Title: 1 etg del 2.pdf
MAIN 12-36 7.9 25.3 42.5 12 9.8 25.3 40.1SR 12-36 7.7 25.3 42.5 36 9.7 25.3 40.1MAIN 36-45 18.1 249.0 4.8 36 17.7 249.0 2.1SR 36-45 17.5 249.0 4.8 36 17.3 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 5.2 16.5 19.9SR 36 2.8 16.6 19.9MAIN 36 9.1 245.5 10.1SR 36 7.4 217.0 10.660500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94