Title: Hardware Installation Guide.pdf
The manufacturing parameters which include the serial number, etc. are invalid. The module must be returned for repair.86Hardware Installation GuideMountingThe DDC can be mounted in the LNL-AL400ULX or LNL-AL600ULX-4CB6 and the LNL-CTX or LNL-CTX6 enclosure using the Universal Mounting Plate (UMP) LNL-CONV-U1.Mounting the DDC in the LNL-AL400ULX and LNL-CTXrevision 6 — 417LNL-1320-U Dual Door Controller ModuleMounting the DDC in the LNL-AL600ULX-4CB6 or LNL-CTX6418 — revision 6Hardware Installation Guide87WiringNote:For UL installations, refer to section UL Listed Installations on page 425.Wire inputs I1 through I8 (J19 - J22) using a twisted pair cable, 30 ohms maximum, 24 AWG minimum.87.1Supervised (Software Configurable) Alarm InputsDDC input wiringNote:For termination resistor values, refer to the Input Resistor Table on page 420.