Title: 2 etg del2.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.8 25.5 42.4 36 11.4 25.5 40.0SR 12-36 10.7 25.5 42.4 36 12.0 25.4 40.0MAIN 36-45 18.9 249.0 4.8 36 18.2 249.5 2.1SR 36-45 17.7 249.5 4.7 36 18.1 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.9 38.5 18.1SR 45 3.6 25.4 19.0MAIN 36 6.6 236.0 10.3SR 36 7.5 241.0 10.2010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1