Title: 1 etg del 2.pdf
Cable ID: T1107 Date / Time: 10/17/2013 03:11:38 PM Headroom 13.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]274 436 33 11.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]5.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.9 59.8 36.0 36 15.9 93.3 29.8SR 12-36 13.3 83.5 33.6 36 15.2 97.8 29.5MAIN 12-36 15.0 93.3 32.8 36 16.1 100.0 29.3SR 12-36 13.4 98.0 32.4 36 15.2 98.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.4 41.0 26.4 36 18.3 39.5 23.7