Title: +038=249.001-#####._05-Lydtest plan 10 og 11 Pareto - Flere rom - Multiconsult.pdf
25031520,519,419,430,930,932,433,440,3n o i t c u d e r d n u o st n e r a p p A504040040,850041,063043,180043,6100047,130125049,1160047,6200051,2250049,520315050,8400055,0500054,2106312525050010002000Hz 4000Frequency, f, Hz Rating according to ISO 717-1 R'w Evaluation based on field measurement results obtained in one-third-octave bands by an engineering method.(C;Ctr) =45(2;8) dBC50-3150 = Ctr,50-3150 =311dB C50-5000 = dB Ctr,50-5000 =211dB C100-5000 = dB Ctr,100-5000 =18dBdBName of test institute:Multiconsult Norge ASNo. of test report:Date:4/27/2020Signature:SUVApparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation between roomsClient: Description:Probea AS Luftlyd horisontaltDate of test:4/27/2020Object:Korridor 10-302 - Møterom 10-103Source room:Receiving room:Condition:Condition: