Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
W605: W615: W625: W605: W615: W625: ± 0.25 %, 100 ppm/K or 0.01 %/K yes (permanent) acc. to standards ENV 50141, EN 55022, EN 61 000-4-2, EN 61 000-4-4, EN 61 000-4-5 typ. 1 ms W605: typ. 0.3 ms W615: typ. 1 ms W615: 110 mA (typ. 80 mA) W605: 55 mA (typ. 45 mA) W615: 110 mA (typ. 80 mA) W625: 0 mA W605/W625: W615: 90 mA max. 90 mA, smoothed Voltage range: RL•20 mAAccuracy at 25°CTemperature error (0 … +55 °C) Short circuit protection: EMC protection:Time constant of output filter:Internal current consumption: (from +5 V bus)Internal current consumption: (from V+ bus) External current consumption:+ 10 … 20 V *e.g. RL=500 Ω → Ue = 20 … 30 VTerminals:RL=0 Ω → Ue=10 … 20 V Pluggable 14-pole spring terminal block (4 405 4998 0), for Ø up to 1.5 mm²,Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-75Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W6x5Connections6Digital/analogue values Output signals and type PCD2.W605 + 10.0 V + 5.0 V