Title: økernvn 94.pdf
Cable ID: D3044 Date / Time: 09/12/2013 09:56:12 Headroom 0.9 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 36]209 332 24 9.0209 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 245.0 35.5 36 1.2 243.5 32.9SR 36-78 8.9 151.0 38.9 12 9.0 244.0 32.9MAIN 36-45 1.0 250.0 35.3 36 1.2 243.5 32.9SR 12-36 9.4 245.5 35.5 12 9.0 245.5 32.8100806040