Title: Data tester Smestad skole - Detaljert.pdf
501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 68,0 57,3 10,7 2,20Remote: 12-45 68,0 57,3 10,7 2,20Worst Value: Local: 12-45 21,2 10,2 11,0 499,00Remote: 45-12 21,6 10,2 11,4 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,8 23,8 3,0 500,00Remote: 36 28,3 23,8 4,5 500,00Worst Value: Local: 36 26,8 23,8 3,0 500,00Remote: 36 28,3 23,8 4,5 500,00PS-ACRF: Pass Worst Margin: Local: 45 71,7 61,2 10,5 1,00Worst Value: Local: 12 20,0 7,3 12,7 495,00Remote: 12 72,4 61,2 11,2 1,00Remote: 12 19,9 7,2 12,7 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:56Signature:______________________ Page: 11Copper Certification Report