Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
The battery rack is provided with leveling feet in each corner. • The battery rack minimum clearances are listed in Table 26 .Table 26: Battery rack minimum clearances From front of rack From back of the rack From top of the cabinet Side to side900 mm 200 mm minimum 300 mm 0 mm5.3.1 Installing the battery rack 1. Place the battery rack in the installation site. 2. Make sure that the rack is not against a wall that could limit the air flow.3. Make sure that there is enough clearance to install the battery packs. For the minimum clearances, see Table 26 .3. Make sure that there is enough clearance to install the battery packs. For the minimum clearances, see Table 26 .4. The battery rack can be attached to the floor through its base.© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL38 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guide5.3.2 Installation and cabling of battery packs and connection unit (DC and CAN connections)1.