Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]26.4 115 2 4.12Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.1 452.0 30.1 36 10.2 465.0 26.7SR 36-45 9.7 489.0 29.5 36 10.0 476.0 26.1MAIN 12-36 9.7 500.0 27.8 36 10.7 497.0 25.1SR 36-45 9.7 489.0 29.5 36 11.0 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.8 4.3 52.7 45 17.9 500.0 8.3SR 78-45 15.8 4.5 52.2 45 18.2 500.0 8.3MAIN 78-45 16.6 500.0 11.3 45 17.9 500.0 8.3