Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Average: 190 Ix, Min: 92.1 Ix, Max: 269 Ix, Min/average: 0.48, Min/max: 0.34 Height: 0.000 m, Wall zone: 0.100 mFalse colors [Ix]196131870.00Scale: 1:75DIALux Page 75Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ < Site 1/ Building 1/ Storey 10 / Trapperom / Workplane (Trapperom) / Perpendicular illuminance (adaptive) =Value grid [Ix](164 193 199 199 201 178 T T}191 245 247 }250 258) 210137 199 254 257 251 T T247 217 189 A L L 243 213 179 | £ + 4 -218 207 178T186 186 170T160 167 160| oY o0 10V139 146 143RESGREL TScale: 1:75The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 76Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Trapperom hall / Room summaryTrapperom hallClearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane