Title: 32 Pumper modbuss teknisk data.pdf.pdf
CIU 260 is now ready to be accessed from a Modbus TCP master via a data connection, or via SMS commands.11.5 CIM 500 Modbus TCP communication setupStepAction1Install CIM 500 in the Grundfos E-pump according to the pump documentation.2Select position 1 at the protocol rotary switch. See section 7.2 Setting the Industrial Ethernet protocol.3Power on the E-pump, and observe LED2 turn permanently green and LED1 remaining off.4Complete the pump configuration, for example sensor configuration and selection of local Operating mode, local Control mode and local Setpoint, for example via Grundfos GO Remote.5Connect one of the CIM 500 Ethernet ports (RJ45) to a PC using an Ethernet cable.6Configure the PC Ethernet port to the same subnetwork as CIM 500, for example 192.168.1.1, and the subnet mask to 255.255.255.0. See sections 1.1 How to configure an IP address on your PC using Windows 7 and 1.2 How to configure an IP address on your PC using Windows 10 on page 51.7