Title: +135.01=370.001-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Modbus module WZU-485E-MODCommunication protocol ModBus® address range Transmission rateMax. 10 Hz YesYes No 0.01 to 10,000,00 liters per pulse In increments of 0,01 liter per pulse In m3, 7 digits, without or with 1 decimal place, depending on parameter setting Approx. 3.3 V Approx. 1 MΩ Approx. 3 μA<0.2 V <50 kΩCollector not fully activated ≥6 MΩ 10 mBACnet MS/TP (RS-485) per ASHRAE 135 and ISO 16484-5 BACnet Application Specific Controller (B-ASC), BACnet Master Mode 1 … 127 9600 to 76800 bps Default: 38400 bps Standby: 60 min. Operating: After each query, max. every 10 seconds Protected against short overload User external resistance (=> 120 Ω) AC 16 … 28 V DC 10 … 32 V < 50 mA (typically < 20 mA at 24 V) 100 mA, slowYes NoModbus RTU5 0 … 247 2400 to 19200 bps Default: 9600 bps41 CE2N5324en 2018-08-1842 Building TechnologiesModbus module WZU-485E-MOD Modbus parity Data update