Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
I7K5MUXADBUSY (adr. 15)DATA OUT10 bits serialA/D act. (addr. 15)s u B O/ IDATAREADWRITEADDRs u B D C PClockVoltage Source 10.000 VRef. Voltage 2.500 VChannel address 0.. 7+5 V..W220 onlyGND+24 VWatchdog: This module cannot be used on the base address 240 (or 496 for the PCD2.M170), because it would interact with the watchdog, and would cause a malfunction.Programming examples for the PCD3.W2x0 can be found in a separate manual and on the TCS Support site www.sbc-support.com.xx7 and RIOs: the firmware reads in the values according to the configuration (I/O Builder or network configurator).Watchdog: This module can interact with the watchdog, if it is used on base address 240. In this case, the last input with address 255 cannot be used. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD3 components.5-65PCD2.W2x0Temperature measurement with Pt 1000