Title: Hardware Installation Guide.pdf
An electronic access control system operated from commercial power shall be provided with standby power with capacity of 7 Ah or 18 Ah to support a full load for a period of 30 minutes (Class II), in the event of primary power loss.Front and rear tampers must be used. A visual and/or audible alarm shall be annunciated if the enclosure is tampered.All card readers must be evaluated by UL, must be ULC or cUL Listed, and be Wiegand compatible.This Class B digital apparatus complies with Canadian ICES-003.54 — revision 66Hardware Installation GuideEN Certified ReadersThe following readers are EN Security Grade 3 approved (Environmental Class III, EN50131-1, -3, EN50133-1) for use with the OnGuard system:AWID Sentinel Prox KP-6840GRMPBarantec Keypad LNL-826S121NNGuardall G-Prox II 111-8267PGuardall G-Prox II 111-8289PHID iCLASS 6100BKT0000LHID iCLASS 6120BGN0000LHID iCLASS 6125BKN0007-G3.0HID iCLASS 6130BKT000709GLHID iCLASS 6136AKN000709G3L