Title: økernvn 94.pdf
100150200250MHzLinkWare Version 7.4Cable ID: D4153 Date / Time: 09/10/2013 05:00:50 Headroom 12.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]176 276 17 7.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.5 95.5 32.6 36 14.6 95.5 29.6SR 12-36 12.6 95.5 32.6 36 14.4 95.5 29.6MAIN 12-36 12.5 95.5 32.6 36 14.6 95.5 29.6SR 12-36 12.6 95.5 32.6 36 14.5 99.5 29.310080604020NEXT (dB)