Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 36]36.2 158 3 5.31Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.2 477.0 29.7 36 7.9 477.0 26.8SR 36-45 9.3 496.0 29.3 36 9.0 496.0 26.5MAIN 36-45 8.2 477.0 29.7 36 7.9 477.0 26.8SR 36-45 9.3 496.0 29.3 36 9.0 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.1 464.0 11.9 45 14.5 4.9 48.5SR 78-45 14.9 466.0 11.9 45 14.5 17.5 37.4MAIN 78-45 15.5 500.0 11.3 45 15.8 500.0 8.3SR 78-45 15.3 490.0 11.4 45 15.6 500.0 8.30100806040200250 MHzACR-F (dB)