Title: datablad gb fx net alc.pdf
FX-ALCA: One addressable detection circuits, with 126 addresses FX-ALCB: Two addressable detection circuits, each 126 addresses FX-CLC: 16 Conventional detection circuits Max. 512 detectors and manual call points / panelFor each FX-ALCA or FX-ALCB: Power supply outputs (2 pcs), short circuit protected, 500mA eachClean contact signal inputs (4 pcs), function to be selected with the con- figuration toolFX-IOC (0 .. 4)Clean contact relay outputs (2 pcs), max 30 VDC/ 1.0 A, function to be selected with the configuration toolAlarm device lines (4 pcs), max 500 mA each, function to be selected with the configuration toolPower supply outputs (2 pcs), short circuit protected, 500mA eachPower supply outputs (2 pcs), short circuit protected, 4 A eachFX-PSB230 VAC / 50Hz / 160VABattery 24VDC (max 4 x (2 x 12V/17Ah))Note! The maximum total load of the panel is 4,5 AFXM NET panel external connectionsOptional serial (RS485) communication with other FX Net panelsFX-SAB/SAC