Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF029 16C2/003 05.11.2020 09:59Z-LINEZ: 0.47ΩIsc: 494A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 188A Isc(0.76%): 375A Isc(1.15%): 568ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF029 16C2/003 05.11.2020 09:58Zs(rcd)Z: 0.33ΩIsc: 701A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF029 16C2/003 05.11.2020 09:59Tallberg Elektro A/S Tlf.22796640Side:10GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.717172727373747475757676TEST RAPPORTResultatRCD II: 28.5mAUci: 0.3V t: 25.0ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF029 16C2/003 05.11.2020 11:14KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF029 16C2/003 05.11.2020 11:32R LOW OhmR: 0.25Ω