Title: 2 etg del2.pdf
Cable ID: D2021 Date / Time: 10/10/2013 12:22:17 PM Headroom 4.0 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]244 372 13 11.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]7.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 4.0 206.0 36.7 78 5.7 206.0 34.1SR 36-78 8.6 227.5 36.0 36 8.8 217.5 33.7MAIN 36-78 4.0 206.0 36.7 78 5.7 206.0 34.1SR 36-78 8.6 227.5 36.0 36 8.8 217.5 33.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.9 181.5 19.0 12 17.3 3.8 49.7