Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
R+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF034 16C2/003 05.11.2020 12:36SPĆNDINGU12: 234V U1pe: 234V U2pe: 0V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF034 16C2/003 05.11.2020 12:36Z-LINEZ: 0.70ΩIsc: 329A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 125A Isc(0.76%): 250A Isc(1.15%): 378ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF034 16C2/003 05.11.2020 12:36Tallberg Elektro A/S Tlf.22796640Side:15GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.103103104104105105106106107107108108TEST RAPPORTResultatZs(rcd)Z: 0.65ΩIsc: 353A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF034 16C2/003 05.11.2020 12:37RCD II: 28.5mAUci: 0.2V t: 17.6ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF034 16C2/003 06.11.2020 13:20R ISOR: >200MΩ Um: 263V