Title: Data tester Smestad skole - Detaljert.pdf
Worst Margin: Local: 12-45 23,1 12,5 10,6 386,00Remote: 45-12 23,5 12,5 11,0 386,00Worst Value: Local: 12-45 21,2 10,2 11,0 500,00Remote: 12-45 21,2 10,2 11,0 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,9 25,4 4,5 449,00Remote: 36 28,1 23,8 4,3 500,00Worst Value: Local: 36 28,3 23,8 4,5 497,00Remote: 36 28,1 23,8 4,3 500,00PS-ACRF: Pass Worst Margin: Local: 12 68,3 56,3 12,0 1,75Worst Value: Local: 12 19,7 7,2 12,5 500,00Remote: 12 65,9 54,3 11,6 2,20Remote: 12 19,4 7,2 12,2 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:04Signature:______________________ Page: 70Copper Certification ReportCable Label: 521.002-UD-168 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name: