Title: Sidewall (1).pdf
The sprinklers are to be installed with an end-of-deflector-boss to wall distance of 1-1/4 to 6 inches.In addition the top-of-deflector-to- ceiling distance is to be within the range (Tables A and B) being hydraulically calculated.Sprinkler SpacingThe minimum spacing between sprin- klers is 8 feet (2,4 m). The maximum spacing between sprinklers cannot exceed the width of the coverage area (Tables A and B) being hydraulically calculated (e.g., maximum 12 feet for a 12 ft. x 12 ft. coverage area, or 16 feet for a 16 ft. x 20 ft. coverage area. ).TFP410Page 4 of 6WET PIPE SYSTEMMax. Coverage Max. Minimum Flow and Residual Pressure(® ©)Area (@ sP;fi"Q Ordinary Temp. Rating |Intermediate Temp. Rating Minimum Width x Length () ¢ 155°F (68°C) 175°F (79°C) Deflector to | Installation | SpacingFt. x Ft. (m) Flow Pressure Ceiling (mx m) GPM PsI L/min] bar] 8.2 (0,57)14 x 14(4,3x4,36inches16 x 18 1 19 19 (4,9 x 5,5) 4,9) (71,9) (1,41) (71,9)