Title: 40 Bender brukermanual.pdf.pdf
For digital inputs the current status (0/1) will be reversed. To prevent unwanted execution of this function, the entry must be confirmed once more.Settings menu 3: Channel6.6.6.3 You make the measuring channel settings in this menu (either individually or for all channels (1…12) simultaneously). Selecting a measuring channel:1. Use the "" button to go to the measuring channel setting. Press the "↵" button.1. Use the "" button to go to the measuring channel setting. Press the "↵" button.2. Use the Up/Down buttons to select a single measuring channel (e.g. 1) or all measuring channels (1…12). Press "↵" to confirm your selection.Setting an individual channel:Chan.: 1 Exit 1.Factor: *1 2.Resp. val.:100mASetting all channels:Chan.: 1..12 Exit 1.Factor: -- 2.Resp. val..:--RCMS460-490_D00067_03_M_XXEN/12.2017