Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,8 3,3 499,00Remote: 45 28,9 23,8 5,1 500,00Worst Value: Local: 36 27,1 23,8 3,3 499,00Remote: 45 28,9 23,8 5,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 23,5 11,8 11,7 296,00Worst Value: Local: 45 20,6 7,2 13,4 500,00Remote: 12 72,4 61,2 11,2 1,00Remote: 36 20,3 7,3 13,0 494,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:55Signature:______________________ Page: 5Copper Certification ReportCable Label: 521.002-ud127 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:16.01.2019 16:14:37 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software: