Title: økernvn 94.pdf
150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz60RL @ Remote (dB)50403020100050100150200250MHzLinkWare Version 7.4Cable ID: D4139 Date / Time: 09/10/2013 02:55:52 Headroom 13.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]86 135 9 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.9 99.8 32.3 36 15.2 99.8 29.3SR 12-36 17.2 88.0 33.2 12 19.5 88.0 30.2