Title: Hardware Installation Guide.pdf
3. Wire the upstream host communication.4. Wire the relay outputs.5. Wire the power input.42.1.1Non-supervised Alarm Inputs: Power Fault and Cabinet Tamper MonitorsThe Input Control Module features two non-supervised alarm inputs that can be used for power fault and cabinet tamper monitoring. These inputs are connected using the BA (power fault) and CT (cabinet tamper) contact terminals on the Input Control Module board.The BA and CT inputs are simple N/C (normally closed) contact closure monitors.Wire the BA and CT inputs using twisted pair cable, 30 ohms maximum. (No EOL resistors are required.)Non-supervised Alarm Input Wiring (BA and CT contacts.)CABINET TAMPERGNDIN 2POWER FAULTGNDIN 1Note:If either of these inputs is not used, a shorting wire should be installed.42.1.2Software Configurable Alarm Inputs