Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
%< 5 % Non Linear Load; < 3 % Linear LoadElectrical Specificationsn - BatteryTypeSealed lead acid maintenance free-expected life 3/5 yearsVoltage369696BUT> 5 min> 9 min> 5 minCharger8 A8 A8 AEnviromentOperating temperature°C0 to 40 1Relative humidity%20 to 90 No CondensingMax. altitudem< 1000 m without deratingAcoustic noisedBAup to 50 dB at front 1 mStandardsSafetyEN 62040-1, EN 60950-1EMCEN 62040-2Product CertificationCEProtection LevelIP20Mechanical Characteristics with standard batteriesDimensions (W x D x H)mm145 x 400 x 220192 x 460 x 347192 x 460 x 347Weightkg137311331131. 15-25 °C for a longer battery life.ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 00ITYS 6 - 1 0 k V A2212. SAFETY STANDARDS12.1. ELECTRICAL REQUIREMENTSThe installation and the system must comply with pertinent national statutory regulations.