Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Z: 0.56ΩIsc: 414A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 10.06.2020 13:04Zs(rcd)Z: 0.51ΩIsc: 447A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATallberg Elektro A/S Tlf.22796640Side:23GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTNr. 156156157157158158159159160160161161162162163163TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 10.06.2020 13:04RCD UbUc: 0.8VRl: 25Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 10.06.2020 13:04RCD tt: 57.6msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 10.06.2020 13:05RCD II: 28.5mAUci: 0.0V t: 101.5ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF037 C16/2 11.06.2020 15:18R ISO