Title: +175=325.001_LV001_Beregning av veksler.Produktinformasjon.pdf
SINGLE PHASE - QUOTATION Heat Exchanger : B35TM4x100/1P-SC-S (4x2 1/2")Art No : 16106-100Connection DataF1 - F2 - F3 - F4 -ISO-G 2 1/2" A(54) ISO-G 2 1/2" A(54) ISO-G 2 1/2" A(54) ISO-G 2 1/2" A(54)Connection LocationsSide 1: Side 2:F3/F1 (In / Out) F2/F4 (In / Out)Fluid Side 1 : Water Fluid Side 2 : Ethylene Glycol - Water (30 %)Flow Type : Counter-Current SSP Alias : B35TM4DUTY REQUIREMENTS Heat load Inlet temperature Outlet temperature Flow rate Max. pressure drop Thermal lengthkW °C °C l/s kPaPLATE HEAT EXCHANGER Total heat transfer area Heat flux Mean temperature difference O.H.T.C. (available/required) Pressure drop -total* - in ports Port diameterm² kW/m² K W/m²,°C kPa kPa mmNumber of channels Number of plates Oversurfacing Fouling factor Reynolds number Port velocity% m²,°C/kWm/swww.swep.netSide 145,00 40,00 9,656 30,0 0,549Side 127,5 5,20 61,0/61,0 (up/down) 492631 3,30