Title: Aggregatkjøring.pdf.pdf
Filter size6x[592x490x25] + 2x[287x490x25]Filter length520mmFilter descriptionCamfil Hi-Flo II XLTRotary heat exchangerData are stated on supply.Systemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.001-1/Unit no. 10Date 18.06.2021Page 12/40Twin fan, PlugAir flow15318m³/hExternal pressure250PaPressure drop23PaStatic pressure (Designed at wet conditions)547PaTotal pressure567PaFan speed1518RPMMaximum fan speed1950RPMTotal efficiency by static pressure, incl. motor and speed control69.3%Total efficiency by total pressure, incl. motor and speed control71.8%K-factor (p=1.2 kg/m³)(2 x 280) 560Fan type - 2xLargeGR50I-ZID.GG.CRErP efficiency n(stat,A)75.2%ErP efficiency class N(actual)/ N(target)80.0 / 62ErP-conformity