Title: Hardware Installation Guide.pdf
3. Workstation running Alarm Monitoring is not in the monitoring zone for the access panel.3. Workstation running Alarm Monitoring is not in the monitoring zone for the access panel.4. Workstation name is incorrect in software configuration for access panel.4. Workstation name is incorrect in software configuration for access panel.Make sure that you have not exceeded the maximum current draw of your power supply.Use the standard naming convention for database location (instead of mapped drive) in your ODBC settings (e.g. \\Server\accessct.mdb). This eliminates the need for mapped drives. Make sure the drive where the database resides is shared.Check end of line termination jumpers. Only the first and the last device on each RS-485 communication line should be terminated.1. Port 1 communication wiring is incorrect. Use meter to check pin-outs, do not rely on coloring schemes.1. Port 1 communication wiring is incorrect. Use meter to check pin-outs, do not rely on coloring schemes.