Title: økernvn 94.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.7 11.5 50.9 12 9.0 11.4 48.6SR 12-36 8.1 11.5 50.9 12 9.6 11.4 48.6MAIN 36-45 12.7 249.0 4.8 36 11.9 248.5 2.2SR 36-45 12.5 250.0 4.7 36 12.1 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.8 12.6 20.5SR 45 3.5 8.0 21.0MAIN 36 8.1 190.5 11.2SR 36 8.5 248.5 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4