Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
6-70Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W4x0I20.1 mA 20 mA 19.94 mATolerance +/- 0.5% typ.Tolerance +/- 0.8% max.0.06 mA 0 mADV60204075 4095TerminalsBus connectorSupply +/-15V and -5V (W610 only)Bus interfaceJumper ‘reset select’ (W610 only)Jumper ‘unipolar/bipolar’ (W610 only)midlowBUD/A converterOutput amplifierV CJumper ‘voltage/current’ (W610 only)Stromversorgung Uext (nur W610)Protection circuit9876A354A232A110A0Screw terminalsUext A3 A2 A1 A0Digital/analogue valuesClassic 4095 4075 2048 20 0Digital values xx7 4095 4075 2048 20 0Simatic 27648 27513 13824 135 0Output signals+20.1 mA +20 mA +10 mA 0 mA 0 mAHardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-71Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W4x0Changing the jumpers