Title: Ahlsell.pdf
Cable ID: UD 29 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 10:28:48 AM Operator: Pam Headroom 6.8 dB (NEXT 1,2-7,8) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]35.6 176 4 5.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 1,2] [Pair 1,2] [Pair 1,2]24.9 500.0 43.8Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-7,8 11.5 5.9 61.5 1,2 12.6 5.9 59.2SR 1,2-7,8 6.8 301.0 34.0 7,8 8.3 292.0 31.6MAIN 3,6-4,5 13.6 491.0 26.9 3,6 15.6 489.0 24.1SR 1,2-7,8 9.6 496.0 26.8 7,8 10.9 476.0 24.510080604020NEXT (dB)