Title: økernvn 94.pdf
50100150200250MHzLinkWare Version 7.4Cable ID: T3422 Date / Time: 09/13/2013 08:48:52 Headroom 3.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]137 210 8 6.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.3 239.0 35.7 12 7.8 240.5 33.0SR 12-36 3.9 177.0 37.8 12 5.5 243.0 32.9MAIN 12-36 8.3 239.0 35.7 12 7.8 240.5 33.0SR 12-36 3.9 243.0 35.5 12 5.5 243.0 32.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)