Title: 1 etg del 2.pdf
MAIN 12-36 9.7 24.9 42.7 12 11.5 24.9 40.3SR 12-36 9.1 24.9 42.7 12 11.0 24.8 40.3MAIN 36-45 17.7 247.5 4.9 36 17.9 250.0 2.0SR 36-45 17.5 247.5 4.9 36 17.3 247.0 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.1 26.8 18.9SR 36 3.2 28.9 18.7MAIN 36 6.1 233.0 10.3SR 36 6.6 237.5 10.2010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1