Title: 1 etg del 2.pdf
206 327 23 8.7206 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.8 * 242.5 35.6 36 1.4 244.5 32.9SR 36-45 1.7 249.5 35.4 36 0.9 *249.5 32.7MAIN 36-45 0.8 242.5 35.6 36 1.4 244.5 32.9SR 36-45 1.7 249.5 35.4 36 0.9 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.1 56.0 29.2 36 14.8 2.5 53.2SR 36-45 13.2 55.8 29.3 36 15.0 2.5 53.2MAIN 36-45 17.0 139.0 21.3 36 18.6 149.0 17.7SR 45-36 16.0 126.0 22.2 36 18.0 149.0 17.7010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz