Title: Aggregatkjøring.pdf.pdf
Fin spacing2.5mmNo. of rows2Coil codeGXH-22-W-4-2-11-995-2015-2.5-CU-Al-*-1 1/4Tap for frost guard1pcsThe extract unit consist ofFilterDimensioning pressure drop101PaInitial pressure drop/Final pressure drop51/151PaVelocity, face area1.98m/sVelocity, filter area0.12m/sFilter classF7 - ePM1 60%Filter size6x[592x490x25] + 2x[287x490x25]Filter length520mmFilter descriptionCamfil Hi-Flo II XLTRotary heat exchangerData are stated on supply.Systemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.002-3/Unit no. 20Date 18.06.2021Page 32/40Twin fan, PlugAir flow14713m³/hExternal pressure250PaPressure drop21Pa