Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]19.6 85 1 3.12Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]31.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 11.1 451.0 30.2 36 10.0 445.0 27.5SR 36-45 6.6 451.0 30.2 45 7.7 446.0 27.5MAIN 36-78 11.6 499.0 27.9 36 10.5 499.0 25.0SR 36-45 7.2 479.0 28.8 36 9.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.9 20.4 39.1 45 13.9 2.3 55.2SR 45-78 14.9 9.8 45.5 45 14.0 8.0 44.2MAIN 45-36 16.5 473.0 11.7 36 19.3 500.0 8.3SR 36-45 16.3 473.0 11.7 45 19.1 500.0 8.30100806040200250 MHzACR-F (dB)