Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
5. Compare the calculated output current (Step 3) to the measured output current (Step 4). If the current from measured output current differs greatly from the calculated output current, replace the transducer. It is normal for the transducer reading to differ Note: somewhat from pressure gauge readings due to multimeter and gauge tolerances, and other factors.5. Compare the calculated output current (Step 3) to the measured output current (Step 4). If the current from measured output current differs greatly from the calculated output current, replace the transducer. It is normal for the transducer reading to differ Note: somewhat from pressure gauge readings due to multimeter and gauge tolerances, and other factors.3. Use the equation in Figure 9 to determine the calculated output current for the 4 mA to 20 mA transducers.I = 4 + 16P - (P )min mA()