Title: 32 Pumper modbuss teknisk data.pdf.pdf
Sets the E-pump setpoint. The scale is 0.01 %, so the value must be from 0 to 10000 to represent the entire 0-100 % range. Closed loop: Percentage of setpoint range. Open loop Percentage of nominal frequency. Common examples 4700: 47 % 8000: 80 %. See section 10.2 Setpoint in closed-loop control. You can read the actual setpoint from register 00338 UserSetpoint19)B G(h si lg n EE n gl is h(G B)Address Register nameRelayControlBit 0: Relay1ControlBit 1: Relay2Control00105Bits 2: Relay3ControlBits 3: Relay4ControlBits 4-15: RESERVED00106SetMaxFlowLimit00107SetPumpUnixRtcHI00108SetPumpUnixRtcLO00109RESERVED00110SetKp00111SetTi00112SetDirectCtr20DescriptionA register to control the relays. It is bitwise interpreted as follows:Controls the state of relay 1. 0: Closed 1: Open Only E-pumps and CUE.Controls the state of relay 2. 0: Closed 1: Open Only CUE, large MGE, MGE model H and later.