Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 41,8 68,0 217,0 12,0 7,4Limit 100,0 - 555,0 50,0 25,0Margin 58,2 - 338,0 38,0 17,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,0 2,3 1,90Worst Value: Local: 36 17,9 43,8 25,9 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 20,3 15,9 4,4 64,75Remote: 78 24,6 18,8 5,8 28,00Worst Value: Local: 12 14,3 9,0 5,3 316,00Remote: 36 15,6 8,0 7,6 500,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,9 26,7 3,2 499,00Remote: 36-45 30,2 26,7 3,5 499,00Worst Value: Local: 36-45 29,9 26,7 3,2 499,00Remote: 36-45 30,2 26,7 3,5 499,00dB 0501000Local250500 MHzdB 050