Title: 91290FDV Campus F13 433.04 West elektro.pdf
Does not apply, since the entire switchgear needs to be evaluated.Meets the product standard's requirements.Does not apply, since the entire switchgear needs to be evaluated.Meets the product standard's requirements.Does not apply, since the entire switchgear needs to be evaluated.Does not apply, since the entire switchgear needs to be evaluated.Is the panel builder's responsibility.Is the panel builder's responsibility.Is the panel builder's responsibility.Is the panel builder's responsibility.Is the panel builder's responsibility.The panel builder is responsible for the temperature rise calculation. Eaton will provide heat dissipation data for the devices.4 / 1010.11 Short-circuit ratingIs the panel builder's responsibility. The speciﬁcations for the switchgear must be observed.10.12 Electromagnetic compatibilityIs the panel builder's responsibility. The speciﬁcations for the switchgear must be observed.10.13 Mechanical function