Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]25.7 111 1 3.90Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.2 407.0 31.2 12 8.0 406.0 28.4SR 12-36 8.9 401.0 31.3 36 8.3 471.0 26.4MAIN 12-36 8.0 500.0 27.8 36 9.3 500.0 25.0SR 12-36 10.6 500.0 27.8 36 9.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.3 6.5 49.0 36 21.3 484.0 8.5SR 45-78 19.3 6.5 49.0 45 21.3 5.9 46.9MAIN 12-36 20.3 483.0 11.6 36 21.3 484.0 8.5