Title: 40 Bender brukermanual.pdf.pdf
Measurement technique: Device not calibrated.12Measurement technique: Wrong measurement p.c.b., incor- rect mounting.13Measurement technique: Hardware error after performing a self test.71BMS interface: No master available resp. has not been que- ried by a master for five minutes.72BMS interface: Fault RS-485 interface.712Measurement technique: Device error on all channels (12/12).Display in the event of a faultRCMS…-D…RCMS…-L…Device error: xxEr xx (alternately displayed)xx = Error code82RCMS460-490_D00067_03_M_XXEN/12.2017Tests, service, troubleshooting7.3.2 Device error display (channel-related) LED "ALARM 1“ lights up. The programmed common alarm relay switches. The following text appears on the display of the RCMS…-D:Fault 1/1 Device error11 Addr.: 2 Chan.: 4Line 1:Line 2:Fault, Alarm 1 of 1 pending alarm. Alarm status and alarm text. No alarm Prewarning Alarm, faultLine 3: Line 4: