Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 36] [Pair 12] [Pair 45]26.2 113 1 4.02Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.6 429.0 30.7 45 9.4 470.0 26.4SR 36-45 7.3 462.0 29.6 45 8.7 461.0 26.9MAIN 12-45 9.7 487.0 28.5 36 10.5 500.0 25.0SR 36-45 8.0 497.0 28.0 36 8.9 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.9 3.8 53.8 45 14.1 2.6 53.9SR 36-45 14.9 3.9 53.5 45 14.0 2.5 54.3MAIN 45-36 15.9 478.0 11.6 36 16.9 478.0 8.6SR 36-45 15.8 478.0 11.6 45 16.3 500.0 8.30100806040200250 MHzACR-F (dB)