Title: Hardware Installation Guide.pdf
Addresses assigned to input/output panels do not need to be consecutive. On the first panel, the inputs/ outputs represent the first sixteen floors (e.g.: Input 1 = first floor, Input 2 = second floor, etc.). The second panel represents the next sixteen floors (floor 17 through 32), etc.Overview of Elevator ControlAccess Control SystemIntelligent System ControllerMaximum: 4000 feet (1219.2 meters) 5 conductorsOutput Control ModuleInput Control ModuleSingle Reader InterfaceSingle Reader Interface ModuleSingle Reader InterfaceUp to 128 Outputs - eight Output Control ModulesUp to 128 Inputs - eight Input Control ModulesElevator Control RoomElevator Reader (inside cab)380 — revision 6Hardware Installation Guide77.7External (Cabinet) TamperAn external cabinet tamper (EXTMP) is configured by connecting a tamper device across pins 3 & 4 of J18 on the SDC. If not used, a jumper must be installed across pins 3 & 4 of J18.Note: