Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Inputs Number of input channels: Signal rangesW500:W510:Galvanic separation: Measuring principle: Conversion timeA/D: Resolution (digital representation): Input resistance:Accuracy (of measured value):} }2 0 … +10 V -10 … +10 V 0 … +20 mA -20 … +20 mA no differential < 30 µs 12 bits (0 … 4095) 0 … +10 V :1 MΩ 0 … +20 mA: 100 Ω unipolar: bipolar:jumper selectable together jumper selectable together± 2 LSB ± 10 LSBRepeating accuracy (under same conditions): Common mode range: Common mode rejection: Overvoltage protection: Time constant of input filter: Outputs Number of output channels: Signal ranges:Galvanic separation: Conversion time D/A: Resolution (digital representation): Load impedance: Accuracy (of output value):± 2 LSB CMR ± 10 V CMRR > 75 dB ± 40 VCC (permanent) 3 ms}2, short circuit protected 0 … +10 V -10 … +10 V no < 20 µs 12 bits (0 … 4095) > 3 kΩ 0.3 % ± 20 mVjumper selectable individuallyTechnical data common to the whole module