Title: økernvn 94.pdf
Cable ID: D4114 Date / Time: 09/10/2013 10:14:08 Headroom 13.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]130 207 15 5.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 18.3 72.5 34.6 36 18.9 92.3 29.9SR 12-36 13.9 87.5 33.3 36 15.2 99.8 29.3MAIN 36-45 18.8 92.0 32.9 36 18.9 92.3 29.9SR 12-36 14.6 99.8 32.3 36 15.2 99.8 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 26.0 67.8 22.0 12 25.9 4.8 42.1