Title: +038=370.101-QH009._01-Siemens Fukt_tempføler QFA3160_AQF3100.pdf
Room sensors QFA31..AC 24 V (cid:114) 20 % or DC13,5…35 V (SELV)orAC/DC 24 V class 2 (US)50 / 60 Hz at AC 24 VFuse slow max. 10 AorCircuit breaker max. 13 ACharacteristic B, C, D according to EN 60898 orPower source with current limitation of max.10 A(cid:100) 1 VArefer to Data Sheet of the device handling the signal0...100 % r. h.(cid:114) 2 % r. h.(cid:100) 0 . 0 5 % r.h. / ° C< 20 sDC 0...10 V 0...100 % r.h. max. 1 mA4…20 mA 0...100 % r.h. refer to "Function"0...50 °C (R2 = factory setting), (cid:16) 35...(cid:14) 35 °C (R1), (cid:16) 40...+70 °C (R3)Pt 1000(cid:114) 0.3 K (cid:114) 0.6 K (cid:114) 0.8 K8.5 min. (according to airflow andwall coupling)DC 0...10 V 0...50/(cid:16) 35...(cid:14) 35/(cid:16) 40...+70 °C max. 1 mA4..20 mA 0...50/(cid:16) 35...(cid:14) 35/(cid:16) 40...+70 °C refer to "Function"EN 60529IP65IP40IP65III according to EN 60730-1 1 (cid:117) 2.5 mm2 or 2 (cid:117) 1.5 mm2 M 16 x 1.5