Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
CAN terminal and termination jumper option for outgoing connection to following rack2CAN terminal incoming connection from CAN gateway or preceding rack to cluster5Top string DC terminal connection to DC tie cabinet3PE terminal connection to battery rack frame© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL19 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guideFigure 8 shows an example of several racks in a rack cluster, which means that they are part of the same CAN bus.Figure 8. CAN bus connection of several connection units1CAN cable coming from DC cabinet2Termination to the last rack of the clusterFigure 9. Connection unit and battery cable connections12 3 4 5PE terminal connection to battery rack frame DC+ top string connection DC+ bottom string connection DC- top string connection DC- bottom string connection67 8 9CAN out top string connection