Title: økernvn 94.pdf
SR 36-45 8.1 29.3 40.8 36 9.6 29.1 38.4MAIN 36-78 20.9 250.0 4.7 45 20.6 248.0 2.2SR 12-36 17.7 250.0 4.7 36 17.4 250.0 2.0010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 3.6 19.4 19.6SR 78 4.3 19.4 19.6MAIN 36 7.3 247.0 10.1SR 45 5.5 98.8 14.1010080050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040200050100150MHzProject: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002187 ft60Insertion Loss (dB)50403020100050100150200250MHz100NEXT @ Remote (dB)806040202500050100150200250MHz100ACR-F @ Remote (dB)806040202500050100150200250