Title: V20-03-02 VVS-anlegg plan 3 - DM3-1.pdf
LD018T Maks:185 m³/h Kjøling: 325 W 0.026 L/s Varme: 225 W 0.005 L/sLD018T Maks:185 m³/h Kjøling: 325 W 0.026 L/s Varme: 225 W 0.005 L/sLD018T Maks:210 m³/h Kjøling: 200 W 0.016 L/s Varme: 225 W 0.005 L/sLD018T Maks:210 m³/h Kjøling: 200 W 0.016 L/s Varme: 225 W 0.005 L/sLD018T Maks:210 m³/h Kjøling: 200 W 0.016 L/s Varme: 225 W 0.005 L/sLD018T Maks:210 m³/h Kjøling: 200 W 0.016 L/s Varme: 225 W 0.005 L/sSystem Produktkode360.014 360.014LD010T LD010TLD033T LD018T LD022T360.014 360.016 360.016 Grand total: 75Kombibaffler-Produktliste, Plan 03PARASOL HF-1192 PARASOL HF-1192ProduktVersjon Se tagg baffel Se tagg baffel03 03PlanPARASOL HF 600x600 WISE Parasol Zenith 1200x600-ø160 kortside WISE Parasol Zenith 600x600-ø160Se tagg baffel Kjøling/varme Kjøling/varme03 03 0330 21 39 3Stk.KommentarEksisterende Gjenbruk ny posisjon Eksisterende Nye NyeVentiler-Produktliste, Plan 03 TypeProduktkode SF001T SF002T SF002T SF002T SF009T SF009T SF009T ST008T ST009T ST009T