Title: 32 Pumper modbuss teknisk data.pdf.pdf
New ControlMode value = 1 (0x0001)If there is no response from the slave, see Fault finding, section 14.1.2 CIM/CIU 200 Modbus communication faults or 14.2.2 CIM/ CIU 260 3G/4G cellular communication faults.13.12 Starting the E-pumpThis section shows how to start the E-pump.In the example, slave address 0x01 is used.Set the ControlRegister to the following values:Bit 0:1 (set the E-pump to remote mode)Bit 1:1 (start the E-pump)Bit 2:0 (do not send a reset fault command)Bit 3:0 (direction: clockwise rotation)Bit 4:0 (do not copy remote settings to local)Bits 5-15: 0 (reserved values)Hence the value to set is 0b0000000000000011: 0x0003.Request from master to slaveFieldValueDescriptionSlave address0x01Function code0x06Write single registerStart address HIStart address LO0x000x64ControlRegister address: 00101 (0x0065)Value HIValue LO0x000x03ControlRegister value: 3 (0x0003)Example of response from slave to masterFieldValue