Title: Aggregatkjøring.pdf.pdf
SystemairModelGeniox 22TypologyNRVU;BVUDrive TypeEC BlueEC BlueVSD OkType of Heat Recovery System (HRS)Rotary heat exchangerThermal efficiency of HRS (dry condition)82%Non Residential unit - flow rate4.174.17m³/sEffective electric power input incl. clean filters and variable drive2.942.90kWSFP internal in W/(m³/s) 2018660344317W/(m³/s)Face velocity1.851.85m/sNominal external pressure250.00250.00PaInternal pressure drop of ventilation components215.88197.22PaOverall static pressure drop with clean filter465.88447.22PaOverall static efficiency of fans with clean filter62.8263.57%Maximum external leakage rate @ ± 400 PaLeakage class L2(R) according to EN 1886. Leakage rate is less than 1%.Maximum internal leakage rate (EATR, ?p = 250 Pa)Leakage rate is less than 3%.Energy class for filtersBBVisual filter warning descriptionControl displayInternet address with information about disassembly