Title: økernvn 94.pdf
250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3401 Date / Time: 09/11/2013 03:24:12 Headroom 6.9 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]174 266 10 8.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]14.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.9 165.0 38.3 36 6.8 204.0 34.2SR 36-78 7.8 165.0 38.3 36 9.3 93.3 39.8MAIN 36-78 6.9 250.0 35.3 36 7.6 250.0 32.7SR 36-78 8.8 233.0 35.8 78 9.6 233.0 33.2100