Title: 32 Pumper modbuss teknisk data.pdf.pdf
Actual selection between Direct/Inverse control. 0: Inverse control 1: Direct control Only available on MAGNA3 and MGE model H and later.23)B G(h si lg n EE n gl is h(G B)9.7 Pump data register blockRegisters in this block can be read by means of function codes 0x03 and/or 0x04. They are read-only. The table below shows which registers each E-pump type supports.Unless otherwise stated, the data type used for counters and scaled values is always an unsigned integer.Table legend3-ph:3-phase only.CUE: CUE drive only.MGE: Pumps with MGE motor only.G:Only available on model G and later versions.H:Only available on model H and later versions.S:Sensor required.:Always available.:If the E-pump is a TPE Series 2000, the value is estimated and always available.Address Register nameDescription00301HeadActual system head/pressure.00302VolumeFlowActual system flow.00303RelativePerformancePerformance relative to maximum performance.00304