Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.0 143 2 4.98Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.3 493.0 29.4 36 8.4 494.0 26.5SR 36-45 7.8 495.0 29.3 45 8.3 495.0 26.5MAIN 36-45 9.4 500.0 29.2 36 8.5 500.0 26.4SR 36-45 7.8 495.0 29.3 45 8.3 495.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.5 483.0 11.6 45 13.5 2.3 55.2SR 78-45 14.5 488.0 11.5 45 13.5 2.3 55.2MAIN 45-78 14.7 500.0 11.3 78 15.1 500.0 8.3SR 78-45 14.6 500.0 11.3 45 15.2 500.0 8.30100806040200250 MHzACR-F (dB)