Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
MAIN 45-78 20.5 73.8 28.9 45 20.1 57.8 30.0SR 36-78 21.9 95.8 24.9 45 21.4 57.8 30.0MAIN 12-36 36.7 497.0 -12.2 36 35.9 496.0 -15.0SR 36-78 36.2 500.0 -12.4 36 35.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 9.0 492.0 8.0SR 45 6.1 492.0 8.0MAIN 45 9.0 492.0 8.0SR 45 6.1 492.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: MCKINSEY 4 ETGMcKinsey 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00428.3 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500