Title: bn305_cgb.pdf
Features•Interactive For interfacing and controlling external units to Autronica’s interactive fire detection systemsMulti function unit: Function selected by switch setting. • • Input/Output signals 2 non-isolated inputs: on /off function with end-of-line monitoring 2 outputs: Potential free contact without end-of-line monitoring 1A 30 VDC dry relay contact for the output ports Includes the SelfVerify function for reduced maintenance/testing and increased reliability on the input for critical alarm functions Short-circuit isolator in each unit Automatic addressing Proven technology