Title: økernvn 94.pdf
Cable ID: T4136 Date / Time: 09/09/2013 03:42:20 Headroom 6.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]79 126 9 3.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.6 214.0 36.4 36 7.4 243.0 32.9SR 12-36 6.4 214.0 36.4 12 7.4 214.0 33.8MAIN 12-36 6.6 214.0 36.4 36 7.4 243.0 32.9SR 12-36 6.4 214.0 36.4 12 7.5 238.5 33.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 15.1 3.3 54.0 45 15.5 2.4 53.7