Title: 1 etg del 2.pdf
Cable ID: REGISTRERING 1 Date / Time: 10/21/2013 02:17:52 PM Headroom 1.6 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]146 222 7 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]17.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.6 245.5 35.5 36 1.6 240.5 33.0SR 12-36 4.8 168.5 38.1 36 6.5 168.5 35.6MAIN 36-45 1.6 247.5 35.4 36 1.6 240.5 33.0SR 12-36 6.1 249.5 35.4 36 6.8 229.0 33.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-36 16.5 238.0 16.7 36 18.4 239.0 13.6