Title: økernvn 94.pdf
MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: D3424 Date / Time: 09/12/2013 12:43:40 Headroom 7.4 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]194 296 11 9.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.2 60.3 45.4 36 8.1 244.0 32.9SR 36-78 7.4 136.0 39.7 78 8.2 136.0 37.1MAIN 12-36 8.4 242.5 35.6 36 8.1 249.5 32.7SR 36-78 8.2 217.5 36.3 36 8.3 219.5 33.610080604020NEXT (dB)