Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 12] [Pair 12] [Pair 12]26.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.6 473.0 29.8 36 8.9 488.0 26.6SR 36-45 9.0 485.0 29.5 36 9.3 497.0 26.4MAIN 12-45 8.6 473.0 29.8 36 9.0 500.0 26.4SR 36-45 9.2 500.0 29.2 36 9.3 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.5 479.0 11.6 45 14.8 8.4 43.8SR 78-45 14.5 479.0 11.6 45 14.7 4.5 49.2MAIN 45-78 14.5 479.0 11.6 78 15.3 479.0 8.6SR 78-45 14.5 479.0 11.6 78 15.4 485.0 8.50100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 22.6 54.8 33.2 45 22.4 46.8 32.8SR 45-78 21.2 45.3 35.7 45 21.9 46.3 33.0MAIN 36-45 36.9 500.0 -12.4 36 36.2 500.0 -15.3SR 36-45 36.3 500.0 -12.4 36 36.3 497.0 -15.10804000250 MHz