Title: +038=433.002-FS019._10-Tavlebyggeren Eaton FDV.pdf
Rated switching capacity acc. to IEC/EN 60947-2kA6Rated switching capacity according to IEC/EN 61009kA6Rated fault currentIΔNA0.03TypeType ATrippingAnon-delayedProduct rangemRB6SensitivityPulse-current sensitiveImpulse withstand currentPartly surge-proof 250 AContact sequenceTechnicaldata Electrical StandardsIEC/EN 61009TrippingAnon-delayedRated operating voltageUeV AC230/400Rated frequencyfHz50Rated fault currentsIΔnmA30, 100, 300Rated non-tripping currentIΔno0.5 x I ∆nSensitivityDC and pulsed currentRated switching capacityIcnkA6Rated currentIeA6 - 25Rated impulse withstand voltageUimpkV4 (1.2/50 µs)CharacteristicB, C, DMaximum max. as short-circuit protective deviceA gL100Selectivity Class3LifespanSElectricalOperations> 4000MechanicalOperations> 20000Mechanical Standard front dimensionmm45Enclosure heightmm80Terminal protectionBusbar tag shroud to VBG4