Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
DM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:36SPĆNDINGUln: 230V Ulpe: 230V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:37Z-LINEZ: 0.42ΩIsc: 552A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:37Zs(rcd)Z: 0.38ΩIsc: 606A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:38Tallberg Elektro A/S Tlf.22796640Side:10GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.7373747475757676777778787979TEST RAPPORTResultatRCD II: 28.5mAUci: 0.2V t: 15.2ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:39SPĆNDINGUln: 231V Ulpe: 231V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:39Z-LINEZ: 0.43Ω