Title: +038=310.101-RF022T_06-multical 62 Vannmåler Kamstrup - Installasjons- og brukerveiledning.pdf
The pulse resolution follows the display (deter- mined by the CCC-code). E.g. CCC=119 (qp 1,5): 1 pulse/kWh and 1 pulse/0.01 m3.The pulse outputs are optoisolated and with- stand 30 VDC and 10 mA.Normally energy (CE) is connected to 16-17 and volume (CV) to 18-19, but other combinations can be selected by means of the PC program METERTOOL, which is also used for selecting the pulse at either 32 or 100 ms.12Kamstrup A/S • 55121068_B3_GB_03.2015MULTICAL® 62 • Water meter6 Retrofitting modulesBoth top modules and base modules for MULTICAL® 62 can be supplied separately for retrofitting. The modules are configured and ready for installation from the factory. Some of the modules require individual configuration after installation, which is possible by means of METERTOOL.Top module Data output + hourly data logger RTC + M-BusRTC + pulse output for CV + prog. data logger2 pulse outputs for CE and CV5 7BC