Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
28.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.7 471.0 29.2 36 7.4 471.0 26.4SR 36-45 6.3 463.0 29.6 36 6.9 419.0 28.1MAIN 36-45 8.5 499.0 27.9 36 8.3 498.0 25.1SR 36-45 6.9 495.0 28.1 36 7.9 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.9 4.3 52.7 45 16.4 3.5 51.4SR 45-78 15.9 4.3 52.7 45 16.4 3.5 51.4MAIN 78-45 16.5 493.0 11.4 45 17.5 484.0 8.5SR 78-45 16.3 500.0 11.3 45 17.5 493.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 23.3 62.8 31.3 12 25.3 113.0 19.6SR 36-78 22.0 89.5 26.0 36 24.1 94.5 22.6MAIN 36-45 35.9 499.0 -12.3 36 36.2 498.0 -15.1SR 36-45 34.4 495.0 -12.1 45 35.8 499.0 -15.20804000250 MHzACR-N (dB)