Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
25.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 499.0 29.3 36 8.1 500.0 26.4SR 36-45 6.2 488.0 29.5 36 7.6 475.0 26.9MAIN 12-36 7.7 500.0 29.2 36 8.1 500.0 26.4SR 36-45 6.2 488.0 29.5 36 7.9 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.8 6.3 49.3 45 19.9 500.0 8.3SR 78-45 18.5 456.0 12.1 45 20.3 456.0 9.1MAIN 78-45 19.6 500.0 11.3 45 19.9 500.0 8.3SR 78-45 18.5 456.0 12.1 45 20.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.0 37.0 38.3 36 22.8 40.5 34.7SR 36-78 22.8 40.5 37.1 36 23.2 40.5 34.7MAIN 12-36 33.1 500.0 -12.4 36 33.6 500.0 -15.3SR 36-45 31.2 488.0 -11.6 36 33.3 499.0 -15.20804000250 MHzACR-N (dB)