Title: V20-10-01 VVS-anlegg plan 10 - DM1.pdf
Møterom 10-103Møterom 10-106ø250 UK=3090 ø250 UK=3090Møterom 10-1055 3 1 3 = K U 0 6 1 ø5 3 1 3 = K U 0 6 1 øø250 UK=3070 ø250 UK=3070SF002T-200Møterom 10-104320.102: 15 mm +c 3273320.102: 15 mm +c 3273ø160 UK=3165STAP/STAD DN 40STAD Dim:09/10 StengtSTAD Dim:09/10 Stengt370.101: 18 mm +c 3273 370.101: 18 mm +c 3273370.101: 42 mm +c 3273 370.101: 42 mm +c 327342 mm +c 3180320.102: 28 mm +c 3180+10 = 370.101 - OE 106 0.527 L/s42 mm +c 3180DN 50 Ned =370.101LD001T Maks:215 m³/h Kjøling: 535 W 0.043 L/s Varme: 480 W 0.012 L/sLD001T Maks:170 m³/h Kjøling: 440 W 0.034 L/s Varme: 360 W 0.009 L/sLD001T Maks:170 m³/h Kjøling: 440 W 0.034 L/s Varme: 360 W 0.009 L/sLD001T Maks:200 m³/h Kjøling: 440 W 0.034 L/s Varme: 360 W 0.009 L/sLD001T Maks:200 m³/h Kjøling: 440 W 0.034 L/s Varme: 360 W 0.009 L/sLD001T Maks:215 m³/h Kjøling: 430 W 0.034 L/s Varme: 480 W 0.008 L/s