Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.10.03-UF100 Date / Time: 27-02-2020 23:16:41 Headroom 9.3 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]30.9 133 1 4.59Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.3 460.0 30.0 36 8.2 478.0 26.8SR 12-45 9.9 486.0 29.5 45 9.3 486.0 26.7MAIN 36-45 9.8 496.0 29.3 36 8.3 496.0 26.5SR 12-45 9.9 486.0 29.5 45 9.3 486.0 26.710080604020NEXT (dB)