Title: DOCA0005EN-12.pdf
1 = for Pulse (digital output is associated with active energy pulse output)Digital output association with overload alarm:02——E011 0110360x0000 = digital output disabled0x0100 = for Alarm (digital output is associated with the overload alarm)Alarm status informationNOTE: E denotes the extension bit; the hex value assumes E = 0.Data formatPrimary VIFManufacturer-specific VIFEDescriptionbinhexAlarm status:02—E011 0111370x0000 = Alarm is inactive0x0100 = Alarm is activeAcknowledgement status:02—E011 1000380x0000 = historic alarm is acknowledged by the user0x0100 = historic alarm is unacknowledged by the user04EDE011 100139Timestamp of last alarm (DD/MM/YYYY hh:mm:ss)05—E011 10103AValue at last alarmOverload alarm configuration:02—E011 0100340x0000 = disabled0x0100 = enabled05—E011 010135The pickup setpoint in kW for the overload alarm