Title: 360.001 - Tilluft.pdf
3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeDUCT187 T-BRANCHDUCT188 SUPPLYDUCTREDUCERDUCT189 T-BRANCHDUCT190 SUPPLYProductTCPU_DK-*-*0,0,1,0Tellus-Lov-H-160MAGIR-CC1-*-*TCPU_DK-*-*0,0,1,0Tellus-Lov-H-160Size250250/160160160250250/200200200/160160160L [m]1,02,70,82,32,85qv [m³/h]460460230230230230230230230230v [m/s]2,62,63,23,21,31,32,02,03,23,2dpt [Pa]0,4 Sound in:Attenuation: Addition:5,3 Sound in:Attenuation: Addition:Dividing:2,6 Sound in:Attenuation: Addition:15,8 Sound in:Attenuation: Addition:Total Lw:0,1 Sound in:Attenuation: Addition:0,1 Sound in:0,7 Sound in:Attenuation: Addition:3,7 Sound in:Attenuation: Addition:Dividing:2,7 Sound in:Attenuation: Addition:15,9 Sound in:Attenuation: Addition:Total Lw:63 [dB]50.80.1 +12.950.70.0 +24.05.445.40.3 +13.345.120.0 +26.7