Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
To plug in or remove the Profibus connector, remove the module. A second Profibus cable to extend the network cannot be plugged directly into the first Profibus connec- tor. There are no problems with the RS-232 cable and the supply connector, which can be plugged in with the module in place.If a Profibus connector with height > 40 mm is used, the module cannot be plugged in to Slot 0 , e.g. with:WAGO 750-970 (height=42mm, contacts the I/O connector)If a PCD3.K106/116 cable is used to connect to the next module holder, do not plug module into Slot 3 (far right).Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs.PCD3.K106/116 cable, hardware version B, with 90° angled connector6-52Digital combined input/output modules6.7Digital combined input/output modulesPCD3.B1002 inputs, 2 outputs, 4 selectable as inputs or outputsDefinition of input signalsfor 24 VDC PCD3.B100; I0 and I1for 24 VDC PCD3.B100; I2 to I532 VDC 24 VDC