Title: Ahlsell.pdf
N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 1,2-4,5 16.5 6.6 56.1 1,2 17.6 6.6 53.8SR 1,2-4,5 17.0 6.5 56.3 1,2 17.9 6.1 54.5MAIN 3,6-4,5 42.8 482.0 -15.6 3,6 45.4 500.0 -20.0SR 3,6-4,5 44.8 482.0 -15.6 3,6 46.1 482.0 -18.50804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 4,5 6.8 456.0 8.0SR 3,6 7.8 462.0 8.0MAIN 4,5 6.8 456.0 8.0SR 3,6 7.8 462.0 8.04060500250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-44030201000250 MHzProject: Ahlsell Site: Not Set Floor: Not Set Rack: Not Set Untitled1Building: Not Set Room: Not Set Patch: Not SetPage 27Test Summary: PASSRemote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 250509416.1 m60Insertion Loss (dB)50