Title: Ahlsell.pdf
LinkWare™ PC Version 11.1Cable ID: UD 2 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 12:36:08 PM Operator: Pam Headroom 6.2 dB (NEXT 1,2-4,5) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 4,5] [Pair 4,5] [Pair 3,6]15.9 78 1 5.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]34.7 500.0 43.8Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 11.1 497.0 26.7 4,5 11.6 26.3 48.8SR 1,2-4,5 6.2 299.0 34.1 1,2 8.7 299.0 31.4MAIN 3,6-4,5 11.1 497.0 26.7 3,6 12.6 497.0 23.8SR 1,2-4,5 8.4 485.0 27.1 4,5 9.7 485.0 24.210080604020NEXT (dB)