Title: +038=320.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Nettserverhåndbok.pdf
Static IP/Zeroconf: With this setting, the possibility is given to assign a pre-defined IP-address to the Energy Valve, as well to assign the subnet mask and gateway to it. This method can be used, if the network administrator is managing the network addresses without a DHCP server. DHCP/Zeroconf: With this setting it is possible, to assign automatically an IP- address to the Energy Valve. If a DHCP Server is available in the network, the Energy Valve is able to receive an IP-address from it. If there is no DHCP Server in the network, the Energy Valve is able, via Zeroconfig, to calculate an IP-address based on the ZeroConfig specification.Settings for the user managemento Users can be added, modified, or deleted..o Under "Edit selected web user" the respective password can be changedo Note: Only users with a lower or equivalent authorization can be editedT5-Webserver Manual Energy Valve• en • v3.3 • 03.2019 • Subject to changeswww.belimo.comSettings - BACnet/MP/Modbuswww.belimo.com