Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.04.05-UF071 Date / Time: 27-11-2022 14:17:49 Headroom 7.0 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]22.2 97 2 3.54Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 459.0 29.8 36 9.0 459.0 27.0SR 12-36 7.0 457.0 29.9 36 8.6 452.0 27.3MAIN 12-36 7.1 459.0 29.8 36 10.8 500.0 25.0SR 12-36 7.8 499.0 27.9 36 9.3 499.0 25.010080604020NEXT (dB)