Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 499,00Remote: 36-45 29,8 26,7 3,1 500,00Worst Value: Local: 36-45 28,9 26,7 2,2 499,00Remote: 36-45 29,8 26,7 3,1 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 62,0 50,9 11,1 4,60Remote: 45-12 62,0 50,9 11,1 4,60Worst Value: Local: 36-12 22,3 10,2 12,1 499,00Remote: 12-36 21,8 10,2 11,6 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 24,0 3,6 493,00Remote: 45 28,9 23,8 5,1 500,00Worst Value: Local: 36 27,4 23,8 3,6 500,00Remote: 45 28,9 23,8 5,1 500,00PS-ACRF: Pass Worst Margin: Local: 12 68,1 56,3 11,8 1,75Worst Value: Local: 36 19,9 7,2 12,7 500,00