Title: +038=442.002-UP022T_03-UP22  TALEXXdriver_LCA_100W_24V_one4all Tridonic Produktblad.pdf
801001204.6 Maximum loading of automatic circuit breakersAutomatic circuit breaker typeC10C13C16C20B10B13B16B20Inrush currentInstallation ØLCA 100W 24V one4all SC PRE1.5 mm2121.5 mm2162.5 mm2182.5 mm2261.5 mm261.5 mm282.5 mm292.5 mm213Imax 43 Atime280 µsTypical values for MCB from ABB series S200 as reference. Actual values can differ due to used MCB types and installation environment.4.7 Harmonic distortion in the mains supply (at 230 V / 50 Hz and full load) in %LCA 100W 24V one4all SC PRETHD 53. 55. 27. 19. 111. 14.8 Dimming5. Interfaces / communicationDimming range 1 % to 100 % Digital control with: • DSI signal: 8 bit Manchester CodeSpeed 1 % to 100 % in 1.4 s5.1 Control input (DA/N, DA/L)Digital DALI signal or switchDIM can be wired on the same terminals (DA/N and DA/L).