Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 15,2 8,0 7,2 460,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 30,1 26,7 3,4 499,00Remote: 36-45 30,1 26,7 3,4 498,00Worst Value: Local: 36-45 30,1 26,7 3,4 499,00Remote: 36-45 30,1 26,7 3,4 498,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 22,4 12,1 10,3 402,00Remote: 12-45 21,8 12,1 9,7 400,00Worst Value: Local: 36-12 22,1 11,5 10,6 430,00Remote: 12-45 21,8 12,1 9,7 401,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,6 23,8 4,8 499,00Remote: 36 28,8 23,9 4,9 496,00Worst Value: Local: 36 28,6 23,8 4,8 499,00Remote: 36 28,7 23,8 4,9 498,00