Title: +038=433.000-NI003._15-Testrapport elektrike anlegg - DM3.E1=433.06.01, Ryggsekk plan 06 (Working Copy).pdf
TEST RAPPORTBruker:Teststed:Tallberg Elektro A/S Stanseveien 4+DM3.E1=433.06.01 Dronning Mauds gate 1-3Instrument dataType:EUROTEST COMBOSer.Nr.:13250825Modell:MI 3125BTProdusent:Metrel d.d.Nr. 11ResultatDM1-3. Plan 6 / DM3.E1=433.06.01 / XF010 FAZ-C25/4 30.11.2020 12:03 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩ22DM1-3. Plan 6 / DM3.E1=433.06.01 / XF011 16C2/003 30.11.2020 12:25 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩ33DM1-3. Plan 6 / DM3.E1=433.06.01 / XF011 16C2/003 30.11.2020 11:52SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0Hz44DM1-3. Plan 6 / DM3.E1=433.06.01 / XF012 16C2/003 30.11.2020 12:25 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩ55