Title: 330-Strømningsvakt.pdf
UL, CUL and CSFM Listed, FM Approved, LPCB Approved, CE Marked (EN12259-5), VdS Approved Service Pressure: 31 BAR (450 PSI) - UL Flow Sensitivity Range for Signal: 15-38 LPM (4-10 GPM) - UL 30-57 LPM (8-15 GPM) - VdS No Signal below 1- LPM (2.6 GPM) - VdS 0.2 BAR (3 PSI) max. at 5 m/s (DN50-100) 0.007 BAR (1 PSI) max. at 5 m/s (DN150-200)Pressure Loss:Maximum Surge: 5.5 m/s (18 FPS) Contact Ratings:Two sets of SPDT (Form C) 10.0 Amps at 125/250 VAC 2.0 Amps at 30VDC Resistive 10 mAmps min. at 24 VDCConduit Entrances: Two knockouts provided for 1/2" conduit. Environmental Specifi cations:NEMA 4/IP54 Rated Enclosure suitable for indoor or outdoor use with factory installed gasket and die-cast housing when used with appropriate conduit fi tting.NEMA 4/IP54 Rated Enclosure suitable for indoor or outdoor use with factory installed gasket and die-cast housing when used with appropriate conduit fi tting.Temperature Range: 4.5°C - 49°C (40°F - 120°F) - UL 1°C - 68°C (34°F - 154°F) - VdS