Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
MAIN 45-78 33.7 234.0 8.2 78 33.7 224.0 6.5SR 12-36 33.9 222.5 9.3 36 34.2 221.5 6.8MAIN 12-36 40.4 492.0 -11.9 45 41.7 496.0 -15.0SR 36-45 41.3 496.0 -12.1 36 41.4 494.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.7 486.0 8.0SR 45 7.2 486.0 8.0MAIN 45 7.7 486.0 8.0SR 45 7.2 486.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: SP1 BANK 4 ETGSMN 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00412.9 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100