Title: Hardware Installation Guide.pdf
No valid manufacturing parameters3 Green, 0 RedThe manufacturing parameters which include the serial number, etc. are invalid. The module must be returned for repair.revision 6 — 277LNL-1100-U Input Control Module48MountingThe ICM can be mounted in the LNL-AL400ULX or LNL-AL600ULX-4CB6 and the LNL-CTX or LNL-CTX6 enclosure using the Universal Mounting Plate (UMP) LNL-CONV-U1.Mounting the ICM in the LNL-AL400ULX and LNL-CTX278 — revision 6Mounting the ICM in the LNL-AL600ULX-4CB6 or LNL-CTX6Hardware Installation Guiderevision 6 — 279LNL-1100-U Input Control Module49WiringWire inputs I1 through I16 (J9 - J16) using a twisted pair cable, 30 ohms maximum, 24 AWG minimum.Note:For UL installations, refer to section UL Listed Installations on page 286.ICM input wiringNote:For termination resistor values, refer to the Input Resistor Table on page 281.49.1Supervised (Software Configurable) Alarm Inputs