Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
BBV39803Isolator for blade-type fuses630 AKTB0630HF•AAV829641000 AKTB1000HF•AAV82964Follow this procedure for installing bolted tap-off units:StepAction1Remove the tap-off unit cover.2Install the protection device in the tap-off unit.NOTE: In tap-off units with PEN, you can remove the connection between the neutral and earth if needed.3Check that the protection device is switched off and carefully inspect the tap-off unit for tools and objects that may have been left inside the tap-off unit.4Check that the run component is not energized. Always use a properly rated voltage sensing device to confirm that the power is off.5Remove the IP protection on the outlet of the run component.6Plug the tap-off unit into the run component.7Screw the tap-off unit onto the run component.8Slide the bolt access shutter on the tap-off unit to align the holes and provide access to the connection bolt.9