Title: 2 etg del2.pdf
255 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.5 245.5 35.5 36 1.1 245.0 32.9SR 36-450.1 *246.5 35.4 36 0.7 *246.5 32.8MAIN 36-45 1.5 245.5 35.5 36 1.1 249.5 32.7SR 36-45 0.1 246.5 35.4 36 0.7 246.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 6.4 43.3 31.5 36 9.3 43.3 28.5SR 36-45 6.6 43.5 31.4 45 9.4 43.3 28.5MAIN 36-45 14.1 246.0 16.4 36 16.9 245.0 13.4SR 45-36 13.4 246.0 16.4 36 15.2 213.0 14.6010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250