Title: V20-05-01 VVS-anlegg plan 5 - DM1.pdf
SQ001T Ø250 Q:770 m³/hSR001T Ø125 Q:100 m³/hJV001T Ø250 Q:770 m³/hSF015T 250x250 ved kjøkkendrift 0m3/h utenom kjøkkendrift 580m3/h500x200 UK=2650ø315 UK=2554SF011T-600x300ø630 OppLD022T Maks:90 m³/h Kjøling: 170 W 0.014 L/s Varme: 200 W 0.005 L/sKorridor 5-301+05 = 360.022 - OE 901500x350 UK=2520Innvendig lydisoleringLD022T Maks:90 m³/h Kjøling: 170 W 0.014 L/s Varme: 200 W 0.005 L/sWISE director (trådløs router)Snitt P5-BSnitt P5-C1150x2017 UK=236750x1750 UK=92 1000x1750 UK=92 ø500 UK=2425 Kondensavløp inntak til sluk 360.021 ø630 UK=1905 Kjølebatteri ø630 UK=1905 ø500 UK=1970 320.101: 28mm 320.101: 28mm MA 75mm Opp 310.001: MA 75mm Fra sluk i plan 6Opp Oppø500 UK=24251000x1750 UK=92 SZ001T Ø500 ø500 UK=174 SZ001T Ø500 ø500 UK=821 800x1050 UK=792 310.003: MA 110 370.102: 54 mm 370.102: 54 mm 320.101: 28 mm 320.101: 28 mm 310.302: Cu 18 310.201: Cu 22 310.101: Cu 28 310.001: MA 110 600x400 UK=2350 600x400 UK=2350 SZ02T 600 x400 SZ02T 600 x400 600x400 UK=2350