Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Note that in most applications the outputs place the heaviest load on the 24 V supply. For 16 outputs with a load current of 0.5 A each, the loading will be 8 A with all outputs connected.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-252-2Cabling230V supply lines and signal lines must be laid in separate cables at least 10 cm apart. Even within the switching cabinet, it is advisable to leave space between power and signal lines. 2230V supply lines and signal lines must be laid in separate cables at least 10 cm apart. Even within the switching cabinet, it is advisable to leave space between power and signal lines. 2Digital signal / bus lines and analogue signal / sensor lines should be laid in separate cables It is advisable to use shielded cables for analogue signal lines.Digital signal / bus lines and analogue signal / sensor lines should be laid in separate cables It is advisable to use shielded cables for analogue signal lines.