Title: +038=432.001-UX002T_01-Eaton-DS-147397-NZMN2-4-VE160-BT-20190730 Eaton Produktblad.pdf
DATASHEET - NZMN2-4-VE160-BTCircuit-breaker, 4p, 160A, box terminals, selectivity protectionPart no. Catalog No.NZMN2-4-VE160-BT 147397EL-Nummer (Norway)4358842Similar to illustrationDelivery program Product rangeCircuit-breakerProtective functionSystems, cable, selectivity and generator protectionStandard/ApprovalIECInstallation typeFixedRelease systemElectronic releaseConstruction sizeNZM2DescriptionR.m.s. value measurement and “thermal memory” Adjustable time delay setting to overcome current peaks tr at 6 x Ir also inﬁnity (without overload releases) Adjustable delay time tsd 2 t constant function: ﬁxed OFFi Set value in neutral conductor is synchronous with set value Ir of main pole.Number of poles4 poleStandard equipmentBox terminalSwitching capacity400/415 V 50 HzIcukA50Rated current = rated uninterrupted currentRated current = rated uninterrupted currentIn = IuA160Neutral conductor% of phase conductorCSA100Setting range