Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
27.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.2 498.0 29.3 36 9.8 499.0 26.4SR 36-78 8.7 478.0 29.7 36 9.4 471.0 27.0MAIN 12-36 8.2 498.0 29.3 36 9.8 499.0 26.4SR 36-78 8.7 478.0 29.7 36 9.7 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.1 6.9 48.5 45 19.3 500.0 8.3SR 78-45 19.1 500.0 11.3 45 19.7 500.0 8.3MAIN 45-78 19.2 500.0 11.3 45 19.3 500.0 8.3SR 78-45 19.1 500.0 11.3 45 19.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 17.8 45.0 35.8 36 19.5 48.8 32.3SR 36-45 17.1 45.0 35.8 36 19.1 48.8 32.3MAIN 12-36 35.5 498.0 -12.3 36 37.1 499.0 -15.2SR 36-78 36.8 497.0 -12.2 36 36.9 498.0 -15.10804000250 MHzACR-N (dB)