Title: økernvn 94.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.5 32.8 39.4 36 16.3 32.8 37.0SR 12-36 13.5 36.8 38.0 36 13.0 32.5 37.1MAIN 36-78 26.8 242.0 5.5 78 26.0 242.5 2.8SR 36-45 19.2 248.0 4.9 36 19.0 247.5 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 1.7 22.6 19.2SR 36 2.7 22.6 19.2MAIN 45 6.7 249.5 10.0SR 36 6.7 240.0 10.2010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4