Title: V20-06-02 VVS-anlegg plan 6 - DM3-1.pdf
WISE RTA WISE IAQMøterom 6-1310 0 4 Ø T 1 0 0 Q Sh/ ³m 0 8 6 1 Q:28mm28mm370.101: 35 mm +c 2790 370.101: 35 mm +c 279042mm42mm370.101: 28 mm +c 2790370.101: 28 mm +c 2790370.101: 28 mm +c 2790 370.101: 28 mm +c 2790STAP/STAD DN20LD007T Maks:200 m³/h Kjøling: 435 W 0.034 L/s Varme: 465 W 0.011 L/s+06 = 320.102 - OE 064 0.117 L/s+06 = 370.101 - OE 064 0.502 L/sOpp/ned 370.101: DN 100mm 370.101: DN 100mmLD007T Q:140 m³/h Kjøling: 350 W 0.028 L/s Varme: 410 W 0.010 L/sLD007T Q: 200 m³/h Varme: 410 W 0.010 L/sLD007T Q: 200 m³/h Varme: 410 W 0.010 L/sLD007T Maks:200 m³/h Kjøling: 315 W 0.025 L/s Varme: 410 W 0.010 L/sOpp/ned 320.102: 54mm 320.102: 54mmSTAP/STAD DN323456Kombibaffler-Produktliste, Plan 06System ProduktkodeProduktVersjonPlanStk.ProduktPlan 06 WISE RTA 06 WISE IAQ 06 WISE RTS 06 WISE director (trådløs router)Romregulering - Plan 06ProduktBørverdiomstiller CO2-, RH- og temperaturgiver Temperaturgiver Wise Director router