Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 39,2 68,0 204,0 12,0 7,0Limit 100,0 - 555,0 50,0 25,0Margin 60,8 - 351,0 38,0 18,0Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,0 2,3 2,80Worst Value: Local: 36 16,8 43,5 26,7 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 14,0 8,0 6,0 478,00Remote: 78 19,2 12,2 7,0 150,50Worst Value: Local: 78 14,0 8,0 6,0 478,00Remote: 45 17,0 8,0 9,0 479,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):