Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
[Pair 12] [Pair 12] [Pair 12]32.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.3 423.0 30.8 45 9.8 453.0 27.3SR 36-45 7.1 448.0 30.3 45 7.5 448.0 27.5MAIN 12-45 8.6 479.0 28.8 45 10.4 492.0 25.4SR 36-45 7.6 498.0 27.9 36 8.2 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.3 149.0 21.8 45 14.0 2.6 53.9SR 36-45 14.3 3.4 54.7 45 14.0 2.6 53.9MAIN 45-36 15.6 476.0 11.7 36 18.2 474.0 8.7SR 36-45 15.5 475.0 11.7 45 18.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 25.5 113.0 22.2 45 27.3 118.0 18.9SR 12-45 27.1 118.5 21.4 12 28.8 119.0 18.8MAIN 12-45 40.6 498.0 -12.3 45 41.8 500.0 -15.3SR 36-45 38.4 498.0 -12.3 45 39.0 498.0 -15.10804000250 MHz