Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.04.05-UF056 Date / Time: 27-11-2022 13:53:04 Headroom 2.5 dB (NEXT 36-78) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]11.0 47 0 1.97Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 78] [Pair 78] [Pair 78]35.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 3.6 448.0 30.3 36 4.7 472.0 26.3SR 36-78 2.5 447.0 30.3 36 4.4 450.0 27.4MAIN 36-78 3.8 470.0 29.3 36 5.0 483.0 25.8SR 36-78 3.8 491.0 28.3 36 5.4 494.0 25.310080604020NEXT (dB)