Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
NOTE Under no circumstances one should not directly pull the dampers’ baffle in order to open or close it. Such action may cause damage of the device self-braking drive mechanics and is not a subject of guarantee.MERCOR SA – The company reserves the right to make modifications and changes5/21Driving and Tripping Systems ____________________________________________________ The driving system for the fire dampers mcr WIP may be:The tripping and control mechanism MERCOR of KW1 type equipped with integrated thermal trip 72°C, driving spring, and lever and cam system. Thi s mechanism may be additionally equipped with the electromagnetic trip 24V AC/DC or 230V AC (controlled by the current pulse or by the current break) and limit switches for signalling the fire damper baffle position state. The mechanism may be additionally equipped with the actuator MERCOR KW for setting the fire damper in the function of waiting for the voltage of 24V AC/DC or 230V AC.