Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]26.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.1 477.0 29.7 45 9.0 475.0 26.9SR 36-45 7.6 489.0 29.5 36 7.4 481.0 26.8MAIN 12-45 8.1 477.0 29.7 36 9.3 500.0 26.4SR 36-45 7.7 490.0 29.4 36 7.7 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-78 15.8 474.0 11.7 45 14.6 2.5 54.3SR 78-36 15.8 474.0 11.7 45 14.6 2.6 53.9MAIN 36-78 15.8 474.0 11.7 45 16.8 500.0 8.3SR 78-36 16.1 492.0 11.4 78 17.2 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.4 44.5 35.9 45 20.6 44.0 33.6SR 45-78 21.4 43.0 36.4 78 21.3 42.5 34.1MAIN 12-45 35.7 500.0 -12.4 12 36.1 500.0 -15.3