Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
0.7 x 106 operations 1.0 x 106 operations 0.3 x 106 operations 3) 0.1 x 106 operations 1)3)6Relay coil supply: 2)Voltage tolerance, dependent on ambient temperature:nominal 24 VDC smoothed or pulsed,9 mA per relay coil 20 °C: 17.0 … 35 VDC 30 °C: 19.5 … 35 VDC 40 °C: 20.5 … 32 VDC 50 °C: 21.5 … 30 VDCOutput delay:typically 5 ms at 24 VDCResistance to interference: acc. to IEC 801-4 Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption:4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 1 … 15 mA typ. 10 mA 0 mAmax. 32 mATerminals:Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²1) With external protective diode 2) With reverse voltage protection 3) These ratings are not UL-listedThe Annex, Section A.4 "Relay contacts" contains measurement details and suggested wiring for the relay contacts. For safe switching and a long service life, these figures must be observed.