Title: DOCA0005EN-12.pdf
SNVT_freq_fFrequencyRelated topicsSee “Network propagation rate setup” on page 75 for information on variables that control the network update rate.See “Network propagation rate setup” on page 75 for information on variables that control the network update rate.You can read the following network variables to obtain configuration and status information about the meter. For information on configuring the meter, see the sections on meter configuration properties and the LonWorks plug-in.Network variable labelSNVT / UCPT typeDescriptionBasic information and meter configurationnvoDateTimeSNVT_time_stamp Meter date and time (DD/MM/YYYY hh:mm:ss)nvoOpTimerSNVT_count_32Meter operation timer: the time in seconds since the meter was last powered upSystem configuration informationPower system configuration:0 = 1PH2W L-N1 = 1PH2W L-LnciSystemTypeSNVT_count2 = 1PH3W L-L with N3 = 3PH3W11 = 3PH4W13 = 1PH4 wire multi L-NnciWireNumSNVT_countNumber of wires2, 3, 4