Title: Hardware Installation Guide.pdf
The application software must be configured for elevator control. This can be done on the Elevator Hardware tab in the Readers window of the System Administration software. The “Elevator” box should be checked. The reader’s type, name, port, address, access panel, can all be defined here.With elevator control on the LNL-1300 reader, door strike and contact are not available, and REX (Request to EXit) has been disabled.Addresses assigned to input/output panels do not have to be consecutive. On the first panel, the inputs/ outputs represent the first sixteen floors (e.g.: Input 1 = first floor, Input 2 = second floor, etc.). The second panel represents the next sixteen floors (floor 17 through 32), etc.Overview of Elevator ControlAccess Control SystemIntelligent System ControllerMaximum: 4000 feet (1219.2 meters) 5 conductorsOutput Control ModuleInput Control ModuleSingle Reader InterfaceSingle Reader Interface ModuleSingle Reader Interface