Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Resistance to interference: acc. to IEC 801-4 Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption:4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 1 … 15 mA typically 10 mA 0 mAmax. 32 mATerminals:Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²1) With external protective diode 2) With reverse voltage protection 3) These ratings are not UL-listedIn the appendix, Chapter A.4 relay contacts, are calculation data and wiring sug- gestions for the relay contacts. These data should be absolutely considered for safe switching and a long life span of the relays.5-36PCD2.A210LEDs and connection terminalsBusBus interfaceA3A0RelayA2A1Contact protectionLEDScrew terminals9876 A354 A232 A110 A0Relay contacts A0 to A3 Supply 24 VDC for Relay coilsOutput circuits and terminal designations u B D C Ps u B O/ IAdress- LED A3