Title: økernvn 94.pdf
SR 45-36 22.4 71.5 21.5 45 26.3 98.5 15.701008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 20.1 22.4 33.7 36 22.3 22.5 30.6SR 12-36 19.5 22.4 33.7 36 21.4 22.4 30.7MAIN 12-36 25.9 99.3 12.0 36 27.3 99.3 9.0SR 12-36 25.4 97.5 12.4 36 26.9 99.5 9.001008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.2 20.9 18.8SR 36 4.9 20.6 18.9MAIN 45 9.1 100.0 12.0SR 45 8.6 51.3 14.901008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 4.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002187 ft60Insertion Loss (dB)