Title: datablad gb fx net alc.pdf
Fault in Fire Alarm Router Equipment (Alarm transmitter) Fault in Fault Warning Router Equipment (Alarm transmitter)Power supply input (2 pcs) from an FX, FXL or FXM panel, separately moni- tored for low voltageFX-CLC (0 .. 1)FX-ALCB: Two addressable detection circuits, each 126 addresses FX-CLC: 16 Conventional detection circuits Max. 512 detectors and manual call points / panelFor each FX-ALCB: Power supply outputs (2 pcs), short circuit pro- tected, 500mA eachClean contact signal inputs (4 pcs), function to be selected with the con- figuration toolFX-IOC (0 .. 1)Clean contact relay outputs (2 pcs), max 30 VDC/ 1.0 A, function to be selected with the configuration toolAlarm device lines (4 pcs), max 500 mA each, function to be selected with the configuration toolPower supply outputs (2 pcs), short circuit protected, 500mA eachNote! The FXS NET panel requires power feed from an FX NET, FXL NET or FXM NET panel. The maximum number of LC, CLC and IOC boards is 1.D01589/GB0 20-2007