Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
[Pair 12] [Pair 45] [Pair 36] [Pair 45]14.5 63 1 2.32Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]34.3 495.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.2 435.0 30.5 36 5.3 420.0 28.1SR 12-36 6.6 461.0 29.7 36 5.8 469.0 26.5MAIN 36-78 5.7 469.0 29.3 36 6.5 494.0 25.3SR 12-36 7.8 494.0 28.1 36 6.6 494.0 25.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.1 8.4 46.8 45 21.5 8.8 43.4SR 45-78 20.1 8.8 46.4 45 21.5 16.0 38.2MAIN 36-12 21.0 434.0 12.5 36 23.8 498.0 8.3SR 12-36 20.9 434.0 12.5 36 23.0 472.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 29.7 204.5 11.1 36 31.0 213.5 7.6