Title: Hardware Installation Guide.pdf
1. Set baud rate, address, and LED control switches.2.Install jumpers.3. Mount the board in the enclosure.Note:The LNL-CONV-U1 Universal Mounting Plate is required when installing the board into a CTX enclosure. For more information, refer to Mounting on page 417.4. Wire the supervised alarm inputs.5. Wire the upstream host communication.6. Wire the relay outputs for door strike and AUX.7. Wire the downstream interface for the keypad or card reader.8. Wire the unsupervised alarm inputs for power fail and cabinet tamper.9. Wire the power and communications inputs.10. Validate proper operation on power up.408 — revision 6Hardware Installation Guide85ConfigurationThe Dual Door Controller (DDC) Interface Module board contains two (2) 8-position DIP switches that are user-selectable to control addressing, baud rate, and other functions, and seven (7) jumpers used to configure your system.85.1Setting DIP SwitchesDDC dip switches85.1.1Communication Baud Rate (SW1)