Title: +038=360.000-LC008T_04-Major line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
0.230.180.350.310.340.310.430.380.070.060.110.090.130.080.300.190.350.210.440.27V10.110.120.150.270.270.330.060.060.060.110.130.16CONDITIONS: Maximum values with outlet open; Supply voltage 230V ± 10% / 50-60HzThe name plate is located on the condensate pan, on the electrical connection sideCoil capacity (litres)MAJOR LINE102A102C202A202C202D302A302B302C402C502C602D2-tube systemHot or cold water coil0.3580.5920.4780.7920.950.6280.8351.0421.2921.5423.846Major Line104X204X304X404X504X604X4-tube systemCold water coilHot water coil0.5920.1230.7920.1631.0420.2131.2920.2631.5420.3133.2060.646Diameters of coil couplings - Type of coil couplings: rotary couplings with flat face; - Type of valve couplings: threaded male couplings must be provided.MAJOR LINE102A102C202A202C202D302A302B302C402C502C602D2-tube system