Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
(for example set=10°C become 10°F) Selection of type of value to be displayed. 0 = Setpoint; 1 = cold room probe (Pb1); 2 = evaporator probe (Pb2) CONFIGURATION Stand-by operating mode. 0 = display switch off; 1 = display switch off, loads and alarms stopped; 2 = display with OFF label, loads and alarms stopped. Configuration of digital inputs/polarity. 0 = disabled; ±1 = defrosting; ±2 = reduced set;±3 = not used; ±4 = door switch; ±5 = external alarm; ±6 = Stand-by (ON-OFF);±7 = reduced set + light OFF. ATTENTION!: the “+”sign indicates that the input is activated when the contact is closed. the “-”sign indicates that the input is activated when the contact is open. DOWN button configurability. 0 = disabled; 1 = defrost; 2 = not used; 3 = reduced set; 4 = stand-by reLease firmware. Device version: read only parameter. tAble of parameters. Reserved: read only parameter. COPY CARD Up load. Programming parameter transfer from instrument to Copy Card. Format. Erasing all data in the copy card.