Title: Simployer - Data testrapport =514.204-FS001.pdf
[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]38.6 199 15 7.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]24.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 9.3 240.5 33.4 3,6 10.9 83.0 38.5SR 3,6-4,5 10.9 115.5 38.9 3,6 11.2 105.0 36.7MAIN 1,2-3,6 9.3 240.5 33.4 3,6 10.9 240.5 30.4SR 1,2-3,6 11.5 218.0 34.1 3,6 12.2 218.0 31.2PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 16.1 190.5 17.7 4,5 17.5 190.5 14.7SR 7,8-4,5 16.2 183.5 18.0 4,5 17.9 203.5 14.1MAIN 7,8-4,5 16.6 208.0 16.9 4,5 17.6 204.0 14.1SR 7,8-4,5 16.8 208.0 16.9 4,5 17.9 203.5 14.1PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 12.9 2.9 61.0 3,6 13.3 2.9 58.0SR 1,2-3,6 12.4 2.9 61.0 3,6 13.2 2.8 58.0