Title: 1 etg del 2.pdf
Cable ID: D1050 Date / Time: 10/17/2013 12:04:55 PM Headroom 14.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]241 384 28 10.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 87.5 33.3 36 15.9 98.5 29.4SR 12-36 15.2 13.4 46.5 36 16.4 98.5 29.4MAIN 12-36 14.5 100.0 32.3 36 15.9 100.0 29.3SR 12-36 16.1 94.3 32.7 36 16.4 98.5 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.7 59.3 23.2 36 17.5 59.3 20.2