Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 45-78 14.9 3.8 53.8 45 13.9 2.6 53.9SR 45-78 14.9 3.8 53.8 45 13.9 2.5 54.3MAIN 45-78 15.3 500.0 11.3 45 17.2 500.0 8.3SR 78-45 14.9 500.0 11.3 45 16.2 477.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 25.6 89.5 26.0 45 25.4 78.5 25.5SR 36-45 23.9 82.5 27.3 36 25.0 79.8 25.3MAIN 36-45 38.9 499.0 -12.3 36 39.1 497.0 -15.1SR 36-78 39.4 497.0 -12.2 36 39.4 497.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.3 447.0 8.0SR 12 6.0 496.0 8.0MAIN 45 6.3 447.0 8.0SR 12 6.0 496.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS