Title: TALEXXdriver_LCA_45W_500-1400mA_one4all_SC_PRE_en+++28000676.pdf
According to IEC 60598-1 Annex Q (informative only!) or ENEC 303-Annex A, each luminaire should be submitted to an isolation test with 500 V DC for 1 second. This test voltage should be connected between the interconnected phase and neutral terminals and the earth terminal. The isolation resistance must be at least 2 MΩ.As an alternative, IEC 60598-1 Annex Q describes a test of the electrical strength with 1500 V AC (or 1.414 x 1500 V DC). To avoid damage to the electronic devices this test must not be conducted.7.2 Conditions of use and storageHumidity:5 % up to max. 85 %, not condensed (max. 56 days/year at 85 %)Storage temperature:40 °C up to max. +80 °CThe devices have to be acclimatised to the specified temperature range (ta) before they can be operated.7.3 Additional informationAdditional technical information at www.tridonic.com → Technical DataGuarantee conditions at www.tridonic.com → Services