Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 36] [Pair 36] [Pair 45]22.9 99 1 3.54Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.2 464.0 29.6 36 7.9 463.0 26.8SR 12-36 9.5 463.0 29.6 36 8.7 463.0 26.8MAIN 12-36 8.7 500.0 27.8 36 8.8 499.0 25.0SR 12-36 11.0 500.0 27.8 36 9.3 487.0 25.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.5 7.6 47.6 78 22.3 6.5 46.0SR 78-45 20.5 7.6 47.6 45 22.1 5.9 46.9MAIN 36-45 23.3 499.0 11.3 45 23.8 500.0 8.3