Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Analogue outputs for modules PCD2.H320 and PCD2.H325Axis 2 OUT 12 bit yes No +/- 10 V 3 kΩAxis 1 OUT 12 bit yes No +/- 10 V 3 kΩOutputs Resolution (incl. sign bit) Short circuit protection Electrical isolation Output voltage fluctuation 1) Minimum load impedance 1) and the value is stored in a digitally programmable potentiometerSetting accuracy ± 5 mV. Balancing output voltage is carried out in the factory,Analogue outputs for modules PCD2.H322 and PCD2.H327Axis 2 NC - - - - -Axis 1 OUT 12 bit yes No +/- 10 V 3 kΩOutputs Resolution (incl. sign bit) Short circuit protection Electrical isolation Output voltage fluctuation 1) Minimum load impedance 1)Setting accuracy ± 5 mV. Balancing output voltage is carried out in the factory, and the value is stored in a digitally programmable potentiometer.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-109Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.H32x