Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Watchdog: This module can interact with the watchdog, if it is used on base address 240. In this case, the last input with address 255 cannot be used. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD3 components.6-96Analogue combined input/output modules, electrically isolated6.13Analogue combined input/output modules, electrically isolatedPCD3.W5254 inputs, 14 Bit, 0…10 V, 0(4)…20 mA, Pt1000, Pt500 or Ni1000 (selectable via DIP switch)and2 outputs, 12 Bit, 0…10 V or 0(4)…20 mA (selectable via software (FBox, FB)Galvanic separation of outputs to Saia PCD®, channels themselves not separatedI/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24?V are disconnected from the power supply.6-97PCD3.W5256.13.1PCD3.W525 analogue combined input/output module with electrical isolationGeneral information