Title: økernvn 94.pdf
50 MHz75100LinkWare Version 7.4Cable ID: T4019 Date / Time: 09/11/2013 09:49:54 Headroom 6.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]173 264 9 7.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]14.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.1 216.0 36.4 36 7.8 216.0 33.8SR 12-36 6.3 225.5 36.1 36 6.9 240.0 33.0MAIN 36-78 7.1 216.0 36.4 36 8.6 247.5 32.8SR 12-36 6.3 225.5 36.1 36 6.9 240.0 33.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)