Title: Simployer - Data testrapport =514.204-FS001.pdf
LinkWare™ PC Version 10.4Cable ID: 521.204-UD34 Date / Time: 28/01/2022 11:15:48 Headroom 9.4 dB (NEXT 3,6-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]55.6 285 20 9.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.3 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 10.1 242.0 33.4 3,6 10.2 91.0 37.8SR 3,6-7,8 9.4 85.0 41.1 3,6 9.9 85.3 38.3MAIN 3,6-7,8 10.1 242.0 33.4 7,8 11.4 243.0 30.4SR 1,2-3,6 10.6 240.0 33.4 1,2 10.6 240.0 30.5