Title: +038=249.001-#####._01-10203518-01-RIA-NOT-007 Lydmålinger Collier_rev01.pdf
Dronning Maugs gt. 1- 3 Lydisolasjon fra korridor til møterom 5- 116Date of test:09.02.2022Object:Møterom med dør (glass og gipsvegg).Source room: korridorReceiving room: 5- 115Condition:Condition:Type:Type:Location:Location:Frequency range according to theArea of common partition:17,63m²curve of shifted reference values (ISO 717- 1)Source room volume:Receiving room volume:113m³→ ⎯ B d65FrequencyR',f1/3 octave'R[Hz]50≥[dB]22,9, x e d ni55638010012516020025024,423,323,023,424,327,531,7n o i t c u d e r d n u o s t n e r a p p A4531535,63540036,950038,463040,580042,0100041,325125041,1160041,8200044,0250046,615315048,2400047,9500048,0Limit of measurement56312525050010002000 Hz 4000Frequency, f, Hz ⎯→