Title: 2wayEPIV_Modbus-Register_en.pdf
-www.belimo.comModbus-Register 2-way EPIV • en • v1.0 • 05.2018 • Subject to changesLowWord HighWordLowWord HighWordAccess R/W R/W R/W R R R R R R -RRAccess R/WRR R - R/W R/W R/W R/W R -R- R/W R/W R/W3 / 62-way EPIVCommunicative characterised control valve with sensor- operated flow control, 2-way (EPIV)Modbus Register DescriptionNo. Adr. DescriptionCommentRange / EnumerationUnit Scaling Values DefaultAccess10 Setpoint0...10'000%0.010R/WSetpoint for actuator between Min (Register 106) and Max (Register 107)21 Override ControlOverriding setpoint with defined values0:None 1:Open 2:Close 3:Min 4:Mid 5:Max0R/W32 CommandInitiation of actuator functions for service and test. After command is sent, register returns to None(0). With Reset(4) all Malfunction and Service Information (Register 105) Information can be reset.0: None 1: Adaption 2: Test 3:Sync 4:Reset0R/W43 Actuator Type