Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]29.2 127 2 4.45Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.1 497.0 29.3 36 6.2 477.0 26.8SR 36-45 7.2 498.0 29.3 36 7.0 497.0 26.4MAIN 36-45 7.1 497.0 29.3 36 6.4 497.0 26.4SR 36-45 7.2 498.0 29.3 36 7.0 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.6 466.0 11.9 45 16.5 3.3 52.0SR 78-45 16.3 466.0 11.9 45 16.5 3.3 52.0MAIN 78-45 16.8 493.0 11.4 45 17.8 500.0 8.3SR 78-45 16.6 500.0 11.3 45 16.8 500.0 8.30100806040200250 MHzACR-F (dB)