Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
OBJEKT / Plan 10 / FUSE040 07.02.2020 09:21KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE040 07.02.2020 09:24R LOW OhmR: 0.37ΩR+: 0.4Ω R-: 0.4Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE040 07.02.2020 09:24SPÆNDINGUln: 232V Ulpe: 232V Unpe: 2V f: 49.9HzOBJEKT / Plan 10 / FUSE040 07.02.2020 09:25Z-LINEZ: 0.98ΩIsc: 234A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE040 07.02.2020 09:28TEST RAPPORTSide:12GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.747475757676777778787979ResultatZs(rcd)Z: 0.83ΩIsc: 278A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE040 07.02.2020 09:29RCD II: 28.5mAUci: 0.1V t: 83.7ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE040 10.02.2020 09:05SPÆNDINGUln: 226V Ulpe: 228V Unpe: 2V f: 49.9Hz