Title: 370.02-SC001 - Siemens VKF41.100 (Stengeventil).pdf
> 100 mm: minimum clearance from the wall or ceilingTypeDN A BCEFEFHkgøøPN 6PN 10, PN 16M16 (4x) M16 (4x) M16 (4x) M16 (8x) M16 (8x) M16 (8x) M20 (8x)40 30 130 87 100 M12 (4x) 110 VKF41.40 50 30 140 97 110 M12 (4x) 125 VKF41.50 65 30 160 117 130 M12 (4x) 145 VKF41.65 VKF41.80 80 30 175 133 150 M16 (4x) 160 VKF41.100 100 30 195 153 170 M16 (4x) 180 VKF41.125 125 40 225 183 200 M16 (8x) 210 VKF41.150 150 40 255 208 225 M16 (8x) 240 VKF41.200 200 40 310 263 280 M16 (8x) 295 M20 (8x) for PN 10 M20 (12x) for PN 16SAL..T10 SAL..T40 275 280 287.5 295 305 325.5 338363[kg]1.72 1.94 2.37 2.63 2.92 5.25 6.298.44DN = Nominal size H = Total actuator height plus minimum distance to the wall or the ceiling for mounting, connection,operation, maintenance etc.7/8Butterfly valves PN6, PN10, PN16CM1N4131en 2013-11-11Spare partsRevision numbers8/8Siemens Building TechnologiesOrder number for spare partsCentering sleevesProduct number VKF41.40VKF41.50VKF41.65