Title: økernvn 94.pdf
50 MHz75100LinkWare Version 7.4Cable ID: D4205 Date / Time: 09/09/2013 02:53:57 Headroom 6.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]180 276 10 8.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]14.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.3 242.5 35.6 36 7.9 243.0 32.9SR 45-78 7.9 178.0 37.8 78 8.5 178.0 35.2MAIN 36-78 6.3 242.5 35.6 36 7.9 247.0 32.8SR 36-78 8.9 250.0 35.3 36 9.4 235.5 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)