Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 41,6 68,0 216,0 12,0 6,8Limit 100,0 - 555,0 50,0 25,0Margin 58,4 - 339,0 38,0 18,2Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,0 2,3 1,75Worst Value: Local: 36 17,9 43,7 25,8 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 14,3 8,8 5,5 334,00Remote: 12 23,4 15,1 8,3 77,75Worst Value: Local: 12 14,3 8,8 5,5 334,00Remote: 12 16,8 8,4 8,4 367,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 30,7 26,7 4,0 500,00Worst Value: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 30,7 26,7 4,0 500,00dB 060