Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
Save the set value by waiting a few seconds, which automatically brings you back to the list of parameters.Go back another step in the menu by pressing the On/Off button.Revert to showing the current inlet temperature by pressing the On/Off button again.7273Use and operationParameter tableCategory ParameterDescriptionRangeDefault valued01Evaporator temperature for starting the defrosting sequence30-5.0 °C0 °Cd02Evaporator temperature for stopping the defrosting sequence0-30 °C13 °Cdd03The minimum time delay between two defrosting sequences30-90 min45 mind04Maximum running time for a defrosting sequence1-20 min8 minrr03Setpoint in heating mode15-40 °C27 °CSensor valuesCategory ParameterDescriptionRangeO01Compressor outputOn/OffOO02Pump outputOn/OffO03Four way valve outputOn/Offt02Inlet temperature30-99 °Ct04Evaporation temperature30-99 °Ctt05Outdoor temperature30-99 °Ct06Hot gas temperature