Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
No modifications to the WINTSYS® unit are permitted without the prior authorization of TECUMSEH. Faulty parts must be replaced with original spare parts and maintenance must be done in accordance with local regulations. In order to maintain the acoustic quality of the product over time, it is recommended to change the external suspensions as soon as they appear to drop off in quality. Access to the Connections, Fan, Compressor compartments can be done using the side door and also from the front of the unit without removing the top.■ 5.1. Condenser The unit heat exchanger should be cleaned at least once a year. It is possible to access the inside of the unit by lifting the front of the fan.■ 5.2. Replacing the fan - Disconnect the fan cable from the unit block. - Remove the 4 support attachment screws. - Extract the fan assembly + support. - Replace the fan motor and its capacitor.366465_b / 03.201711/44R FE DS ET IU RL PS E X E N N AInstallation Instructions |