Title: +038=370.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Merknader for prosjektering.pdf
The power output at the heat exchanger is influenced not only by the flow vol- ume but also by the water temperature. A changed supply temperature, for example, can adversely affect the power output and thus comfort. In the power control function, the Energy Valve automatically compensates for the influence of the differential pressure in addition to the influence of the temperature. Due to the pressure and temperature-independent operating mode, optimum comfort is always ensured.[kW]20Heating or cooling performanceExample: power control with set Q'max = 20 kW The positioning signal directly requires a power output at the heat exchanger.12.50Y [V]Actuation signal27108Notes for project planning / Design and dimensioningValve design