Title: +038=310.101-SC020T_02-FDV-dokumentasjon - Danfoss AS - VA_VVS 5640952 med flere - Danfoss spoler.pdf
22.5 VA AC coils onlyInsulation of coil windingsClass H according to IEC 85ConnectionSpade connector in accordance with DIN 43650 form AEnclosure, IEC 529IP00 with spade connector, IP65 with cable plugDuty ratingContinuousPlug typeCable plug (042N0156)Dimensions and weightTypeL without cable plug [mm]L with cable plug [mm]L with protective cap [mm]Weight [kg]AM4872640.10IC.PD.600.1A.02 | 16AP, Compact UL recognised coilsy Cable plug enclosure:IP00 version with DIN 43650 A spade connectors - IP20 version with protective cap - IP65 version with cable plugy For UL recognised valves y Ambient temperature: Up to 50 °C / 122 °F y In accordance with:RoHS Directive 2011/65/EU - Low Voltage Directive 2014/35/EU - EN60730-1 - EN60730-2-8TypeTambient [°C / °F]Supply voltage [V]Voltage variationFrequency [Hz]Power consumption[W][VA]ApprovalCode no.AP240C40T50 / -40T122208 – 240230±10%±10%60505.57.51115042N4191AP120B