Title: FDV 16678-4 (2) .pdf
Early-make time of the HIV compared to the main contacts during with make andbreak switching.(switch times with manual operation):NZM1, PN1, N(S)1: ca. 20 msNZM2, PN2, N(S)2: ca. 20 msNZM3, PN3, N(S)3: ca. 20 msNZM4, N(S)4: approx. 90 ms, the HIV switch early Offswitching not forward.M22-(C)K10(01)M22-CK11(02)(20)XHIVbeiAC =50/60HzBemessungsbetriebsstrom AC-15115V Ie A 4 4 4 230V Ie A 4 4 4 400V Ie A 2 - 2 500V Ie A 1 - 1 DC-1324 V Ie A 3 3 3 42 V Ie A 1.7 1 1.5 60 V Ie A 1.2 0.8 0.8 110V Ie A 0.6 0.5 0.5 220V Ie A 0.3 0.2 0.2OperationsOperationsOperationsOperations2200.11Rated operational voltageRated operational voltagePvidPvid104Short-circuit protectionAAAAAAmax. fuseA gG/gL00V DCHeat dissipation per pole, current-dependentRated operational voltage, max.1x 106x 106x 106x 1061.25 A – 600 V AC1 A - 250 V DCUeUeUeIeIeIeIeFAZ-B6/B1Maximum equipment and position of the internal accessoriesUL/CSAIn