Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Mote 6_1Motte 6_1DIALux Page 33Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Mete 6_1 / Results summary, EN 12464/ENTSKMgote 6_1 B il L X P e EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 6 Perpendicular illuminance (adaptive) [Ix] 491 (= 500) 418 532 0.85 0.79 Surrounding area: 0.500 m 2 Surrounding area 6 Perpendicular illuminance (adaptive) [Ix] 394 (= 300) 295 485 0.75 0.61 3 Background area 5 Perpendicular illuminance (adaptive) [Ix] 210 (= 100) 158 258 0.75 0.61Wall zone: 0.500 mThe results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 34Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Mate 6_1 / Visual task area 6 / Perpendicular illuminance (adaptive)Visual task area 6 / Perpendicular illuminance (adaptive)—_—RIWRGIRSAL