Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Tallberg Elektro A/S Tlf.22796640Side:42GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 290290291291292292293293294294295295296296297297TEST RAPPORTResultatDM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 27.11.2020 11:42R LOW OhmR: 0.18ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 30.11.2020 11:59 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 26.11.2020 14:25Zs(rcd)Z: 0.51ΩIsc: 455A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 26.11.2020 14:25Z-LINEZ: 0.49ΩIsc: 472A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 26.11.2020 14:28SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0Hz