Title: V20-08-01 VVS-anlegg plan 8 - DM1.pdf
STAD Dim:10/09 StengtLD018T Maks:120 m³/h Kjøling: 210 W 0.016 L/s Varme: 160 W 0.004 L/sSTAD Dim:10/09 StengtLD018T Maks:140 m³/h Kjøling: 430 W 0.034 L/s Varme: 535 W 0.013 L/s11LD018T Maks:140 m³/h Kjøling: 335 W 0.027 L/s Varme: 375 W 0.009 L/sLD018T Maks:140 m³/h Kjøling: 335 W 0.027 L/s Varme: 375 W 0.009 L/sLD018T Maks:140 m³/h Kjøling: 335 W 0.027 L/s Varme: 375 W 0.009 L/s12LD018T Maks:150 m³/h Kjøling: 440 W 0.038 L/s Varme: 360 W 0.010 L/sLD018T Maks:180 m³/h Kjøling: 475 W 0.038 L/s Varme: 420 W 0.010 L/sLD018T Maks:180 m³/h Kjøling: 475 W 0.038 L/s Varme: 420 W 0.010 L/sRomregulering - Plan 08ProduktPlan 09 WISE RTA 09 WISE IAQ 09 WISE RTS 09 WISE director (trådløs router)ProduktBørverdiomstiller CO2-, RH- og temperaturgiver Temperaturgiver Wise Director router13LD018T Maks:210 m³/h Kjøling: 580 W 0.046 L/s Varme: 700 W 0.017 L/sLD018T Maks:210 m³/h Kjøling: 580 W 0.046 L/s Varme: 700 W 0.017 L/s141516LD021T Maks:210 m³/h Kjøling: 580 W 0.046 L/s