Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
Water flow l/h 493 383 318 749 512 365 886 663 423 1152 912 734 1817 1262 842EmissionkW 2,87 2,22 1,85 4,36 2,98 2,12 5,15 3,85 2,46 6,70 5,30 4,27 10,56 7,34 4,90Water flow l/h 272 213 178 420 290 209 494 373 241 642 512 415 1015 713 481EmissionkW 3,17 2,48 2,07 4,89 3,38 2,43 5,75 4,34 2,81 7,47 5,95 4,82 11,81 8,29 5,60Water flow l/h 330 257 214 505 347 249 595 448 288 774 615 497 1222 854 574EmissionkW 3,83 2,99 2,49 5,87 4,04 2,90 6,92 5,20 3,35 9,00 7,15 5,78 14,21 9,93 6,67Water flow l/h 387 300 250 589 404 289 696 522 335 904 717 578 1428 994 666EmissionkW 4,49 3,49 2,91 6,85 4,70 3,36 8,09 6,07 3,89 10,51 8,34 6,72 16,60 11,56 7,74Water flow l/h 500 387 322 758 517 368 896 670 427 1165 922 741 1837 1274 849EmissionkW 5,82 4,51 3,75 8,81 6,01 4,28 10,42 7,79 4,96 13,54 10,72 8,61 21,37 14,82 9,87Emission correction factors for different working conditions. Multiply the factors by the emission figures in the 7-12°C table above.Water (°C) 7/12 °C 10/15 °C 14/18 °C