Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12 16,3 8,8 7,5 334,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,6 26,8 2,8 496,00Remote: 36-45 29,4 26,7 2,7 499,00Worst Value: Local: 36-45 29,6 26,8 2,8 496,00Remote: 36-45 29,4 26,7 2,7 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 68,8 57,3 11,5 2,20Remote: 12-36 23,4 11,6 11,8 426,00Worst Value: Local: 12-45 22,8 10,2 12,6 499,00Remote: 12-45 22,5 10,2 12,3 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,7 25,4 4,3 447,00Remote: 36 28,1 23,8 4,3 500,00Worst Value: Local: 36 28,1 23,9 4,2 496,00Remote: 36 28,1 23,8 4,3 500,00