Title: Kjøring av Refra varmepumpe - Kjøling - 152 kW.pdf
6FE-44Y Refrigeration and Air conditioning R134a Dew point temp. 2,00 °C 48,0 °C 5,00 K 10,00 °C Auto 400V-3-50Hz 100% 100%Compressor Capacity steps Cooling capacity Cooling capacity * Evaporator capacity Power input Current (400V) Voltage range Condenser Capacity COP/EER COP/EER * Mass flow Operating mode Discharge gas temp. w/o cooling6FE-44Y-40P 100% 78,9 kW 76,1 kW 78,9 kW 24,4 kW 47,6 A 380-420V 103,3 kW 3,23 3,11 1953 kg/h Standard 72,7 °CTentative Data. *According to EN12900 (20°C suction gas temp., 0K liquid subcooling)Application Limits 100%Legend4 / 10additional coolingsuction gas superheat >10KM1: motor 1M2: motor 2M3: motor 3Døli KjøledriftBITZER Software v6.5.0 rev160728.09.2016 / All data subject to change.Technical Data: 6FE-44YDimensions and ConnectionsTechnical Data