Title: Data tester Smestad skole - Detaljert.pdf
Worst Margin: Local: 12-45 26,8 15,8 11,0 262,00Remote: 45-12 63,2 52,1 11,1 4,00Worst Value: Local: 12-45 22,1 10,2 11,9 500,00Remote: 12-45 22,7 10,2 12,5 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,9 23,8 4,1 499,00Remote: 45 28,7 23,8 4,9 499,00Worst Value: Local: 36 27,8 23,8 4,0 500,00Remote: 45 28,7 23,8 4,9 499,00PS-ACRF: Pass Worst Margin: Local: 45 73,1 61,2 11,9 1,00Worst Value: Local: 45 21,5 7,2 14,3 500,00Remote: 12 72,4 61,2 11,2 1,00Remote: 45 21,1 7,2 13,9 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 48Copper Certification ReportCable Label: 521.002-UD-147 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name: