Title: Hardware Installation Guide.pdf
For best results, run the cable in an individual conduit with at least 12 inches distance from the AC power, computer data cables, and cables for electrical locking devices.Use recommended cable. Do not use any unshielded “twisted pair” type cable.Use the largest wire gauge possible.Use dedicated and linearly regulated power supply, where applicable.Use Single Point Grounding (Earthing). Do not use ground loops.101.2.1General Wiring RequirementsAll the reader wiring must be continuously shielded. Use 22 AWG up to 18 AWG, six or seven-conductor shielded cables. Longer distances and higher current consumption on the power supply line will require larger gauge wires.101.2.2Power