Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]13.6 59 1 2.34Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]34.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.2 453.0 30.1 36 9.0 470.0 26.4SR 36-45 7.8 461.0 29.7 45 8.6 469.0 26.5MAIN 36-78 10.4 496.0 28.0 36 9.5 497.0 25.1SR 36-45 7.9 469.0 29.3 45 8.8 477.0 26.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.5 5.0 51.3 45 14.2 2.9 53.1SR 36-45 15.5 5.0 51.3 45 14.3 3.4 51.7MAIN 36-45 16.0 483.0 11.6 45 17.8 483.0 8.6SR 36-45 15.9 475.0 11.7 45 17.3 466.0 8.90100806040200250 MHzACR-F (dB)