Title: Simployer - Data testrapport =514.204-FS001.pdf
33.8 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD53 Date / Time: 28/01/2022 13:08:11 Headroom 8.1 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]29.2 149 10 6.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]26.8 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 8.1 70.3 42.5 3,6 9.1 69.8 39.8SR 1,2-7,8 9.5 112.0 39.1 1,2 10.3 112.0 36.2MAIN 1,2-3,6 8.9 246.5 33.2 1,2 10.2 246.5 30.3SR 3,6-7,8 11.9 250.0 33.1 3,6 11.8 250.0 30.2