Title: 2022-04-20 HYDRAULISK BEREGNING.pdf
1560.20221.311665631001.00.112080.030411667.860.021L < 50 mm[kg/m³][kg/ms x 10e-6][m²]H = 6.8 [m]H = 9.8 [m][mbar][mbar][l/min][mbar][l/min][l/min]UnitPropertyInaccuracy of the pressure:Inaccuracy of the flow:Total area of coverage:Average area of coverage:Flow density at the weakest sprinkler:Average density of 4 weakest sprinklers:Four weakest sprinklers:Average flow density:Number of sprinklers:Average sprinkler height:Volume:330.001 Brannslokking våtSprinkler results: 01-01 BUNNPRISLevelNodeProductPlan 01146 006 SSU STDPlan 01148 006 SSU STDPlan 01150 006 SSU STDPlan 01152 006 SSU STDPlan 01154 006 SSU STDPlan 01156 006 SSU STDPlan 01158 006 SSU STDPlan 01160 006 SSU STDPlan 01162 006 SSU STDPlan 01164 006 SSU STDPlan 01166 006 SSU STDPlan 01168 006 SSU STDPlan 01170 006 SSU STDPlan 01172 006 SSU STDPlan 01174 006 SSU STDPlan 01176 006 SSU STDPlan 01