Title: DOCA0005EN-12.pdf
– by Internal Clock: the device clock controls the active tariff. If you set the Control Mode to by Internal Clock, you must also configure the schedule. Set the time when each tariff period starts, using the 24 hour clock format (00:00 to 23:59). The start time of the next tariff is the end time of the current tariff. For example, T2 start equals the end of T1.ContrastContrast1-9Increase or decrease the value to increase or decrease the display contrast.Password (iEM3110 / iEM3115 / iEM3310)Password0-9999Sets the password for accessing the meter configuration screens and resets.Reset ConfigReset Config—Settings are reset to their defaults, except for Password. Meter restarts.Configuration menu for iEM3150 / iEM3350WiringTypeFrequencyFrequencyDateDateTimeTimeCommunicationSlave AddressBaud RateParityContrastContrastReset ConfigReset ConfigSectionParameterOptionsDescription3PH4W1PH2W L-NWiringType1PH2W L-L1PH3W L-L-N