Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: D3092 Date / Time: 09/11/2013 02:21:23 Headroom 5.3 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]94 149 11 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.7 245.5 35.5 78 9.0 234.5 33.2SR 36-45 5.3 239.0 35.7 36 5.5 235.0 33.2MAIN 36-78 8.7 245.5 35.5 36 9.2 244.5 32.9SR 36-45 5.5 250.0 35.3 36 5.5 238.5 33.010080604020NEXT (dB)