Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Colliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 4 10.03.2022 13:41 (TomekElektriker)KONTINUITET: R200mA LPER: 0.20ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF023 C16/2/003 10.03.2022 11:40 (TomekElektriker)SPENNING TRMS Uln: 234V Ulpe: 234V Unpe: 1V f: 49.93HzSYS.: TN/TTZ-LINEZ: 0.50ΩIsc: 462A R: 0.50Ω Xl: 0.05Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 28.5mAUci: 0.0V t: 53.5ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 522V Rnpe: >30.0MΩ Um: 515VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF023 C16/2/003 / Mal 1 10.03.2022 11:21 (TomekElektriker)TALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:5GODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*Nr.17171818TEST RAPPORTResultat SPENNING TRMS Uln: 236V Ulpe: 235V Unpe: 1V f: 50.03HzSYS.: TN/TTZ-LINEZ: 0.40Ω