Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Grenseverdi: 1MQSPENDINGUln: 234VUlpe: 234VUnpe: 0Vf: 50.1HzR LOW Ohm GODKJENTR: 0.04QR+: 0.0QR: 0.0QGrenseverdi: 1.ZLINE GODKJENTZ: 0.49QIsc: 469ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AI GODKJENT28.5mAUci: 0.1Vt: 11.8msIdn: 30mAtype: ACN\,Ulim: 25VKONTINUITETR: 0.1QGrenseverdi: 1.0QZs(rcd) GODKJENTZ: 0.34QIsc: 681ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ATEST RAPPORTGODKJENTR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQR LOW Ohm GODKJENTR: 0.07QR+: 0.1QR: 0.1QGrenseverdi: 1.0QGODKJENTSikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AZs (red) GODKJENTZ: 0.53QIsc: 435ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AGODKJENT30mAtype: ACHN,Ulim: 25VKONTINUITET GODKJENTR: 0.1QGrenseverdi: 1.0QTEST RAPPORTil | R ISO GODKJENT | R: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQSPENDINGUln: 236VUlpe: 236VUnpe: 0V