Title: 330-Strømningsvakt.pdf
DWG 1146-4Do not drill into the base as this creates metal shavings which can create electrical hazards and damage the device. Drilling voids the warranty.An uninsulated section of a single conductor should not be looped around the terminal and serve as two separate connections. The wire must be severed, thereby providing supervision of the connection in the event that the wire become dislodged from under the terminal. Failure to sever the wire may render the device inoperable risking severe property damage and loss of life. Do not strip wire beyond 3/8" of length or expose an uninsulated conductor beyond the edge of the terminal block. When using stranded wire, capture all strands under the clamping plate.Fig. 4 Typical Electrical ConnectionsWIRE CAPNEUTRALNEUTRAL FROM BREAKERNEUTRAL FROM BELLBELLZONE 1A C BREAKERLINELINE FROM BREAKERL O A D T O B E L LZONE 2ZONE 3NOTE: When connecting to a UL Listed control panel, use the panel’s resistor valve for circuit supervision.