Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:01Zs(rcd)Z: 0.35ΩIsc: 648A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:02SPĆNDINGUln: 234V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:02Z-LINEZ: 0.41ΩIsc: 563A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:02SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:03Z-LINEZ: 0.44ΩIsc: 528A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:02Zs(rcd)Z: 0.35ΩIsc: 650A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:16Tallberg Elektro A/S Tlf.22796640Side:20