Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Isc: 482A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 12.06.2020 11:25Tallberg Elektro A/S Tlf.22796640Side:22GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.150150151151152152153153154154155155TEST RAPPORTResultatRCD tt: 57.9msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 12.06.2020 11:26RCD II: 27.0mAUci: 0.0V t: 225.2ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 12.06.2020 12:23R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF036 C16/2 12.06.2020 12:23KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 10.06.2020 11:11SPĆNDINGUln: 231V Ulpe: 231V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 10.06.2020 13:03Z-LINE