Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Isc: 393A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 149A Isc(0.76%): 299A Isc(1.15%): 452ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 06.11.2020 10:05Zs(rcd)Z: 0.63ΩIsc: 364A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 06.11.2020 10:06Tallberg Elektro A/S Tlf.22796640Side:24GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.160160161161162162163163164164165165TEST RAPPORTResultatZs(rcd)Z: 0.74ΩIsc: 312A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 06.11.2020 10:07RCD II: 28.5mAUci: 0.2V t: 102.0ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 06.11.2020 13:22R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 05.11.2020 11:26