Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Temperature mode Pt1000 (-50...400 ˚C) Pt500 (-50...400 ˚C) Ni1000 (-60...200 ˚C) Resistor mode 0...2500 ΩConfiguration of outputsAs the outputs are configured using software (with the relevant FBox or FB), it is not necessary to configure the operating mode of the outputs using jumpers or DIP switches.6-99Power supplyPCD3.W525s must have an external power supply. This power supply is electrically isolated from both the Saia PCD® and the inputs/outputs of the W525. The design also allows the use of the same power supply for the PCD and the W525 without losing the galvanic separation. The diagram below shows the various areas of separation:TimingInputsInternally, the W525 captures a new value for each input channel every 2 msThis value can be read by the Saia PCD® at any time.Depending on the speed of the Saia PCD®, the transmission time for each individual value scaled to 16 bit (14 bit → 16 bit) (for a single input channel) is normally 100 μs.