Title: 370.011 LC002_22 kW isvannsenhet OPU 30B.pdf
Panelfilter Trykkvakt for tett filter alarmQuantity Filtering efficency : Suggested final pressure drop Dimensions[n][Pa] [mm]2 G4 250 700 x 640 x 48CHILLED WATER CIRCUITIsvanns coilRegulating valve :3 way ball valveCHILLED WATER CIRCUIT PERFORMANCESPerformance are declared according EN 14511 (at gross of the heat generated by the fan)Fluid 100 % recirculation Re-suction air Re-suction air Discharge air Discharge air Total cooling capacity: Sens.cooling capacity: EER (Energy Effinciency Ratio)[°C] [%] 50,0 [°C] [%] [kW] [kW]Water + Glycole 0,0%WB [°C]24,0 17,0 15,0 89,0 22,3 22,3 16,16[°C] [°C] [l/h] [kPa] [kPa] [kPa]Water temp.inlet: Water temp.outlet: Chilled water flow : Coil pressure drop . Valve pressure drop Total pressure drop : EER = total cooling capacity / fans power input.10,0 16,0 3.200 17,8 10,2 28,0VENTILATING SECTIONPlug fan EC type, air flow control according cooling capacity EC type plug fan for supply air flow regualtion in