Title: +038=370.001-RD001._01-Siemens Differanstrykk væske QBE3000-D6.pdf
Operating voltage QBE3100-D..DC 11...33 VPower consumpt. (at nom. pressure)<20 mAFrequency50 / 60 Hz at AC 24 VExternal supply line protectionFuse slow max. 10 AorCircuit breaker max. 13 ACharacteristic B, C, D according to EN 60898 orPower source with current limitation of max. 10 AOutput signalShort-circuit proof and proof polarity reversalQBE3000-D..DC 0...10 VWorking resistance> 10 kWQBE3100-D..DC 4…20 mAWorking resistancePower supply – 11 V≤ [Ohm]0.02 ADifferential pressure rangeRefer to "Type summary"Measuring elementCeramicMeasuring accuracyFactory calibratedSum of linearity, hysteresisand repeatability< ± 0.5 % FS(FS = Full Scale)Zero point, Full scale< ± 0.4 % FSTC zero point< ± 0.04 % FS / KTC sensitivity< ± 0.015 % FS / KLong-term stability DIN EN 60770± 0.5 % FSResolution0.1 % FSOverload on one side P1 / P2≤ 2 × nominal pressureSystem pressure at nom. pressure range(simultaneous P1 and P2)≤ 6 bar