Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.4 457.0 29.9 36 9.5 457.0 27.1SR 12-36 5.8 353.0 32.5 36 7.7 465.0 26.7MAIN 12-36 8.8 497.0 28.0 36 9.9 498.0 25.1SR 12-36 8.1 500.0 27.8 36 9.0 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.2 6.5 49.0 45 20.5 500.0 8.3SR 45-78 19.2 6.5 49.0 45 20.8 473.0 8.7MAIN 78-45 21.6 500.0 11.3 45 20.5 500.0 8.3SR 36-45 21.4 500.0 11.3 45 21.1 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.7 61.0 31.7 36 20.2 61.3 29.1SR 36-45 20.2 61.3 31.6 36 20.9 61.5 29.1MAIN 12-36 36.4 497.0 -12.2 36 37.5 498.0 -15.1