Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
CN16FMFan motorGNDFSFlow switch22Y/GBLUHPHigh pressure protectionHPHPBRNLPLPFSFSITInlet water temperature3230VK1Relay of compressorTCLPLow pressure protectionHPFSLP12VControllerOTOutlet water temperatureTCTransformer4V4-way valveP20/P307813Technical data ModelP10P15P20P30Heat output1kW3.04.26.68.3Heating capacity2m35-1510-3530-4540-60Input powerkW0.730.971.471.94Operating voltageV~50Hz230V 1NOperating current3A3.34.26.49.0Fuse size, Type CA10164.14.34.54.3COPRefrigerant quantity (R32)kg0.270.40.530.58CompressorRotary compressorExpansionCapillary tubeHeat exchangerTitanium heat exchangerFan motorAC motorCabinetGrey painted steel cabinetNoise level (at 1 m)dB(A)49515354Water connectionmm50 mmm3/h1.52.33.04.5