Title: DOCA0005EN-12.pdf
Replace all devices, doors and covers before turning on power to this equipment.Do not exceed the device’s ratings for maximum limits.Do not touch the current terminal when the meter is energized.Failure to follow these instructions will result in death or serious injury.1. Turn off all power supplying this device and the equipment in which it is installedbefore working on the device or equipment.2. Always use a properly rating voltage sensing device to confirm that all power is off.All meters have sealing covers and sealing points to help prevent access to inputs and outputs and current and voltage connections.1718iEM3000 series user manualInput, output and communications wiring considerationsThe pulse output is compatible with S0 format, and the programmable digital output is compatible with S0 format when configured as a pulse output.The digital input and output are electrically independent.The digital output is polarity-independent.