Title: +175=737.001_IK001_Brukermanual for Refra varmepumpe.Produktinformasjon.pdf
Measure the pressure drop across the evaporator using the fittings installed by the customer for the selection pressure (the pressure drop across the valve or mesh filters should not be included in measurement). Change the value of liquid flow through the evaporator during operation of the compressor is not recommended: Setpoint change on the basis of flow rate constant and changing temperature.Check the installation. Perform all necessary tests of strength, leakage. Check functional of safety devices, check of the complete installation before putting into operation.ELECTRICAL CONNECTIONSControl panel for powering the unit has one input power cable. The decision on selecting the correct power cord must be made by work organization performing assembly, which in this case is fully responsible for the correctness of wiring installation. It should be borne in mind that information about the parameters of the cable datasheet installs only recommendatory order.