Title: +038=370.104-OE004T_01-Multical 801 Energimåler Kamstrup - Installasjons- og brukerguide.pdf
Standard measurement of heat and cooling Sensor in inlet pipe (red) Sensor in outlet pipe (blue) Flow sensor in inlet or outlet pipe -Heat measurement and leak surveillance Sensor in inlet pipe (red) Sensor in outlet pipe (blue) Flow sensor in inlet pipe Flow sensor in outlet flow pipe Tank/heat exchanger temperatureEnergy measurement in open systems Sensor in inlet pipe (red) Sensor in outlet pipe (blue) Flow sensor in inlet pipe Flow sensor in outlet pipe Reference sensor (grey)Other makes of flow sensors are usually connected to terminals 10B and 11B.14Kamstrup A/S • 5512603_C1_GB_03.20167.1Examples of connectionsThe active pulse output is direct connected to the not galvanically separated flow sensor input. This permits a cable length of up to 10 m between flow sensor and calculator.