Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]23.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.5 464.0 29.9 36 9.5 496.0 26.5SR 12-36 7.7 465.0 29.9 36 7.5 475.0 26.9MAIN 12-36 9.8 496.0 29.3 36 9.6 500.0 26.4SR 12-36 7.9 499.0 29.3 36 7.8 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.0 472.0 11.8 45 17.7 500.0 8.3SR 78-45 18.9 500.0 11.3 45 17.8 500.0 8.3MAIN 36-45 19.2 500.0 11.3 45 17.7 500.0 8.3SR 78-45 18.9 500.0 11.3 45 17.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 17.3 28.3 41.5 45 18.5 28.3 39.1SR 36-45 14.9 28.3 41.5 45 17.1 28.1 39.1MAIN 12-36 33.0 496.0 -12.1 36 33.0 500.0 -15.3