Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Mate 6_2 / Room summaryMgte 6_2Tf—— sClearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 48.4%, Floor 20.0%, Light loss factor: 0.80EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 7 Perpendicular illuminance (adaptive) [Ix] 539 (= 500) 388 615 0.72 0.63 Surrounding area: 0.500 m 2 Surrounding area 7 Perpendicular illuminance (adaplive) [Ix] 463 (z 300) 261 619 0.56 0.42 3 Background area 6 Perpendicular illuminance (adaptive) [Ix] 333 (= 100) 220 409 0.66 0.54 Wall zone: 0.500 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 4 iGuzzini illuminazione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 114.3HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 11248 98.4 114.3