Title: a4000-8001.pdf
Air connection 4 x 6 mm plastic tubePower consumption 350 mW (24mA at 15VDC)Output load Min. 5 k Ohms / Max. 2 mA∆P Ranges See Ordering dataRepeatability & Hyst. 1%Linearity ± 2% from 0 to 500 Pa± 5% from 500 to 750 PaAdjustment 1 potentiometer for 0 point, 0-25% of range1 potentiometer for span adjustment, ± 50% of nominal range(max 750 Pa)Output Voltage shift 0-25°C+ 0.08% °C25-55 °C – 0.08% °CResponse Time 50 ms max.Electrical connection Terminal block for 2.5 mm2 (maximum) section wireHousing material PolypropyleneEnclosure protection class IP 20, IP54, (IEC 60529)Weight 0,1 kgStorage Temp. limits -40 to +70 °CCompliance EMC (89/336 EEC) according to the standard EN 50081-1and EN 50082-1