Title: Data tester Smestad skole - Detaljert.pdf
Length (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 43,6 68,0 226,0 12,0 7,3Limit 100,0 - 555,0 50,0 25,0Margin 56,4 - 329,0 38,0 17,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 0,9 3,1 2,2 3,10Worst Value: Local: 45 18,6 43,5 24,9 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 24,8 16,1 8,7 62,25Remote: 12 17,6 11,6 6,0 173,00Worst Value: Local: 36 18,1 8,0 10,1 500,00Remote: 36 16,1 8,0 8,1 490,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-36 32,2 29,8 2,4 402,00Remote: 36-45 30,0 26,7 3,3 500,00Worst Value: Local: 36-45 29,3 26,7 2,6 500,00Remote: 36-45 30,0 26,7 3,3 500,00dB 0601200Local250500 MHzdB 0601200