Title: V20-09-02 VVS-anlegg plan 9 - DM3-1.pdf
LD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD006T Maks:140 m³/h Kjøling: 110 W 0.009 L/s Varme: 135 W 0.003 L/s0 0 1 : 1ø160 UK=270515 mm UK = 2843 15 mm UK = 284315 mm UK = 2843 15 mm UK = 2843Møterom 9-122STAD Dim:10/09 StengtMøterom 9-12122 mm +c 2850 22 mm +c 285015 mm +c 2850 15 mm +c 2850Åpent kontorlandskap 9-120LD001T Maks:210 m³/h Kjøling: 585 W 0.047 L/s Varme: 600 W 0.014 L/s1 : 1Opp MA 110MA 110 UK = 2744SF002T-160SF002T-160ø160 UK=267528 mm +c 2820 28 mm +c 2820WISE IAQWISE RTAWISE RTAWISE IAQLD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/sLD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/s0B1A2Sluk 75mm. Rør fra sluk legges i dekke før det går ned i eks. utsparing i dekke1100x800 SZ002T 1100 x800310.003: PE80 56mm 310.001: MA 110mm 310.002: MA 110mmPlan 10Plan 1035.07 m1000x600 UK=22501100x80035.07 m 310.001: MA 75mm Avkastkammer