Title: 1 etg del 2.pdf
Measurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T1112 Date / Time: 10/17/2013 03:13:19 PM Headroom 1.2 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]265 418 27 11.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.2 249.0 35.4 36 1.4 247.0 32.8SR 36-78 5.5 247.5 35.4 36 6.5 247.0 32.8MAIN 36-45 1.2 250.0 35.3 36 1.4 247.0 32.8SR 36-78 5.5 247.5 35.4 36 6.5 247.0 32.810080604020NEXT (dB)