Title: 1 etg del 2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]100 159 12 4.2100 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]21.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.7 * 246.0 35.5 36 0.5 * 236.0 33.1SR 36-450.1 *249.5 35.4 36 0.5 *249.0 32.7MAIN 36-45 0.7 246.0 35.5 36 0.5 246.0 32.8SR 36-45 0.1 249.5 35.4 36 0.5 249.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 20.2 6.6 47.8 45 21.1 249.0 13.3SR 12-45 20.3 6.6 47.8 36 21.3 172.5 16.5