Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
241241242242243243244244245245TEST RAPPORTResultat R LOW OhmR: 0.30ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF046 C16/2 12.06.2020 12:14KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF047 C16/2 10.06.2020 11:25R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF047 C16/2 11.06.2020 15:31SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.1HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF047 C16/2 11.06.2020 15:49Z-LINEZ: 0.42ΩIsc: 544A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF047 C16/2 11.06.2020 15:50Zs(rcd)Z: 0.36ΩIsc: 647A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF047 C16/2 11.06.2020 15:50RCD II: 28.5mAUci: 0.2V t: 25.4ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF047 C16/2 11.06.2020 15:52Tallberg Elektro A/S Tlf.22796640Side:36