Title: +135.01=544.001-XS001T_01-Pasientsignal operating_and_installation_instruction_2011.pdf
Devices for operation with text displays1.5 m to 1.8 m (such as terminals with display) The installation locations must be selected such that none of the components are exposed to direct sunlight.Devices in installation units1.6 m to 1.8 m (such as medical care units)Signal lamps and large text displays 1.5 m to 2.2 mSignal lamps and large text displays 1.5 m to 2.2 mControl units, energy supply devicesCentral control devices, energy supply devices and other parts without operating or signalling functions may only be installed in dry rooms (max. humidity 75% at approx. 18 °C), however not in patient rooms. They must be easily accessible at all times (inspection access with width of at least 60 cm). Heat dissipation must not be obstructed. For installation in switch cabinets or the like, it may be necessary to employ forced ventilation to dissipate the waste heat.