Title: 2 etg del2.pdf
Cable ID: D2029 Date / Time: 10/10/2013 12:05:51 PM Headroom 11.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]81 129 9 3.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.5 80.5 33.9 36 13.4 88.5 30.2SR 12-36 12.1 92.5 32.9 12 14.2 92.5 29.9MAIN 12-36 11.8 92.5 32.9 36 13.5 92.5 29.9SR 12-36 12.1 92.5 32.9 12 14.2 92.8 29.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 22.1 95.8 19.0 36 23.3 3.1 45.7