Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
4. Mount the control panel to the wall5.Install accessory modules6. Power up the system7. Test the system5.1Mounting a PRCAB cabinet1. Remove the securing screws and door (paragraph 3.1 - [D]).2. Remove the front-plate grounding conductor (paragraph 3.1 - [C]) and, if present, the CAN wire.3. Push the hinge grips, located at the top and bottom of the door hinges, inwards (paragraph 3.1 - [E]) to release the cabinet front plate.3. Push the hinge grips, located at the top and bottom of the door hinges, inwards (paragraph 3.1 - [E]) to release the cabinet front plate.4. Remove the seals from the cable entries you intend using (paragraph 3.1 - [I]).Note:In order to guarantee the IP30 protection grade, do no remove any other seals.5. Pull the cables through the open cable entries.6. By means of the holes on the back of the cabinet, mount it to the wall (paragraph 3.1 - [G]). Use anchor screws (stop screws) with 8mm diameter minimum.