Title: +038=360.012-#####._06-BA-ESR NI-DV Controller Nicotra Gebhardt - Operating Instruction.pdf
The Modbus cable entry features 3-point strain relief, which must be used.3.4.10. Spring terminalsIf multi-core cables/leads are used, core sleeves/ end sleeves must always be used.The connectionterminals are spring loaded and the stripped wire can be easily inserted into the terminal by carefully pushing the wire into the terminal without using tools. Alternatively, the terminal loosened by spring can be pressing a screwdriver or similar implement. See fig. 3-9.itlightly withFig. 3-9: • Solid and multi-core cables/leads can be used. • Stripped wire ends or end sleeves must be between 8 and 15 mm. • Wires can be removed by carefully loosening the terminal spring bypressing lightly with a screwdriver or similar implement. See fig. 3-9BA-ESR_NI-DV 1.0 – 11/2015English3.4.11. Terminal and connector overviewFig. 3-103.4.12. Motor connectionThe motorcable must be connected to the terminals marked ”U”, ”V”, ”W” and ”PE”.