Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,4 23,8 3,6 499,00Remote: 45 27,6 23,8 3,8 498,00Worst Value: Local: 36 27,4 23,8 3,6 499,00Remote: 45 27,6 23,8 3,8 500,00PS-ACRF: Pass Worst Margin: Local: 12 72,1 61,2 10,9 1,00Worst Value: Local: 45 19,6 7,2 12,4 500,00Remote: 45 71,1 61,2 9,9 1,00Remote: 45 19,3 7,2 12,1 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:00Signature:______________________ Page: 38Copper Certification ReportCable Label: 521.002-UD-204 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:48:37 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software: