Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
jumper selectable commonlyGalvanic separation: Measuring principle: Conversion time A/D: Resolution (digital representation): Input resistance: Accuracy (of measured value):no differential < 30 µs 12 bits (0…4095) W500: 0…+10 V: 1 MΩ unipolar: ± 2 LSB bipolar:± 10 LSBRepeating accuracy (under same conditions): Common mode range: Common mode rejection: Overvoltage protection W500: Overvoltage protection W510: Time constant of input filter: Outputs Number of output channels: Signal ranges:Galvanic separation: Conversion time D/A: Resolution (digital representation): Load impedance: Accuracy (of output value):± 2 LSB CMR CMRR > 75 dB ± 40 VCC (permanent) 45 mA 3 ms±10 V2, short circuit protected 0…+10 V -10…+10 V no < 20 µs 12 bits (0…4095) >3 kΩ 0.3% ± 20 mV}jumper selectable individuallyTechnical data common to the whole module