Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]23.6 103 2 3.55Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]30.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.0 467.0 29.4 36 8.2 448.0 27.5SR 12-45 9.4 450.0 30.2 36 9.9 494.0 25.3MAIN 36-78 9.6 499.0 27.9 36 8.5 499.0 25.0SR 36-78 10.2 493.0 28.2 36 9.9 494.0 25.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 3.8 53.8 45 13.3 2.1 55.7SR 36-45 14.6 3.5 54.4 45 13.3 2.1 55.7MAIN 36-45 15.4 478.0 11.6 45 16.7 500.0 8.3SR 45-36 15.5 478.0 11.6 45 17.3 500.0 8.30100806040200250 MHzACR-F (dB)