Title: +038=75.001-RS002._02-Værstasjon Meteodata 140 Basic KNX Instell Installasjonsveiledning.PDF
This installation method is recommended if wind is to be registe- red from all directions5. Electrical connectionBus terminal for bus connectionWasherRubber sealFeed in linesFeed cable for bus through the rubber seals provided- and plugthe lines into the bus terminal.KNX6. Enter physical addressPress the programming push button 3 on the bottom of the device with a screwdriver.The programming LED flashes.Meteodata 140 basic KNX is in program mode.27. Technical dataOperating voltage KNX: 21 – 32 V DC Power input KNX bus: ≤10 mA • Permissible ambient–20 °C ... +55 °C III IP 44 in accordance with EN 60529 JSTY 2 x 2 x 0.8 mm (bus cable) Dm 50–60 mm (accessory 9070380) 2–30 m/stemperature: • Protection class: • Protection rating: • Cable: • Mast installation: • Wind sensor: • Brightness sensor (3): 1–100,000 lux • Temperature sensor:–30 °C to +60 °CThe ETS database is available at www.theben.de Please refer to the KNX Handbook for detailed functional descriptions.