Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 45-36 17.4 469.0 11.8 45 19.7 475.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 30.1 177.5 14.0 45 30.1 151.5 14.4SR 36-45 28.1 152.5 16.9 45 28.8 152.5 14.3MAIN 12-45 41.6 493.0 -11.9 45 41.5 492.0 -14.7SR 36-78 43.1 492.0 -11.9 36 42.9 492.0 -14.70804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.8 493.0 8.0SR 45 5.7 425.0 8.0MAIN 45 5.8 493.0 8.0SR 45 5.7 425.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00416.8 m60Insertion Loss (dB)504030201000250 MHz500100