Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 10.06.2020 10:47R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 10.06.2020 10:50SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 10:12Z-LINEZ: 0.48ΩIsc: 483A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 10:12Zs(rcd)Z: 0.41ΩIsc: 566A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 10:13Tallberg Elektro A/S Tlf.22796640Side:10GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESNr.6969707071717272737374747575TEST RAPPORTResultatRCD tt: 64.1msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25V