Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
6. By means of the holes on the back of the cabinet, mount it to the wall (paragraph 3.1 - [G]). Use anchor screws (stop screws) with 8mm diameter minimum.7.Insert and secure the various modules inside the cabinet and on the front plate.8. Replace the front plate and reconnect the grounding conductor and CAN wire.9. Complete the wiring of the internal modules.Installation31This operation allows you to join together up to 4 cabinets.1. Remove all modules and wire/cables from the cabinets,2. Remove the seals from holes used for affixing cabinets together.3. Align the cabinets and, using the bolts (supplied with each cabinet), secure them together (paragraph 3.1 - [H]).3. Align the cabinets and, using the bolts (supplied with each cabinet), secure them together (paragraph 3.1 - [H]).4. Connect the CAN drive bars of each cabinet together using the CAN wire (supplied with each cabinet).