Title: Sprinklerhode våt.pdf
A minimum discharge of 0.1 gpm/ft2 over the “design area” comprised of the four most hydraulically demanding sprinklers for actual coverage areas protected by the four sprinklers.The number of “design sprinklers” specified in NFPA 13 for wet pipe systems is to be applied when designing dry pipe systems.