Title: økernvn 94.pdf
01008060402002550 MHzACR-F (dB)N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.8 4.6 49.7 12 20.4 4.6 46.7SR 12-36 17.7 4.9 49.2 12 20.3 4.9 46.2MAIN 12-36 28.2 96.8 12.5 36 30.1 96.8 9.5SR 12-36 27.1 96.8 12.5 36 28.9 96.8 9.501008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 10.0 78.8 13.0SR 78 9.1 78.5 13.1MAIN 78 10.0 78.8 13.0SR 78 9.1 78.8 13.001008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575100100100100Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA00265 ft60Insertion Loss (dB)50403020100025