Title: DM1-3 plan 05 lysberegningsrapport.pdf
Laser Blade XS - Downlight HC 23.1WTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 450 kWh/aPΦ23.1 W1452 lmCheckLuminous efficacy62.9 lm/W106201104 DM1-3 McKinseyBuilding 1 · Storey 1 · TR 3 SummaryGround area: 10.76 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.850 m | Mounting height: 2.850 m107201104 DM1-3 McKinseyBuilding 1 · Storey 1 · TR 3 SummaryResultsSymbolCalculatedVisual task areasĒ Task Area851 lxg1 Task Area0.79Ē Surrounding area458 lxg1 Surrounding area0.41Ē Background areag1 Background areaConsumption valuesConsumption130 kWh/aLighting power densityRoom6.44 W/m²Utilisation profile: Offices, Conference and meeting roomsLuminaire listpcs.Manufacturer Article No.Article name3IGUZZINIQ509Laser Blade XS - Downlight HC 23.1WTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 400 kWh/a