Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]98 157 12 4.398 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]21.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.1 * 242.0 35.6 36 0.1 * 249.0 32.7SR 12-36 6.5 156.0 38.7 36 7.0 245.0 32.9MAIN 36-45 0.1 249.0 35.4 36 0.1 249.0 32.7SR 12-36 6.7 235.5 35.8 36 7.0 245.0 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.9 236.0 16.7 45 17.5 194.5 15.4SR 45-36 14.7 227.0 17.1 36 16.7 226.5 14.1MAIN 36-45 14.9 236.0 16.7 45 18.2 250.0 13.2SR 45-36 14.7 236.0 16.7 36 16.7 226.5 14.1010080604020050100150MHzACR-F (dB)2002500100806040