Title: +038=360.012-#####._06-BA-ESR NI-DV Controller Nicotra Gebhardt - Operating Instruction.pdf
MODBUS RTU RS485 (Baudrate: 9,6-19,2-38,4-115,2 kBaud) 2 × RJ12 & 2 × spring terminals 1 × RJ12 connection 0-10 V=, 100 % @ 9,5 V= ±2 % +10 V= Start/stop with internal pull-up Alarm reset Tacho: 1 pulse/revolution | Alarm/running signal Lit: Power connected | Flashing: Active communication Flashing: Alarm but still running | Constantly lit: Critical alarm - stop motorsec. sec.sec.Sinusoidal back-EMF signal controlled via FOC (Field Oriented Control) Yes, typically below 30% of max. speed depending on load and fan weight 15-300 15-300 Yes Via digital input, Modbus or powering down for more than 60 seconds The braking system stops the fan as quickly as possible. Braking time will depend on the inertia of the fan. Operating hours, alarms, loads, software version, max. temp., max. motor voltage, max. motor current, max. ripple voltage, max. ripple current Yes, via serial interface Preprogrammed by OJ or on-site configuration Nominal power for 1 hour at 70°C ambient temperature Yes Yes Integrated