Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
[Pair 45] [Pair 45] [Pair 45]28.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.6 447.0 30.3 36 8.2 465.0 26.7SR 36-45 10.8 489.0 29.5 36 10.7 469.0 26.5MAIN 12-36 8.1 500.0 27.8 36 9.4 500.0 25.0SR 12-36 11.7 497.0 28.0 36 11.2 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.3 6.1 49.5 45 19.8 500.0 8.3SR 45-78 19.3 6.1 49.5 45 20.8 500.0 8.3MAIN 36-45 21.1 500.0 11.3 45 19.8 500.0 8.3SR 78-45 21.2 500.0 11.3 45 20.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 21.2 61.5 31.6 36 21.5 61.3 29.1SR 36-45 20.8 61.0 31.7 36 21.4 61.0 29.2MAIN 12-36 35.5 500.0 -12.4 36 36.9 500.0 -15.3SR 12-36 39.2 497.0 -12.2 36 38.7 497.0 -15.10804000250 MHz