Title: 2 etg del2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]236 376 28 10.1236 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.8 * 246.0 35.5 36 0.5 * 247.5 32.8SR 36-450.5 *249.5 35.4 36 1.0 *250.0 32.7MAIN 36-45 0.8 247.5 35.4 36 0.5 247.5 32.8SR 36-45 0.5 249.5 35.4 36 1.0 250.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.0 200.0 18.2 36 18.4 200.0 15.2SR 36-45 16.5 199.5 18.2 45 17.5 223.0 14.2MAIN 45-36 16.3 243.5 16.5 36 18.5 248.5 13.3SR 36-45 16.8 243.5 16.5 45 18.3 248.5 13.3010080604020050100150MHzACR-F (dB)2002500100