Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
see module overview 500 V, electrical isolation of outputs to Saia PCD®, channels themselves not separated 10 bits (0…1023) W605: W615: W625: W605: W615: W625: ± 0.25%, 100 ppm/K or 0.01%/K yes (permanent) acc. to standards ENV 50 141, EN 55 022, EN 61000-4-2, EN 61000-4-4, EN 61000-4-5 typ. 1 ms W605: typ. 0.3 ms W615: typ. 1 ms W615: 110 mA (typ. 80 mA) W605: 55 mA (typ. 45 mA) W615: W625: 110 mA (typ. 80 mA) 0 mA>3 kΩ <500 Ω* >3 kΩ ± 0.4% ± 0.7% ± 0.4%Internal current consumption: (from V+ bus) External current consumption:max. 90 mA, smoothed (W615 only) Voltage range: RL•20 mA+ 10…20 V *e.g. RL=500 Ω → Ue = 20…30 VRL=0 Ω → Ue=10…20 VTerminals:Pluggable 14-pole spring terminal block (4 405 4998 0), for Ø up to 1.5 mm²,6-88PCD3.W6x5ConnectionsTerminal 0TerminalsW6 0 50 1 2 3 4 5 6 7 8 9 10 11 12 13A0 – A1 – A2 – A3 – A4 – A5 –V 0 1 . . 5 . 0 0 6 s W t u . p 3 t D u o C P 6Ad e t a r a p e S c n a vila G0123456Description- labelW6 1 5