Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12-45 68,8 57,3 11,5 2,20Worst Value: Local: 12-45 24,1 12,3 11,8 395,00Remote: 45-12 24,3 12,3 12,0 391,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 31,0 27,7 3,3 384,00Remote: 36 31,7 27,1 4,6 401,00Worst Value: Local: 45 27,9 23,8 4,1 498,00Remote: 45 28,5 23,8 4,7 498,00PS-ACRF: Pass Worst Margin: Local: 12 66,1 54,3 11,8 2,20Worst Value: Local: 45 22,2 9,3 12,9 395,00Remote: 12 73,0 61,2 11,8 1,00Remote: 12 22,6 9,5 13,1 383,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:59Signature:______________________ Page: 30Copper Certification ReportCable Label: 521.002-UD007 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 15:07:54 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein