Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]26.4 115 2 4.02Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.8 415.0 31.0 36 10.1 490.0 25.5SR 36-45 9.1 461.0 29.7 36 9.6 461.0 26.9MAIN 12-45 10.7 490.0 28.3 36 10.3 495.0 25.2SR 36-45 10.4 500.0 27.8 36 10.2 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.7 500.0 11.3 45 13.7 6.0 46.7SR 78-45 14.7 500.0 11.3 45 13.6 2.9 53.1MAIN 78-45 14.7 500.0 11.3 45 15.6 500.0 8.3SR 78-45 14.7 500.0 11.3 45 15.5 500.0 8.30100806040200250 MHzACR-F (dB)