Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]26.0 111 0 3.83Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.5 459.0 29.8 36 7.1 455.0 27.2SR 12-36 7.7 455.0 30.0 36 9.0 455.0 27.2MAIN 36-78 9.0 500.0 27.8 36 7.7 497.0 25.1SR 12-36 8.8 497.0 28.0 36 9.4 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.4 7.4 47.9 45 21.2 32.3 32.1SR 45-78 19.4 7.4 47.9 45 21.2 33.8 31.7MAIN 36-45 23.9 491.0 11.4 45 24.1 500.0 8.3SR 45-36 24.0 491.0 11.4 36 25.0 495.0 8.30100806040200250 MHzACR-F (dB)