Title: datablad gb fx net alc.pdf
FX-IOC (0 .. 2)Clean contact relay outputs (2 pcs), max 30 VDC/ 1.0 A, function to be selected with the configuration toolAlarm device lines (4 pcs), max 500 mA each, function to be selected with the configuration toolPower supply outputs (2 pcs), short circuit protected, 500mA eachPower supply outputs (2 pcs), short circuit protected, 2 A eachFX-PSA230 VAC / 50Hz / 80VABattery 24VDC (max 2 x (2 x 12V/17Ah))Note! The maximum total load of the panel is 2,2 A. The maximum total number of LC, CLC and IOC boards is 2.FXS NET panel external connectionsFX-SAB/SACOptional serial (RS485) communication with other FX NET panelsOptional serial (RS485) communication with INFO/FMP/MCO/ABCSerial (RS232) communication with printer or maintenance tool (PC)FX-MC NETFire Alarm Router Equipment (Alarm transmitter) Fault Warning Router Equipment (Alarm transmitter)Power supply output, short circuit protected, 500mAFire Alarm Devices (Bells, sounders, flashlights), 500mA