Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Background Perpendicular illuminance (adaptive) [Ix] 248 (= 100) 126 329 0.51 0.38 Height: 0.000 m, Wall zone: 0.100 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 6 iGuzzini illuminazione - Q510 Laser Blade XS - Downlight HC 23.1W 1452 231 62.9 Total via all luminaires 8712 138.6 62.9Lighting power density: 5.02 W/m? (Floor area of room 27.63 m? ), Lighting power density: 5.44 W/m? = 2.20 W/m2/100 Ix (Area of working plane 25.46 m?)Consumption: 170 - 270 kWh/a of maximum 1000 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels. The results are informative. The energy consumption of a building results from the sum of all consumptions in the rooms.The resulls were calculaled wilhoul consideralion of objects and furniture. No results were determined on their surfaces.