Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF032 16C2/003 27.11.2020 12:02KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF033 16C2/003 30.11.2020 10:54Tallberg Elektro A/S Tlf.22796640Side:16GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.111111112112113113114114115115116116117117TEST RAPPORTResultatSPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 49.9HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF033 16C2/003 30.11.2020 10:54Z-LINEZ: 0.78ΩIsc: 295A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF033 16C2/003 30.11.2020 10:54Zs(rcd)Z: 0.81ΩIsc: 284A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF033 16C2/003 30.11.2020 10:57RCD II: 28.5mAUci: 0.0V t: 88.1ms Idn: 30mA type: AC Ulim: 50V