Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
130150180200240260300EvaporatorMinimum system water volume, air conditioning application (litres)61,571,778,891,8104,6116,6145,3158,5184,4209,8236,40,5 / 3,80,5 / 4,10,5 / 4,10,6 / 4,70,8 / 5,40,8 / 9,21,1 / 10,31,3 / 10,91,5 / 12,5Min/max water type heat exchanger flow rate without hydraulic module (l/s)0,6 / 51/ 9,9Low pressure3,53,83,84,14,34,56,16,26,36,48,1Maximum water type heat exchanger flow rate with low pressure hydraulic module (l/s)High pressure3,73,93,94,34,54,87,98,18,38,48,8CondenserMinimum system water volume, air conditioning application (litres)7587,595110125140175192,5222,5252,52850,3 / 3,80,3 / 4,10,3 / 4,10,4 / 4,70,4 / 5,40,5 / 7,50,5 / 7,80,6 / 8,20,6 / 9,3Min/max water type heat exchanger flow rate without hydraulic module (l/s)0,4 / 50,4 / 7Low pressure3,53,73,744,24,45,45,65,75,87,4