Title: +038=433.002-FS026._02-FDV 16490-39.pdf
Disconnection characteristicShort-time delayedSurge current capacitykA3Voltage typeACFrequency50 HzRelease characteristicCConcurrently switching N-neutralNoWith interlocking deviceNoOver voltage category3Pollution degree2Ambient temperature during operating°C25 - 40Width in number of modular spacings2Built-in depthmm70Suitable for ﬂush-mounted installationNoAnti-nuisance tripping versionYesDegree of protection (IP)IP20Connectable conductor cross section solid-coremm²1 - 25Connectable conductor cross section multi-wiredmm²1 - 2501/18/2020Eaton Industries GmbH http://www.eaton.eu © 12/2019 by Eaton Industries GmbH Eaton Y7-300489 ED2019 V63.0 EN2 / 2DATASHEET - NDRBM-16/2/C/003-FElectronic RCD/MCB combination, 16 A, 30 mA, MCB trip characteristic: C, 2p, RCD trip characteristic: FPart no. Catalog No.NdRBM-16/2/C/003-F 300495Delivery program Basic functionCombined RCD/MCB device, digitalNumber of poles2 pole