Title: økernvn 94.pdf
Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: D4178 Date / Time: 09/09/2013 02:12:33 Headroom 6.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]174 266 10 8.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]14.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.3 213.0 36.5 36 8.8 250.0 32.7SR 12-36 6.1 246.0 35.5 36 7.3 161.0 35.9MAIN 36-78 9.0 249.0 35.4 36 8.8 250.0 32.7SR 12-36 6.1 246.0 35.5 36 7.4 246.0 32.810080604020NEXT (dB)