Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
IntroductionWhere Canalis KT system passes though a partition wall or a floor slab, it inherently acts as a fire barrier for up to 30 minutes. For greater protection levels of up to 120 minutes, a fire-barrier kit must be installed.CAUTIONHAZARD OF IRRITATIONWear suitable personal protective equipment, including gloves, goggles, and a protective mask while installing the fire-barrier kit.Failure to follow these instructions can result in injury or equipment damage.ProcedureThe procedure for installing the fire-barrier kit is described in the instruction sheet S1A68982, available on the Schneider Electric website.StepAction1Check the dimensions of the hole through the partition wall or floor slab.2Define the position of the fire-barrier kit on the run component. The fire-barrier kit must be positioned more than 200 mm from any joint block (seepage66).3