Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
4.6.2 Mechanical features Table 16: Mechanical featuresModel rating (1.0 p.f.)xStorage Dimensions (width x depth x height) Weight Weight, ECM (power module) External battery cabinet dimensions (width x depth x height)50 kW100 kW560 x 914 x 1876 mm150 kW200 kW 760 x 914 x 1876 mm1 ECM: 288 kg 2 ECMs: 338 kg 3 ECMs: 438 kg 4 ECMs: 556 kg50 kgxStorage Cable entryBottom / RearTop / Bottom / RearxStorage Degree of protection xStorage colourIP 20Frame: Black; RAL 9005, Door: Grey; RAL 70124.6.3 Table 17: Environmental featuresEnvironmental featuresModel rating (1.0 p.f.)50 kW100 kW150 kW200 kWxStorage ambient temperature range during storage and transit xStorage ambient temperature range during op- eration Relative humidity range25°C to + 55°C without batteries, indoors in the protective package5°C to + 40°C without output power derating5 to 95%, no condensation allowed1000 m (3300 ft) above sea level at 40°CMaximum service altitude