Title: 1 etg del 2.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.3 21.0 44.6 36 11.1 21.0 42.2SR 12-36 12.4 21.0 44.6 36 12.7 21.0 42.2MAIN 36-45 16.5 249.5 4.7 36 16.3 249.0 2.1SR 12-36 20.7 248.5 4.8 36 22.3 247.0 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 2.9 28.4 18.7SR 36 3.5 70.3 15.5MAIN 45 8.3 238.0 10.2SR 36 4.9 250.0 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1