Title: Instructions manual - THGT fan.pdf
Avoid risk of foreign objects, debris being drawn into, or falling into fan impeller. Allow safe access to fan for inspection, maintenance, replacement of parts, cleaning / housekeeping, especially for dust hazards, typically:- For small fans, access with suitable lifting, should be provided, greater than largest fan dimension, or minimum of 1 metre, to allow removal of complete fan to safe location for repair. For large fans, access with suitable lifting to repair in-situ, should be provided, greater than largest impeller / motor dimension, or minimum of 1 metre. Provision of beam fixed to structure, over fan location, to assist lifting, may be considered good practice, for future maintenance. Ensure all necessary safety guards are fitted and secure to prevent injury. Ensure safe transport of hazardous substances without leakage to non-hazardous areas, especially via duct connections, where appropriate sealing may be required. Axial fans should be installed with clear, unobstructed airflow upstream and