Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13Tallberg Elektro A/S Tlf.22796640Side:45GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTMISLYKKESNr.312312313313314314315315316316317317318318319319320320TEST RAPPORTResultat KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 10:25KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13R LOW OhmR: 0.01ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:35KONTINUITET R: 2.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:30R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0Ω