Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]23.1 100 1 3.47Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.4 457.0 29.9 36 7.7 457.0 27.1SR 36-45 7.0 467.0 29.4 36 7.4 498.0 25.1MAIN 36-45 9.0 498.0 27.9 36 8.2 498.0 25.1SR 36-45 7.2 498.0 27.9 36 7.4 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.1 6.9 48.5 45 21.7 500.0 8.3SR 45-78 20.1 7.1 48.2 45 21.6 500.0 8.3MAIN 78-45 21.0 500.0 11.3 45 21.7 500.0 8.3SR 45-78 21.1 499.0 11.3 45 21.6 500.0 8.30100806040200250 MHzACR-F (dB)