Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
MAIN 36-45 16.2 26.9 42.1 36 17.5 27.4 39.4SR 36-45 16.7 27.0 42.0 45 18.0 26.9 39.6MAIN 12-36 30.4 500.0 -12.4 36 30.5 500.0 -15.3SR 12-36 30.5 500.0 -12.4 36 29.7 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.9 489.0 8.0SR 45 6.8 500.0 8.0MAIN 45 8.9 489.0 8.0SR 45 6.8 500.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: MCKINSEY 4 ETGMcKinsey 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00443.0 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500