Title: +038=370.101-QH009._01-Siemens Fukt_tempføler QFA3160_AQF3100.pdf
Jumper in the left position (R1) = (cid:16) 35...(cid:14) 35 °C, Jumper in the middle position (R2) = 0...50 °C (factory setting) Jumper in the right position (R3) = (cid:16)40...+70 °C(cid:120) For the active test function:Jumper in the horizontal position: The values available at the signal output are those given in the table “Test function active“.(cid:120) For the measured value display (QFA31..D)Jumper vertical in the right position - Jumper vertical in the left position= =°C (factory setting) °F(cid:120) Should the temperature sensor become faulty a voltage of 0 V (4 mA) will be applied at signal output U2 (I2) after 60 seconds, and the humidity signal at signal output U1 (I1) will reach 10 V (20 mA).(cid:120) Should the humidity sensor become faulty a voltage of 10 V (20 mA) will be applied at signal output U1 (I1) after 60 seconds, and the temperature signal will remain active.Room sensors QFA31..CE1N1858en 2016-07-21Outdoor mounting kit AQF3100Service set AQF3153