Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
LC elbows must be supported from the bottom if the distance between the angle and the centre of thenearest joint block is greater than 350 mm.QGH3492101-01 11/201823Supports and Run ComponentsSupports for LP Flatwise Elbows With a Vertical BranchLP flatwise elbows with a vertical branch must be supported close to the angles.24QGH3492101-01 11/2018Supports and Run ComponentsInstallation of Horizontal RunsIntroductionFollow these stages to install a horizontal run:StageDescription1Install the supports (seepage25).2Install the run components on the supports (seepage27).3Install the joint blocks (seepage30).Horizontal SupportsHorizontal supports allow run components to be installed horizontally and adjusted along the length. They also help absorb any movement of the run components. Horizontal supports can be installed on the ceiling or the wall.Types of Horizontal Supports