Title: økernvn 94.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.1 18.1 46.2 36 14.7 18.1 43.8SR 12-36 8.2 49.8 34.0 36 10.3 18.4 43.7MAIN 36-78 24.5 248.0 4.9 36 24.5 248.0 2.2SR 12-36 14.5 250.0 4.7 36 14.5 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 6.2 247.0 10.1SR 12 5.7 41.0 17.9MAIN 36 6.2 248.5 10.0SR 45 8.6 206.0 10.906050050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4