Title: økernvn 94.pdf
4020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 7.4Cable ID: T4089 Date / Time: 09/11/2013 12:33:24 Headroom 12.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]96 153 11 4.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.3 85.0 33.5 36 13.8 85.0 30.5SR 12-36 12.7 61.3 35.8 36 14.5 68.0 32.1MAIN 12-36 12.9 98.8 32.4 36 13.8 99.0 29.4SR 12-36 12.7 95.3 32.7 36 14.5 95.5 29.610080604020NEXT (dB)