Title: økernvn 94.pdf
SR 36-12 22.2 83.8 20.2 36 25.1 96.0 16.001008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.0 12.1 40.5 36 17.3 10.5 38.9SR 12-36 15.4 10.4 42.0 12 18.1 10.4 39.0MAIN 12-36 19.0 97.8 12.3 36 20.1 98.3 9.2SR 12-36 20.4 100.0 11.9 12 22.3 99.3 9.001008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 5.7 44.0 15.6SR 36 4.5 46.8 15.3MAIN 12 8.1 98.3 12.1SR 36 4.5 46.8 15.301008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002194 ft60Insertion Loss (dB)