Title: 32 Pumper modbuss teknisk data.pdf.pdf
To configure CIM 260 for a data connection, follow the instructions in the "CIM 260 SMS commands installation and operating instructions", which you can download from Grundfos Product Center.8To verify the APN settings after completion, use the SMS command "APNSETTINGS". To verify that the data connection is working, use the SMS command "APNSTATUS". The connection state must be "Context active" if ready and "Connected" if a Modbus TCP master is already communicating.CIM 260 is now ready to be accessed from a Modbus TCP master via a data connection, or via SMS commands.31)B G(h si lg n EE n gl is h(G B)11.4 Hardware setup, CIU 260 data connectionStepAction1Connect the GENIbus cable from CIU 260 to the Grundfos product. See the CIU quick guide instruction.2Fit an antenna to the CIM module SMA connector. See section 6.1.1 Fitting a cellular antenna.3Insert the SIM card in CIM 260. See section 6.1.2 Inserting the SIM card.4