Title: 1 etg del 2.pdf
Cable ID: T1052 Date / Time: 10/17/2013 02:57:59 PM Headroom 11.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]234 370 26 9.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.9 78.5 34.0 36 16.7 95.3 29.7SR 12-36 11.9 95.3 32.7 36 14.1 95.3 29.7MAIN 12-36 15.0 95.3 32.7 36 16.7 95.3 29.7SR 12-36 11.9 95.3 32.7 36 14.1 95.3 29.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.4 60.0 23.1 36 18.2 60.0 20.1