Title: 2 etg del2.pdf
Cable ID: T2214 Date / Time: 10/11/2013 07:53:20 AM Headroom 11.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]235 372 26 10.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.1 82.5 33.7 36 13.8 82.5 30.7SR 36-45 19.0 28.8 41.1 36 20.0 28.8 38.1MAIN 12-36 11.7 100.0 32.3 36 13.9 97.8 29.5SR 36-78 20.2 96.8 32.5 78 21.3 96.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 24.2 86.3 19.9 12 25.3 84.8 17.1