Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Temperature error: Burst protection: (IEC 801-4) Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption:) Factory setting 8 bits (0..0.255) < 5 µs ≥ 3 kΩ for 0…10 V: 0…500 Ω for 0…20 mA: 0…500 Ω for 4…20 mA: 1% ± 50 mV for 0…10 V: 1% ± 0.2 mA for 0…20 mA: 1% ± 0.2 mA for 4…20 mA: < 15 mV pp for 0…10 V: < 50 µA pp for 0…20 mA: for 4…20 mA: < 50 µA pp typ. -.2% (across temperature range 0…+55 °C) ± 1 kV, with unshielded cables ± 2 kV, with shielded cables 1 mA 30 mA max. 0.1 A (type PCD3.W410 only, for current outputs)) Factory setting 8 bits (0..0.255) < 5 µs ≥ 3 kΩ for 0…10 V: 0…500 Ω for 0…20 mA: 0…500 Ω for 4…20 mA: 1% ± 50 mV for 0…10 V: 1% ± 0.2 mA for 0…20 mA: 1% ± 0.2 mA for 4…20 mA: < 15 mV pp for 0…10 V: < 50 µA pp for 0…20 mA: for 4…20 mA: < 50 µA pp typ. -.2% (across temperature range 0…+55 °C) ± 1 kV, with unshielded cables ± 2 kV, with shielded cables 1 mA 30 mA max. 0.1 A (type PCD3.W410 only, for current outputs)