Title: etg u1.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.5 22.1 44.0 12 9.8 18.4 43.7SR 12-36 7.7 22.1 44.0 12 9.6 18.4 43.7MAIN 36-45 17.0 249.5 4.7 36 16.8 249.5 2.1SR 12-36 16.3 249.5 4.7 36 15.7 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.7 31.8 18.5SR 45 4.2 31.8 18.5MAIN 36 8.4 245.0 10.1SR 36 6.7 241.5 10.2010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1