Title: BREEAM-0062-8875 Revisorrapport DM1-3 DS Prosjekteringsfase.pdf
Confirmation of compliance Schematic electrical sub-metersEne2.v02List of electrical sub-metersEne2.v03Memo from Electrical consultantValidation StatementCriterion 2. A BMS (Building Management System) has been installed with individual monitoring and outputs for the following systems (where present):a. Space Heating b. Domestic Hot Water c. Humidification d. Cooling e. Fans (major) f. Lighting g. Small Power (lighting and small power can be on the same sub-meter where supplies are taken at each floor/department). h. Other major energy-consuming items where appropriatePlanned energy meters are described by the electrical consultant in Ene2.v03. All systems listed above are included, except humidification, which is not included: Major energy consuming items are lifts, UPS-system, automation system on level U1, restaurant and external lighting (Ene2.v03).Planned meters are listed n Ene2.v02 and are shown on the schematic Ene2.v01.