Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]22.4 97 1 3.51Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]31.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.9 412.0 31.1 36 7.2 465.0 26.7SR 12-36 7.9 395.0 31.5 36 9.1 460.0 26.9MAIN 12-36 7.7 498.0 27.9 36 8.4 498.0 25.1SR 12-36 9.6 496.0 28.0 36 10.0 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.9 6.0 49.7 45 20.0 5.9 46.9SR 78-45 17.9 6.0 49.7 45 19.9 5.4 47.6MAIN 36-45 21.2 500.0 11.3 45 22.4 500.0 8.3