Title: Operating instructions - K3G500PB3301.pdf
Any further mounting data required can be taken from the product drawing or Section Chapter 4.1 Mechanical connection.its packaging.NOTE Damage to the device from vibration Bearing damage, shorter service lifeStrength class of screws8.8→ The fan must not be subjected to force or excessive vibrationfrom sections of the installation.; Secure the screws against unintentional loosening (e.g. use self-→ If the fan is connected to air ducts, the connection shouldlocking screws).be isolated from vibration, e.g. using compensators or similar elements.3.6 Transport and storage conditions→ Ensure stress-free attachment of the fan to theMax. permitted ambient temp. for motor (transport/ storage) Min. permitted ambient temp. for motor (transport/ storage)+80 °C40 °Csubstructure.; The fan may not be handled in the area around the inlet nozzle duringtransport and installation. There is a risk of damage to the impeller.