Title: Ø94, Medistim - innregulering ventilasjon, avtrekk sjakt 1.pdf
AVTREKK MÅLEPROTOKOLLANLEGG:SYSTEM NR.:PLAN:ETGROM/GRENNR. 1 1 1 1 1 1 1 1 1 1NAVN/NR A1 A2 A3 A4 A5 A6 A7 A8 A9 A10SUMANMERKNINGERLUFT KONTROLLØKERNVEIEN 94 Sjakt 1 1 ETGDATO:FREKVENS / TRYKK:SIGNATURKANALPROSJEKTERTMÅLTFORHOLDTempØ.DIM.[m3/h] 600 600 410 150 500 100 100 100 100 540[m3/h] 650 645 435 160 550 109 108 110 110 590[%] 108 % 108 % 106 % 107 % 110 % 109 % 108 % 110 % 110 % 109 %C32003467108 %12.03.2013H.BANMERKNING