Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.04.05-UF054 Date / Time: 27-11-2022 13:47:39 Headroom 5.9 dB (NEXT 36-78) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 36]19.4 84 1 3.11Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.8 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.9 234.0 35.8 36 7.6 259.0 32.4SR 12-36 6.1 359.0 32.3 36 7.7 265.0 32.3MAIN 12-36 7.9 476.0 29.0 36 8.4 481.0 25.9SR 12-36 7.9 500.0 27.8 36 9.4 500.0 25.010080604020NEXT (dB)