Title: økernvn 94.pdf
MAIN 12-36 11.5 38.5 37.4 12 12.9 33.3 36.8SR 12-36 11.9 38.3 37.5 12 13.2 33.3 36.8MAIN 12-36 20.6 249.5 4.7 36 20.1 249.5 2.1SR 36-45 20.1 246.5 5.0 36 20.3 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.1 30.4 18.6SR 45 3.8 30.3 18.6MAIN 36 7.9 223.0 10.5SR 36 5.8 223.0 10.5010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94