Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
31.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.9 457.0 29.9 36 7.2 457.0 27.1SR 36-45 8.1 473.0 29.1 36 7.9 498.0 25.1MAIN 36-45 8.9 499.0 27.9 36 7.4 499.0 25.0SR 36-45 8.4 499.0 27.9 36 8.0 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.1 494.0 11.4 45 21.3 500.0 8.3SR 45-78 20.2 494.0 11.4 45 20.9 500.0 8.3MAIN 78-45 20.2 500.0 11.3 45 21.3 500.0 8.3SR 45-78 20.3 498.0 11.3 45 20.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 27.6 85.8 26.7 36 28.0 91.3 23.2SR 36-45 26.4 86.3 26.6 36 27.9 86.0 24.1MAIN 36-45 38.6 499.0 -12.3 36 37.0 499.0 -15.2SR 36-45 38.1 499.0 -12.3 36 37.6 499.0 -15.20804000250 MHzACR-N (dB)