Title: Hydrauliske beregninger sprinkler Kontorer plan 3 78m².pdf
78.91755001001.00.112012080.034631065.356.641[kg/m³][kg/ms x 10e-6][m²]H = 193.7 [m]H = 204.2 [m][mbar][mbar][l/min][mbar][l/min][l/min]UnitPropertyInaccuracy of the pressure:Inaccuracy of the flow:Total area of coverage:Average area of coverage:Flow density at the weakest sprinkler:Average density of 4 weakest sprinklers:Four weakest sprinklers:Average flow density:Number of sprinklers:Average sprinkler height:Sprinkler results: Kontorer plan 3 78m²LevelNodeProduct3. Etasje56 CU/P-15-K80-68DGR-QR3. Etasje65 CU/P-15-K80-68DGR-QR3. Etasje67 CU/P-15-K80-68DGR-QR3. Etasje69 CU/P-15-K80-68DGR-QR3. Etasje71 CU/P-15-K80-68DGR-QR3. Etasje73 CU/P-15-K80-68DGR-QR3. Etasje75 CU/P-15-K80-68DGR-QR3. Etasje79 CU/P-15-K80-68DGR-QR3. Etasje81 CU/P-15-K80-68DGR-QR3. Etasje83 CU/P-15-K80-68DGR-QR3. Etasje85 CU/P-15-K80-68DGR-QR3. Etasje87 CU/P-15-K80-68DGR-QR3. Etasje89 CU/P-15-K80-68DGR-QR