Title: etg u1.pdf
148 235 17 6.3148 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.4 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.7 * 248.5 35.4 36 1.1 246.5 32.8SR 36-450.8 *248.5 35.4 36 2.3 243.5 32.9MAIN 36-45 0.7 248.5 35.4 36 1.1 246.5 32.8SR 36-45 0.8 248.5 35.4 36 2.3 243.5 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 19.8 178.5 19.2 45 20.4 4.6 47.9SR 45-12 19.8 183.5 18.9 45 20.2 4.6 47.9MAIN 45-12 20.7 237.0 16.7 45 22.4 246.5 13.4SR 45-12 20.8 238.5 16.6 45 22.1 246.5 13.4010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz