Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
WARNING! Use type A two-pole selective (S) RCDs. Any leakage currents at the loads will be added to that of the UPS, so that current peaks can occur during transients (loss and restoration of mains supply), although these will be of very short duration. Where loads generate high leakage current, ensure the rating of the RCD is suitably matched. Always conduct a preliminary test for current leakage to earth. When connecting the UPS to the mains and the load, it is strongly recommended that protective devices are installed. The protective devices must use approved components that meet safety standards.Always refer to local wiring regulations for correct cable sizes and protective device ratings depending on instal- lation environment.ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0013. REAR VIEWFanInput protection (magneto-thermal)Input and output terminal boardUSB serial portITYS 6 kRS232 serial connectorEPO (Emergency Power Off)Dry contactSlot for optional communication cardsParallel port