Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.5 369.0 32.1 36 6.6 454.0 27.2SR 12-36 8.2 455.0 30.0 36 8.4 467.0 26.6MAIN 12-36 8.1 500.0 27.8 36 7.5 499.0 25.0SR 12-36 9.3 497.0 28.0 36 9.2 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 21.1 7.4 47.9 45 21.2 500.0 8.3SR 45-78 21.1 7.4 47.9 45 21.7 500.0 8.3MAIN 78-45 21.5 495.0 11.3 45 21.2 500.0 8.3SR 45-78 21.8 495.0 11.3 45 21.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 29.8 146.0 17.7 12 31.9 146.0 15.1SR 36-45 30.3 135.0 19.1 36 30.7 134.0 16.7MAIN 12-36 39.7 500.0 -12.4 36 39.1 499.0 -15.2SR 12-36 41.0 497.0 -12.2 36 40.8 499.0 -15.20804000250 MHzACR-N (dB)