Title: +038=433.000-NI003._23-Testrapport Elektriske Anlegg Plan7 DM3.E2=433.07.02.docx
Testresultater for Tavle +DM3.E2=433.07.02Kurs Kontinuitet Ω MΩ Jordfeilbyter mA Jordfeilbryter mS KW 01 28,5 293 KW 20 0,24 1000 27,0 83 KW 21 0,22 1000 28,5 11 KW 22 0,18 1000 27,0 124 KW 23 0,19 1000 28,5 11 KW 24 0,13 1000 28,5 70 KW 25 0,13 1000 28,5 17 KW 26 0,11 1000 27,0 51 KW 27 0,12 1000 28,5 17 KW 28 0,16 1000 28,5 16 KW 29 0,17 1000 28,5 11 KW 30 0,12 1000 27,0 51 KW 31 0,23 1000 28,5 16 KW 32 0,25 1000 27,0 263 KW 33 0,15 1000 27,0 261 KW 34 0,02 1000 28,5 10 KW 35 0,01 1000 27,0 267 KW 36 0,02 (CHASSI) 1000 28,5 11 KW 37 28,5 11 KW 38 27,0 23 KW 39 27,0 84 KW 40 27,0 42 KW 70 22,5 27 KW 71 24,0 17 KW 72 27,0 102 KW 73 27,0 41 KW 74 27,0 102 KW 75 27,0 41 KW 76 27,0 83 KW 77 28,5 11 KW 101 0,01 1000 KW 102 0,01 1000 KONTINUITET LEDENDE DELER Kontinuitet Ω KULVERT 0,05 + 0,03 + 0,04 HIMMLING 0,02 + 0,01 + 0,02 VENTILASJON 0,06 + 0,05