Title: 360.002 - Tilluft.pdf.pdf
0,23,30,10,6Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:24003,40,9 Sound in:Attenuation: Addition:24003,49,1 Sound in:Attenuation: Addition:Dividing:12004,30,1 Sound in:Attenuation: Addition:12004,34,8 Sound in:Addition:12004,30,4 Sound in:Attenuation: Addition:12004,32,8 Sound in:Attenuation: Addition:963 [dB]35.50.0 +0.040.10.0 +0.051.00.2 +24.750.80.0 +35.35.545.50.0 +25.745.5+40.446.70.1 +25.746.60.0 +35.3125 [dB]27.50.0 +0.032.10.0 +0.043.80.2 +23.643.60.4 +31.25.538.00.0 +24.638.2+29.738.80.1 +24.638.90.0 +31.2250 [dB]18.70.0 +0.023.60.0 +0.037.60.2 +22.637.50.9 +26.35.531.50.0 +23.632.1+26.733.20.1 +23.633.61.2 +26.3500 [dB]14.80.0 +0.020.40.0 +0.034.10.3 +21.634.0