Title: 2 etg del2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]231 366 25 10.0231 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.0 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 246.0 35.5 36 0.8 * 246.0 32.8SR 12-36 9.1 246.0 35.5 36 8.6 246.0 32.8MAIN 36-45 0.9 246.5 35.4 36 0.8 246.0 32.8SR 12-36 9.1 246.0 35.5 36 8.6 246.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.9 209.0 17.8 36 18.4 42.3 28.7SR 45-12 17.5 163.0 19.9 45 18.1 207.0 14.9MAIN 45-36 17.9 250.0 16.2 36 19.2 237.5 13.7