Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
DM1-3. Plan 8 / DM3.E3=433.08.03 / XF041 16C2/003 06.11.2020 11:01Zs(rcd)Z: 0.43ΩIsc: 536A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF041 16C2/003 06.11.2020 11:01RCD II: 27.0mAUci: 0.2V t: 188.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF041 16C2/003 06.11.2020 13:22R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 05.11.2020 12:24SPĆNDINGU12: 234V U1pe: 234V U2pe: 0V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 05.11.2020 12:24Z-LINEZ: 0.35ΩIsc: 659A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 250A Isc(0.76%): 501A Isc(1.15%): 757ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 05.11.2020 12:25Zs(rcd)Z: 0.32ΩIsc: 710A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 05.11.2020 12:25