Title: økernvn 94.pdf
SR 36-45 14.7 12.5 42.3 45 16.5 76.0 23.6MAIN 12-45 18.7 248.0 16.3 45 20.6 248.0 13.3SR 12-45 19.8 249.0 16.3 12 19.6 248.0 13.3010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.8 23.1 43.5 45 14.3 24.9 40.3SR 36-45 14.2 13.1 49.6 36 15.1 29.9 38.1MAIN 45-78 21.1 249.0 4.8 78 20.8 249.0 2.1SR 36-78 20.5 249.5 4.7 36 21.3 249.5 2.1010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.4 37.3 18.1SR 12 4.9 45.3 17.4MAIN 36 8.3 246.0 10.1SR 36 8.1 246.0 10.1010080050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040200050100150MHzProject: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASS