Title: Økernveien 94 Sprinklerberegning U2.pdf
Brline PIPE4 f11Fmain PIPE5 b65Brline PIPE5 b64Brline PIPE5 b70Brline PIPE6 b66Brline PIPE6 b67Brline PIPE6 b68Brline PIPE7 b63Brline PIPE8 b56Brline PIPEDate 29.05.2018Schedule Size2448 652448 652448 652448 652448 652448 652448 652448 652448 652448 652448 652448 322448 322448 322448 652448 322448 322448 322448 652448 322448 322448 322448 322448 322448 322448 322448 32Hydraulic Calculations / Fluid Delivery Time AnalysisPipe DataHWC Rough.Fittings Eq.Len.Length Total Len.Flow VelocityFr.Resist. Loss Frict.Vel.Pres. Loss Elev.Start EndStart Disch. End Disch.mmmm ml/min m/sbar/m barbar barl/min l/min120 0.10161(eu.TeeScr-Run); 3.5422.42 1.810.0063 0.020.02 0n14 n16120 0.10161(eu.TeeScr-Run); 3.5428.18 1.840.0064 0.020.02 0n12 n14120 0.10161(eu.TeeScr-Run); 3.5431.11 1.850.0065 0.020.02 0n10 n12120 0.10161(eu.TeeScr-Run); 3.5433.62 1.86