Title: 36 Siemens GDB181-MO.pdf.pdf
A6V10631862_en--_d 2019-09-13Register “Status”Supported function codes34 / 40Siemens Smart InfrastructureReg.NameR/WValueExampleDevice information1281Factory IndexRTwo bytes, each coding an ASCII char.00 5A à 00 “Z” Device is of Series “Z”1282Factory Date HWordRTwo bytes, the lower coding the Year (hex)Read 1282 à 000FRead 1283 à 04181283Factory Date LWordRHigh byte: coding the month (hex)HWordLWordLow byte: coding the day (hex)Hex--00YY MM DD0F0418Dec00150424à Device was manufactured 24 April, 201512841285Factory SeqNo HWord RFactory SeqNo HWord RHword + LWord = HEX-representation of Sequence number:Read 1284 à 000ARead 1285 à A206AA206(hex) à 696838 (dec) à Device has sequence number 69683814091410TypeASN [Char_16..1] RTypeASNEach register: Two bytes, each coding an ASCII char.Example: 0x47 44 = GD0x42 31 = B114111412TypeASNTypeASNASN is coded beginning with reg. 14090x38 31 = 81