Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 12-45 7.9 471.0 29.8 36 8.9 491.0 26.6SR 36-78 7.6 485.0 29.5 36 7.9 485.0 26.7MAIN 12-45 7.9 471.0 29.8 36 8.9 491.0 26.6SR 36-78 7.6 485.0 29.5 36 8.2 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.6 466.0 11.9 45 13.8 2.6 53.9SR 78-45 14.5 430.0 12.6 45 13.8 2.6 53.9MAIN 45-78 15.1 490.0 11.4 78 15.8 499.0 8.3SR 78-45 14.9 491.0 11.4 45 15.7 491.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.8 45.5 35.6 45 19.7 45.8 33.1SR 36-45 19.5 45.5 35.6 45 19.0 45.8 33.1MAIN 12-45 35.8 497.0 -12.2 36 36.3 498.0 -15.1SR 36-78 34.5 485.0 -11.4 36 35.4 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.4 498.0 8.0SR 12 4.9 475.0 8.0MAIN 45 7.4 498.0 8.0SR 12 4.9 475.0 8.040010080250 MHzRL (dB)