Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.8 500.0 29.2 36 5.0 500.0 26.4SR 36-45 7.8 499.0 29.3 36 7.5 500.0 26.4MAIN 36-45 5.8 500.0 29.2 36 5.0 500.0 26.4SR 36-45 7.9 500.0 29.2 36 7.5 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.0 500.0 11.3 45 20.1 500.0 8.3SR 78-45 17.8 500.0 11.3 45 19.9 500.0 8.3MAIN 78-45 18.0 500.0 11.3 45 20.1 500.0 8.3SR 78-45 17.8 500.0 11.3 45 19.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 23.2 29.5 41.0 45 23.7 29.0 38.8SR 36-45 22.4 27.5 41.8 36 23.7 30.0 38.4MAIN 36-45 28.7 500.0 -12.4 36 28.3 500.0 -15.3SR 36-45 30.8 500.0 -12.4 36 30.8 500.0 -15.30804000250 MHzACR-N (dB)