Title: DM1-3 plan 05 lysberegningsrapport.pdf
Target≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 350 kWh/aPΦ23.1 W1452 lmCheckLuminous efficacy62.9 lm/W110201104 DM1-3 McKinseyBuilding 1 · Storey 1 · Teeming area OV gt SummaryGround area: 268.47 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.850 m | Mounting height: 1.500 m - 2.850 m111201104 DM1-3 McKinseyBuilding 1 · Storey 1 · Teeming area OV gt SummaryResultsSymbolCalculatedWorkplaneĒ329 lxg10.043Visual task areasĒ Task Area505 lxg1 Task Area0.56Ē Surrounding area375 lxg1 Surrounding area0.40Ē Background area300 lxg1 Background area0.16Consumption valuesConsumption[2550 - 3800] kWh/aLighting power densityRoom7.35 W/m²Workplane7.35 W/m²2.24 W/m²/100 lxUtilisation profile: Places of public assembly - General areas, Entrance hallsLuminaire listpcs.Manufacturer Article No.Article name1BEGA45486.1