Title: +038=434.005-KW001._01-FXQJ-EMC-Pure 3X240 FV120 Draka Produktblad.pdf
ApplicationEMC shielded power cable with copper conductors. Halogen free, ﬂame retardant and self-extinguishing in the event of ﬁre. Smoke in the eventof ﬁre is minimal, transparent and not harmful to electronic equipment. For ﬁxed installation, indoors, outdoors, in pipes, ground or water.Suitable for switchgear and potentially explosive areas. Can be plowed down when care is taken. The copper screen has 100% coverage andmeets EMC Directive with appropriate installation.Alternative Product NameN1XCZ1-R, N1XCZ1-SApprovalCEEnvironmentalEnviromantal Declaration - FXQJ-EMCPureStandardCENELEC HD 604 Part 5 Section DHarmonized construction standardCENELEC HD 604Halogen free materialSS-EN 60754-1, -2Corrosive gasesSS-EN 61034-1, -2Smoke densityEN 50575:2014Power, control and communication cables - Cables for general applications in constructionworks subject to reaction to ﬁre requirementsConstructionCable ShapeRoundConductorsStranded and annealed copper acc. to IEC 60228 class 22,5-35 mm2: round (FR)50-240 mm2: