Title: +038=320.001-LV007._02-BD Oslo 92kW tappevann.docx
___________________________________________________________________________________ PerformanceNoteBrazed Plate Heat ExchangerTechnical SpecificationModel: CB60-100H ItemId: 32870 7964 8Projekt: BD osloUnits: 1ItemName: TappevannDate: 20.02.2019Hot sideCold sideS4S3S2S1FluidWaterWaterDensitykg/m³992.7994.4Specific heat capacitykJ/(kg*K)4.184.18Thermal conductivityW/(m*K)0.6240.617Viscosity inletcP0.6541.31Viscosity outletcP0.9600.680Mass flow ratekg/s1.2220.7845Inlet temperature°C40.010.0Outlet temperature°C20.038.0TryckfallkPa9.162.92Heat exchangedkW92.00L.M.T.D.K5.6O.H.T.C clean conditionsW/(m²*K)2881O.H.T.C serviceW/(m²*K)2911Heat transfer aream²5.68Fouling resistance*10000  m²*K/W 0.000Duty margin%-1.00Relative direction of the fluidsCountercurrentNumber of passes11Materialplate/ brazingAlloy 316 / CuConnectionS1 (Cold-Ut)Threaded (External)/ 1 1/4" ISO 228/1-G (V24) Alloy 316