Title: 360.002 - avkast.pdf
Project InformationProject name:Brandengen skoleProject address:ProsjektadresseProject issue date:24.05.2016Organization description:RivSoftware version:MagiCAD for Revit 2021 UR-1.1Project Calculation DataSystems:/ - / - / -Total flow:14480 m³/hHighest LpA (10 m2 sab):54.5 dBCalculation Input ValuesOut of dp-range warning tolerance:0 %Calculation Results / Outdoor exhaustLocationLevelNodeTypeProductSize3. etasje171 AHE/AHUGeniox 22 360.3. etasjeDUCT1000x19503. etasjeREDUCERLDR_SE-*-*-*-*-* 2000x1000/19503. etasjeDUCT2000x10003. etasjeSILENCERLKK-1209D H=1 2000x1000L [m]0,20,2Sound Calculation ReportProject number:Client name:Organization name:Author:Calculation date:Total pressure:qv [m³/h]v [m/s]dpt [Pa]14480+250,0Total Lw:144802,10,0 Sound in:Attenuation: Addition:144802,10,0 Sound in:144802,00,0 Sound in:Attenuation: Addition:144802,014,7 Sound in:Attenuation: