Title: økernvn 94.pdf
100002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: T4039 Date / Time: 09/11/2013 10:04:26 Headroom 13.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]148 234 16 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.6 95.3 32.7 36 15.3 93.0 29.8SR 12-36 13.1 53.0 36.8 36 14.4 99.8 29.3MAIN 12-36 13.6 95.3 32.7 36 15.6 99.8 29.3SR 12-36 13.3 99.8 32.3 36 14.4 99.8 29.3