Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
supplied by IFM24160 moduleOperating temperaturefrom -5°C to +40°Cstand-by12mA35mAConsumption @ 27.6Vmaximum45mA400mA3.6IFM24160, power-supply moduleThe IFM24160 internal module supplies and distributes power through the CAN drive connection bar and through the two outputs, OUT 1 and OUT 2.In installations where several control panels are connected in a network, it is necessary to use an IFM24160 power-supply module for each control panel.In installations where the control panel comprises more than one cabinet, you can install a power supply in each cabinet. The total voltage available equals the sum of the voltages of each power supply added together minus 1A for correct cable balance.FPMCPU comes with:battery connection wire with thermal probe • battery to battery connection wire • 3 screws for securing the module to the grounding bar • wire with eyelet terminal for connection to earth • 1 ferrite • Instructions manual[A]Status LED[B]Mini USB portABCDEF