Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Uci: 0.0V t: 12.7ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE045 06.02.2020 08:39R LOW OhmR: 0.62ΩR+: 0.6Ω R-: 0.6Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE015 07.02.2020 12:59Z-LINEZ: 1.71ΩIsc: 135A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE020 06.02.2020 09:10R LOW OhmR: 0.07ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE030 10.02.2020 09:01SPÆNDINGUln: 231V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE030 06.02.2020 09:08R LOW OhmR: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩTEST RAPPORTSide:18MISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESGODKJENTGODKJENTGODKJENT*GODKJENT*GODKJENTNr. 112112113113114114ResultatOBJEKT / Plan 10 / FUSE030 10.02.2020 09:02RCD II: 28.5mAUci: 0.2V t: 22.8ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE030 06.02.2020 08:34KONTINUITET R: 0.6ΩGrenseverdi: 1.0Ω