Title: økernvn 94.pdf
Cable ID: D3190 Date / Time: 09/11/2013 03:09:15 Headroom 4.4 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]114 173 5 5.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]20.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 4.4 44.0 47.6 36 6.5 237.0 33.1SR 36-45 4.6 247.0 35.4 36 4.5 203.0 34.2MAIN 36-78 5.8 237.0 35.7 36 6.5 237.0 33.1SR 36-45 4.6 247.0 35.4 36 5.1 247.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.9 164.5 19.9 36 15.3 170.5 16.6