Title: 563-Beckhoff-buskobler BK1150.pdf
Bus interface2 x RJ 45Power supply24 V DC (-15 %/+20 %)Input current70 mA + (total K-bus current) /4, 500 mA max.Starting currentapprox. 2.5 x continuous currentRecommended fuse≤ 10 ACurrent supply K-bus2,000 mAPower contacts24 V DC max./10 A max.Electrical isolation500 V (power contact/supply voltage/Ethernet)Distance between stations100 m (100BASE-TX)Dimensions (W x H x D)44 mm x 100 mm x 68 mmWeightapprox. 110 gOperating/storage temperature25…+60 °C/-40…+85 °CRelative humidity95 %, no condensationVibration/shock resistanceconforms to EN 60068-2-6/EN 60068-2-27EMC immunity/emissionconforms to EN 61000-6-2/EN 61000-6-4Protect. class/installation pos.IP 20/variableBECKHOFF New Automation TechnologyWe reserve the right to make technical changes.AccessoriesKS2000configuration software for extended parameterisationCordsetscordsets and connectorsFC90xx-00xxPC Fieldbus Cards with PCI interfaceOrdering informationDescription