Title: 2 etg del2.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.8 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 2.2 248.5 35.4 36 1.5 249.5 32.7SR 36-450.3 *248.5 35.4 36 0.8 *235.0 33.2MAIN 12-36 2.2 248.5 35.4 36 1.5 249.5 32.7SR 36-45 0.3 248.5 35.4 36 0.8 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 7.6 42.8 31.6 36 10.2 42.8 28.6SR 36-45 7.7 42.8 31.6 45 10.3 42.8 28.6MAIN 36-12 17.0 244.5 16.4 12 18.5 245.0 13.4SR 36-12 16.2 244.5 16.4 12 19.3 249.0 13.3010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250