Title: +038=360.000-LC007T_04-Coadis line 600 Fan-coil CIAT - Manual.pdf
4.2. Air connections (cid:121)(cid:3)(cid:36)(cid:76)(cid:85)(cid:3)(cid:84)(cid:88)(cid:68)(cid:79)(cid:76)(cid:87)(cid:92) Comfort units are not designed to control the humidity of outside air. Fresh air handling must be provided by an independent system in accordance with accepted engineering practice (see CIAT air handling unit ranges).(cid:121)(cid:3)(cid:41)(cid:76)(cid:87)(cid:87)(cid:76)(cid:81)(cid:74)(cid:3)(cid:87)(cid:75)(cid:72)(cid:3)Visual 180 ° or Visual 360 ° return/discharge panel (Fig. 5): We recommend fitting this component only when the box is already installed in the suspended ceiling to prevent damage to the panel or clogging of the filter during tests when switching on for the first time.Remove the electrostatic film applied to the box's air intake.Open and remove the intake grille on the nozzle (Fig. 5, a).Fit the panel (Fig. 5, b). Warning: for improved efficiency, direct the Visual 180°nozzle towards the glass walls.