Title: økernvn 94.pdf
SR 36-45 10.6 2.3 57.1 36 12.7 2.0 55.2MAIN 45-12 18.2 239.0 16.6 12 19.7 239.0 13.6SR 36-45 16.2 181.0 19.0 45 18.7 239.5 13.6010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.6 11.1 51.2 36 8.1 11.1 48.9SR 12-36 6.7 11.0 51.3 12 8.0 11.0 49.0MAIN 36-45 9.2 250.0 4.7 36 8.7 249.5 2.1SR 36-45 9.8 250.0 4.7 36 9.3 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.1 8.4 21.0SR 45 3.8 8.4 21.0MAIN 36 8.1 204.0 10.9SR 36 6.4 175.0 11.606050050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active