Title: +038=30.001-NI003._16-V20-08-02 VVS-anlegg plan 8 - DM3.pdf
LD021T Maks:220 m³/h Kjøling: 420 W 0.033 L/s+08 = 320.102 - OE 082 0.081 L/sLD018T Maks:220 m³/h Kjøling: 420 W 0.033 L/s Varme: 480 W 0.012 L/sLD021T Maks:220 m³/h Kjøling: 420 W 0.033 L/sOpp/ned 320.102: 54 mm 320.102: 54 mm8SZ001T Ø3151:60LD018T Q: 190 m³/h Varme: 510 W 0.012 L/s370.101: 35 mm +c 3520370.101: 35 mm +c 3520ø250 UK=334522 mm +c 3435320.102: 18 mm UK = 3511320.102: 18 mm UK = 351175 UK = 3391Garderobe 8-009ø315 UK=326515 mm UK = 3300 15 mm UK = 3300ø250 UK=32981:601:60Sluk 75mm+08 = 360.018 - OE 901Teknisk rom 8-508p p ot s a k v Aø400 UK=2925ø400 UK=2925ø400 UK=2375110 UK = 2260SZ001T Ø400ø400 UK=3195Rens 8-008STAD Dim:10/09 StengtSF002T-200SF002T-200ø315 UK=3258ø200 UK=3385SF002T-200SF002T-200ø200 UK=3374Opp 310.002: 110 310.002: 110Møterom 8-007Møterom 8-006110 UK = 33995 1 3 3 = K U 0 0 2 ø0 6 : 1STAP/STAD DN 20Circular Duct Fan Ø400 Q:1050 m³/hSZ001T Ø4001:60Oppø200 UK=3380