Title: +135.01=564.001-XS020T_01-Montasje 5202AB13_bma_d-e-blinds_Norsk.pdf
Actions configured for execution on bus voltage recovery are only executed and possible new positions transmitted, if no alarm or blockage was active before bus voltage failure. The in- formation (not the object values) about alarm and blockage be- fore bus voltage failure is only saved for the initialization phase after bus voltage recovery. It is reset (no alarm active, no block- age active) after initialization. Consequently, if e.g. before bus voltage failure a blockage was active, the solar protection can- not be moved into a configured position on bus voltage failure or on bus voltage recovery. If after bus voltage recovery further messages to move the solar protection are received, then these are executed because the blockage present before bus voltage failure is not saved. Thus an explicit release of a blockage after bus voltage recovery is not required. If alarm surveillance periods are configured, then these are re- started on bus voltage recovery. The synchronization is retained on bus voltage