Title: 32 Pumper modbuss teknisk data.pdf.pdf
Permanently redCIM 260 does not support the connected version of the E-pump.Permanently greenThe connection between CIM 260 and the E- pump is OK.120 2 8 08 1 1 67 0 M T7. CIM 500 Modbus TCPWARNINGElectric shockDeath or serious personal injury - Connect CIM 500 only to SELV or SELV-E circuits.7.1 Connecting the Ethernet cableUse RJ45 plugs and Ethernet cable. Connect the cable shield to protective earth at both ends.It is important to connect the cable shield to earth through an earth clamp or to connect the cable shield to earth in the connector.CIM 500 is designed for flexible network installation; the built-in two port switch makes it possible to daisy chain from product to product without the need for additional Ethernet switches. The last product in the chain is only connected to one of the Ethernet ports. Each Ethernet port has its own MAC address.Ethernet switchCIM 500CIM 500CIM 500CIM 500Fig. 17 Example of Industrial Ethernet network213456789