Title: +038=360.000-OU045T_05-PCD2.m4160 PLS SBC - User Manual.pdf
The local slots on the base unit (CPU) are numbered starting at the upper left slot  0 clockwise to slot 3. The expansion module holders are also numbered clockwise  from slot 4 upwards, etc. The I/O addresses are also numbered in the same way.PCD2.C1000 and PCD2.C2000 serve as bus repeaters and provide +5V and V+  internally for a segment of I/O modules.The order of the expansion module holders is freely selectable.User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-214-3On-boardPCD3.C200 expansion module holders can also be used.PCD3.Cxxx expansion module holders enable the use of PCD3 manual control  modules e.g. the «Light and Shading» module PCD3.A860Connections of the PCD2.C1000 and PCD2.C2000 expansion module holdersINOUTPower supply of the expansion module holder24 VDC Error29Pin DésignationSignification29Power Fail (Panne de courant)+5 V ou V+ non disponible28Power GoodTensions présentes27COMPort commun26n.c.non connecté2025