Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]42.3 184 3 6.17Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]23.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 10.5 500.0 29.2 36 10.3 500.0 26.4SR 36-45 8.1 483.0 29.6 36 8.3 491.0 26.6MAIN 12-45 10.5 500.0 29.2 36 10.3 500.0 26.4SR 36-45 8.3 491.0 29.4 36 8.3 491.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.9 4.5 52.2 45 14.0 3.5 51.4SR 36-45 14.9 4.5 52.2 45 14.0 3.0 52.7MAIN 12-45 17.4 500.0 11.3 45 16.7 476.0 8.7SR 45-12 17.4 500.0 11.3 45 16.8 477.0 8.70100806040200250 MHzACR-F (dB)