Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Module overviewRsolution *)PCD2.W300:Voltage 0..10 V2,442 mVPCD2.W310: PCD2.W340:PCD2.W350:PCD2.W360:Current 0...20 mA General purpose module 0 … 10 V 0 … 20 mA Pt/Ni 1000 (default) Pt 1000: Ni 1000: Temperature sensor Pt/Ni 100 Pt 100: Ni 100: Temperature sensor Pt 10004.884 μA2,442 mV 4.884 μA50 … +400 °C 0.14 … 0.24 °C -50 … +200 °C 0.09 … 0.12 °C50 … +600 °C 0.14 … 0.20 °C -50 … +250 °C 0.06 … 0.12 °C50 … +150 °C 0.07 … 0.09 °C (resolution < 0.1 °C)6Method of linearization for temperature inputs: by software *) Resolution = value of least significant bit(LSB)Technical datasee module overview noInput ranges: Galvanic separation: Resolution (digital representation): 12 bit (0 … 4095) Measuring principle: Input resistance:non-differential, single-ended W300: W310: W340: W350: W360: 2.0 mA20 kΩ / 0.15 % 125 Ω / 0.1 % U: 200 kΩ / I: 125 Ω not relevant not relevantMaximum measurement current for temp.measurement probes: Accuracy at 25°C