Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
Table 29: Minimum recommended multi-core cable 50 kWModel rating100 kW150 kW200 kWPhase cables [mm2]1x35 mm21x95 mm21x150 mm21x240 mm2PE cable [mm2]1x16 mm21x50 mm21x95 mm21x120 mm2Battery cable, pos. & neg line1x50 mm22x50 mm22x95 mm22x120 mm2For the calculation of the size of wires and cables, local and national electrical code requirements must always be followed.5.6.4CAN communications cablingConnect the communication cables to the respective terminals and peripherals located in the communication area in the front side.Figure 22. PCS Medium CAN communication interface1CAN bus connector2CAN end of bus connector© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL50 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guide5.7Installation and cabling of grounding