Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
Date / Time 05/19/2022 08:54 AM 05/19/2022 08:57 AM 05/19/2022 10:05 AM 05/19/2022 10:37 AM 05/19/2022 10:55 AM 05/19/2022 11:04 AM 05/19/2022 11:09 AM 05/19/2022 11:11 AM 05/19/2022 11:19 AM 05/19/2022 11:37 AM 05/19/2022 11:40 AM 05/19/2022 11:50 AM 05/19/2022 11:51 AM 05/19/2022 11:55 AM 05/19/2022 12:22 PM 05/19/2022 12:26 PM 05/19/2022 01:10 PMTotal Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 2 05/25/2022 12:14:00 PM Untitled1395.9 m 17 17 0 0 0Cable ID: UD01 Date / Time: 05/19/2022 08:54:48 AM Headroom 7.2 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 45] [Pair 12] [Pair 12] [Pair 36]36.6 168 3 6.3Wire Map (T568B) PASS