Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
non-differential, single-ended W300: W310: W340: W350: W360: 2.0 mA20 kΩ / 0.15 % 125 Ω / 0.1 % U: 200 kΩ / I: 125 Ω not relevant not relevantMaximum signal current for the resistance thermometers: Accuracy at 25 °CW300, 310: ± 0.5 % W340, 350, 360: ± 0.3 % ± 0.05 %Repeating accuracy: Temperature error (0 … +55 °C) ± 0.2 % < 10 µs Conversion time A/D: W340: Overvoltage protection: W300 *): W340: W310 *): yes± 50 VDC (permanent) + 50 VDC (permanent) ± 40 mA (permanent) + 40 mA (permanent)Overcurrent protection:EMC protection:5-67PCD2.W3x0Time constant of input filter:Internal current consumption: (from +5 V bus) Internalcurrent consumption: (from V+ bus)External current consumption: Terminals:W300: W310: W340typically 10.5 ms typically 12.4 ms typically 7.8 ms typically 24.2 ms typically 24.2 ms typically 16.9 ms typically 16.9 msV: C: T:W350: W360: < 8 mA for all module types