Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 36] [Pair 36] [Pair 45]45.1 196 3 6.59Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]21.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.1 493.0 29.4 36 8.3 493.0 26.5SR 12-45 10.0 458.0 30.1 36 11.2 491.0 26.6MAIN 36-45 8.1 493.0 29.4 36 8.3 493.0 26.5SR 12-45 10.0 458.0 30.1 36 11.3 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.2 393.0 13.3 45 14.4 354.0 11.3SR 78-45 14.1 397.0 13.3 45 14.2 397.0 10.3MAIN 45-36 15.6 500.0 11.3 45 15.8 483.0 8.6SR 36-45 15.4 500.0 11.3 45 15.9 500.0 8.30100806040200250 MHzACR-F (dB)