Title: Hardware Installation Guide.pdf
Only OnGuard 2013 (6.6.xxx), OnGuard 7.0 (7.0.xxx), OnGuard 7.1 (7.1.xxx), and OnGuard 7.2 (7.2.xxx) Monitoring Software was evaluated for use.Portal locking devices must be ULC or cUL Listed, and be constructed so that they do not interfere with egress, with their locking action capable of being released when emergency egress is required. Compliance with this requirement will be determined by demonstrating operability with ULC-S533, Standard for Egress Door Securing and Releasing Devices, compliant devices. If the application requires fire resistance, devices will be both ULC-S533 and ULC-CAN4-S104, Standard Method for Fire Tests of Door Assemblies, compliant.Installation must be in accordance with CSA 22.1, National Electrical Code.RS-485 cable must be shielded.Pass codes used with keypads will be system generated or generated by a system administrator, and the maximum number of users shall not exceed 500 (for Class II).