Title: +038=310.101-RF022T_06-multical 62 Vannmåler Kamstrup - Installasjons- og brukerveiledning.pdf
The module itself is fitted with a line of light emitting diodes indicating signal strength which are very useful during installation. Furthermore, it is indicated whether the module is connected to a 2G or a 3G network.Regarding mounting we refer to installation instructions (DK: 5512-1121, GB: 5512-1122, DE: 5512-1123, FI: 5512-1124, SE: 5512-1125).) RTU : Remote Terminal Unit.10Kamstrup A/S • 55121068_B3_GB_03.2015MULTICAL® 62 • Water meter5.1.15 Ethernet/IP module (IP201), type 602-00-82The IP module functions as transparent communication between reading software and MULTICAL® 62 and is used for data reading. The Module supports both dynamic and static address- ing. This is specified in the order or selected during subsequent configuration. The module has no built-in security and must, therefore, always be used in connection with a firewall or NAT. The Ethernet/IP module must be used together with high-power mains supply (230 VAC: 602-00-00-3 and 24 VAC: 602-00-00-4).