Title: BREEAM-0062-8875 Revisorrapport DM1-3 DS Prosjekteringsfase.pdf
Criterion 2: Where a Building Management System (BMS) is specified, the following commissioning procedures must be carried out: a. Commissioning of air and water systems is carried out when all control devices are installed, wired and functional b. In addition to air and water flow results, commissioning results include physical measurements of room temperatures, off coil temperatures and other key parameters as appropriate c. The BMS/controls installation should be running in auto with satisfactory internal conditions prior to handover d. All BMS schematics and graphics (if BMS is present) are fully installed and functional to user interface before handover e. The occupier and operator will be fully trained in the operation of the system. Man1.v03 documents that the commissioning procedures are according to the criteria stated above.Criterion 3: The above appointment(s) include the following seasonal commissioning responsibilities over a minimum 12 month period, once the building becomes occupied: