Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
[Pair 45] [Pair 45] [Pair 45]32.8 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.5 451.0 30.2 36 6.9 467.0 26.6SR 36-45 5.8 474.0 29.1 36 6.6 467.0 26.6MAIN 36-45 8.2 499.0 27.9 36 7.4 499.0 25.0SR 36-45 6.5 499.0 27.9 36 7.2 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.8 9.6 45.6 45 21.6 8.5 43.6SR 45-78 19.8 9.8 45.5 45 21.2 500.0 8.3MAIN 36-12 20.4 434.0 12.5 45 21.7 500.0 8.3SR 12-36 20.3 434.0 12.5 45 21.2 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 31.8 146.0 17.7 12 32.4 145.5 15.2SR 12-36 31.0 146.0 17.7 36 32.6 146.0 15.1MAIN 36-45 39.8 499.0 -12.3 36 39.0 499.0 -15.2SR 36-45 38.1 499.0 -12.3 36 38.8 499.0 -15.20804000250 MHz