Title: økernvn 94.pdf
MAIN 12-36 6.5 23.6 43.3 12 8.0 9.6 50.3SR 12-36 6.9 12.4 50.1 12 8.5 9.6 50.3MAIN 36-45 11.1 249.5 4.7 36 10.6 250.0 2.0SR 12-36 11.9 243.0 5.4 36 11.7 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.9 26.6 18.9SR 45 4.5 7.8 21.0MAIN 45 9.7 237.5 10.2SR 36 8.0 235.0 10.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94