Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF022 C16/2 10.06.2020 10:46R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF022 C16/2 10.06.2020 11:11SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF022 C16/2 12.06.2020 11:19Tallberg Elektro A/S Tlf.22796640Side:3GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.222223232424252526262727TEST RAPPORTResultatZ-LINEZ: 0.47ΩIsc: 489A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF022 C16/2 12.06.2020 11:20Zs(rcd)Z: 0.45ΩIsc: 512A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF022 C16/2 12.06.2020 11:23RCD tt: 68.0msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25V