Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
5. Compare the calculated output voltage (Step 3) and the measured output voltage (Step 4). If the measured output voltage differs greatly from the calculated output voltage, replace the transducer. It is normal for the transducer reading to differNote: somewhat from pressure gauge readings due to voltmeter and gauge tolerances, and other factors.Figure 7: Voltage calculation for 0.5 VDC to 4.5 VDC ratiometric transducersP499 Series Electronic Pressure Transducers Product/Technical Bulletin55. Compare the calculated output current (Step 3) to the measured output current (Step 4). If the current from measured output current differs greatly from the calculated output current, replace the transducer. It is normal for the transducer reading to differ Note: somewhat from pressure gauge readings due to multimeter and gauge tolerances, and other factors.