Title: B   Porkka Kjole- og Fryserom   Bruksanvisning.pdf
Before erecting the room ensure there is sufﬁ cient ventilation in the area where rooms is to be positioned. In operation the room will dissipate a heat load in the area in question in region of 1 - 2,1 kW per hour when running. This heat must be removed from the area by means of ventilation such as louvers or extraction systems. If impractical, consult your supplier for the possibilities of using our heat disposal system. The refrigeration systems are designed to operate satisfactorily in ambients between +5 and 32°C. Ensure that the ﬂ oor area to be used is level. Requirement of the eveneness is max ±3 mm/m. Correct any unevenness at this time. It is recommended to leave a gap of 50mm minimum between a freezer room and the fabric of the surrounding building for air circulation purposes.