Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 465.0 29.9 36 7.9 471.0 27.0SR 12-36 7.9 500.0 29.2 36 7.8 499.0 26.4MAIN 12-36 8.2 500.0 29.2 36 8.2 500.0 26.4SR 12-36 7.9 500.0 29.2 36 7.8 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.8 500.0 11.3 45 19.0 499.0 8.3SR 45-36 19.9 500.0 11.3 45 18.9 500.0 8.3MAIN 36-45 19.8 500.0 11.3 45 19.0 499.0 8.3SR 45-36 19.9 500.0 11.3 45 18.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.8 34.5 39.1 36 17.3 34.5 36.7SR 36-45 16.3 34.5 39.1 36 17.7 34.5 36.7MAIN 12-36 32.9 500.0 -12.4 36 33.0 500.0 -15.3