Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.04.04-UF063 Date / Time: 10-12-2022 15:48:43 Headroom 7.7 dB (NEXT 36-78) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]41.2 178 2 6.08Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]23.0 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.8 498.0 29.3 36 9.2 500.0 26.4SR 36-78 7.7 472.0 29.8 36 7.6 472.0 26.9MAIN 12-36 8.8 498.0 29.3 36 9.2 500.0 26.4SR 36-78 7.7 472.0 29.8 36 7.7 500.0 26.410080604020NEXT (dB)