Title: 32 Varmepumpe brukermanual.pdf.pdf
Export Alarms - If BACnet objects are created for the alarms in the AK2 device.Port - The UDP port that the BACnet server listens to (default 47808 = 0xBAC0)Device ID - The BACnet Device ID used by the gateway, should be unique on the siteCANbusBaudrate - Transmission speed (kbps) used on the networkM2M2 CAN ID - Node ID used by the gatewayActive Nodes - A list with currently active nodes on the CANbus networkCAN State - Status for the bus network, may indicate any errors that occur.Modbus RTUStatus - Shows if the Modbus RTU slave service is enabled or not.Slave ID - Modbus slave/unit id (station address) used by the gatewayBaudrate - Baudrate currently used by the gatewaySettings - RS485 settings used by the gatewayExample: 8E1 = 8 data bits, Even parity, 1 stop bitModbus TCPStatus - Shows if the Modbus RTU slave service is enabled or not.Slave ID - Modbus slave/unit id (station address) used by the gateway11M2M2-10, User Guide - Rev. 2020-09-04