Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
24.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.8 500.0 29.2 36 8.4 500.0 26.4SR 36-45 7.7 483.0 29.6 36 7.9 486.0 26.7MAIN 36-45 7.8 500.0 29.2 36 8.4 500.0 26.4SR 36-45 7.8 486.0 29.5 36 8.0 492.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 13.6 382.0 13.6 45 13.5 2.3 55.2SR 45-78 13.7 382.0 13.6 45 13.4 2.6 53.9MAIN 78-45 14.6 430.0 12.6 45 15.3 426.0 9.6SR 45-78 14.1 408.0 13.0 45 15.5 413.0 9.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 24.1 47.0 35.2 45 24.2 31.8 37.7SR 36-45 21.7 31.5 40.2 45 21.0 31.8 37.7MAIN 36-45 32.0 500.0 -12.4 36 32.6 500.0 -15.3SR 36-45 32.6 500.0 -12.4 36 32.5 500.0 -15.30804000250 MHzACR-N (dB)