Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Saia-Burgess Controls Ltd.OverviewPlanning an applicationIf necessary, select the PCD2.C2000/C1000 expansion housing: ● ● ●PCD2.C2000 8 module slots or PCD2.C1000 4 module slots PCD2.K106 26-core extension cable to connect PCD2 CPUs. PCD3.K1x6 26-core extension cable to connect the last PCD2.C2000/C1000 expansion housing in a row to attached further rows of PCD2.C2000/C1000 expansion housings.2PCD2.K010 Connector to link PCD2.C2000 expansion housingsfor mounting side-by-side.For the connecing cables and plugs required, see also section 3.4.3. If PCD2.Wxxx and PCD2.Hxxx modules are used, calculate the load current at the internal +5V and V+ supply (use the worst, i.e. highest values) Check that the max. supply current for the CPU is sufficient; it generally shouldbe. Estimate consumption from the 24 V supply. Use estimated values. Theestimated values can be found in the section on the Current consumption of the PCD2 input/output modules.