Title: 360.001 - Tilluft.pdf
3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeProductDUCTMAGID-C1-31524 FLOWDAMPER LEO-0-315DUCTMAGID-C1-315SILENCERLKR-315-1200DUCTMAGID-C1-315BEND-90MAGIB-C3-90-315DUCTMAGID-C1-315BEND-30MAGIB-C3-30-315DUCTMAGID-C1-315FIREDAMPER FKR-EU/DE/315/ZXX315315315315315315315315315315SizeSound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]0,912004,312004,30,312004,312004,37,712004,312004,30,012004,312004,30,812004,312004,3240,7 Sound in:Attenuation: Addition:18,0 Sound in:Addition:0,2 Sound in:Attenuation: Addition:11,0 Sound in:Attenuation:5,5 Sound in:Attenuation: Addition:2,8 Sound in:Attenuation: Addition:0,0 Sound in:Attenuation: Addition:1,2 Sound in:Attenuation: Addition:0,6 Sound in:Attenuation: Addition:4,8 Sound in:Addition:63 [dB]35.70.1 +25.736.0+47.547.80.0 +25.747.84.043.80.8 +25.743.10.0 +35.3