Title: 2 etg del2.pdf
SR 12-36 8.4 16.8 47.0 36 9.5 16.8 44.6MAIN 36-45 14.3 250.0 4.7 36 14.2 250.0 2.0SR 36-45 13.6 246.0 5.1 36 13.1 246.0 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.7 20.0 19.5SR 36 2.6 13.5 20.3MAIN 36 9.2 239.0 10.2SR 36 7.4 245.5 10.1010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94