Title: +038=434.005-KW001._01-FXQJ-EMC-Pure 3X240 FV120 Draka Produktblad.pdf
sector shaped (FV)Conductor InsulationXLPEFillerHalogen free polymer (on sizes <16 mm2)Marking of cores3-core: brown, black, grey4-core: brown, black, grey, blueInner coveringHalogen free, tapeShield / ScreenSolid copper strip and overlying copper wiresOuter SheathHalogen free polymer, blackExample of marking on sheathFXQJ-EMC Pure IFSI-EMC MCCMK-HF 0,6/1 kV 3x16 FR/16 D-s2d2a2 DRAKA "Date", metremarkedTemperatureMaximum operating Temperature90 ºCTemparatures at installation [°C]Lowest cable temperature during installation -20 ºC, below 0 ºC special precaution shall betaken.FeaturesCPR Performance classCca-s1d1a1 for sizes ≤ 16 mm2Dca-s2d2a2 for sizes ≥ 25 mm2UV resistanceFairBending radiusWhen ﬁxed: 8 x DWhen installing: 12 x DWhen plowing: 8 x D