Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]23.6 103 2 3.59Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.1 466.0 29.5 36 8.9 476.0 26.1SR 36-78 9.2 474.0 29.1 36 9.0 480.0 25.9MAIN 36-45 9.1 466.0 29.5 36 9.7 496.0 25.2SR 36-45 10.0 496.0 28.0 45 9.5 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.5 3.5 54.4 45 14.0 3.5 51.4SR 36-45 14.6 114.5 24.1 45 13.9 2.5 54.3MAIN 45-36 15.6 481.0 11.6 45 17.6 497.0 8.3