Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
E616: 0.2 ms 1.0 msElectrical isolation voltage: Optocoupler isolation voltage:1000 VAC, 1 min. 2.5 kVElectrical isolation of outputs to the PCD. The channels are not isolated from each otherInternal current consumption: (from +5 V bus)1 … 24 mA typ. 12 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption: max. 40 mA (all inputs=1) at 24 VDC, (source operation),max. 18 mA (sink operation)Terminals:Pluggable 10-pole spring terminal block (4 405 4847 0), for wires up to 1.5 mm²Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-17Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.E61xLEDs and connection terminalsBus connectorBus interface and threshold switchInput circuitsElectrical isolation by OptocouplersLEDsScrew terminals9876543210LE7E6E5E4E3E2E1E06Inputs E0 to E7 Input load resistors User ground (-)