Title: +038=365.009-SS002._02-mcr WIPT Stengespjeld Mercor - DOP.pdf
8. Declared performance: Essential characteristics EN 15650:2010 Performance Result WIP/S WIPT Nominal activation 4212 Pass conditions/sensitivity 42122 According to 1ISO 10294-4:2001, section 4.2 Pass 4.2.1.2.3 According to 1ISO 10294-4:2001, section 4.2 Pass Response time/Closure time 4.2.1.3 < 2 minutes Pass Operational reliability/Cycling 4.3.1. a) C50 Pass Fire resistance - integrity 4.1.1a) E120/E60 E120 Pass Fire resistance — insulation 4.1.1b) 160 1120 Pass Fire resistance - smoke leakage 4.1.1¢) S120/S60 - Pass Durability of operational reliability 4.3.3.2 C10,000 Pass Fire resistance classification 4.3.2 EI 60 (v.i < 0) S EI 120 (vei = 0) I Pass Fire resistance classification 4.3.2 E120 (vei©0) S E 120 (Vei <> 0) I* Pass Size range rectangular damper or rectangular damper with round adapters of the following dimensions: width: from 120 to 1,000 [mm], height: from 160 to 1,000 [mm] Installation rigid walls/shafts made of concrete blocks, hollow masonry units, masonry walls/ shafts — min. thickness