Title: +038=370.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Merknader for prosjektering.pdf
The dimensions of the actuator combination used depend on the design and nominal diameter used. The dimensions can be found in the associated data sheets.Pipeline clearancesThe minimum clearances between the pipelines and the walls and ceilings required for project planning depend not only on the valve dimensions but also on the design. The dimensions can be found in the associated data sheets.2-way version2-way Belimo Energy Valves™ are throttling devices. The installation in the return flow is recommended. This leads to lower thermal loads on the sealing ele- ments of the valve.Flow directionObserve the specified direction of flow.Water qualityAdhere to the water quality requirements specified in VDI 2035.StrainerThe Belimo Energy Valve™ is a regulating device. Central strainers are recom- mended to ensure the control task in the long term.Design water systemApplication is permitted only in closed water circuits.Open/close valves