Title: +038=433.002-FS020._12-Tavlebyggeren Eaton FDV.pdf
With XFI earth-fault release: - NZM1, N1, NZM2, N2: vertical and 90° in all directions with plug-in unit - NZM1, N1, NZM2, N2: vertical, 90° right/left with withdrawable unit: - NZM3, N3: vertical, 90° right/left - NZM4, N4: vertical with remote operator: - NZM2, N(S)2, NZM3, N(S)3, NZM4, N(S)4: vertical and 90° in all directionsDirection of incoming supplyas requiredDegree of protectionDeviceIn the operating controls area: IP20 (basic degree of protection)EnclosuresWith insulating surround: IP40 With door coupling rotary handle: IP66TerminationsTunnel terminal: IP10 Phase isolator and strip terminal: IP00Other technical data (sheet catalogue)Temperature dependency, DeratingCircuit-breakers Rated current = rated uninterrupted currentIn = IuA160Rated surge voltage invariabilityUimpMain contactsV8000Auxiliary contactsV6000Rated operational voltageUeV AC690Overvoltage category/pollution degreeIII/3Rated insulation voltageUiV1000