Title: DOCA0005EN-12.pdf
0x0100 = Digital Output associated to overload alarmActivated Status:0xAFCC45005R1Bitmap–0x0000 = Alarm is inactive0x0100 = Alarm is activeUnacknowledged Status:0xAFCD45006R1Bitmap–0x0000 = Historic alarm is acknowledged by the user0x0100 = Historic alarm is unacknowledged by the user0xAFCE45007R4DATETIME –Last Alarm - Time Stamp0xAFD245011R2Float32kWLast Alarm - ValueLVCT Angle compensation and Ratio compensation (iEM3455 / iEM3555)AddressRegisterAction (R/W/WC)SizeTypeUnitsDescription0xDEB657015R2Float32radAngle compensationRange: -7 to 10xDEB857017R2Float32–Ratio compensationRange: 0 to 264DOCA0005EN-12iEM3000 series user manualCommunications via ModbusRead Device IdentificationThe meters supports the Read Device Identification function with the mandatory objects VendorName, ProductCode and Revision Number.Object IDName/Description LengthValueNote0x00VendorName16