Title: 40 Bender Datablad.pdf.pdf
W…, WR…, WS…, WF… series (Type A), W…AB series (Type B) on/off (on)* 68 Ω 1 Ω 800 V type A and type B depending on measuring current transformer series (type A)* 0…2000 Hz (Type B) / 42…2000 Hz (type A) none, IEC, 50 Hz, 60 Hz (none)* 0…30 A (measuring current transformer type A) 0…20 A (measuring current transformer type B) Crest factor up to 10 A = 4, up to 20 A = 2 100 mA…125 A 10 mA…10 A (type B) 6 mA…20 A (type A) (100 mA overcurrent)*CT monitoring Rated burden RCMS…-D/-L Rated burden RCMS…-D4/-L4 (channels 9…12 only) Rated insulation voltage (measuring current transformer) Operating characteristics acc. to IEC/TR 60755Rated frequency Cut-off frequency Measuring range RCMS…-D/-LMeasuring range RCMS…-D4/-L4 (channels 9…12 only) Rated residual operating current IΔn2 (alarm)Rated residual operating current IΔn2 (alarm) for RCMS…-D4/-L4 (channels 9…12 only)