Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
Heat dissipation when discharging, 50% load1178 W2356 W3534 W4166 WHeat dissipation when discharging, 25% load840 W1680 W2521 W2521 W© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL29 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guideElectrical characteristics4.6.5 Table 19: Electrical characteristics, Grid-tie mode - RectifierModel rating (1.0 p.f.)50 kW100 kW150 kW200 kW220/380 V; 230/400 V; 240/415 VRated input voltage Voltage tolerance, rectifier input Rated input frequency Frequency tolerance Number of input phases, rectifier input Number of input phases, bypass input Input power factor, 100% load Rated input r.m.s. current, 380V Rated input r.m.s. current, 400V Rated input r.m.s. current, 415V Maximum input r.m.s. current Input current distortion at rated input current, re- sistive load In-rush current AC power distribution system compatibility Rectifier ramp-up, rectifier start and load step80 A75 A70 A