Title: Data tester Smestad skole - Detaljert.pdf
1200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 23,0 12,4 10,6 390,00Remote: 12-45 23,0 12,3 10,7 393,00Worst Value: Local: 12-45 22,8 10,2 12,6 500,00Remote: 12-45 22,9 10,2 12,7 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,6 23,8 4,8 499,00Remote: 45 28,8 23,8 5,0 497,00Worst Value: Local: 36 28,6 23,8 4,8 499,00Remote: 45 28,8 23,8 5,0 498,00PS-ACRF: Pass Worst Margin: Local: 12 68,2 56,3 11,9 1,75Worst Value: Local: 45 20,5 7,2 13,3 500,00Remote: 12 72,6 61,2 11,4 1,00Remote: 12 20,4 7,2 13,2 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:08Signature:______________________ Page: 96Copper Certification Report