Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.3 467.0 29.9 36 6.3 500.0 26.4SR 36-45 8.7 498.0 29.3 36 8.4 498.0 26.4MAIN 12-36 7.7 500.0 29.2 36 6.3 500.0 26.4SR 36-45 8.8 500.0 29.2 36 8.4 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.6 500.0 11.3 45 19.8 500.0 8.3SR 78-45 18.5 494.0 11.4 45 20.0 500.0 8.3MAIN 78-45 18.6 500.0 11.3 45 19.8 500.0 8.3SR 78-45 18.5 494.0 11.4 45 20.0 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.2 31.8 40.1 45 18.8 29.8 38.5SR 36-45 19.7 26.8 42.1 36 20.6 26.8 39.7MAIN 36-78 30.3 500.0 -12.4 36 29.1 500.0 -15.3SR 36-45 31.1 500.0 -12.4 36 31.0 498.0 -15.10804000250 MHzACR-N (dB)