Title: +038=310.000-NI024T_01-Innreg. protokoll OAR.xlsx
Ventil: Målt mengde Prosjektert Trykk. Strup. Type % avvik Kommentar: Kolonne1 Navn/nr. [L/s] [L/s] [kPa] Pos.nr.: Dim: Prosj./måling - Pareto plan 11 - 320.102 SV 111 Akse 3 A 0.21 0.193 3.66 3.66 DN 20 1.088083 320.102 SV 114 Akse 3 D 0.27 0.24 3.3 2.5 DN 25 1.125 370.101 SV 111 Akse 4 A 0.52 0.483 7.7 2.1 DN40 1.076605 370.101 SV 114 Akse 4 D 0.57 0.51 3.52 3.3 DN32 1.117647 - Pactum plan 10 - 320.102 SV 101 Akse 3 A 0.14 0.129 3.58 2.5 DN 20 1.085271 320.102 SV 104 Akse 3 D 0.156 0.15 3.66 2.6 DN 20 1.04 370.101 SV 101 Akse 4 A 0.39 0.36 3.41 2.6 DN32 1.083333 370.101 SV 104 Akse 4 D 0.57 0.51 3.52 3.3 DN32 1.117647 - Pareto plan Pareto 10 - 320.102 SV 102 Akse 8 A 0.14 0.129 3.58 2.5 DN 20 1.085271 320.102 SV 105 Akse 8 D 0.156 0.15 3.66 2.6 DN 20 1.04 370.101 SV 102 Akse 7 A 0.39 0.36 3.41 2.6 DN32 1.083333 370.101 SV 114 Akse 7 D 0.57 0.51 3.52 3.3 DN32 1.117647 - Pareto/Pecunia plan 10 - 320.102 SV 103 Akse 13 A 0.12 0.104 4.32 2.1 DN 20 1.153846 320.102 SV 106 Akse 13 D 0.14 0.119 4.73 2.4 DN 20