Title: 360.002 - Tilluft.pdf.pdf
0.6 +13.420.33.0 +13.418.80.2 +13.419.81.5 +0.04.114.20.4 +2.214.127.00.00.0 +2.24.23.0 +2.24.70.3 +2.28k [dB]12.50.5 +6.413.10.6 +6.413.43.0 +6.411.90.2 +6.412.81.5 +0.04.17.60.4 +0.07.919.00.00.0 +0.03.03.0 +0.03.00.3 +0.0Lp [dB]LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeType156 SUPPLYDUCTREDUCERDUCT157 T-BRANCHDUCTSILENCERDUCTBEND-90DUCTProductSizeTellus-LOV VAV-200250MAGIR-CC1-*-* 250/200200TCPU_DK-*-*0,0 200/200200LEV-200-L1200200MAGIB-C4-*-*200200L [m]0,23,71,81,10,3Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]3002,763,2 Sound in:Attenuation: Addition:Total Lw:4202,40,1 Sound in:Attenuation: Addition:4202,40,3 Sound in:4203,73,6 Sound in:Attenuation: Addition:4203,79,1 Sound in:Attenuation: Addition:Dividing:3002,7