Title: økernvn 94.pdf
50 MHz75100LinkWare Version 7.4Cable ID: D3415 Date / Time: 09/11/2013 03:30:22 Headroom 5.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]119 182 6 5.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]19.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.4 232.5 35.9 36 5.3 232.0 33.2SR 12-36 5.2 237.5 35.7 12 6.5 237.5 33.1MAIN 36-78 5.7 244.5 35.5 36 5.3 232.0 33.2SR 12-36 5.2 237.5 35.7 12 6.5 237.5 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)