Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uci: 0.1V t: 31.7ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 27.11.2020 11:41KONTINUITET R: 0.3ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 27.11.2020 11:41R LOW OhmR: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 30.11.2020 11:58 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF087 16C2/003 27.11.2021 10:42ISOLASJON: ALLERln: >30.0MΩ Um: 1041V Rlpe: >30.0MΩ Um: 1061V Rnpe: >30.0MΩ Um: 1063VUiso: 1000V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF088 16C2/003 26.11.2020 14:32SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF088 16C2/003 27.11.2021 10:42Tallberg Elektro A/S Tlf.22796640Side:39GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*