Title: Data tester Smestad skole - Detaljert.pdf
1000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,9 23,9 4,0 496,00Remote: 36 28,1 23,8 4,3 500,00Worst Value: Local: 36 27,8 23,8 4,0 497,00Remote: 36 28,1 23,8 4,3 500,00PS-ACRF: Pass Worst Margin: Local: 45 21,1 9,3 11,8 395,00Worst Value: Local: 45 20,1 7,3 12,8 497,00Remote: 45 21,1 9,3 11,8 394,00Remote: 12 20,4 7,2 13,2 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:19Signature:______________________ Page: 169Copper Certification ReportCable Label: 521.002-UD-196 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:43:52 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: