Title: DM1-3 plan 09 lysberegningsrapport.pdf
Object Installation Project number Date: : : :DM 1-3 plan 9 283 15.10.2019Room 1Description, Room 1Floor plan[m] 5.55.04.54.03.53.02.52.01.51.00.50.0x 49.25 m 49.25 m 46.75 m 46.75 mWall 1 2 3 4 Floor Ceiling Room height Height of ref. planey 10.16 m 15.77 m 15.77 m 10.16 m2.50 m 0.75 m191015 test plan 9.rdf0.00.4Length 2.49 m 5.61 m 2.49 m 5.61 m0.81.21.6Reflectance 50.0 % 50.0 % 50.0 % 50.0 % 20.0 % 70.0 %2.02.4N[m]Object Installation Project number Date: : : :DM 1-3 plan 9 283 15.10.2019Room 1Summary, Room 1Result overview, Measuring area 1[m] 5.5N5.04.54.03.53.02.52.01.51.00.50.00.0 0.6 1.2 1.8 2.4[m]Illuminance [lx]2003005007501000General Calculation algorithm used Height of evaluation surface Height of luminaire plane Maintenance factorAverage indirect fraction 0.75 m 2.50 m 0.80Total luminous flux of all lamps Total power Total power per area (13.98 m²)