Title: 2wayEPIV_Modbus-Register_en.pdf
Communicative characterised control valve with sensor- operated flow control, 2-way (EPIV)No. Adr. DescriptionCommentRange / EnumerationUnit Scaling Values Default10099 Bus TerminationBy activating the bus termination a 120Ω resistor will be set0: inactive 1: active0101100 Series Number 1st partEach device has an unambiguous series number which is either impressed on or glued to the housing. The series number consists of 4 segments, although only parts 1, 2 and 4 are displayed on Modbus. Example 00839-31324-064-008 1st part: 00839 2nd part: 31324 3rd part: 008102101 Series Number 2nd part103102 Series Number 4th part104103 Firmware VersionFirmware version of communication module Example 302 : Version 3.02105104 Malfunction and Service InformationValue is bit-coded. More than one bit can be set to 1. Bit3 to Bit4 and Bit10 to Bit15 are not used for this actuator range.