Title: E.433.SK.U11.pdf
BJORN JORGENSEN A/SRADGIVENDE INGENIBRFIRMA ELEKTRO Sofiesgate 60 0168 OSLO t1f 22853700o i;iW%%rmutzfordelwng 433.01 433U1-0E001 xao02 [<¥n 1 XS001 In=63A | Lateskillebryter max: 7.0kA # Felt for lys, side 2 |n=200A Ikmin: 2,3 kA | ® ° XQ003 | By ot In=125A | T INNSTILLW Felt for teknisk, side 3, & Mellomvern | | L | —Malersignal til 434-fordeling. M-BUS —_ p— —_ — —_ —_ —Utlest overspenningvern signal til SD 434-001 fordeling o ELiW%%rmx§ fordeling 433.U21 25.0119 Som bygget EA Rev.nr Dato Revisjonstekst Signatur Dato Tegn. Smestad skole 25.01.19 TS M8l Godkjen; U1 % % UNDERFORDELING Prosiet e ™) 1630 lav b HAIKO ELEKTRO 43301 Tegn.nr. Rev.nr. 400V TN-5 E433.SKUN| .KURS ENLINJESKJEMA KABELTYPE KABELNR. : ADRESSE MERKNADER2x10A/BXF100 —| Styrestrem210A/C ‘XF101 | I¢ 3G1,5mm2 - Lys taviekott 065E‘ 1 DALI-kabel KX 001 - System 564.002 - Linje 1 - Lepenummer 001-064g gw 2 DALI-kabel KX 002 4 System 564.002 - Linje 2 - Lepenummer 065-128p gm P Cat Se KX 003 < Komm. DALI-router<|— 20V