Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF039 16C2/003 05.11.2020 11:31R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 28.10.2020 14:12SPĆNDINGU12: 234V U1pe: 0V U2pe: 234V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 28.10.2020 14:12Z-LINEZ: 0.39ΩIsc: 585A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 222A Isc(0.76%): 445A Isc(1.15%): 673ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 28.10.2020 14:13Tallberg Elektro A/S Tlf.22796640Side:21GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.141141142142143143144144145145146146TEST RAPPORTResultatZs(rcd)Z: 0.30ΩIsc: 768A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF040 16C2/003 28.10.2020 14:14RCD II: 28.5mA