Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
MULTICAL® 801 has data connection on terminals 62-63-64. The data connection is passive and optoisolated, as shown in the block diagram below. Adaption to RS 232 level is possible via data cable type 66-99-106. Adaption to USB is possible via data cable 66-99-098.The data connection uses the KMP protocol. Please contact Kamstrup for further details on the KMP protocol.9.4 Valve control [16B-18B] MULTICAL® 801 has a built-in valve control, which makes it possible to automatically restrict power, flow, differential or outlet temperature to a preprogrammed limit.Note: 24 VACFor further details about installation and setup, you can order installation instructions 5512-498.82Kamstrup A/S · Technical Description · 5512-571_R1_GB_11_2016MULTICAL® 801