Title: 1 etg del 2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]79 125 8 3.379 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.7 * 250.0 35.3 36 0.2 * 244.0 32.9SR 36-78 7.1 244.5 35.5 36 6.8 244.5 32.9MAIN 36-45 0.7 250.0 35.3 36 0.2 244.0 32.9SR 36-78 7.1 244.5 35.5 36 6.8 244.5 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 18.9 246.5 16.4 12 19.8 129.5 18.9SR 36-45 19.1 246.5 16.4 45 19.8 246.5 13.4MAIN 45-36 18.9 246.5 16.4 36 21.0 250.0 13.2SR 36-45 19.1 246.5 16.4 45 19.8 246.5 13.4010080604020050100150MHzACR-F (dB)2002500100806040