Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 21,7 10,2 11,5 498,00Remote: 12-36 21,2 11,6 9,6 426,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,8 3,8 499,00Remote: 36 30,7 25,3 5,4 451,00Worst Value: Local: 36 27,6 23,8 3,8 499,00Remote: 36 29,4 23,8 5,6 500,00PS-ACRF: Pass Worst Margin: Local: 36 20,2 8,9 11,3 412,00Worst Value: Local: 36 20,2 8,9 11,3 412,00Remote: 12 71,9 61,2 10,7 1,00Remote: 36 20,4 8,7 11,7 421,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:00Signature:______________________ Page: 41Copper Certification ReportCable Label: 521.002-UD-139 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:51:52 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: