Title: 2 etg del2.pdf
604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 8.1Cable ID: T2026 Date / Time: 10/11/2013 08:49:24 AM Headroom 11.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]86 135 9 3.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.5 95.8 32.6 36 12.9 95.5 29.6SR 12-36 11.0 84.3 33.5 36 13.1 91.8 29.9MAIN 12-36 11.7 99.5 32.3 36 13.0 99.5 29.3SR 12-36 11.1 95.8 32.6 36 13.2 99.5 29.3