Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 17.0 5.0 51.3 45 17.8 37.0 30.9MAIN 78-45 19.0 500.0 11.3 45 20.5 500.0 8.3SR 78-45 19.0 500.0 11.3 45 20.0 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 30.6 146.5 17.6 78 31.5 140.5 15.8SR 12-36 28.3 136.0 19.0 36 28.4 136.0 16.4MAIN 36-45 40.1 500.0 -12.4 36 39.5 499.0 -15.2SR 36-45 38.3 494.0 -12.0 45 38.5 486.0 -14.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.5 485.0 8.0SR 12 5.0 485.0 8.0MAIN 45 7.5 485.0 8.0SR 12 5.0 485.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS