Title: økernvn 94.pdf
Cable ID: T3189 Date / Time: 09/11/2013 06:09:25 Headroom 2.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]107 166 9 4.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]20.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.0 189.5 37.3 36 7.9 239.5 33.0SR 12-36 2.8 216.5 36.4 36 3.4 217.0 33.7MAIN 12-36 7.9 239.0 35.7 36 7.9 239.5 33.0SR 12-36 2.8 216.5 36.4 36 3.6 249.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.4 235.0 16.8 12 15.1 2.4 53.7