Title: Hardware Installation Guide.pdf
40.16.5Fiber ConnectionNote:Earlier versions of these part numbers may be marked with the GE Security logo. When using existing equipment, ensure the part numbers and revisions match as above to ensure proper support.252 — revision 6LNL-1100 INPUT CONTROL MODULEHardware Installation Guide41Overview of the LNL-1100The Input Control Module (ICM) provides the access control system with high-speed acknowledgment of critical alarm points in monitored areas. It has sixteen configurable input control points and two output control relays. The ICM supports normally open, normally closed, supervised and non-supervised circuits.The input circuits are scanned at a rate of sixty (60) times per second, with a debounce timing of 64 mS. The digitized input status signal is software monitored and controlled, resulting in the ability for each input point to be programmed as a supervised or non-supervised alarm point, normally open or normally closed monitoring point.