Title: Hardware Installation Guide.pdf
Inputs: - -Eight (8) unsupervised/supervised, standard EOL, 1k/1k ohm, 1% 1/4 watt Two (2) unsupervised, dedicated for cabinet tamper and UPS fault monitoringReader interface: -Reader power (jumper selectable): 12 VDC + 10% regulated, 125mA maximum each reader or 12 to 24 VDC ±10% (input voltage passed through) 125mA maximum each reader Reader LED output: TTL compatible, high > 3V, low < 0.5V, 5mA source/sink maximum Reader buzzer output: Open collector, 5 VDC open circuit maximum, 10mA sink maximum Reader data inputs: TTL compatible inputs or 2-wire RS-485- -Communication: RS-485 two-wire, 9600 to 115,200 bps- - -Cable requirements: - -