Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 18.1 8.0 47.2 45 17.9 3.5 51.4MAIN 78-45 18.8 500.0 11.3 78 19.5 490.0 8.4SR 78-45 18.8 500.0 11.3 36 19.7 490.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 28.3 111.5 22.4 36 29.0 119.5 18.7SR 36-78 25.4 141.0 18.3 36 27.4 110.5 20.0MAIN 36-45 39.2 499.0 -12.3 36 39.8 499.0 -15.2SR 36-45 36.8 493.0 -11.9 36 37.7 493.0 -14.80804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.5 498.0 8.0SR 12 6.1 491.0 8.0MAIN 45 7.5 498.0 8.0SR 12 6.1 491.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS