Title: 1 etg del 2.pdf
Measurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T1286 Date / Time: 10/17/2013 02:15:09 PM Headroom 14.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]77 124 10 3.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.5 92.5 32.9 36 16.3 92.3 29.9SR 12-36 18.9 92.5 32.9 36 19.7 92.5 29.9MAIN 12-36 14.5 92.8 32.8 36 16.3 92.8 29.8SR 12-36 18.9 92.5 32.9 36 19.7 92.5 29.910080604020NEXT (dB)