Title: Aggregatkjøring.pdf.pdf
The controller has individual schedules for start, stop and normal/reduced/high airflow rate for each weekday as well as schedules for holidays. The controller has automatic summer-winter-time change over. Outside normal operating hours, free cooling is available according to settings.Cooling recoveryIf the extract air temperature is lower than the outdoor air temperature, and there is a cooling demand in the rooms, the cooling recovery will be activated. The heat exchanger signal is reversed to give increasing cooling recovery on increasing demand.Access rights - passwordsThere are 3 different user levels • End-user - (no password) - access to read values on the start page, see the flow diagram, possibilityto start/stop the unit, adjust the temperature setpoint and activate extended running.