Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.10.03-UF066 Date / Time: 27-02-2020 22:13:57 Headroom 8.9 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]26.2 113 1 3.98Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.9 356.0 32.4 36 8.8 454.0 27.2SR 36-45 10.1 471.0 29.2 36 9.8 479.0 26.0MAIN 36-45 10.1 500.0 27.8 36 9.8 500.0 25.0SR 36-78 11.0 497.0 28.0 36 10.3 498.0 25.110080604020NEXT (dB)