Title: 40 Bender brukermanual.pdf.pdf
1. Use the "" button to go to the measuring channel setting. Press the "↵" button.2. Use the Up/Down buttons to select a single measuring channel or all measuring channels (1…12). Press "↵" to confirm your selection.Chan.: 1 Exit 1.Modific.: 10% 2.Overwrite:yesIf the measuring channel settings only differ slightly, we recommend to proceed as follows: - first set all the measuring channels (1…12) to the same value - then modify the settings of an individual measuring channel.s1. Modific. A new measured value will be saved if it differs from the previous measured value by the percentage value defined here. Setting range: 0…100 %, resolution of setting 1 %.70RCMS460-490_D00067_03_M_XXEN/12.2017NoIf the memory (300 measuring values) for this measuring channel is full, the oldest measured value is deleted to create space for the new measured value entry. Data logger records 300 measured values then stops.