Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
In the absence of other information from the customer the inputs will be configured as FF=24 and GG=24.Input A Terminal 65-66 Max. input f ≤1Hz 100 m³ h 50 m³ h 25 m³ h 10 m³ h 5 m³ h 2.5 m³ h 1 m³ hFF01 02 03 04 05 06 07Input B Terminal 67-68 Max. input f ≤1 Hz 100 m³ h 50 m³ h 25 m³ h 10 m³ h 5 m³ h 2.5 m³ h 1 m³ hGG01 02 03 04 05 06 07Precounter1 2 4 10 20 40 100Wh/imp- - - - - -l/imp100 50 25 10 5.0 2.5 1.0Measuring unit anddecimal pointvol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3)000000.0000000,0000000.0 000000.0 000000.0 000000.0 000000.024 25 26 2710 m³ h 5 m³ h 2.5 m³ h 1 m³ h24 25 26 2710 m³ h 5 m³ h 2.5 m³ h 1 m³ h1 2 4 10- - -10 5.0 2.51,0vol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3) vol A/vol b (m3)00000.00 00000.00 00000.0000000,00401,000 m³ h401,000 m³ h11000vol A/vol b (m3)0000000FFMax. Input f ≤3 HzGGMax. Input f ≤3 HzPrecounter