Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 12] [Pair 12] [Pair 12]35.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.4 295.0 34.2 45 9.0 286.0 31.7SR 36-45 8.0 463.0 29.6 36 8.3 472.0 26.3MAIN 36-78 9.5 491.0 28.3 36 10.3 492.0 25.4SR 36-45 8.3 472.0 29.2 36 8.8 491.0 25.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.1 3.9 53.5 45 14.7 4.4 49.4SR 78-45 16.0 3.9 53.5 45 14.6 3.8 50.8MAIN 45-36 17.2 477.0 11.7 45 18.0 457.0 9.0SR 36-45 17.2 477.0 11.7 45 18.1 467.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 35.1 286.0 3.6 45 35.6 286.0 1.0SR 36-45 34.8 277.0 4.4 45 35.2 286.0 1.0MAIN 36-78 44.1 491.0 -11.8 36 44.7 492.0 -14.7SR 36-78 43.9 491.0 -11.8 36 43.1 491.0 -14.70804000250 MHz