Title: Aggregatkjøring.pdf.pdf
90/6140/100%Capacity256.03kWTemperature efficiency82.4%Dry efficiency according to EN 308 at 14400 m³/h82%Humidity efficiency86.8%Heat exchanger typeP - Condensation (Temperature)Temperature efficiencyHigh efficiencyDescriptionP135_340_1-2240*Rotor driveVariable speedElectrical data1x230V, 40W, 0.7AmpOACF1.02Purging sector1pcsTwin fan, PlugAir flow14400m³/hExternal pressure250PaPressure drop21PaStatic pressure (Designed at wet conditions)551PaTotal pressure568PaFan speed1486RPMMaximum fan speed1950RPMTotal efficiency by static pressure, incl. motor and speed control69.7%Total efficiency by total pressure, incl. motor and speed control71.9%K-factor (p=1.2 kg/m³)(2 x 280) 560Fan type - 2xLargeGR50I-ZID.GG.CRErP efficiency n(stat,A)75.2%ErP efficiency class N(actual)/ N(target)80.0 / 62ErP-conformityYesDirect driveMotorMotor typesEC motorMotor types-sizeZID.GG.CR