Title: økernvn 94.pdf
MAIN 36-45 19.0 44.5 35.5 36 18.6 44.0 33.2SR 12-36 13.6 65.5 30.0 36 14.7 44.3 33.1MAIN 45-78 27.9 245.0 5.2 45 28.1 248.0 2.2SR 36-45 21.3 250.0 4.7 36 20.7 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.5 214.0 10.7SR 36 4.6 24.1 19.1MAIN 36 3.5 214.0 10.7SR 45 6.3 191.5 11.206050050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94