Title: 30. Technoporten_Brannalarmutstyr datablad.pdf
The Single Monitored Input/Output Unit BN-304 has been designed for use with Autronica’s fire detection systems Autroprime (version 1.1.0 or newer) and AutroSafe (version 4.3.1 or newer), and includes the SelfVerifyfunction. This function ensures the highest grade of reliability and reduces the need for manual testing because the panel is able to continuously and automatically check all units that include this function. Function CFault condition signalling input unit with relay feedback Function DUncommitted input unit (Output follows input) Function EPre Alarm and Alarm condition signalling input unit with configurable input delay and relay feedback Function FFault, Pre Alarm and Alarm condition signalling inputNote: External devices attached to this interface unit require a separate power source (they can not be powered by the detector loop). SelfVerify: The unit’s ability to initiate alarm is regularly checked. Function G