Title: Eurotester målerestultat.pdf
41414242434344444545TEST RAPPORTResultatZ-LINEZ: 0.82ΩIsc: 279A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 106A Isc(0.76%): 212A Isc(1.15%): 321ABytesteinen 1 / =433.202 / SIKRING16 30.03.2021 14:04:34RCD II: 22.5mAUc: 9.9V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING16 30.03.2021 14:05:07R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING16 30.03.2021 14:05:30R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING16 30.03.2021 14:05:42R LOW OhmR: 0.14ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING17 30.03.2021 13:53:45Z-LINEZ: 0.84ΩIsc: 274A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 104A Isc(0.76%): 208A Isc(1.15%): 315ABytesteinen 1 / =433.202 / SIKRING17 30.03.2021 13:54:03Testet av: Andreas PedersenSide:7GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT