Title: Hardware Installation Guide.pdf
Power: 18 AWG, 1 stranded twisted pair RS-485: 24 AWG, 120 ohm impedance, stranded twisted pair with shield, 4000 feet (1219 m) maximum Alarm inputs: 1stranded twisted pair per input, 30 ohms maximum Outputs: As required for the load Reader data (TTL): 6 conductors, 18 AWG stranded, 500 feet (150 m) maximum Reader data (RS-485): 24 AWG, 120 ohm impedance, stranded twisted pair with shield, 2000 feet (609.6 m) maximumMechanical:Dimension: 6 x 8 x 1 in. (152 x 203 x 25 mm)- Weight: 11 oz. (312 g) nominalEnvironmental: - -Temperature: 0 to +70° C operating, -55 to +85° C storage Humidity: 0 to 95% RHNCCertifications: - - - - - - - WEEEUL294 & UL1076 Listed ULC Listed FCC Part 15 C-Tick CE marking RoHS compliant404 — revision 6LNL-1320-U DUAL DOOR CONTROLLER MODULEHardware Installation Guide83Overview of the LNL-1320-U Board