Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD06 Date / Time: 05/19/2022 11:04:37 AM Headroom 8.2 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 12] [Pair 36] [Pair 36] [Pair 36]23.1 107 3 3.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.2 448.0 30.3 36 10.0 448.0 27.5SR 36-45 9.5 483.0 29.6 36 10.2 468.0 27.0MAIN 12-36 8.2 448.0 30.3 36 10.0 448.0 27.5SR 36-45 9.6 496.0 29.3 36 10.3 497.0 26.41008060