Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
The condensate pipe must be insulated with a condensation-proof material such as polyurethane, propylene or neoprene of 5 to 10 mm thickness. If more than one unit is installed in the room, the drain system can be made as shown in the drawing fig.23.To drain the unit completely, refer to “SYSTEM DRAINAGE” in the Maintenance section.Checking On the unit startup, check if water flows correctly from the pump or check the pipe slope and make sure the pipes are not obstructed.All units are equipped with a fuse for machine protection and one for control protection (type gF 1A). Refer to table I when replacing the fuse for unit protection.Control box panels: The control box panel is positioned on the external side of the unit (fig. 1-2). Remove the fixing screws and the cover of the control box panel. The control box panels contain the terminal blocks for connections as shown in the wiring diagrams and fig. 36-38-39-40.42 GW27