Title: KS-Fukt3.pdf
N25N031062530.01.201903.12.2019N35N025103530.01.201903.12.2019© MYCOTEAM AS | Telefon: 469 75 500 / 469 75 504 | Telefax: 22 46 55 52 | E-post: post@mycoteam.no | www.mycoteam.noPostadresse: Postboks 5 Blindern, 0313 OSLO | Besøksadresse: Forskningsveien 3 B | Org.nr.: NO 940351022Dronning Mauds gate 1-3 BREEAM (201910198)MåleprotokollMåle- punktNrMåle- dybde(mm)Sensor- IDStartMåletidAvlestAvlest RF(%)Avlest temp.(°C)Kalibrert RF(%)Korr. for RF ved 20 °C +/– (%)Korr. for fuktkapasitet +(%)Usikkerhet k=2 +(%)Sluttverdi RF(%)RF middel- verdi(%)1a90N1306.12.19 13:0009.12.19 07:3087,119,786,90,00,52,389,71b60N1106.12.19 13:0009.12.19 07:3084,719,884,80,00,52,387,61) 87,61c30N2606.12.19 13:0009.12.19 07:3082,519,982,70,00,52,385,52a90N3406.12.19 13:0009.12.19 07:3082,219,282,60,10,52,385,52b60N2106.12.19 13:0009.12.19 07:3082,619,382,9