Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.1 499.0 29.3 36 8.5 499.0 26.4SR 36-45 7.6 494.0 29.4 36 8.0 497.0 26.4MAIN 36-78 9.1 499.0 29.3 36 8.5 499.0 26.4SR 36-45 7.6 494.0 29.4 36 8.0 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.4 483.0 11.6 45 14.3 2.6 53.9SR 45-78 14.7 483.0 11.6 45 14.4 28.1 33.3MAIN 78-45 14.5 496.0 11.3 45 16.3 498.0 8.3SR 45-78 14.9 499.0 11.3 78 15.6 483.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.7 40.0 37.3 45 20.2 34.0 36.9SR 45-78 19.5 37.3 38.2 45 19.5 34.3 36.8MAIN 36-78 34.6 499.0 -12.3 36 33.9 499.0 -15.2