Title: +038=320.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Nettserverhåndbok.pdf
The time remaining before deactivation is displayedThe override function is deactivated automatically after 2 hours.Installation positionThe correct setting is important for the allocation of the consumed energy as cooling or heating energyo Valve in return pipe o Valve in supply pipeMediaSelection of the medium used:o Water o Monoethylenglycol o 1.2 PolypropylenglycolConcentrationo Percentage concentration of the glycol o The selection is only displayed when 'Monoethylenglycol' or '1.2Polypropylenglycol' has been selectedCable lengtho The cable length of the sensor which is away from the valve is setted to the correctvalue of 3 meters (DN15…DN50) or 10 meters (DN65…150) ex works.T5-Webserver Manual Energy Valve• en • v3.3 • 03.2019 • Subject to changes9 / 20Settings – analog feedbackNoteThese settings configure the analog feedback signal U510 / 20Setting of the value unitsTemperature ◦ °C (*) ◦ °F ◦ K Flow rate ◦ m3/h ◦ m3/s ◦ l/s ◦ l/min (*) ◦ l/h ◦ gpm ◦ cfm