Title: +175=574.001_OE001_Manual - Varmemåler M3 - Løs fra rør.Produktinformasjon.pdf
Confirm the selected parameter by holding the T2 button for more than 3 seconds, thus moving to the next parameter.4) The fourth parameter that has be configured is the update of the consumption data reported on the C1 hot/cold water meter dial. Select the digit using the T2 button and change the single numbers with the T1 button.Confirm the selected parameter by holding the T2 button for more than 3 seconds, thus moving to the next parameter.Hydrosplit M3 Manuale utente – User manual - v1.6.5_ITA_ENG425) The fifth parameter that has be configured is the enabling/disabling of the anti-tampering contact of the C1 cold/hot water meter. By using the T1 button, proceed with the enabling [1] or disabling [0].Confirm the selected parameter by holding the T2 button for more than 3 seconds, thus moving to the next parameter.6) The sixth parameter that has be configured is the pulse value "k" of the C2 cold/hot water meter.