Title: Igangkjøringsprotokoller på sirkulasjonspumper V.2017.07.17.pdf
ENGINEERING SOLUTIONSPRESTARTup checklistCIRCULATION PUMPSCommissioning report No. _0)0y Date: /& /OZ /7 Service partner:| Dataaboutinstallation SRl Name of instalation: Nitedal DoliAddress: Vargveien 1, 1488 Hakadal,Operational Manager: Audrius DaniulisPhone/e-mail: +370 676 19634 / audrius.daniulis@ensoprojects.com Required flow (designed): 34 m*hRequired head (designed): 12mWater temperature: 60 °C Fluid: Water Operation mode: Open loop / delta TDo SR. '-Pump name/Wpe S IL 50/120Product No. : 2120875Marking in the system: 320.010-JP404Nom. flow: Nom. Pressure: 11.2mMax. Liquid temp. : -25..140 °C Head max: 14.8mTETTor o DR Al s o SR S e P RCheck expanSIon joints installed: okCheck vibration damper installed: okCheck air locks are avoided (suction side): okCheck for pipes adequate support: okCheck mechanical seal for leaks: ok { Pump start :frrx ; R : :Real setpoint (head pressure): 7.0mFlow at preseted setpoint (all valves opened): 12.5m3/h