Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Ulpe: 234VUnpe: 0Vf: 50.0HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 026 GODKJENT* 12.03.2020RCD T .iDronning M.g.13 /1270852020 _ 1630KONTINUITETR:16527GODKJENT28.5mAUci: 0.3Vt: 14.2msIdn: 30mAtype: ACH\,Ulim: 25VGODKJENT *E.433.11.01 TNS / Sikring 026GODKJENT0.1QGrenseverdi: 1.0QDronning M.g.13 /12.03.2020R LOW OhmR:E.433.11.01 TN~S / Sikring 026 GODKJENT*16:30GODKJENT0.08QR+: 0.1QR: 0.1QGrenseverdi: 1.0QDronning M.g.13 /12.03.2020ZLINEZ:E.433.11.01 TN-S / Sikring 026 GODKJENT* 16:38GODKJENT0.34QIsc: 685ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.13 / E.433.11.01 TNS / Sikring 02612.03,2020. 16139,ZsZ:(red) GODKJENT0.14QIsc: 1.70kAGODKJENT*Sikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0ANr.TEST RAPPORTResultatR ISO GODKJENTR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQ