Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]35.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.7 457.0 29.9 36 6.7 461.0 26.9SR 36-45 6.7 472.0 29.2 36 7.3 500.0 25.0MAIN 36-45 7.2 492.0 28.2 36 7.3 500.0 25.0SR 36-45 7.1 492.0 28.2 36 7.3 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.5 9.8 45.5 45 21.0 6.6 45.8SR 45-78 19.5 9.8 45.5 45 21.0 6.1 46.5MAIN 12-36 22.2 473.0 11.7 12 24.4 496.0 8.3SR 12-36 22.8 496.0 11.3 12 23.2 463.0 8.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 35.0 262.0 5.7 36 37.2 261.0 3.1SR 12-36 35.7 261.0 5.8 36 37.9 261.0 3.1MAIN 36-45 41.4 492.0 -11.9 36 41.6 500.0 -15.3