Title: V20-03-02 VVS-anlegg plan 3 - DM3.pdf
ø250 UK=2568WISE IAQø315 UK=25350 0 2 Ø T 1 0 0 K Sh / ³m 0 8 3 : Q0 5 2 Ø T 1 0 0 Q Sh / ³m 0 2 7 Q:ø250 UK=2600SF002T-250 Tilpasses himlingsgridWISE IOREOpp/ned 320.102: 54 mm UK = 154 320.102: 54mmø200 UK=2650LD010T Maks:120 m³/h Kjøling: 345 W 0.027 L/sLD010T Maks:120 m³/h Kjøling: 345 W 0.027 L/sLD010T Maks:120 m³/h Kjøling: 345 W 0.027 L/sLD010T Maks:120 m³/h Kjøling: 100 W 0.008 L/sLD010T Maks:120 m³/h Kjøling: 100 W 0.008 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/sLD010T Maks:120 m³/h Kjøling: 280 W 0.022 L/s Varme: 300 W 0.007 L/s+03 = 370.101 - OE 034 0.375 L/sSTAP/STAD DN 32