Title: +038=370.104-OE004T_01-Multical 801 Energimåler Kamstrup - Installasjons- og brukerguide.pdf
Kamstrup A/S • 5512603_C1_GB_03.2016MULTICAL® 801Insertion of modules8.16 Data modules are retrofitted by placing the module in the PCB holder in the left side of the meter and ”clicking” on the module.Module and meter are electrically connected using a 6-pole jumper.Kamstrup A/S • 5512603_C1_GB_03.201623MULTICAL® 8019Information codes ”INFO”MULTICAL® 801 constantly monitors a series of important functions. If a serious error occurs in the measuring system or in the installation, ”INFO” appears in the display and an info code can be read by activating the upper front plate button until the measuring unit shows ”INFO” in the display. The info code is only visible while the error exists.Info codeDescriptionResponse time0No irregularities1Supply voltage has been cut off8Temperature sensor T1 outside measuring range1…10 min.4Temperature sensor T2 outside measuring range1…10 min.32Temperature sensor T3 outside measuring range1…10 min.64