Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 16.1 446.0 12.2 45 17.1 3.9 50.5MAIN 78-45 16.1 487.0 11.5 45 18.1 496.0 8.3SR 45-78 16.6 487.0 11.5 45 17.9 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 23.9 96.0 24.9 12 24.5 95.8 22.4SR 36-78 27.8 98.5 24.5 36 28.3 93.5 22.8MAIN 36-45 36.5 499.0 -12.3 36 35.7 499.0 -15.2SR 36-45 37.1 495.0 -12.1 36 37.5 494.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.7 93.3 14.3SR 45 6.0 497.0 8.0MAIN 45 9.3 497.0 8.0SR 45 6.0 497.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS