Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Surrounding area: 0.500 m2 Surrounding area 4 Perpendicular illuminance (adaptive) [Ix] 385 (= 300)3 Background area 4 Perpendicular illuminance (adaptive) [Ix] 240 (= 100)Wall zone: 0.500 m374 556 0.75220 488 0.57161 289 0.670.670.450.56The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 30Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Mete 12/ Visual task area 4 / Perpendicular illuminance (adaptive)Visual task area 4 / Perpendicular illuminance (adaptive)oL.Surface Result Average Min Max Min/average Min/maxVisual task area 4 Perpendicular illuminance (adaptive) [Ix] 502 374 556 0.75 0.67 Surrounding area: 0.500 mSurrounding area 4 Perpendicular illuminance (adaptive) [Ix] 385 220 488 0.57 0.45Background area 4 Perpendicular illuminance (adaptive) [Ix] 240 161 289 0.67 0.56Wall zone: 0.500 mFalse colors [Ix]295 500 Ix