Title: DM1-3 plan 05 lysberegningsrapport.pdf
Ground area: 16.92 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.520 m | Mounting height: 2.600 m55201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M6 SummaryResultsSymbolCalculatedVisual task areasĒ Task Area847 lxg1 Task Area0.80Ē Surrounding area599 lxg1 Surrounding area0.65Ē Background area210 lxg1 Background area0.74Consumption valuesConsumption[120 - 190] kWh/aLighting power densityRoom5.91 W/m²Utilisation profile: Offices, Conference and meeting roomsLuminaire listpcs.Manufacturer Article No.Article name2Fagerhult22226-402Notor Rec Delta 3K 2400 white HL Single CLOTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 600 kWh/aPΦ50.0 W4996 lmCheckLuminous efficacy99.9 lm/W56201104 DM1-3 McKinseyBuilding 1 · Storey 1 · Corridor and reception Summary