Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
29.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.0 466.0 29.5 45 10.1 218.5 33.7SR 36-45 9.9 468.0 29.4 36 10.1 469.0 26.5MAIN 12-45 9.3 474.0 29.1 36 10.9 496.0 25.2SR 36-45 10.5 496.0 28.0 36 10.2 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.4 500.0 11.3 45 14.3 3.5 51.4SR 78-45 14.1 500.0 11.3 45 14.2 2.6 53.9MAIN 45-78 14.4 500.0 11.3 78 16.2 500.0 8.3SR 78-45 14.1 500.0 11.3 45 15.9 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.9 66.5 30.5 45 21.3 66.5 28.0SR 36-45 21.6 66.5 30.5 45 23.5 66.8 27.9MAIN 12-45 39.4 497.0 -12.2 36 39.5 496.0 -15.0SR 36-45 38.8 496.0 -12.1 36 38.8 496.0 -15.00804000250 MHzACR-N (dB)