Title: Eurotester sluttmålinger =433.205.pdf
2222232324242525ResultatRCD II: 25.5mAUci: 0.2V t: 20.3ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING12 31.01.2022 09:58:06RCD II: 28.5mAUci: 0.2V t: 10.3ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING13 31.01.2022 09:58:22RCD II: 21.0mAUci: 0.1V t: 20.0ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING14 31.01.2022 08:54:59Z-LINEZ: 0.90ΩIsc: 195A Sikringstype: B SIKRING I: 16A SIKRING T: 35ms Isc_lim: 80.0A Isc(0.38%): 97.7A Isc(0.76%): 195A Isc(1.15%): 296ASimployer / =433.205 / SIKRING14 31.01.2022 08:55:21RCD II: 24.0mAUci: 0.1V t: 19.9ms Idn: 30mA type: AC Ulim: 50VSimployer / =433.205 / SIKRING14 31.01.2022 08:55:33R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩSimployer / =433.205 / SIKRING14 31.01.2022 08:55:41TEST RAPPORTSide:4GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT