N.pdf
Tripping curve B curve (3 In-5 In) protection and control of the circuits against overloads and short-circuits; protection for people and big length cables in TN and IT systems. C curve (5 In-10 In) protection and control of the circuits against overloads and short-circuits; protection for resistive and inductive loads with low inrush current.1.3 Approvals and certificates CE/CB/KEMA1.4 Add-on devices XF9 auxiliary contacts S9 shunt release V9 under voltage release OVT-1 over voltage releaset(s) 10000 5000 1h 2000 1000 500C Curve200 100 50 20 10 52 1 0.5 0.2 0.10.05 0.02 0.01 0.005 0.002 0.0010.5123 4 5 7 10 20 30 50 70 100 200I/InModular DIN Rail ProductsRCBO2.2StandardIEC/EN 61009-1Type (wave form of the earth leakage sensed)A, ACThermo-magnetic release characteristicB, CRated current InA6, 10, 13, 16, 20, 25, 32, 40Poles3P+NRated voltage UeV400Rated sensitivity I△nA0.03Rated residual making and breaking capacity I△mA3,000Electrical