Title: 2wayEPIV_Modbus-Register_en.pdf
0:Actuator not connected 1:Air/Water 2:VAV / EPIV 3:Fire 4:Energy Valve 5:6way EPIVR54 Relative Position0...10'000%0.01R65 Absolute Position0...max angle°1R76 Relative volumetric flow0...100%0.01RRelative volumetric flow of Vnom87 Absolut volumetric flow0...Vnoml/min1R98 Sensor 1 ValueCurrent value of sensor 1, depending on the setting of the Sensor Type (Register 108)0...65'535mV 0 / 11 10.1 0.1R1091110 Absolute volumetric flow in selected unitsUnitSel0.001RAbsolute flow in unit selected (Register 118) LowWord. Lower 16 bit of 32 bit value1211 Absolute volumetric flow in selected unitsAbsolute flow in unit selected (Register 118) HighWord. Upper 16 bit of 32 bit value1312 Setpoint Analog0...10'000%0.01RShows the setpoint in % if actuator is control by analog signal.4 / 6Modbus-Register 2-way EPIV • en • v1.0 • 05.2018 • Subject to changeswww.belimo.com2-way EPIV