Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
36.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.2 451.0 30.2 36 5.5 452.0 27.3SR 36-45 6.5 468.0 29.4 36 7.7 466.0 26.6MAIN 36-78 6.3 495.0 28.1 36 6.3 497.0 25.1SR 36-45 6.8 500.0 27.8 36 7.8 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 21.5 9.5 45.7 45 23.0 23.1 35.0SR 45-78 21.5 9.8 45.5 45 23.0 13.5 39.6MAIN 36-12 23.1 475.0 11.7 12 25.2 466.0 8.9SR 12-36 22.8 475.0 11.7 36 24.9 475.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 36.5 322.0 0.6 36 37.4 320.0 -1.9SR 12-36 37.0 321.0 0.7 36 38.4 320.0 -1.9MAIN 36-78 41.2 495.0 -12.1 36 41.0 497.0 -15.1SR 36-45 41.6 500.0 -12.4 36 42.5 499.0 -15.20804000250 MHzACR-N (dB)