Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3003 Date / Time: 09/11/2013 04:51:58 Headroom 15.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]163 258 18 7.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 17.8 61.0 35.8 78 19.6 99.3 29.4SR 12-36 15.3 99.8 32.3 36 16.3 92.5 29.9MAIN 36-78 17.8 98.5 32.4 78 19.6 99.8 29.3SR 12-36 15.3 99.8 32.3 36 16.4 99.8 29.310080604020NEXT (dB)