Title: Operating instructions - K3G560PC0401.pdf
Function/assignment Supply connection, power supply, phase, see nameplate for voltage range Supply connection, power supply, phase, see nameplate for voltage range Supply connection, power supply, phase, see nameplate for voltage range Ground connection, PE connection Status relay, floating status contact, make for failure Status relay, floating status contact, changeover contact, common connection, contact rating, max. 250 VAC/2 A (AC1)/min. 10 mA Status relay, floating status contact, break for failure Bus connection RS485, RSA, MODBUS RTU; SELV Bus connection RS485, RSB, MODBUS RTU; SELV Reference ground for control interface, SELV Analog input 1, set value: 0-10 V, Ri = 100 kΩ, adjustable curve, only usable as alternative to input Ain1 I; SELV Fixed voltage output 10 VDC, +10 V ± 3%, max. 10 mA, short-circuit-proof, power supply for external devices (e.g. pot); SELVItem no. 54422-5-9970 · ENU · Change 242236 · Approved 2021-10-27 · Page 10 / 15