Title: økernvn 94.pdf
SR 36-45 15.6 21.1 37.7 45 17.6 29.9 31.7MAIN 36-12 18.2 250.0 16.2 36 19.5 248.0 13.3SR 36-12 18.7 249.5 16.2 36 19.4 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 12.8 18.3 46.1 36 13.6 15.1 45.7SR 36-45 11.0 243.0 5.4 36 11.1 20.8 42.3MAIN 12-36 17.5 233.5 6.3 12 17.9 233.5 3.7SR 36-45 11.1 249.5 4.7 36 11.8 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 2.7 27.9 18.8SR 36 3.2 27.9 18.8MAIN 36 5.8 245.0 10.1SR 36 7.5 156.0 12.1010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active