Title: +038=360.000-JV042._02-HMa-1,5 Avtrekksvifte R&H - Teknisk spesifikasjon.pdf
Order project Position373169 Dronning Maudsgt. 1-3 360,xxxPlug fanExhaust airFan Air volume [m³/h] External press [Pa]RLM E3-3540-BE-QG-M 4.500 250Press static [Pa] Press dynamic [Pa] Total pressure [Pa]382 31 4130,644Fan shaft power [kW] Sound pow. vacuum/pressure [dB71.9 / 77.7 Efficiency total / static [%] System efficiency tot. / stat. [%] Speed [1/min] K-Factor Delta p with Vn (IMV) [Pa]80,18 / 74,16 65,43 / 60,52 1.652 128 573Fan octave band sound power level (Lokt) [dB] Frq. [Hz] Inlet Outlet63 125 61,3 67,0 66,1 65,3 63,1 68,0 66,3 70,0250 500 1000 2000 4000 8000 66,5 64,2 65,9 55,8 74,7 69,7 69,4 60,61setoutlet guard GIrevision door with dual hingeOpeningnoise calculationsound power [dB] Frq. [Hz] Inlet Outlet casing63 125 250 500 1000 2000 4000 8000 63,5 60,2 61,9 51,8 74,7 69,7 69,4 60,6 61,7 56,7 41,4 23,660,3 66,0 64,1 63,3 63,1 68,0 66,3 70,0 56,1 61,0 54,3 57,0sound pressure level [dB]