Title: +038=433.002-FS030._05-Eaton Tavlebyggeren Produktblad.pdf
(cid:129) -OL Types: Speciﬁ cally designed to fulﬁ ll the tripping characteristic requirements of I2  Iz in the Norwegian electrotechnical standard NEK 400-8-823.(cid:129) Pressing the test key “T” serves the only purpose of function testing theresidual current device (RCD). This test does not make earthing resistance measurement (RE), or proper checking of the earth conductor condition redun- dant, which must be performed separately.Accessories: Auxiliary switch for subsequent installationTripping signal switch for subsequent installation Shunt trip releaseZP-IHK ZP-WHK ZP-NHK ZP-ASA/..286052 286053 248437 248438, 2484394EATON CORPORATION xxxxx+xxxx-xxxxENCombined RCD/MCB Devices NdRBM, Technical DataLocal Indication RCDgreenSelf check (power ON) 2 sI  50% InredI = 30-50% InamberI  30% IngreenService Mode (measuring of residual current I) Pressing test button twice to activate Service-Modepress (0,1 - 0,4 s)release (0,1 - 0,4 s)press (0,1 - 0,4 s)