Title: 1 etg del 2.pdf
Cable ID: T1035 Date / Time: 10/17/2013 02:39:22 PM Headroom 11.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 5 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 78]106 168 12 15.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 78] [Pair 78] [Pair 78]14.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.7 89.3 33.1 36 14.1 89.5 30.1SR 12-36 12.4 89.5 33.1 36 14.8 89.5 30.1MAIN 12-36 11.8 92.5 32.9 36 14.3 92.8 29.8SR 12-36 12.5 98.8 32.4 36 14.9 98.8 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 26.2 6.5 42.4 45 26.6 4.8 42.1