Title: 563.X0X-RY001 SLASXCX - temperatur og CO2 sensor.pdf
SLAWXCV2SLA Prem HSG CO2 BlankNoneNDIR CO2 / VOC2% RH SensorOptimum, WhiteSLAWXCVXSLA Prem HSG CO2 BlankNoneNDIR CO2 / VOCNoneOptimum, WhiteSLAWXCXSLA Prem HSG CO2 BlankNoneNDIR CO2NoneOptimum, WhiteReplaceable RH ElementsModelRH Accuracy Calibration Certificate DescriptionSLXRHS1N±1%XReplaceable RH Sensor, 1% w/NIST CertSLXRHS2N±2%XReplaceable RH Sensor, 2% w/NIST CertSLXRHS2X±2%Replaceable RH Sensor, 2%© 2021 Schneider Electric. All rights reserved. All trademarks are owned by Schneider Electric Industries SAS or its affiliated companies.September 2021F-28161-6 nkschneider-electric.com | 3SpecificationsOperating EnvironmentRange0 to 50 °C (32 to 122 °F)Input powerClass 2; 20 to 30 Vdc, 24 Vac, 50 to 60 HzDisplay ModelsAnalog outputOperating temp. range Operating hu- midity range Housing materialIP ratingSelectable 4 to 20 mA, 0 to 5 V, 0 to 10 V0 to 50 °C (32 to 122 °F)0 to 95% RH non-condensing