Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]30.9 135 3 4.59Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]27.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.0 472.0 29.8 36 7.3 472.0 26.9SR 36-45 6.7 491.0 29.4 36 7.2 491.0 26.6MAIN 36-45 7.1 499.0 29.3 36 7.4 499.0 26.4SR 36-45 6.7 491.0 29.4 36 7.2 491.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 30.1 35.7 45 13.8 2.4 54.7SR 36-45 14.7 44.5 32.3 45 13.9 2.6 53.9MAIN 78-45 14.8 438.0 12.4 78 15.7 474.0 8.7