Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
29.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.2 461.0 29.7 36 6.8 452.0 27.3SR 12-36 6.6 447.0 30.3 36 6.3 457.0 27.1MAIN 36-78 8.6 497.0 28.0 36 8.0 497.0 25.1SR 12-36 7.6 497.0 28.0 36 7.0 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.8 500.0 11.3 45 20.6 500.0 8.3SR 78-45 18.5 500.0 11.3 45 19.6 500.0 8.3MAIN 45-78 18.8 500.0 11.3 45 20.6 500.0 8.3SR 78-45 18.5 500.0 11.3 45 19.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.4 66.5 30.5 36 24.1 66.5 28.0SR 36-45 25.1 66.8 30.4 36 26.2 67.0 27.8MAIN 36-78 37.0 497.0 -12.2 36 36.3 497.0 -15.1SR 36-45 35.7 497.0 -12.2 36 35.3 497.0 -15.10804000250 MHzACR-N (dB)