Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
) jumper selectable6I/O modules and I/O terminal blocks may only be plugged in and removed when the PCD and the external +24 V are disconnected from the power supply.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-48Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W2x06.8.1 PCD2.W2x0, analogue inputs, 8 channels, 10 bit resolutionApplicationWith its short conversion time of <50 µs, this module is universally suitable for recording analogue signals. The only limitations are with weak signals, as with Pt 100 resistive temperature sensors, or with thermocouples.Module overviewPCD2.W200 PCD2.W210 PCD2.W220 PCD2.W220Z02 PCD2.W220Z128 channels for signals 0 … 10 V 8 channels for signals 0 … 20 mA 8 channels for resistive temperature sensors Pt/Ni 1000 8 channels for NTC10 temperature sensors 4 channels for signals 0 … 10 V 4 channels for resistive temperature sensors Pt/Ni 10006Technical dataSignal ranges:see module overview