Title: Installasjonsmanualer.pdf
4-1Normally open switch. Connect the switch between pin 4 and 5.4-2Normally close switch. Short the pin 4 and 5 and connect the switch between pin 3 and 4.1 2 3 4 5 6Close the switch for one second to stop the UPSX X - 2 T R T E N W R D 3 1 21 2 3 4 5 6Open the switch for one second to stop the UPSX X - 2 T R T E N W R D 3 1 210.5 WEB/SNMP CARD (OPTION)With this card installed, the UPS can be connected directly to a LAN (RJ45 ethernet) and controlled remotely from a WEB browser using TCP/IP protocol. Reference should be made to the dedicated literature for a full description of the functionalities.10.6 USE OF WARNING RELAY INTERFACEThis is an optional card (slot-mounted) that will manage 6 indication circuits with isolated contacts carrying information on the status of the UPS. The maximum voltage that can be applied to the contacts is 24 VDC, and the maximum current 500 mA.