Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Side:21GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.143143144144145145146146147147148148149149TEST RAPPORTResultatRCD UbUc: 0.2V Rl: 6Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 12:11KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 12:11R LOW OhmR: 0.31ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 10.06.2020 11:05R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 11.06.2020 15:30SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 12.06.2020 10:22Z-LINEZ: 0.54ΩIsc: 425A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 12.06.2020 10:22Zs(rcd)Z: 0.48Ω