Title: +038=310.101-RF048._01-Siemens vannmåler WFK40.D080.pdf
The water meter should be easily accessible to ensure ease of reading. - Neither upstream nor downstream settling paths are required. - During the construction phase, a spacer should be fitted in place of the meter. - Before mounting the meter, the piping must be thoroughly flushed. - The flow measuring section must be fitted between 2 shutoff valves, and the arrow on the body must accord with the direction of flow.The water meter should be easily accessible to ensure ease of reading. - Neither upstream nor downstream settling paths are required. - During the construction phase, a spacer should be fitted in place of the meter. - Before mounting the meter, the piping must be thoroughly flushed. - The flow measuring section must be fitted between 2 shutoff valves, and the arrow on the body must accord with the direction of flow.Preference should be given to horizontal mounting, which ensures a higher metrological class than vertical mounting.