Title: crouse-hinds-powerplus-panelboards-brochure-brochure.pdf
breaker type) -FDB:2and3pole600V -FD:1,2(277V)and3pole(600V) -HFD:1,2(277V)and3pole(600V)EHD:1,2(277V)and3pole(480V)Main Breaker Trip Ratings2 and 3 pole (contact factory for single phase sizes B, C, D) • Size B, C: 15 to 100 amps • Size D, F: 15 to 225 ampsMain LugsSize B, C, F: 225 amps • Size D: not available; main breaker onlyAmpere Interrupting CapacityAll size panels are certified to 10kAIC • Breaker AIC ratings:GHBbreaker:14kAICat480Y/277EHDbreaker:14kAICat480VBreaker types optional with sizes B, C and D panel only:GDBbreaker:14kAICat480VBreaker types optional with size F panel only:FDBbreaker:14kAICat480Vand600V -FDbreaker:18kAICat600Vand35kAICat480Vand277V -HFDbreaker:25kAICat600Vand65kAICat480Vand277VD2L/EPL Series:Branch Breakers (120/240 VAC BAB Series Quicklag® Bolt-on) Trip Ratings