Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
29.3 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.9 486.0 28.5 36 7.4 478.0 26.0SR 12-36 6.7 459.0 29.8 36 7.8 459.0 27.0MAIN 36-45 7.4 500.0 27.8 36 8.1 500.0 25.0SR 12-36 8.2 499.0 27.9 36 9.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.5 6.5 49.0 45 20.0 500.0 8.3SR 78-45 18.4 6.0 49.7 45 20.3 4.9 48.5MAIN 78-45 19.9 499.0 11.3 45 20.0 500.0 8.3SR 45-78 20.2 499.0 11.3 45 20.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 26.0 63.5 31.1 45 25.4 63.5 28.6SR 36-45 22.3 66.5 30.5 45 22.4 67.0 27.8MAIN 36-45 35.4 500.0 -12.4 36 36.2 500.0 -15.3SR 12-36 36.1 499.0 -12.3 36 37.2 500.0 -15.30804000250 MHzACR-N (dB)