Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]26.2 113 1 3.93Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.5 451.0 30.2 36 7.2 461.0 26.9SR 12-36 10.0 461.0 29.7 36 9.4 461.0 26.9MAIN 36-78 8.9 497.0 28.0 36 7.9 497.0 25.1SR 12-36 10.3 497.0 28.0 36 9.8 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.0 500.0 11.3 45 20.8 500.0 8.3SR 45-78 20.2 495.0 11.3 45 20.4 500.0 8.3MAIN 78-45 20.0 500.0 11.3 45 20.8 500.0 8.3SR 45-78 20.2 495.0 11.3 45 20.4 500.0 8.30100806040200250 MHzACR-F (dB)