Title: 4. Leieavtaler.pdf
2015-01-07: Based on infonnation given during the meeting this will not be a problem. Details/calculations will be sent later for review by FM Global.5. Seal all openings in fire-rated floors and walls through which pipes, wires, and cables pass with an FM Approved or listed penetration seal with a fire -resistance rating equivalent to the rating of the wall or floor.20IS-01-07: Information regarding suppliers of FM-Approved penetration seals has been sent to the client. This is not foreseen to be a problem. Details wilt be sent later for review by FM Global.6. Where possible, install non-combustible or FM Approved rooflights/skylights. If plastic, install less combustible plastic materials such as polycarbonate, polyethylene terephthalate or polyvinyl chloride in accordance with FM Global Loss Prevention Data Sheet 1-57, Plastics in Construction, Section 2.6.