Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]28.5 124 2 4.40Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]27.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.8 500.0 29.2 36 8.9 500.0 26.4SR 12-36 8.7 471.0 29.8 36 8.8 500.0 26.4MAIN 12-36 8.8 500.0 29.2 36 8.9 500.0 26.4SR 12-36 8.8 500.0 29.2 36 8.8 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.4 5.0 51.3 45 18.8 500.0 8.3SR 78-45 17.4 5.5 50.4 45 19.7 499.0 8.3MAIN 78-45 19.0 500.0 11.3 45 18.8 500.0 8.3SR 78-45 19.5 500.0 11.3 45 19.7 499.0 8.30100806040200250 MHzACR-F (dB)