Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]34.4 149 2 5.09Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.1 500.0 29.2 36 8.5 499.0 26.4SR 36-78 8.4 483.0 29.6 36 8.9 483.0 26.7MAIN 36-45 9.1 500.0 29.2 36 8.5 499.0 26.4SR 36-78 8.4 483.0 29.6 36 8.9 483.0 26.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 13.4 494.0 11.4 45 14.1 4.9 48.5SR 78-45 13.2 494.0 11.4 45 14.1 5.0 48.3MAIN 45-78 13.4 494.0 11.4 78 14.9 494.0 8.4