Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,2 26,7 2,5 498,00Remote: 36-45 29,2 26,7 2,5 498,00Worst Value: Local: 36-45 29,2 26,7 2,5 498,00Remote: 36-45 29,2 26,7 2,5 498,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 22,9 12,3 10,6 394,00Remote: 45-12 23,1 12,3 10,8 394,00Worst Value: Local: 12-45 22,8 12,2 10,6 397,00Remote: 45-12 23,0 12,2 10,8 397,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 32,6 29,3 3,3 345,00Remote: 36 28,0 23,8 4,2 498,00Worst Value: Local: 36 27,6 23,8 3,8 498,00Remote: 36 28,0 23,8 4,2 498,00PS-ACRF: Pass Worst Margin: Local: 45 20,3 9,1 11,2 404,00Worst Value: Local: 45 20,3 9,1 11,2 404,00Remote: 45 21,1 9,3 11,8 394,00