Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 45-36 15.5 3.8 53.8 45 14.3 2.9 53.1SR 36-45 15.5 4.3 52.7 45 14.4 3.5 51.4MAIN 36-45 17.0 470.0 11.8 45 19.4 470.0 8.8SR 45-36 17.1 471.0 11.8 45 19.5 470.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 30.4 168.5 15.0 12 30.7 169.0 12.3SR 36-45 30.5 158.0 16.2 36 32.2 160.5 13.3MAIN 36-45 42.1 500.0 -12.4 36 41.3 495.0 -14.9SR 36-78 42.5 480.0 -11.1 36 42.5 495.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.5 493.0 8.0SR 12 5.1 493.0 8.0MAIN 12 6.5 493.0 8.0SR 12 5.1 493.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS