Title: økernvn 94.pdf
150200250MHzLinkWare Version 7.4Cable ID: D4171 Date / Time: 09/09/2013 02:09:31 Headroom 6.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]196 300 12 9.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.4 206.0 36.7 78 9.2 206.0 34.1SR 12-36 6.8 234.5 35.8 12 8.0 234.5 33.2MAIN 36-78 9.6 250.0 35.3 78 9.2 250.0 32.7SR 12-36 6.8 234.5 35.8 12 8.0 234.5 33.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)