Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
OBJEKT / Plan 10 / FUSE036 10.02.2020 09:16Zs(rcd)Z: 0.20ΩIsc: 1.16kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE036 10.02.2020 09:16RCD II: 28.5mAUci: 0.2V t: 32.4ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE036 10.02.2020 09:18RCD AUTOt : 67.9ms t : 71.6ms t : 29.1ms t : 29.5ms t : >300ms t : >300ms I I: 28.5mA : 28.5mAUc: 0.1V Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE036 10.02.2020 09:38KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE036 10.02.2020 09:39R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE036 10.02.2020 09:55TEST RAPPORTSide:9GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.575758585959606061616262ResultatR ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩOBJEKT / Plan 10 / FUSE037 06.02.2020 15:11RCD AUTO