Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 12-45 8.3 468.0 29.9 45 8.6 491.0 26.6SR 36-45 8.2 487.0 29.5 36 8.3 484.0 26.7MAIN 12-45 8.4 491.0 29.4 45 8.6 491.0 26.6SR 36-45 8.2 487.0 29.5 36 8.4 487.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.0 471.0 11.8 78 14.3 493.0 8.4SR 78-45 14.0 494.0 11.4 45 14.3 471.0 8.8MAIN 45-78 14.1 494.0 11.4 78 14.3 493.0 8.4SR 78-45 14.0 494.0 11.4 45 14.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.5 46.5 35.4 36 20.6 42.0 34.2SR 36-78 20.9 49.3 34.6 36 21.0 49.3 32.1MAIN 12-45 34.0 491.0 -11.8 45 34.9 500.0 -15.3SR 36-45 33.9 488.0 -11.6 36 35.1 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.8 491.0 8.0SR 12 7.5 495.0 8.0MAIN 12 6.8 491.0 8.0SR 12 7.5 495.0 8.040010080250 MHz