Title: 360.002 - Tilluft.pdf.pdf
14.0+0.014.20.0 +3.514.50.5 +3.514.40.0 +3.5Lp [dB]LocationLevel2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeType93 T-BRANCHDUCTBEND-90DUCT94 T-BRANCHREDUCERDUCT95 T-BRANCHDUCTBEND-90ProductSizeTCPU_DK-*-*0,0 315/315315MAGIB-C4-*-*315315TCPU_DK-*-*0,0 315/315MAGIR-CC1-*-* 315/250250TCPU_DK-*-*0,0 250/200200MAGIB-C4-*-*200L [m]1,74,41,50,6Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]9103,27,9 Sound in:Attenuation: Addition:Dividing:8303,00,6 Sound in:Attenuation: Addition:8303,01,4 Sound in:Attenuation: Addition:8303,01,6 Sound in:Attenuation: Addition:8303,07,0 Sound in:Attenuation: Addition:Dividing:5802,1Sound in:5803,30,9 Sound in:Attenuation: Addition:5803,36,9 Sound in:Attenuation: Addition: