Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
27.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.7 500.0 29.2 36 6.3 500.0 26.4SR 36-45 6.9 500.0 29.2 36 6.6 486.0 26.7MAIN 36-45 5.7 500.0 29.2 36 6.3 500.0 26.4SR 36-45 6.9 500.0 29.2 36 6.7 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.6 472.0 11.8 45 16.9 30.1 32.7SR 78-45 16.5 476.0 11.7 45 16.8 23.4 34.9MAIN 45-78 16.7 475.0 11.7 45 17.5 500.0 8.3SR 78-45 16.8 499.0 11.3 45 17.2 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 28.5 128.0 20.0 12 29.0 128.0 17.5SR 36-45 23.9 47.5 35.1 36 25.7 54.8 30.7MAIN 36-45 32.9 500.0 -12.4 36 34.1 500.0 -15.3SR 36-45 34.1 500.0 -12.4 36 34.5 500.0 -15.30804000250 MHzACR-N (dB)