Title: Bytesteinen 1 - =514.202-FS001.pdf
MAIN 1,2-4,5 4.3 9.4 50.7 4,5 6.5 5.0 54.3SR 1,2-4,5 6.6 4.0 58.9 4,5 7.6 3.3 58.0MAIN 1,2-4,5 21.0 227.5 -0.3 4,5 25.3 247.5 -5.5SR 4,5-7,8 31.5 242.5 -2.0 4,5 32.1 244.5 -5.2PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 7,8 2.9 172.5 9.6SR 7,8 8.9 60.3 14.2MAIN 7,8 2.9 172.5 9.6SR 1,2 9.5 180.0 9.4Measurement is within the accuracy limits of the instrument.LinkWare™ PC Version 10.4Project: Bytesteinen 1 Untitled1Site: =514.202-FS001Cable ID: 521.202-UD024 Date / Time: 30/03/2021 10:33:42 Headroom 5.6 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]38.4 195 12 6.6Wire Map (T568B) FAILInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)