Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
33.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 10.3 422.0 30.8 36 9.5 459.0 27.0SR 36-45 8.6 403.0 31.3 36 9.0 489.0 25.5MAIN 36-78 11.0 497.0 28.0 36 9.7 496.0 25.2SR 36-45 9.0 474.0 29.1 36 9.0 489.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.6 3.8 53.8 45 13.8 2.9 53.1SR 45-36 15.6 3.8 53.8 45 13.8 2.9 53.1MAIN 45-36 17.5 464.0 11.9 45 20.0 464.0 8.9SR 36-45 17.5 464.0 11.9 45 19.6 471.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 30.7 172.5 14.5 45 30.6 158.0 13.6SR 36-45 31.5 159.0 16.1 45 31.5 165.5 12.7MAIN 36-78 43.8 497.0 -12.2 36 42.5 496.0 -15.0SR 36-45 42.6 489.0 -11.7 36 41.6 489.0 -14.50804000250 MHzACR-N (dB)