Title: økernvn 94.pdf
Cable ID: D3193 Date / Time: 09/11/2013 03:11:30 Headroom 1.9 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]164 250 8 7.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]15.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 3.4 43.8 47.6 36 5.4 43.8 45.2SR 36-45 1.9 43.3 47.7 36 4.2 43.3 45.3MAIN 12-36 5.8 213.0 36.5 12 7.0 213.0 33.9SR 36-45 5.4 250.0 35.3 36 6.1 248.5 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 11.7 200.0 18.2 45 14.1 158.5 17.2