Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
5. Ensure condensing unit fan blades rotate freely. 6. Inspect the installation for any possible defects. 7. The design of the refrigerant system should be such that it does not allow the compressor to start more than 6 to 8 times per hour.Checks after start-up After several hours of operation, perform the following checks: 1. Voltage and current absorbed by the unit. 2. Safety pressure switch adjustments. 3. High and low pressure of the system. 4. Condensing unit fan rotates freely. 5. System overheat and subcooling. 6. Checks on the compressor oil level. 7. Check again for refrigerant leaks. 8. For offset units, please refer to the manual for usagerecommendations.