Title: +038=534.001-RA001._02-Porttelefon Siedle Systemanvisning.pdf
Where there are more than 20 backlit call buttons, an additional 12 V AC supply for instance TR 603-… must be installed due to the current consumption. To use the additional supply, remove the jumpers on the SATLM… connection board from b1/c1 to b/c and connect the terminals b/c of the call buttons directly to the additional supply. • Supply limits ATLC/NG 670-… (For detailed information, see page 19, 24) w) Separate power supply required. x) A separate potential-free switching input is required for each mail notification system. • You must configure each switching input in the Access administration interface. • You can run up to 7 mail notifica- tion systems with the fully extended system (1 ATLC and 3 ATLCEs).12710.4 Siedle Steel Code lock module (Digital call)SACMSATLMV1 V2 S1 S2 S3 S4 D1 D2ButtonsSCOMDevice requirementSiedle Steel SACM 673-... SATLM 670-... SCOM 611-...Remarkso)128Door release (Tö) 12 V AC/DC min. 20 OhmN L1ANG 600-...C A V 0 3 22324