Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
29.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 456.0 29.9 36 8.1 456.0 27.1SR 12-36 9.3 466.0 29.5 36 10.2 465.0 26.7MAIN 12-36 7.9 497.0 28.0 36 8.8 498.0 25.1SR 12-36 10.9 498.0 27.9 36 11.2 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.3 8.9 46.3 45 21.0 500.0 8.3SR 45-78 20.3 8.9 46.3 45 20.9 500.0 8.3MAIN 36-45 21.7 500.0 11.3 45 21.0 500.0 8.3SR 78-45 21.6 500.0 11.3 45 20.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.5 63.5 31.1 36 21.2 67.8 27.7SR 36-45 21.0 67.5 30.2 36 21.4 67.8 27.7MAIN 12-36 36.0 497.0 -12.2 36 36.9 498.0 -15.1SR 12-36 39.0 498.0 -12.3 36 39.3 498.0 -15.10804000250 MHzACR-N (dB)