Title: +038=433.000-NI003._02-Testrapport Elektriske Anlegg Plan7 DM3.E5=433.07.04.docx
27,0 11 KW 51 1000 28,5 17 KW 52 0,17 1000 28,5 11 KW 53 0,17 1000 28,5 30 KW 54 0,17 1000 27,0 63 KW 55 0,30 1000 27,0 71 KW 56 0,08 1000 28,5 17 KW 57 1000 28,5 11 KW 58 0,14 1000 27,0 101 KW 59 0,18 1000 28,5 17 KW 60 1000 27,0 23 KW 61 1000 28,5 11 KW 62 1000 27,0 47 KW 63 401 27,0 92 KW 64 514 28,5 11 KW 65 346 28,5 16 KW 66 1000 28,5 15 KW 67 1000 28,5 22 KW 68 1000 28,5 14 KW 69 650 28,5 27 KW 70 1000 28,5 13 KW 71 0,02 1000 27,0 121 KW 72 1000 28,5 11 KW 73 28,5 11 KW 74 27,0 27 KW 75 27,0 41 KW 76 28,5 11 KW 77 27,0 242 KW 78 28,5 10 KW 79 28,5 17 KW 80 28,5 62 KW 81 27,0 244 KW 82 27,0 57 KW 101 (UPS) 0,03 1000 KW 102 (UPS) 0,04 1000 KW 202 (UPS) 0,07 1000 KW 201 KW 202 0,07 1000 KW 203 1000 KW 204 1000 KONTINUITETSMÅLING LEDENDE DELER LOKASJON (NORD / SØR / KORRIDOR) LOKASJON AKSE Kontinuitet Ω HIMLING N 11 0,01 VENTILASJON N 11 0,02 VINDUSKARM N 11 0,01 HIMLING S 11 0,06 VENTILASJON S 11 0,05 HIMLING K 12 0,02 DØRKARM K 12 >1999 (PUMPE FRAKOBLET) HIMLING S 12 0,01 KULVERT S 13 0,01 VINDUSKARM S