Title: etg u1.pdf
Cable ID: D0010 Date / Time: 10/22/2013 12:09:17 PM Headroom 1.4 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]166 264 19 7.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.2 238.0 35.7 78 9.3 246.0 32.8SR 36-45 1.4 244.5 35.5 36 1.2 248.0 32.8MAIN 36-78 9.2 238.0 35.7 78 9.3 246.0 32.8SR 36-45 1.4 250.0 35.3 36 1.2 249.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 18.4 215.5 17.5 45 19.4 4.4 48.4