Title: +175=432.001_432 Hovedfordelinger.Beskrivelse.pdf
The unit is provided with a microprocessor-based circuit, which is connected to a mechanical counier for registration of the consumption in kWh.The TAE-2 is furthermore provided with a relay contact output. The unit can consequently be connected to various measuring terminals, tariff units, computers, etc.The measuring range of the energy meter depends on the ratio of the external current transformers. The measuring range is set by the user on the front of the meter.On the front the TAE-2 is equipped with a LED for indication of correct connection of the unit. At correct conneciion the LED flashes at a frequency corresponding to 125Wh, irrespective of the selected current transformer ratio. lf the ÏAE-2 has been incorrectly connected, the LED is lit continuously.The IAE-2 is CE marked to EN 61036 and IEC 1036TechnicaltionsConnectionMeasuring voltage