Title: Instructions manual - THGT fan.pdf
Correct and rebalance Correct and replace bearings Correct or replace belts Correct and refix mountings Correct and replace bearings Correct and replace shaft and bearings Correct and replace bearings Correct and clean Correct and level fan assemblyCorrect and re-commision fan Correct and re-commision fan8. Repairs8.1 Repairs must be carried out by competent personnel and in accordance with applicable International, National and Local regulations, especially for hazardous areas. Fan equipment should be electrically isolated and locked out before any work started. It may be desirable to remove fan to a non-hazardous area / workshop for repairs.Any work undertaken on ATEX fan equipment by persons other than those from manufacturer or agreed with manufacturer, will invalidate the provisions of the guarantee. When any repair is made to ATEX fan equipment an “R” label with relevant data to indicate “Repair” and who is responsible, must be applied to product – Refer IEC EN 60079-19.8.2 Replacement parts