Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Total lamp luminous flux: 798190 Im, Total luminaire luminous flux: 624288 Im, Total Load: 7066.1 W, Luminous efficacy: 88.3 Im/WDIALuxPage 6Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10/ Hall / Room summaryHallReflection factors: Ceiling 70.0%, Walls 26.4%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Hall) Perpendicular illuminance (adaptive) [Ix] 200 (= 100) 80.5 339 0.40 0.24 Height: 0.000 m, Wall zone: 0.300 m # Luminaire ®(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 13 iGuzzini illuminazione - Q497 Laser Blade XS - Downlight HC 12.4W 739 124 59.6 Total via all luminaires 9607 161.2 59.6Lighting power density: 2.81 W/m? (Floor area of room 57.28 m? ), Lighting power density: 4.17 W/m? = 2.08 W/m2/100 Ix (Area of working plane 38.68 m?)Consumption: 180 kWh/a of maximum 2050 kWh/a