Title: +038=249.001-#####._01-10203518-01-RIA-NOT-007 Lydmålinger Collier_rev01.pdf
n o i t c u d e r d n u o s t n e r a p p A4531537,43540041,550044,463046,780047,2100047,325125047,7160048,7200050,8250052,415315053,4400054,3500054,7Limit of measurement56312525050010002000 Hz 4000Frequency, f, Hz ⎯→Rating according to ISO 717- 1 R'w Evaluatio n based o n field measurement results o btained in o ne-third-o ctave bands by an engineering metho d.(C;Ct r) =45(3;8) dBC50-3150 = Ctr,50-3150 =413dB C50-5000 = dB Ctr,50-5000 =313dB C100-5000 = dB Ctr,100-5000 =28dBdBName of test institute:MulticonsultNo. of te st re port:5Date:09.02.2022Signature:HGA10203518-RIA-NOT-00722. februar 2022 / Revisjon 00Side 13 av 30Dronning Mauds gate 1-3multiconsult.noKontrollmålinger av lydisolasjon plan 5, akse 0-8Vedlegg 2.6Apparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation betw een roomsClient: Description: