Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
For transformers installed in an enclosure, make a cut-out on the top plate of the enclosure for the installation of a KTB••••CR• protective cover.5If the installation is flatwise, attach the KTB••••YE• angle brackets on the end feed unit.6Check that the distance from the conductors of the end feed units to the transformer bars is correct.40QGH3492101-01 11/2018Transformer ConnectionsStepAction7Determine the number of flexible links according to the rating (seepage41).8Attach the flexible links to the end feed unit and tighten the bolts to a torque of 60 N•m.9Attach the flexible links to the transformer with bolts and tighten the bolts to the torque recommended for the bolts used.10Check for correct clearances between the flexible links and between the bar clamps and the base of the transformer bar.11If the transformer is installed in an enclosure, install the KTB••••CR• protective cover in the cut-out made on the top plate of the enclosure.