Title: +039=442.001-UP008T_01-UP08 Iguzzini Q497_EN laser blade xs Produktblad.pdf
Wiring On the power supply unit with terminal board included.Complies with EN60598-1 and pertinent regulationsTechnical datalm system: W system: lm source: W source: Luminous efficiency (lm/W, real value): lm in emergency mode: Total light flux at or above an angle of 90° [Lm]: Light Output Ratio (L.O.R.) [%]: Beam angle [°]: CRI: Colour temperature [K]: MacAdam Step: Life Time LED 1:739 12.4 890 9.9 59.608358° 90 3000 2 > 50,000h - L80 - B10 (Ta 25°C)Ballast losses [W]: Voltage [Vin]: Lamp code: Number of lamps for optical assembly: ZVEI Code: Number of optical assemblies: Power factor: Inrush current: Maximum number of luminaires of this type per miniature circuit breaker:Minimum dimming %: Overvoltage protection:Dimming mode: Control:2.5 230 LED 1LED 1See installation instructions 5 A / - µs B10A: 81 luminaires B16A: 130 luminaires C10A: 135 luminaires C16A: 221 luminaires 1 2kV Common mode & 1kV Differential mode CCR DALIPolarUtilisation factorsQ497_EN 1 / 2