Title: 370.011 RT400 og RT500 Siemens temperaturfoler.pdf
8 0 D 7 4 8 1(cid:45) [°C]LegendR (cid:45) (cid:39)(cid:45)Resistance value in Ohm Temperature in degrees Celsius Temperature differential in KelvinMechanical designThe immersion temperature sensors consist of the following components: (cid:120) Two-sectional plastic housing comprised of base with connection terminals and re-movable cover (snap-on design)(cid:120) Immersion rod complete with sensing element The connection terminals can be accessed after removing the cover. The cable entry is via a grommet which, if required, can be replaced by a cable entry gland M16 (IP54).Accessories (not included in standard delivery)NameMaterialNominal pressureType of sealingImmersion lengthType referenceCompression fitting V4A (1.4571)PN 16Threaded with sealing means---AQE2102Protection pocketBrass (CuZn37)PN 10Threaded with sealing means100 mmALT-SB100Protection pocketBrass (CuZn37)PN 10Threaded with sealing means150 mmALT-SB150Protection pocket