Title: økernvn 94.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.1 22.9 43.6 36 11.6 22.9 41.2SR 12-36 15.9 26.4 42.0 36 16.0 26.4 39.6MAIN 36-45 16.5 248.5 4.8 36 16.3 248.0 2.2SR 36-78 23.6 248.5 4.8 36 24.2 247.0 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.4 24.5 19.1SR 36 3.7 24.5 19.1MAIN 45 8.0 214.5 10.7SR 45 4.3 243.5 10.106050050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4