Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 15.06.2020 11:37Tallberg Elektro A/S Tlf.22796640Side:1Rapport opprettet10.09.2020GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.778899101011111212TEST RAPPORTResultatZs(rcd)Z: 0.38ΩIsc: 606A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 15.06.2020 11:38RCD II: 28.5mAUci: 0.2V t: 15.2ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 15.06.2020 11:39Z-LINEZ: 0.43ΩIsc: 539A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 15.06.2020 11:39Zs(rcd)Z: 0.37ΩIsc: 623A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 10.06.2020 15:06R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩ