Title: 360.001 - Avtrekk.pdf
SizeDUCT500FIREDAMPER FKR-EU/DE/500/500DUCT500214 FLOWDAMPER LEO-0-500500DUCT500SILENCERLEV-500-L1500DUCT500REDUCERMAGIR-RC-*-*-* 1000x500/500DUCT1000x500215 EXTRACTGRLc 1000-500 1000x500L [m]0,20,10,00,00,2qv [m³/h]440044004400440044004400440044004400440015v [m/s]6,26,26,26,26,26,26,26,22,42,4dpt [Pa]0,2 Sound in:Attenuation: Addition:3,9 Sound in:Addition:0,1 Sound in:Attenuation: Addition:40,1 Sound in:Addition:0,0 Sound in:Attenuation: Addition:6,8 Sound in:Attenuation:0,0 Sound in:Attenuation: Addition:3,8 Sound in:0,0 Sound in:Attenuation: Addition:7,6 Sound in:Attenuation: Addition:Total Lw:63 [dB]44.80.0 +37.845.6+49.551.00.0 +37.851.2+49.553.40.0 +37.853.53.050.50.0 +37.850.850.80.2 +21.650.60.0 +29.850.6125 [dB]40.20.0 +36.841.9+43.145.50.0 +36.846.1+49.551.10.0 +36.851.32.049.30.0 +36.8