Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Isc: 205A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE043 06.02.2020 12:00R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩOBJEKT / Plan 10 / FUSE044 06.02.2020 14:41RCD II: 28.5mAUci: 0.1V t: 87.4ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE044 07.02.2020 12:57SPÆNDINGUln: 234V Ulpe: 233V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE044 07.02.2020 12:57Z-LINEZ: 1.72ΩIsc: 134A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATEST RAPPORTSide:16GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESMISLYKKESNr. 9999100100101101102102103103104104105105ResultatOBJEKT / Plan 10 / FUSE044 07.02.2020 12:58Zs(rcd)Z: 1.43ΩIsc: 161A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE044 06.02.2020 08:36R LOW OhmR: 0.50ΩR+: 0.5Ω R-: 0.5Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE045 06.02.2020 14:36