Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 44,5 68,0 231,0 13,0 7,8Limit 100,0 - 555,0 50,0 25,0Margin 55,5 - 324,0 37,0 17,2Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 0,9 3,1 2,2 3,10Worst Value: Local: 45 19,5 43,8 24,3 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 27,5 19,2 8,3 23,05Remote: 12 19,0 11,6 7,4 172,00Worst Value: Local: 78 17,4 8,0 9,4 495,00Remote: 78 17,2 8,0 9,2 436,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,6 26,8 2,8 496,00Remote: 36-45 30,7 26,7 4,0 500,00Worst Value: Local: 36-45 29,6 26,8 2,8 496,00Remote: 36-45 30,7 26,7 4,0 500,00dB 0601200Local250500 MHzdB 060