Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:39R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:39KONTINUITET R: >1999ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:17KONTINUITET R: >1999ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:17Tallberg Elektro A/S Tlf.22796640Side:46GODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESNr.321321322322323323324324325325326326327327328328TEST RAPPORTResultat R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13R LOW OhmR: 0.06ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:12R LOW OhmR: 0.16ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0Ω