Title: Hardware Installation Guide.pdf
Input I2 “Do not supervise for UL” and therefore cannot be used for UL installations.RS-485, clock & data reader communications “Not Evaluated by UL” and therefore cannot be used in UL installations.RS-485 4-wire is “Not Evaluated by UL” and therefore cannot be used in UL installations.The use of AC Strikes is “Not Evaluated by UL” and therefore cannot be used in UL installations.Reader power for UL installations: 300 mA maximum for an operating temperature range of -10 to +49°C (14 to 120°F).Environmental for UL installations: - -Temperature: -10 to +49°C (14 to 120°F) operating Humidity: 85+/-5% at 30+/-2°C (86°F)382 — revision 6Hardware Installation Guide78SpecificationsNote:For UL installations, refer to section UL Listed Installations on page 382.The LNL-1300-U is for connection to low voltage, class 2 power-limited circuits only. These specifications are subject to change without notice.Primary power: - - - -