Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]17.8 77 1 2.87Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.5 469.0 29.3 45 8.5 469.0 26.5SR 12-45 8.2 429.0 30.7 45 9.3 402.0 28.5MAIN 12-45 8.7 496.0 28.0 45 9.3 496.0 25.2SR 12-45 8.4 476.0 29.0 36 10.3 495.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.5 3.8 53.8 45 14.6 3.8 50.8SR 78-45 15.5 3.9 53.5 45 14.6 3.9 50.5MAIN 36-45 18.0 466.0 11.9 45 19.8 500.0 8.3SR 45-36 18.0 466.0 11.9 45 20.0 490.0 8.40100806040200250 MHzACR-F (dB)