Title: Sirkulasjonspumper.pdf
0.5 l/s 75 kPa 100 dm 110 CE,VDE,EAC,CN ROHS,WEEE DStainless steel EN 1.4308 ASTM 351 CF8 PES 30%GF0 .. 40 °C 10 bar G 1 1/2" PN 10 180 mmVann -10 .. 110 °C 20 °C 998.2 kg/m³ 1 mm²/s9 .. 153 W 50 / 60 Hz 1 x 230 V 0.09 .. 1.33 A X4D F0.18 5.12 kg 5.98 kg 0.015 m³ 380795100 5803237 4615645 9042356 DE 84137030Utskrift fra Grundfos Product Center [2021.21.005]Firmanavn: Grundfos Laget av: Telefon:Aleksander StortjønnliDato:23.08.2021H [kPa]MAGNA3 25-100 N110100Q = 0.4999 l/s H = 75 kPa n = 84 % / 3811 rpm Pumpemedie = Vann Væsketemperatur under drift = 20 °C Massetetthet = 998.2 kg/m³9080706050403020100Eta pumpe+motor+frekvensomf. = 41.2 %00,51,01,52,02,53,0Q [l/s]P1 [W]140120100806040200P1 (motor+frekv.omf) = 90.95 W1111.554239185901135 20 9 10 8 18 5 18 56971Example of plug-connected motor with mains switch, backup fuse and additional protectionLLRCD/RCCBNNt snp uiag i t