Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Schneider Electric recommends that you perform an insulation test on the run components before installation. This is to check for damage or contamination during shipment or storage.When the rated operating voltage Ue<500 Vac, perform an insulation test on each run component as follows:  Using a megohmmeter of at least 500 Vdc (DC to avoid inductive and capacitive currents), makemeasurements between active conductors and exposed conductive parts (phase-to-phase, phase-to- neutral, phase-to-ground, and neutral-to-ground). The test is satisfactory if the insulation resistance between active conductors and exposed conductiveparts is at least 1000 Ω/V per circuit, referred to the supply voltage to ground of these circuits.NOTE: When the rated operating voltage Ue>500 Vac, perform the test at 1000 Vdc. The insulation resistance must be not less than 1 MΩ.14QGH3492101-01 11/2018Preparation and OrganizationPhase Order CheckChecking the Phase OrderDANGERHAZARD OF ELECTRIC SHOCK