Title: Sprinklerhode våt.pdf
Step A. Install recessed pendent sprinklers in the pendent position with the deflector parallel to the ceiling.Step B. After installing the Style 20 Mounting Plate over the sprinkler threads and with pipe thread sealant applied to the pipe threads, hand- tighten the sprinkler into the sprinkler fitting.(Continued on Page 5)TFP400Page 4 of 6WET PIPE SYSTEM Minimum Flow and Residual Pressure(®. ¢Intermediate Temp. Rating175°F (79°C)Flow PressureMax.CoverageArea (@Ft. x Ft.(mxm)Ordinary Temp. Rating155°F (68°C)PressurePSI(bar)InstallationTypeDeflector toFlow CeilingGPM(L/min)SmoothCeilings11/4 to4lnches Recessedusing Style 20Boamed Escutcheon orCeilings perNFPA 13Dor 13Rnonrecessedper NFPA 13D,13R, or 1318x 18 il 12, 17 (5,5 x 5,5) (64,3 (0,83) (64,3) 20x 20 20 16.7 20 16.7 (6,1 x86,1) (75,7) (1,15) (75,7) (1,15) @)