Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-33Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.A2206.5.3 PCD2.A220, 6 relays with make contacts, without contact protectionApplicationThe module contains 6 relays with normally-open contacts for direct or alternating current up to 2 A, 250 VAC. The module is especially suited wherever AC switching circuits with infrequent switching have to be controlled. For space reasons, there is no integrated contact protection. Each group of 3 relays has a common connection.Technical dataNumber of outputs:3 + 3 make contacts with shared terminalType of relay (typical):RE 030024, SCHRACKSwitching capacity: (contact lifetime)2 A, 250 VAC AC1 1 A, 250 VAC AC11 2 A, 50 VDC DC1 1 A, 24 VDC DC110.7 x 106 operations 1.0 x 106 operations 0.3 x 106 operations 3) 0.1 x 106 operations 1)3)6Relay coil supply: 2)Voltage tolerance, dependent on ambient temperature: