Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
kW 2,29 1,93 1,49 2,54 2,22 1,76 3,14 2,48 1,76 3,60 2,84 2,22 6,93 5,48 4,51 8,34 6,17 4,92 9,64 7,60 4,92Water flow l/h 261 219 169 298 260 209 378 298 209 426 341 267 783 618 508 946 697 555 1092 858 555kW 3,03 2,54 1,96 3,46 3,02 2,43 4,40 3,46 2,43 4,95 3,97 3,10 9,10 7,19 5,91 11,00 8,10 6,45 12,70 9,98 6,45Water flow l/h 325 272 210 358 312 247 444 350 247 510 401 312 970 766 629 1170 864 686 1353 1064 686kW 3,78 3,17 2,44 4,17 3,63 2,87 5,17 4,07 2,87 5,93 4,67 3,63 11,28 8,90 7,31 13,60 10,04 7,98 15,74 12,37 7,98Emission correction factors for different working conditions. Multiply the factors by the emission figures in the 7-12°C table above.Water (°C) 7/12 °C 10/15 °C 14/18 °CTotal emissionAir (°C) K K K25-18 26-18.5 28-20 Water (°C) 0,82 0,56 0,350,89 0,63 0,411,11 0,82 0,527/12 °C 10/15 °C 14/18 °CSensible emission Air (°C) K K K25-18 26-18.5 28-20 1,06 0,94 0,9 0,78 0,72 0,580,9 0,72 0,5Note:the correction factors are indicative, as they are average values.