Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
14QGH3492101-01 11/2018Preparation and OrganizationPhase Order CheckChecking the Phase OrderDANGERHAZARD OF ELECTRIC SHOCKWrong phase order can result in short circuit.Failure to follow these instructions will result in death or serious injury.Perform the following phase order checks:  Check the phase order of the layout and the existing connected equipment (for example, transformersand switchboards). Check the phase order of the run components before installation. This is important for the correctinstallation of the run, as the Canalis KT run components are asymmetric. You can check the phase order by:  Locating and aligning the neutral conductor.  Checking the labels on the run components. Check whether the reinforced protective earth (PER) is being used.  Check the phase orders of end feed units.Locating and Aligning the Neutral Conductor