Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 53,7 68,0 279,0 15,0 9,7Limit 100,0 - 555,0 50,0 25,0Margin 46,3 - 276,0 35,0 15,3Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,1 3,1 2,0 3,10Worst Value: Local: 36 22,7 43,8 21,1 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 24,8 18,5 6,3 31,75Remote: 78 12,6 8,0 4,6 470,00Worst Value: Local: 78 14,9 8,0 6,9 495,00Remote: 78 12,6 8,0 4,6 470,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass