Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]43.3 186 1 6.19Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]22.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.6 455.0 30.1 36 6.6 500.0 26.4SR 36-45 8.4 498.0 29.3 36 7.9 499.0 26.4MAIN 12-36 6.9 500.0 29.2 36 6.6 500.0 26.4SR 36-45 8.4 498.0 29.3 36 7.9 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.5 500.0 11.3 45 18.9 500.0 8.3SR 78-45 17.4 488.0 11.5 45 19.1 500.0 8.3MAIN 78-45 17.5 500.0 11.3 45 18.9 500.0 8.3SR 78-45 17.5 500.0 11.3 45 19.1 500.0 8.30100806040200250 MHzACR-F (dB)