Title: Maaleprotokoll 360.001-004 Ventilasjonsaggregat 25.11.16.pdf
Måleprotokoll.Vanntemp:KjøledriftBenevnelse360.01-SB502360.01-SB503 360.01-SB504 360.02-SB502 360.02-SB503 360.02-SB504 360.02-SB505 360.02-SB506 360.03-SB502 360.03-SB503 360.03-SB504 360.03-SB505 360.04-SB502 360.04-SB503 360.04-SB504 360.04-SB5057/12 °CTilhørighet360.01-LV/LK402360.01-LV/LK403 360.01-LV/LK404 360.02-LV/LK402 360.02-LV/LK403 360.02-LV/LK404 360.02-LV/LK405 360.02-LV/LK406 360.03-LV/LK402 360.03-LV/LK403 360.03-LV/LK404 360.03-LV/LK405 360.04-LV/LK402 360.04-LV/LK403 360.04-LV/LK404 360.04-LV/LK405Innreguleringsprotokoll vann:Dato:25.11.2016BRV59Utført av: Andreas HellemSystem:360.01-04 Ventilasjonsaggregat Side 1 av 1GK Rør TrøndelagTrykkfallVentiltype DimensjonForinnst. Prosjektert Målt l/hl/hkPa ▲PMålt/Prosj: Merknader:Fusion-P 407,9456045218,60,996,2Fusion-P 50 Fusion-P 40 Fusion-P 50 Fusion-P 32 Fusion-P 50 Fusion-P 32 Fusion-P 40 Fusion-P 50 Fusion-P 40 Fusion-P 50 Fusion-P 40 Fusion-P 40 Fusion-P 40 Fusion-P 40 Fusion-P 40