Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 53,0 68,0 275,0 15,0 9,0Limit 100,0 - 555,0 50,0 25,0Margin 47,0 - 280,0 35,0 16,0Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,0 3,0 2,0 2,35Worst Value: Local: 36 22,3 43,8 21,5 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 14,7 9,0 5,7 314,00Remote: 78 20,7 16,9 3,8 51,75Worst Value: Local: 12 14,7 9,0 5,7 314,00Remote: 78 12,7 8,0 4,7 398,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass