Title: økernvn 94.pdf
75100LinkWare Version 7.4Cable ID: D4042 Date / Time: 09/10/2013 12:43:11 Headroom 14.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]226 359 26 9.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.4 85.0 33.5 36 16.0 93.8 29.8SR 12-36 15.5 79.3 34.0 36 17.1 95.3 29.7MAIN 12-36 14.5 92.3 32.9 36 16.1 98.0 29.4SR 12-36 15.7 93.8 32.8 36 17.1 96.5 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)