Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 36,1 68,0 187,0 10,0 6,4Limit 100,0 - 555,0 50,0 25,0Margin 63,9 - 368,0 40,0 18,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 1,90Worst Value: Local: 36 15,5 43,6 28,1 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 24,4 15,3 9,1 74,75Remote: 12 15,5 8,0 7,5 500,00Worst Value: Local: 12 18,3 9,2 9,1 305,00Remote: 12 15,5 8,0 7,5 500,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: Pass