Title: 1 etg del 2.pdf
4020002550 MHz75100100ACR-F @ Remote (dB)80604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: T1005 Date / Time: 10/17/2013 02:09:15 PM Headroom 5.4 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 36] [Pair 36] [Pair 45]79 120 4 3.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.4 235.5 35.8 36 6.7 236.0 33.1SR 12-78 8.3 121.0 40.5 36 8.8 236.0 33.1