Title: Ø94, Medistim - innregulering ventilasjon, avtrekk U1.pdf
AVTREKK MÅLEPROTOKOLLANLEGG:SYSTEM NR.:PLAN:ETGROM/GRENNR. U1 U2 U3 U4 U5 U6 U7 U8 U9 U10NAVN/NR A1 A2 A3 A4 A5 A6 A7 A8 A9 A10SUMANMERKNINGERLUFT KONTROLLØKERNVEIEN 94DATO:FREKVENS / TRYKK:U1 ETGSIGNATURKANALPROSJEKTERTMÅLTFORHOLDTempØ.DIM.[m3/h] 450 250 1460 500 300 150 500 800 1200 1000[m3/h] 480 255 1500 300 312 100 529 830 1200 1020[%] 107 % 102 % 103 % 60 % 104 % 67 % 106 % 104 % 100 % 102 %C6610652699 %12.03.2013H.BANMERKNING