Title: Sprinklerhode våt.pdf
Ordinary Temp. Rating 155°F (68°C) 175°F (79°C) Flow Pressure Flow Pressure GPM PSI GPM PSI (L/min) (bar) (L/min) (bar) 12x12 13 7. 13 0 (3,7x3,7) (49,2) (0,48) (49,2) (0,48) 14 x 14 14 8.2 14 8.2 (4,3x4,3) (63,0) (0,57) (53,0) (0,57) 16 x 16 9 4 4,9x4,9) (56,8) ) (0,65) 18x 18 20 x 20 18.4 21 6,1 x6,1) (1,27) (79,5) (1,27)(a) For coverage area dimensions less than or between those indicated, use the minimum required flow for the next highest coverage area for which hydraulic design criteria are stated.(b) Requirement is based on minimum flow in GPM (LPM) from each sprinkler. The associated residual pressures are calculated using the nominal K-factor. Refer to Hydraulic Design under the Design Criteria section.(c) For NFPA 13 residential applications, the greater of 0.1 gpm/ft2 over the design area of the flow in accordance with the criteria in this table must be used.MaximumCoverageArea (@Ft. x Ft.(mxm)Intermediate Temp. RatingInstallationTypeDeflector toCeilingSmoothCeilings