Title: 32 Pumper modbuss teknisk data.pdf.pdf
SS00356HeatDiffTemp►Differential temperature between forward and return pipe used for heat calculation.0.01 KH + SS00357 003580035900360Volume1HI Volume1LO HeatEnergyCounter2HI► HeatEnergyCounter2LO►Total pumped volume (direction 1).Total accumulated heat energy in pump lifetime (direction 2).0.01 m31 kWhH + SH + SCUE + SS0036100362Volume2HIVolume2LOTotal pumped volume (direction 2).0.01 m3H + S►: The availability of these measurements requires that the data register 00302 VolumeFlow is available and that a differential temperature measurement is established by one of the below means:MGE model H and later:MAGNA3:For the calculation, an estimated flow value and measurement of the liquid temperature by the build-in temperature sensor is used. Connection of an external temperature sensor is needed for the pump to calculate the needed differential temperature.