Title: 1 etg del 2.pdf
Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T1125 Date / Time: 10/21/2013 07:58:57 AM Headroom 1.3 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]189 300 21 7.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 250.0 35.3 36 1.6 250.0 32.7SR 36-78 7.7 245.5 35.5 78 8.8 246.0 32.8MAIN 36-45 1.3 250.0 35.3 36 1.6 250.0 32.7SR 36-78 7.7 245.5 35.5 78 8.8 246.0 32.810080604020NEXT (dB)