Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]25.7 111 1 3.83Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.3 453.0 30.1 36 6.8 453.0 27.3SR 12-36 8.3 444.0 30.4 36 9.5 458.0 27.0MAIN 12-36 8.6 500.0 27.8 36 7.6 500.0 25.0SR 12-36 9.1 500.0 27.8 36 9.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.4 12.0 43.7 45 21.8 6.1 46.5SR 45-78 20.4 12.0 43.7 45 21.9 5.9 46.9MAIN 36-12 22.2 473.0 11.7 45 24.6 500.0 8.3SR 12-36 22.1 473.0 11.7 36 23.9 473.0 8.70100806040200250 MHzACR-F (dB)