Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Isc: 492A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE035 10.02.2020 09:14RCD AUTOt : 54.1ms t : 63.2ms t : 28.8ms t : 29.0ms t : >300ms t : >300ms I I: 27.0mA : 27.0mAUc: 0.1V Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE035 10.02.2020 09:39R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE035 10.02.2020 09:55R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩOBJEKT / Plan 10 / FUSE036 10.02.2020 09:15SPÆNDINGUln: 227V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE036 10.02.2020 09:15TEST RAPPORTSide:8GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.515152525353545455555656ResultatZ-LINEZ: 0.64ΩIsc: 362A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE036 10.02.2020 09:16Zs(rcd)Z: 0.20Ω