Title: 2 etg del2.pdf
SR 36-45 9.8 250.0 16.2 45 12.7 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.2 16.9 47.0 36 10.7 15.4 45.6SR 36-45 10.4 20.3 45.0 36 12.1 18.8 43.4MAIN 36-45 11.8 249.5 4.7 36 12.6 250.0 2.0SR 36-78 20.7 240.5 5.6 12 21.5 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.5 14.0 20.3SR 36 2.5 14.0 20.3MAIN 36 7.4 159.5 12.0SR 36 4.7 207.0 10.860500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030