Title: 1 Pos. HFPD 4000x1500x480 (1).PDF
All dimensions are in millimetres - Recommended hood hanging height 2000- 2100 mm from finished floor - Verify building entry conditions and limitations for access upon approval - Nuventas will not accept claims for problems that result from sub-standard installation - Airflow rate calculations are based on EN 16282 detailed calculations method and are provided as an accurate reference. The contractor is responsible for balancing and fine-adjusting the airflow rates on-site Exhaust Hood Details: 4000x1500x480 2 Cyclonic 8 N/A Exhaust No Grease box LED IP65, min. 500lx None 4x 315 4x 250 4x 125Hood Size (LxWxH) No. of Hood Sections Filter Type Filter Quantity Approx. Hood Weight Dampers Integrated Air Jet Fan Grease Drain Type Lighting Type Lighting Details UV-C System Exhaust Collars Supply Collars Air Jet CollarsAirflow Rate Calculations: