Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Ulim: 25V135| Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 034 GODKJENT * 12.03:2020! 12351KONTINUITET GODKJENTR: 0.2QGrenseverdi:Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 034 GODKJENT * 12.03.2020 15:08SPENDING1.0QUln: 233VUlpe: 233VUnpe: 0Vf: 49.9HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 034 GODKJENT * 1125,0852020: 13:39(red) GODKJENTZ: 0.59QIsc: 390ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160C.0AZsTEST RAPPORTResultatR ISOR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQGODKJENTDronning M.g.13 / E.433.11.01 TNS / Sikring 03512.03.2020 13347SPENDINGUln: 235VUlpe: 235VUnpe: 0Vf: 50.1HzR ISOR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQGODKJENT*GODKJENTDronning M.g.13 / E.433.11.01 TNS / Sikring 03611.03.2020 10:23SPENDINGUln: 234VUlpe: 235VUnpe: 0OVf: 49.9HzR ISOR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQGODKJENT*GODKJENT