Title: 2 etg del2.pdf
[Pair 12] [Pair 45] [Pair 45] [Pair 45]96 146 5 4.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]21.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 232.5 35.9 36 7.1 218.5 33.7SR 36-78 5.3 218.5 36.3 36 5.0 225.5 33.5MAIN 12-36 7.1 232.5 35.9 36 7.1 218.5 33.7SR 36-78 6.0 248.0 35.4 36 5.7 249.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.3 5.3 49.8 12 16.1 2.6 52.8SR 12-36 16.3 5.3 49.8 12 16.1 2.8 52.4MAIN 12-36 17.4 233.5 16.8 36 18.5 247.0 13.3SR 12-36 16.9 236.5 16.7 36 18.5 236.5 13.7010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-78 21.4 60.3 31.3 12 21.4 60.0 28.8