Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Uci: 0.2V t: 23.5ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 05.11.2020 11:31R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 05.11.2020 11:20KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 06.11.2020 13:22R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF041 16C2/003 06.11.2020 11:01SPĆNDINGU12: 234V U1pe: 0V U2pe: 235V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF041 16C2/003 06.11.2020 11:01Z-LINEZ: 0.42ΩIsc: 545A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 207A Isc(0.76%): 414A Isc(1.15%): 626ATallberg Elektro A/S Tlf.22796640Side:22GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTNr. 147147148148149149150150151151152152153153TEST RAPPORTResultat