Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
R LOW ChmR: 0.07QR+: 0.1QR: 0.1QGrenseverdi: 1.0QTEST RAPPORTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTTEST RAPPORTNr. ResultatR ISO GODKJENTR: >200MQ Um: 262VUiso: 250VGrenseverdi. :1MQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT* | 12.03%2020 14:18SPENDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.1Hz 169 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT * | 12.03.2020 14:18 Z-LINE GODKJENT Z: 0.16Q Isc: 1.47kA Sikringstype: C SIKRING I: 1l6A SIKRING T: 35ms Isc lim: 160.0A170 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT*12.03.2020 14:19Zs (rcd) GODKJENTZ: 0.10QIsc: 2.31kASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT * 12.03.2020 14:19RCD I GODKJENTI: 28.5mAUci: 0.3Vt: 87.6msIdn: 30mAtype: ACH,Ulim: 25V