Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
release: conductor 0.6m, 2x0.5mm2 -limit switch: conductor 0.6m, 6x0.5mm2 92° Max 2s – spring Left 1.4kgrelease: conductor 0.6m, 2x0.5mm2 -limit switch: conductor 0.6m, 6x0.5mm2 92° Max 2s – spring Left 1.4kg1.5kgKW1/230P…. 230V AC 2.5W 12daN1.5kgSupply of mechanism KW1: Wire number: 1-2Limit switch WK1d Wire number: 3-4 – NO type (normally open) Wire number: 4-5 – NC type (normally closed)Limit switch WK2d Wire number: 6-7 – NO type (normally open) Wire number: 7-8 – NC type (normally closed)Note: Position of limit switches of the mechanism has been specified for the safety position of the fire damper.In the case of the fire damper released using the mechanism KW1 and equipped with the actuator for setting the fire damper in the waiting position, besides the 8-wire conductor of the mechanism KW1 described above, available are two supply wires of the actuator MERCOR KW (BL24-48 KW).Technical data SupplyBL 24-48 KW AC 24V…48V 50/60Hz DC 24V…48VBL 110-230 KW AC 230V 50/60Hz