Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-45 16.1 475.0 11.7 45 16.3 478.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.7 42.8 36.4 36 25.2 39.5 35.0SR 36-45 22.7 39.3 37.5 36 23.8 39.3 35.1MAIN 36-45 34.3 500.0 -12.4 36 34.2 500.0 -15.3SR 36-45 33.9 494.0 -12.0 36 34.6 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.5 495.0 8.0SR 12 6.2 466.0 8.0MAIN 45 7.5 495.0 8.0SR 12 6.2 466.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00435.3 m60Insertion Loss (dB)504030201000250 MHz500