Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD86 Date / Time: 28/01/2022 14:02:09 Headroom 8.8 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]35.0 180 13 6.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 9.0 239.5 33.4 3,6 9.6 100.5 37.0SR 1,2-3,6 8.8 85.3 41.1 1,2 10.5 47.3 42.7MAIN 4,5-7,8 9.0 239.5 33.4 4,5 10.7 239.5 30.5SR 1,2-3,6 10.4 239.5 33.4 3,6 12.2 236.0 30.6PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)