Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
conditions are met, e.g. photoelectric barrier coveredCounting with recognition of count direction for incremental shaft encoders providing simple motion controlCounting with recognition of count direction for incremental shaft encoders providing simple motion controlTechnical dataNumber of systems: Counting range: Counting frequency: Data protection:1 0…65,535 (16 bit) (can be extended with CPU counters) max. 20 kHz (at pulse/pause ratio 50%) All data in this module are volatile (non-volatile Saia PCD® registers are available).Digital inputs “IN-A” and “IN-B” signal voltages:Input current: Input filer: Process output Counter controlled output CCO: Current range:Nominal voltage: 24 VDC “low” range: “high” range: typically 7.5 mA 25 kHz30…+5 V +15…30 V for source operationcounter output (switches when count is 0 or 65,535) 5…500 mA(max. current leakage 1 mA) (min. load resistance 48 Ω in voltage range 5…24 V).