Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
RCD II: 28.5mAUci: 0.1V t: 83.7ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE040 10.02.2020 09:05SPÆNDINGUln: 226V Ulpe: 228V Unpe: 2V f: 49.9HzOBJEKT / Plan 10 / FUSE041 07.02.2020 09:23KONTINUITET R: 0.4ΩGrenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE041 07.02.2020 09:23R LOW OhmR: 0.37ΩR+: 0.4Ω R-: 0.4Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE041 07.02.2020 09:47RCD II: 28.5mAUci: 0.3V t: 18.3ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE041 07.02.2020 09:48Zs(rcd)Z: 0.53ΩIsc: 437A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATEST RAPPORTSide:13GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 8080818182828383848485858686ResultatOBJEKT / Plan 10 / FUSE041 07.02.2020 09:49Z-LINEZ: 0.98ΩIsc: 235A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE041 07.02.2020 09:49SPÆNDING