Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 45-36 17.6 467.0 11.8 45 20.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 28.5 124.5 20.5 45 28.4 125.0 17.9SR 45-78 29.6 108.5 22.9 45 29.6 102.5 21.3MAIN 36-45 40.3 498.0 -12.3 45 40.5 499.0 -15.2SR 36-45 37.5 498.0 -12.3 36 38.6 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.2 500.0 8.0SR 45 5.7 500.0 8.0MAIN 45 6.2 500.0 8.0SR 45 5.7 500.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00420.1 m60Insertion Loss (dB)504030201000250 MHz