Title: 1 etg del 2.pdf
LinkWare Version 8.1Cable ID: D1110 Date / Time: 10/17/2013 12:30:19 PM Headroom 11.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]259 413 31 11.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.6 92.0 32.9 36 14.3 92.0 29.9SR 12-36 11.7 67.8 35.1 36 13.7 99.3 29.4MAIN 12-36 12.9 96.8 32.5 36 14.3 93.3 29.8SR 12-36 11.7 98.3 32.4 36 13.7 99.5 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)