Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]37.2 160 1 5.62Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 78] [Pair 78] [Pair 78]24.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.5 464.0 29.9 36 7.9 465.0 27.1SR 12-36 7.0 444.0 30.4 36 6.7 500.0 26.4MAIN 12-36 8.0 499.0 29.3 36 8.3 497.0 26.4SR 12-36 7.1 499.0 29.3 36 6.7 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 18.9 499.0 11.3 45 18.9 488.0 8.5SR 45-12 18.9 499.0 11.3 45 18.5 490.0 8.4MAIN 12-45 18.9 499.0 11.3 45 19.0 500.0 8.3