Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
14 bit differential 4 yes, 500 V yes, 500 V no two cables per channel using DIP switches ± 0.2% max. ± 0.05% max. ± 70 ppm/°C ± 50 V min. ± 35 mA min. ± 50 V min. 70 dB min.2 ms 40 dB min. between 49.5 and 50.5 Hz 40 dB min. between 59.5 and 60.5 Hz14 Bit; 0.61 mV per LSB125 Ω 14 Bit; 1.22 µA per LSB 13.7 Bit; 1.22 µA per LSB0.1 °C 0.2 °C 0.1 °C 0,2 Ω 2.5 mW max.6-101PCD3.W525Outputs General: Resolution: Number of channels: Galvanic separation of the Saia PCD®: Galvanic separation of external supply: Galvanic separation between channels: Type of connections:12 bit 2 yes yes no two cables per channelConfiguration of operating mode: Accuracy at 25°C: Repeat accuracy: Temperature drift (0…55°C) max.: Overcurrent protection: Time constant for filter: Voltage mode: Max. load to maintain specified accuracy: Resolution range 0 … 10 V:using software (FBOX, FB) ± 0.5% max. ± 0.1% max. ± 70 ppm/°C short circuit protected 1 ms> 700 Ω 12 Bit; 2.44 mV per LSB