Title: 32 Pumper modbuss teknisk data.pdf.pdf
Confirm that the GENIbus LED is permanently green and that the Modbus LED is either off, if no master is actively polling the slave, or flashing green, indicating error-free communication.CIM 200 is now ready to be accessed via the Modbus network.11.2 Hardware setup, CIU 200StepAction1Complete the pump configuration, for example sensor configuration and local mode. This can be done either via Grundfos GO Remote or Grundfos PC Tool E-Products.2Select the Modbus slave address (1-247).3Select the transmission speed of the Modbus slave.4Select parity and stop bits of the Modbus slave, even parity with 1 stop bit or no parity with 2 stop bits.5If necessary, set line termination.6Connect the GENIbus cable from CIU 200 to the E-pump.7Connect the necessary cables from CIU 200 to the Modbus network.8Connect the power cable to CIU 200, and switch the unit on.9