Title: +039=335.001-NT001._01-2016_001.pdf
If only one IS8 actuator is connected to ACTUATOR 1°, the ACTUATOR 2* must be connected with a resistor 6K8 ohm, because of the monitoring for Sigma XT. (If the resistor is not mounted, Sigma XT will show a fault). If the junction box is connected to a controt panel with duat actuator output (flg. 3), the two jumpersJ1/and J2 that are placed below the terminals from the control panel, must be cut.Fig. 4 Control panet with one activation and pressure switchDocument: 540351 ¢4 Junction box baskc Category: [ o] Electrical comp.Tel 457022 2769FIRE EATER www.fireeater.comDriftsog vedlikeholdsmanuaiFIRESAFE/Prosjekt: Mckinsey & Company INC NorwayProsjektnummer:223188Ansvarlig:Roy MortensenFIRESAFE/Type dokument:Driftsog vedlikeholdsmanualUtfgrt av:Roy MortensenDato:15.12.2021Engineering data sheetInstallation continuedBefore installation, the power must be off.