Title: +038=433.000-NI003._05-Testrapport elektriske anlegg - DM3.E3.433.09.02, Pareto plan 09.pdf
Uc: 0.1V Rl: 4Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 15.06.2020 12:19R LOW OhmR: 0.20ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF029 C16/2 10.06.2020 14:38SPĆNDINGUln: 233V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E3.433.09.02 / XF029 C16/2 10.06.2020 14:58R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF029 C16/2 15.06.2020 09:24RCD II: 28.5mAUci: 0.1V t: 18.0ms Idn: 30mA type: AC Ulim: 25VTallberg Elektro A/S Tlf.22796640Side:8GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTNr. 58585959606061616262636364646565TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E3.433.09.02 / XF029 C16/2 15.06.2020 09:32Z-LINEZ: 0.23ΩIsc: 1.02kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E3.433.09.02 / XF029 C16/2 15.06.2020 09:32Zs(rcd)