Title: Hardware Installation Guide.pdf
The Output Control Module board contains two (2) 8-position DIP switches that are user selectable to control addressing, baud rate, and other user functions, and one (1) RS-485 termination jumper used to configure the system.57.1Setting DIP Switches57.1.1Communication Baud Rate (SW1)Configure the baud rate using SW1 switches 1 and 2. (Switches 3 through 8 are not used.)Baud rateSW1 switch for host1:2:2400 bpsoffoff9600 bpsONoff19200 bpsoffON38400 bpsONONrevision 6 — 309LNL-1200-U Output Control Module57.1.2Device Address (SW2)Configure the board address using SW2. (Switches 6-8 are not used.)AddressSW2 switch1:2:3:4:0offoffoffoff1ONoffoffoff2offONoffoff3ONONoffoff4offoffONoff5ONoffONoff6offONONoff7ONONONoff8offoffoffON9ONoffoffON10offONoffON11ONONoffON12offoffONON13ONoffONON14offONONON15ONON