Title: 2 etg del2.pdf
Cable ID: T2016 Date / Time: 10/11/2013 08:17:58 AM Headroom 5.0 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]83 127 5 3.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.0 244.0 35.5 36 6.2 240.5 33.0SR 36-78 7.6 115.0 40.9 36 8.4 207.5 34.1MAIN 36-78 5.0 244.0 35.5 36 6.2 244.5 32.9SR 12-36 8.2 240.0 35.6 36 8.7 240.0 33.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.4 6.6 47.8 12 18.7 3.5 50.3