Title: SysAQ R32 100HP.pdf
The certified performances, conditions and the certification of the software have to be verified in www.eurovent-certification.com Systemair AC SELECT v1.0| 2022-08-15SYSAQUAR32 HSYSAQUA R32 100.H.AC‘systemairREFRIGERANT CIRCUIT The unit has one refrigerant circuit consisting of: scroll tandem compressors, plate heat exchanger, electronic expansion valve, 4-way reversecycle valve and liquid receiver, condenser coil, as well as safety and control devices such as high pressure switch, additional pressure relief valve for sizes 150 and 170 and high/low pressure transducers.COMPRESSORSThe unit is equipped with 2 scroll compressors assembled together to form tandem compressors. The compressors are mounted on rubber pads in order to eliminate noise and vibration transmissions. A phase sequence monitor is supplied as standard.INDOOR HEAT EXCHANGER