Title: 564 SBR-SBC-U6-U10.0.1-84 Tenton termostat med 6-10knapper-temp-co2.pdf
Connection of the integrated KNX bus coupler according to connecting diagram: ■ Connect the device at the back of the coupler to the KNX bus linewith the enclosed 2-pin bus connection terminal.Notice ■ Check that the polarity is correct! ■ Devices with CO2 sensors must be protected against dust,otherwise incorrect measurements could result.[a] [b] [c] [d] [e] [f]Actual temperature Relative humidity / air pressure / CO2 Fan coil status / manual stage setting for fan coil Temperature setpoint Heating or cooling status RTC iconsNotice After a reset or a mains failure, the device re-calibrates itself automatically. When the first reliable measured values are available, the device switches to the default display.CommissioningVarious functions can be implemented via the ETS commissioning software. The functions depend on the parameters selected via the respective software application.