Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12 16,0 8,4 7,6 366,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 29,6 26,7 2,9 500,00Worst Value: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 29,6 26,7 2,9 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 67,6 57,3 10,3 2,20Remote: 12-45 67,6 57,3 10,3 2,20Worst Value: Local: 12-45 20,9 10,3 10,6 495,00Remote: 45-12 21,3 10,3 11,0 495,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,9 3,7 496,00Remote: 36 28,5 23,8 4,7 500,00Worst Value: Local: 36 27,6 23,8 3,8 498,00