Title: V20-05-01 VVS-anlegg plan 5 - DM1.pdf
Tur/retur ligger over hverandre bak drager 320.102: 18mmSTAP/STAD DN2013+05 = 320.102 - OE 053 0.056 L/sLD007T Maks:230 m³/h Kjøling: 465 W 0.037 L/s Varme: 395 W 0.009 L/sLD007T Maks:230 m³/h Kjøling: 465 W 0.037 L/s Varme: 395 W 0.009 L/s14LD018T Maks:130 m³/h Kjøling: 650 W 0.052 L/s Varme: 280 W 0.007 L/sLD018T Maks:200 m³/h Kjøling: 850 W 0.064 L/s Varme: 545 W 0.013 L/s+05 = 360.021 - SB 501+05 = 360.021 - OE 90115Elektrisk varmebatteri Kjølebatteri kobles til prosesskurs.Stuss rist Profilteam B1150xH2017Snitt P5-A161150x2017 UK=19128 mm370.101: 42 mm +c 2790370.101: 42 mm +c 2790r e g a r dr e d n us å slMøterom 5-009r ø R320.102: 28 mm +c 2790320.102: 28 mm +c 2790t r e t n o m e d e r el lag g e VWISE RTA WISE IAQPure water 65mmSF002T-200Pure water legges frem hit for fremtidig tilkoblingSF002T-200SF002T-200SF002T-200SF002T-200SF002T-200ST020T-160 150 m³/hSF002T-200SF002T-200Forrom 5-408