Title: Sirkulasjonspumper.pdf
2.72 l/s 159.7 kPa 270 dm 145 mm BQQE ISO9906:2012 3B2 AStøpejern EN-GJL-250 ASTM class 35 Stainless steel EN 1.4301 AISI 304 A20 .. 50 °C 16 bar 16 bar / 120 °C DIN DN 40 PN 16 320 mm FT115 F Vann -25 .. 120 °C 20 °C 998.2 kg/m³ 1 mm²/s20 .. 50 °C 16 bar 16 bar / 120 °C DIN DN 40 PN 16 320 mm FT115 F Vann -25 .. 120 °C 20 °C 998.2 kg/m³ 1 mm²/s90SC IE5 1.5 kW 50 Hz 1 x 200-240 V 9.10-7.60 A 0.99 360-4000 omdr/min 87.4% 87.4 % 2 IP55 F ELEC 98362278HMI300 - grafisk FM300 - Avanceret Built-in0.70 67.1 kg 76.6 kg 0.23 m³ 99145774Utskrift fra Grundfos Product Center [2021.21.005]Firmanavn: Grundfos Laget av: Telefon:Aleksander StortjønnliDato:23.08.2021H [kPa]TPED 40-270/2, 1*230 V110 %Q = 2.72 l/s H = 159.7 kPa n = 87 % / 2569 rpm Pumpemedie = Vann Væsketemperatur under drift = 20 °C Massetetthet = 998.2 kg/m³300100 %25020015010050025 %Eta pumpe = 56.5 % Eta pumpe+motor+frekvensomf. = 49.3 %00,51,01,52,02,53,03,54,04,5Q [l/s]P [kW]2.0