Title: økernvn 94.pdf
SR 12-36 19.5 96.8 23.9 36 19.3 71.8 26.2MAIN 36-45 23.6 247.0 5.0 36 23.6 247.5 2.3SR 36-45 27.6 250.0 4.7 36 27.3 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.9 94.3 14.3SR 78 5.6 77.0 15.1MAIN 36 6.6 249.5 10.0SR 36 6.9 250.0 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94