Title: Bytesteinen 1 - =514.202-FS001.pdf
MAIN 1,2-3,6 14.0 3.9 59.1 1,2 14.6 3.4 57.7SR 1,2-3,6 15.7 7.5 52.9 3,6 15.3 7.1 50.9MAIN 1,2-3,6 33.0 250.0 -2.8 1,2 33.3 250.0 -5.8SR 1,2-3,6 33.8 250.0 -2.8 1,2 35.0 250.0 -5.8PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 1,2 3.4 178.5 9.5SR 1,2 8.8 184.5 9.3MAIN 1,2 3.4 178.5 9.5SR 1,2 9.0 205.0 8.9Project: Bytesteinen 1 Untitled1Site: =514.202-FS001Test Summary: FAILModel: DTX-ELT Main S/N: 9862060 Remote S/N: 9862059 Main Adapter: DTX-CHA001 Remote Adapter: DTX-CHA00138.2 mLinkWare™ PC Version 10.4Cable ID: 521.202-UD022 Date / Time: 30/03/2021 10:32:02 Headroom 4.6 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]38.2 194 12 6.6