Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 27.11.2020 11:53R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF027 16C2/003 27.11.2020 11:53KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 30.11.2020 10:34SPĆNDINGUln: 236V Ulpe: 236V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 30.11.2020 10:34Tallberg Elektro A/S Tlf.22796640Side:11GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.7676777778787979808081818282TEST RAPPORTResultatZ-LINEZ: 0.84ΩIsc: 274A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF028 16C2/003 30.11.2020 10:34Zs(rcd)Z: 0.84ΩIsc: 274A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A