Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
SR 78-45 14.9 500.0 11.3 45 15.5 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 19.8 45.5 35.6 45 20.3 48.3 32.4SR 36-45 25.6 47.8 35.0 36 25.6 51.8 31.5MAIN 12-45 35.1 500.0 -12.4 45 36.1 500.0 -15.3SR 36-45 36.2 495.0 -12.1 36 36.9 495.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.4 481.0 8.0SR 45 8.9 495.0 8.0MAIN 12 7.4 481.0 8.0SR 45 8.9 495.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Uni ConsultUniconsult tester.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00431.3 m60Insertion Loss (dB)504030201000250 MHz500