Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Isc: 578A R: 0.40Ω Xl: 0.00Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.1V t: 204.0ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTTALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:2GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENTNr.889910101111TEST RAPPORTResultatISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 530V Rnpe: >30.0MΩ Um: 514VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 1 10.03.2022 13:39 (TomekElektriker)KONTINUITET: R200mA LPER: 0.14ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF022 C16/2/003 / Mal 2 10.03.2022 11:25 (TomekElektriker)SPENNING TRMS Uln: 234V Ulpe: 234V Unpe: 1V f: 50.03HzSYS.: TN/TTZ-LINEZ: 0.42ΩIsc: 548A R: 0.42Ω Xl: 0.01Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mA