Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
“ cycle will start 6 hours after pressing the button.”(see fig. b) for 5 seconds. The next automatic defrostcold room drill or links defects, temperature out of the temperature limit.  "E2" flashing on the display: corruption of the configuration data in the memory; try to turn off the appliance and start it again, if the alarm message disappears, change the heat regulator.  Chamber temperature: if the display shows a correct value, but the value is flashing, the temperature scanned by the probe is behind the prefixed limits.The appliance is supplied with an automatic evaporation control for the condensed steam. ALARMS AND SIGNALS (EVERY CONTROL)ALARMS AND SIGNALS (ELIWELL)Alarms must be silenced by the “” key.The alarm condition is always signalled by the buzzer (ifAny alarm and signalling are visualized on the display:present) and by the led of the alarm icon To silence alarms press any key.. ” led on indicates that the compressor is