Title: Data tester Smestad skole - Detaljert.pdf
Remote: 45-12 25,4 14,0 11,4 324,00Worst Value: Local: 12-45 21,9 10,4 11,5 490,00Remote: 45-12 22,4 10,4 12,0 490,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,8 23,8 4,0 500,00Remote: 36 28,3 23,8 4,5 497,00Worst Value: Local: 36 27,8 23,8 4,0 500,00Remote: 36 28,3 23,8 4,5 497,00PS-ACRF: Pass Worst Margin: Local: 12 71,7 61,2 10,5 1,00Worst Value: Local: 45 20,7 7,3 13,4 495,00Remote: 45 71,0 61,2 9,8 1,00Remote: 45 20,3 7,2 13,1 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:06Signature:______________________ Page: 85Copper Certification ReportCable Label: 521.002-UD-64 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:16:09 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein