Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]16.8 73 1 2.70Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.7 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.2 449.0 30.3 45 8.0 442.0 27.6SR 12-45 8.7 422.0 30.8 45 9.0 290.0 31.6MAIN 12-45 9.3 493.0 28.2 45 9.1 492.0 25.4SR 36-78 10.4 492.0 28.2 36 10.5 492.0 25.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.7 4.5 52.2 45 14.7 4.5 49.2SR 78-45 15.7 4.5 52.2 45 14.6 4.3 49.7MAIN 36-45 17.5 469.0 11.8 45 20.2 500.0 8.3SR 45-36 17.4 469.0 11.8 45 19.7 475.0 8.70100806040200250 MHzACR-F (dB)