Title: +038=433.002-FS034._06-Tavlebyggeren Eaton FDV.pdf
Electric engineering, automation, process control engineering / Electrical installation, device / Residual current protection system / MCB/RCCB combination (ecl@ss10.0.1-27-14-22-07 [AFZ810015])Number of poles (total)2Number of protected poles2Rated voltageV240Rated insulation voltage UiV250Rated impulse withstand voltage UimpkV4Rated currentA20Rated fault currentA0.03Leakage current typeFCurrent limiting class3Rated short-circuit breaking capacity acc. EN 61009kA10Rated short-circuit breaking capacity IEC 60947-2kA0Rated short-circuit breaking capacity Icn acc. EN 61009-1kA10Disconnection characteristicShort-time delayedSurge current capacitykA3Voltage typeACFrequency50 HzRelease characteristicCConcurrently switching N-neutralNoWith interlocking deviceNoOver voltage category3Pollution degree2Ambient temperature during operating°C25 - 40Width in number of modular spacings2Built-in depthmm70