Title: +038=370.001-RD001._01-Siemens Differanstrykk væske QBE3000-D6.pdf
UseCE1N1922en 2018-11-191922Differential Pressure SensorQBE3000-D.. QBE3100-D..for neutral and mildly corrosive liquids and gasesDifferential pressure sensor, suitable for gases or liquids, for the measurement of pressure differentials in HVAC systems. · Ceramic measuring system · Robust construction for highly reliable operation · For neutral and mildly corrosive liquids and gases · Supply voltage AC 24 V / DC 18...33 V or DC 11...33 V · DC 0...10 V output signal or DC 4...20 mA · Male-threaded G1/8" connection · Delivery includes 2 screwed fittings for copper pipes, 6 mm diameterThe differential pressure sensor is particularly suitable for use in HVAC systems for continuous monitoring of the level or flow rate of neutral or mildly corrosive gases or liquids.The sensor can be used as: · Control sensor · Measured value transmitter for building automation and control systemsBuilding TechnologiesCompatibilityTechnologyMechanical design2/6Siemens Building TechnologiesType