Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-49Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W2x0If an input receives a signal with incorrect polarity, the measurement results for the other channels will be significantly distorted.ConnectionsBus connectorBus interfaceReference voltage (and source)A/D converter and multiplexer6Input filterScrew terminals9876543210E7654321E0Digital/analogue valuesInput signals and type PCD2.W200 + 10.0 V + 5.0 VPCD2.W210 + 20 mA + 10 mA + 4 mA 0 mA – 20 mA0 V – 10.0 VPCD2.W220 Calculate the appropriate values with the formulae at the end of this sectionClassic 1023 512 205 0 0Digital values xx7 1023 512 205 0 0Simatic 27648 13824 5530 0 0Connection diagram for PCD2.W200Power PCDPCD2/3.W200E7E6E5E4E3E2E1E0PGND98765432102m c