Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
1) galvanic separation of outputs to Saia PCD®, the channels themselves are not separated against each other5-1OverviewTypeDes- igna- tionNo. I/Os or modDescriptionInput/output signal rangePagePCD2 digital output modules, electrically isolated PCD2.A2004 O44 make contacts 2 APCD2.A2104 O44 break contacts 2 APCD2.A2206 O66 make contacts 2 APCD2.A2508 O88 make contacts 2 APCD2.A4108 O88 outputs 0.5 A, electrically isolated 1)250 VAC 50 VDC 250 VAC 50 VDC 250 VAC 50 VDC 48 VAC 50 VDC 5 … 32 VDC5-325-345-365-385-40PCD2 digital, combined I/O modules PCD2.B10082I + 2O + 4I/O2 inputs, 2 outputs, 4 select- able as inputs or outputs24 VDC 5 … 32 VDC 24 VDC5-43PCD2 multi-functional I/O modules PCD2.G40024 VDC 0 … 10 V Pt/Ni 1000 24 VDC 0 … 10 VDC 24 VDC I/U/T 250 VAC U/I