Title: +135.01=564.001-XS020T_01-Montasje 5202AB13_bma_d-e-blinds_Norsk.pdf
Because the electromechanical end position switch does not close at the same time the solar protection leaves the end posi- tion, it is necessary to block evaluation of the end position for this period. This “blocking period” can be configured via a pa- rameter. Typical values for the blocking period” are 0.5 to 1.0 seconds.Behavior at bus voltage failure / recovery In the event of bus voltage failure the current positions of solar protection and slats as well as the travel time configuration is permanently saved to be restored on bus voltage recovery. Ob- ject values are not saved. Status objects are not read after a bus reset. Actions configured for execution on bus voltage failure are only executed, if no alarm or blockage is active.