Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12-45 22,1 11,3 10,8 442,00Worst Value: Local: 12-45 21,5 11,3 10,2 443,00Remote: 12-45 22,1 11,3 10,8 442,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,7 23,8 3,9 499,00Remote: 45 28,4 23,8 4,6 497,00Worst Value: Local: 36 27,7 23,8 3,9 499,00Remote: 45 28,4 23,8 4,6 497,00PS-ACRF: Pass Worst Margin: Local: 45 20,1 8,3 11,8 442,00Worst Value: Local: 45 20,1 8,3 11,8 442,00Remote: 45 73,1 61,2 11,9 1,00Remote: 45 19,9 7,2 12,7 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 52Copper Certification ReportCable Label: 521.002-UD-130 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 12:02:24 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein