Title: Bytesteinen 1 - =514.202-FS001.pdf
Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]39.7 203 14 7.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]24.0 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 7.3 214.0 34.3 7,8 9.4 217.5 31.2SR 4,5-7,8 8.1 249.5 33.1 4,5 10.4 217.5 31.2MAIN 4,5-7,8 7.3 214.0 34.3 7,8 9.4 217.5 31.2SR 4,5-7,8 8.1 249.5 33.1 4,5 10.5 249.5 30.2PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 14.2 4.6 50.0 4,5 15.1 3.1 50.4SR 4,5-7,8 14.3 2.9 54.1 4,5 15.1 3.1 50.4MAIN 4,5-7,8 15.1 199.0 17.3 4,5 16.5 195.0 14.5