Title: V20-09-01 VVS-anlegg plan 9 - DM1-1.pdf
LD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sSF002T-160WISE RTAø125 UK=2736ø160 UK=2693SF002T-160NedEks. trapp 9-530:Opp 310.101 KV: Cu 35mm 310.201 VV: Cu 28mm310.302 VVC: Cu 22mmKondensavløp, Ned 310.001: MA 58mmCu 28mmST008T-125 50 m³/hPatcherom 9-501.2-sDN25 0,017 l/sNed 320.101: 28mm 320.101: 28mm 310.001: MA 110mm 370.102, tur: 28mm 370.102, retur: 28mm 310.003: MA 110mm Opp 310.001: MA 110mm Opp 310.001: MA 110mm Brannskap 320.101, tur: 28mm 320.101, retur: 28mmMA 110 UK = 2617 B Opp 310.001: MA 110mm 370.102, tur: 28 mm +c 2813 370.102, retur: 28 mm +c 2813Fancoil, 2kW Tilkobles prosesskjølingXLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sÅpent kontorlandskap 9-101LD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sSK001T Ø125 Q:50 m³/hSF002T-125ø125 UK=2693C