Title: Swegon Ventiler_baffler-Injusteringsguide.pdf
PARAGON / PARAGON WALLStorlek (mm) Dystryck (Pa)90050 - 200 PaLuftﬂöde (l/s)10,6 - 21,2Kpl 1,5090050 - 200 Pa12,0 - 24,01,7090050 - 200 Pa13,4 - 26,71,8990050 - 200 Pa16,8 - 33,52,3790050 - 200 Pa18,2 - 36,32,5790050 - 200 Pa22,9 - 45,83,24110050 - 200 Pa13,7 - 27,41,94110050 - 200 Pa15,5 - 31,02,19110050 - 200 Pa17,3 - 34,52,44110050 - 200 Pa21,7 - 43,43,07110050 - 200 Pa23,5 - 47,03,32110050 - 200 Pa29,6 - 59,34,19130050 - 200 Pa16,4 - 32,82,32130050 - 200 Pa18,5 - 37,12,62130050 - 200 Pa20,6 - 41,32,92130050 - 200 Pa25,9 - 51,83,66130050 - 200 Pa28,0 - 56,03,96130050 - 200 Pa35,4 - 70,75,00150050 - 200 Pa13,9 - 27,91,97150050 - 200 Pa18,8 - 37,62,66150050 - 200 Pa23,7 - 47,43,35150050 - 200 Pa25,1 - 50,23,55150050 - 200 Pa30,0 - 60,04,24150050 - 200 Pa36,2 - 72,45,12Injusteringsguide 2014:12Dysinställning