Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
successive switch-on. delay between power-on. Delay between switch-ons; the indicated time must elapse between two successive switch-ons of the compressor. delay Output (from power) On. Delay time in activating the outputs after switch-on of the instrument or after a power failure. DEFROST defrost interval time. Interval between the start of two successive defrosting operations. defrost Counting type. Selection of count mode for the defrosting interval. 0 = compressor operating hours (DIGIFROST® method); Defrosting active only if compressor is on; 1 = Real Time - equipment operating hours; defrost counting is always active when the machine is on and start everytime the instrument switch on; 2 = compressor stop. Each time the compressor stops a defrosting cycle is performed according to parameter dtY. defrost Offset Hour. Start-of-defrosting delay time from the call. defrost Endurance time. Defrosting time-out; determines duration of defrosting. defrost (at) Power On. Determines if at the start-up the