Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
[Pair 78] [Pair 78] [Pair 78]25.2 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.3 499.0 29.3 36 9.3 477.0 26.8SR 12-36 6.9 499.0 29.3 36 7.0 500.0 26.4MAIN 12-36 10.3 499.0 29.3 36 9.5 491.0 26.6SR 12-36 6.9 499.0 29.3 36 7.0 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.0 8.0 47.2 45 19.9 498.0 8.3SR 45-78 19.1 8.4 46.8 45 20.8 500.0 8.3MAIN 36-45 20.8 498.0 11.3 45 19.9 498.0 8.3SR 45-36 21.2 498.0 11.3 45 20.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 21.6 51.5 34.0 36 22.0 40.5 34.7SR 36-45 18.1 39.8 37.4 45 19.0 40.0 34.8MAIN 12-36 36.0 499.0 -12.3 36 35.0 491.0 -14.7SR 12-36 32.6 499.0 -12.3 36 32.8 500.0 -15.30804000250 MHz