Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.0 113 2 3.98Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.7 496.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.2 473.0 29.1 36 8.5 473.0 26.3SR 36-45 5.6 457.0 29.9 36 6.4 457.0 27.1MAIN 36-45 10.2 500.0 27.8 36 9.2 496.0 25.2SR 36-45 6.8 493.0 28.2 36 7.7 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.2 482.0 11.6 45 17.5 91.0 23.1SR 45-78 17.6 482.0 11.6 45 17.4 91.0 23.1MAIN 78-45 17.5 500.0 11.3 78 18.5 482.0 8.6SR 45-78 17.9 500.0 11.3 45 17.6 500.0 8.30100806040200250 MHzACR-F (dB)