Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,6 25,3 3,3 452,00Remote: 36 28,4 23,8 4,6 500,00Worst Value: Local: 36 27,9 23,8 4,1 498,00Remote: 36 28,4 23,8 4,6 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,6 61,2 11,4 1,00Worst Value: Local: 12 20,1 8,3 11,8 439,00Remote: 12 71,6 61,2 10,4 1,00Remote: 12 20,7 8,4 12,3 434,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:07Signature:______________________ Page: 90Copper Certification ReportCable Label: 521.002-UD-209 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:21:38 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software: