Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
50000250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.04.05-UF004 Date / Time: 27-11-2022 12:15:42 Headroom 6.3 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]21.7 94 1 3.43Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]31.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.3 358.0 32.4 36 7.8 463.0 26.8SR 12-36 7.3 408.0 31.1 36 8.3 459.0 27.0MAIN 12-36 7.4 478.0 28.9 36 8.1 479.0 26.0SR 12-36 8.6 500.0 27.8 36 9.3 498.0 25.110080604020NEXT (dB)