Title: 40 Produktark nettanalysator 4x-serie.pdf.pdf
On the following table, possible connection errors that may be encountered during connection test and their corresponding error codes that are displayed on the device screen.Test Error CodeTest Code Description0All connections are correct1Phase-1 current direction is reversed2Phase-2 current direction is reversed3Phase-3 current direction is reversed4Phase-1 and Phase-2 voltage connections are reversed5Phase-1 and Phase-3 voltage connections are reversed6Phase-2 and Phase-3 voltage connections are reversed7Voltage connection phase sequence will be changed as L1,L2,L3 - L3,L1,L2.8Voltage connection phase sequence will be changed as L3,L2,L1 - L3,L1,L2.9CT-1, CT-2 will be swapped.10CT-1, CT-3 will be swapped.11CT-2, CT-3 will be swapped.12Test conditions are not met.Line Termination Resistor