Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]31.6 136 1 4.72Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.6 453.0 30.2 12 7.5 453.0 27.3SR 12-36 8.1 461.0 30.0 36 8.8 469.0 27.0MAIN 12-36 6.4 495.0 29.3 36 7.6 499.0 26.4SR 12-36 8.5 499.0 29.3 36 9.2 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.7 4.5 52.2 45 18.3 4.5 49.2SR 45-78 15.8 5.0 51.3 45 18.3 3.9 50.5MAIN 78-45 19.1 500.0 11.3 45 19.9 500.0 8.3SR 78-45 18.9 500.0 11.3 45 20.8 500.0 8.30100806040200250 MHzACR-F (dB)