Title: +038=310.101-SC020T_02-FDV-dokumentasjon - Danfoss AS - VA_VVS 5640952 med flere - Danfoss spoler.pdf
GM 209 J (Black)DesignDIN 43650-BCable glandPG 9Poles2 + PEMax. voltage250 V AC / DCApprovalsCSAEnclosureIP65 (IEC 60529)Max. operating current16 AContact resistance< 10m ΩCable diameterØ4.5 – 7 mmWire cross sectionMax. 1.5 mm2Ambient temperature30 – 90 °C / -22 – 194 °FContacts:CuSn (Tin plated)MaterialsTerminal block:Flat gasket: Housing:PA 6 GFNBR PA 6 GFøDimensions and weightøWeight 0.023 kg / 0.050 lbsIC.PD.600.1A.02 | 20Cable plug (LED + Varistor)y Enclosure: Up to IP65y For use with Danfoss coils type AM, AK, AL, AS,AZ, BA, BD, BB, and BYy 24 V AC / DC and 230 V AC version y DIN 18 y Approved in accordance with:CSAy In accordance with: - RoHS 2011/65/EU - LVD 2014/35/EUVoltageCable plug size[V DC] 24 –[V AC] 24 DIN 18 DIN 18 230 1) Protects against voltage peaksVoltage variation ±10% ±10%Suitable for coil types AM, AL, AS, AZ, BA, BB, BD, BY AM, AL, AS, AZ, BA, BB, BD, BYLED colour Red Red