Title: Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.pdf
6.3 m³/h4.1 kgVUE025F300DN 2510 m³/h4.7 kgVUE032F300DN 3216 m³/h7.3 kgVUE040F300DN 4022 m³/h8.6 kgVUE050F300DN 5028 m³/h11.2 kgVUE050F200DN 5040 m³/h11.2 kgAccessoriesTypeDescription0372240001Manual adjustment for valves with 8 mm stroke0372249001Adaptor required when temperature of the medium is 100...130 °C (recommended for tempera- tures < 10 °C) DN 15...500372249002Adaptor required when temperature of the medium is >130 up to 150 °C, DN 15...500378284100Stuffing box heater 230V~, 15 W for medium below 0 °C0378284102Stuffing box heater 24V~, 15 W for medium below 0 °C0378368001Complete replacement stuffing box for DN 15...50Combination of VUE with electric actuators/ Warranty: The technical data and pressure differences indicated here are applicable only in com- bination with SAUTER valve actuators. The warranty does not apply if used with valve actuators from other manufacturers.