Title: 1 etg del 2.pdf
100150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz100RL @ Remote (dB)806040200050100150200250MHzLinkWare Version 8.1Cable ID: D1227 Date / Time: 10/17/2013 11:43:23 AM Headroom 6.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]86 130 4 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.0 221.5 36.2 36 7.0 217.5 33.7SR 12-36 6.8 213.5 36.5 36 7.9 213.5 33.8MAIN 12-36 6.0 221.5 36.2 36 7.4 245.0 32.9SR 36-78 7.3 249.5 35.4 78 7.9 249.0 32.7