Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
The circuitry and labelling have been completely revised. When I/O modules are replaced, the electronic components on the CPU are protected. However, the I/O modules themselves must not be plugged in or removed with the power on, the supply voltage and the external +24 V must be disconnected. As with the PCD3, the CPU has no jumpers; all the required functions have to be configured in "Hardware Settings". The unit provides 4 integrated ports and two RJ45 Ethernet sockets, including switch. These make the Saia® PCD2.M5_ an extremely powerful communication system. FTP and web access are also supported directly via http.On the motherboard there are also 6 digital inputs (4 interrupt inputs or one encoder connection) and 2 outputs. The option to configure the inputs as interrupt or encoder inputs and the outputs as pulse-width-modulated (PWM) means that the Saia® PCD2.M5_ can be used as a "low-cost solution" for machinery and systems.Saia® S-Net networking concept