Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Isc: 257A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE042 10.02.2020 09:06Z-LINEZ: 0.90ΩIsc: 256A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE042 10.02.2020 09:06Zs(rcd)Z: 0.82ΩIsc: 282A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE042 10.02.2020 09:06RCD II: 28.5mAUci: 0.1V t: 22.7ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE043 07.02.2020 12:50TEST RAPPORTSide:15GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTNr.939394949595969697979898Resultat R LOW OhmR: 0.42ΩR+: 0.4Ω R-: 0.4Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE043 07.02.2020 12:51Z-LINEZ: 1.32ΩIsc: 174A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE043 07.02.2020 12:52Zs(rcd)Z: 1.12Ω