Title: økernvn 94.pdf
Cable ID: D3186 Date / Time: 09/11/2013 03:08:02 Headroom 4.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]126 192 6 5.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]18.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.1 206.5 36.7 36 7.3 230.5 33.3SR 36-78 4.2 243.0 35.5 36 3.9 243.0 32.9MAIN 36-78 5.1 206.5 36.7 36 7.3 230.5 33.3SR 36-78 4.2 243.0 35.5 36 3.9 243.0 32.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 12.0 190.5 18.6 36 14.0 162.0 17.0