Title: +175=453.001_LZ001_Manual - Selvregulerende varmekabel isvannskrets.Produktinformasjon.pdf
Intelligent HeatingGB Connection kits for joining all types ofDevi self limiting heating cables to cold tailsCold tail fitting set: • 1 crimp tube type 12/3, L =20 mm • 2 crimp tubes, type 3/1, L = 15 mm • 3 squeeze connection tubes, type fitcrimp 1 • 1 crimp tube, type ESP 18/6, L = 125 mmSealing set for cable-end: • 1 crimp tube, type ESP 12/4, L = 60 mm • 1 crimp tube, type ESP 12/4, L = 25 mm • 1 crimp tube, type KYNAR 3/4, L = 100 mm • 1 piece of adhesive tape, L = 100 mm • 1 piece of assembly wirePractical fitting instructionsIt is very essential to follow this instruction very carefully that when finished no connec- tions are missing or wrong with the risk of the cable not working or being overheated.A temperature of 150°C ± 30° is necessary to skrink the crimp tubes. A hot air gun with a temperature regulator is the most appropriate tool.Therefore, read the entire instruction to the end before you start.However, a blow torch with a moderate flame or a gas lighter can also be used.