Title: 2 etg del2.pdf
604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 8.1Cable ID: T2095 Date / Time: 10/11/2013 08:14:49 AM Headroom 13.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]83 133 10 3.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.2 93.5 32.8 36 15.3 93.5 29.8SR 12-36 14.0 93.5 32.8 36 16.1 89.5 30.1MAIN 12-36 13.2 93.5 32.8 36 15.3 93.5 29.8