Title: økernvn 94.pdf
MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: D4192 Date / Time: 09/10/2013 04:52:19 Headroom 8.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]253 388 15 11.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]6.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-78 9.3 170.0 38.1 78 8.2 247.5 32.8SR 12-36 8.7 236.5 35.7 36 9.0 234.5 33.2MAIN 36-78 9.8 247.5 35.4 78 8.2 247.5 32.8SR 12-36 8.7 236.5 35.7 36 9.0 234.5 33.210080604020NEXT (dB)