Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36-45 29,5 26,7 2,8 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 67,5 57,3 10,2 2,20Remote: 45-12 67,5 57,3 10,2 2,20Worst Value: Local: 12-36 21,1 10,4 10,7 489,00Remote: 12-36 21,2 10,5 10,7 482,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,6 23,9 2,7 496,00Remote: 36 28,4 23,8 4,6 500,00Worst Value: Local: 36 26,6 23,9 2,7 496,00Remote: 36 28,4 23,8 4,6 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,4 61,2 11,2 1,00Worst Value: Local: 45 19,6 8,0 11,6 459,00Remote: 12 71,0 61,2 9,8 1,00Remote: 12 19,7 8,0 11,7 459,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:04Signature:______________________ Page: 73