Title: 32 Pumper modbuss teknisk data.pdf.pdf
Remote pressure 2Remote diff. pressureFeed tank levelStorage tank levelPump flowRemote flowPumped liquid tempTemperature 1Temperature 2Remote diff. tempAmbient temperatureMotor bearing temp. BEMotor bearing temp. NDEOther parameter9.9 Alarm simulation register block (not CUE)Alarm simulation can be used to simulate alarms and warnings on the E-pump. This is typically used when testing alarm event handling in BMS/SCADA system controllers. Whether the Simulation. AlarmCode register or the Simulation. WarningCode register is used makes no difference. The pump will in both cases react according to the predefined reaction to the code in question.For the complete list, see chapter 10.4 Alarms and warnings.Not all codes apply to all E-pump types.Address Register nameDescription00701Simulation. AlarmCodeAlarm code to simulate. See section 17. Grundfos alarm and warning codes.00702Simulation. WarningCode