Title: +038=310.101-RF022T_06-multical 62 Vannmåler Kamstrup - Installasjons- og brukerveiledning.pdf
Response time - - After reset (e.g. cover off and on) as well as automatically after max. 24 hours (at 00:00) 24 hoursThe Water has not been stagnant in the meter for minimum one continuous hour during the latest 24 hours.This can be a sign of a leaky faucet or toilet cistern.2048 Flow meter V1, wrong pulse figure 4096 Flow meter V1, signal too weak (air) 16384 Flow meter V1, wrong flow directionAfter reset (e.g. cover off and on) as well as automatically after max. 24 hours (at 00:00)If several info codes appear at a time, the sum of the info codes is displayed.Example: E2064 = E16 + E2048.7.1 Transport mode The meter leaves the factory in transport mode, i.e. the info codes are active in the display only, not in the data logger. This prevents “infoevent” from counting during transportation and non-relevant data from being saved in the info logger. The first time the meter totalizes the volume register after the installation, the info codes automatically become active.