Title: 1 etg del 2.pdf
150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz60RL @ Remote (dB)50403020100050100150200250MHzLinkWare Version 8.1Cable ID: T1028 Date / Time: 10/17/2013 02:27:11 PM Headroom 12.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]93 147 10 3.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.0 99.0 32.4 36 14.2 99.3 29.4SR 12-36 12.6 99.3 32.4 36 14.9 99.3 29.4MAIN 12-36 12.0 99.0 32.4 36 14.2 99.3 29.4SR 12-36 12.6 99.3 32.4 36 14.9 99.3 29.4