Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
SPENNING TRMS Uln: 233V Ulpe: 233V Unpe: 1V f: 49.98HzSYS.: TN/TTColliers Plan 5 / DM3.E2=433.05.02 / XF039 C16/2/Res 11.03.2022 10:23 (TomekElektriker)RCD: Utlřsningstidt: 58.3msUc: 0.2V Idn: 30mA type: MUL.: x1 Ulim: 50V SYS.: TN/TTColliers Plan 5 / JORDING / VENTILASJON 10.03.2022 13:44 (TomekElektriker)KONTINUITET: R200mA LPER: 0.03ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩColliers Plan 5 / JORDING / VENTILASJON 10.03.2022 13:33 (TomekElektriker)KONTINUITET: R200mA LPER: 0.01ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩColliers Plan 5 / JORDING / GULV KANAL 10.03.2022 13:43 (TomekElektriker)KONTINUITET: R200mA LPER: 0.01ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩColliers Plan 5 / JORDING / GULV KANAL 10.03.2022 13:44 (TomekElektriker)KONTINUITET: R200mA LPER: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩTALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:24GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT