Title: økernvn 94.pdf
50100150200250MHzLinkWare Version 7.4Cable ID: T3416 Date / Time: 09/13/2013 08:39:45 Headroom 6.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]115 177 7 5.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]19.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.8 218.5 36.3 36 7.9 218.5 33.7SR 12-36 7.0 233.0 35.8 36 6.5 239.0 33.0MAIN 12-36 6.8 218.5 36.3 12 8.4 242.0 32.9SR 12-36 7.0 233.0 35.8 36 6.5 239.0 33.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)