Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 43,7 68,0 227,0 12,0 7,4Limit 100,0 - 555,0 50,0 25,0Margin 56,3 - 328,0 38,0 17,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,8 3,0 2,2 2,80Worst Value: Local: 45 18,6 43,8 25,2 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 17,8 12,1 5,7 153,50Remote: 78 14,8 11,3 3,5 184,50Worst Value: Local: 36 15,2 8,0 7,2 500,00Remote: 36 14,3 8,0 6,3 500,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,0 26,7 1,3 499,00Remote: 36-45 28,8 26,7 2,1 500,00Worst Value: Local: 36-45 28,0 26,7 1,3 499,00Remote: 36-45 28,8 26,7 2,1 500,00dB 0601200Local250500 MHzdB 0