Title: 360.002 - Tilluft.pdf.pdf
Lp [dB]LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeBEND-15DUCTBEND-90DUCT155 T-BRANCHDUCTSILENCERDUCTBEND-90DUCTProductSizeMAGIB-C4-*-*250250MAGIB-C4-*-*250250TCPU_DK-*-*0,0 250/200200LKR-200-1200200200MAGIB-C4-*-*200200L [m]2,70,81,70,21,5Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]7204,10,6 Sound in:Attenuation: Addition:7204,12,4 Sound in:Attenuation: Addition:7204,13,0 Sound in:Attenuation: Addition:7204,10,7 Sound in:Attenuation: Addition:7204,110,8 Sound in:Attenuation: Addition:Dividing:3002,70,9 Sound in:Attenuation: Addition:3002,72,5 Sound in:Attenuation:3002,70,1 Sound in:Attenuation: Addition:3002,71,4 Sound in:Attenuation: Addition:3002,70,8 Sound in:Attenuation: Addition:5563 [dB]32.90.0 +22.633.30.3 +22.633.40.0 +33.336.4