Title: økernvn 94.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 16.4 48.3 34.4 36 16.2 44.3 33.1SR 12-36 14.2 41.3 36.5 12 15.1 38.5 34.9MAIN 36-78 25.9 238.0 5.9 36 26.8 243.5 2.7SR 36-45 20.7 249.5 4.7 36 20.3 243.5 2.7010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 1.0 30.0 18.6SR 45 1.1 30.0 18.6MAIN 45 4.9 250.0 10.0SR 45 5.8 211.5 10.706050050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4