Title: EDM_AQAR32_01-S-2GB.pdf
23.5 58.0 11.7 2 x 302 6.4 22 6.4 32 6.4 3150 156.0 46.1 3.39 A 4.92 194170 176.0 53.7 3.28 A 4.95 195123 362 276141 379 29319.220.00/45/55/100 0/38/62/100 66 / 10566 / 10527.2 39.1 19.1 4 x 3030.7 49.6 19.1 4 x 302 8.7 32 8.7 3EC2Air flow Rotational speed Power input each fan kWm³/h 41 300 Rpm 780 0.82 41 300 780 0.82 41 300 780 1.02 41 300 780 1.03 56 205 780 0.83 56 205 780 0.8WATER CONNECTIONS Type Inlet diameter Outlet diameter Type Inlet diameter Outlet diameterEvaporatorDesuperheaterinch inchinch inchMale gas threaded 2"1/2 2"1/2 Male gas threaded 1''1/4 1''1/42"1/2 2"1/21''1/4 1''1/42"1/2 2"1/21''1/4 1''1/42"1/2 2"1/21''1/4 1''1/42"1/2 2"1/21''1/4 1''1/42"1/2 2"1/21''1/4 1''1/4BUFFER TANK (OPTION) Volume DIMENSIONS Length without/with tank Width Height WEIGHT Operating weight (STD) ACOUSTICAL DATA Sound power level Sound pressure level (*)L300mm mm mmkg734dB(A) 81.7 dB(A) 49.8300300300300300