Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
XBCABDEE38InstallationInstallation manualWhen connecting the loop devices it is not necessary to follow the input/output order indicated in the figure. Connect the cable shield only at the start of the loop ([D], the shield can be connected to the terminal indicated in the figure or directly to the grounding bar). Take care to link the interrupted shields in correspondence with the device connections ([E]).EN54:A Previdia Max control panel can support up to 3840 fire detectors and/or manual call points (240 devices per loop).5.8IFMNET internal module wiring - Hornet+ network connectionThe connection of two or more control panels in a Hornet+ network can be achieved by means of two RS485 communication ports (paragraph 3.11 - [C] - [D]).Each connection in the network must be completed in accordance with the instructions in paragraph 5.5.1.Cables: