Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
Consult dealerPossible causeRemedyNo input voltageCheck the building wiring and input cable.Check if the input breaker is closed.Inverter not switched onPress On-Switch “I” to turn on UPS.Input voltage and/or frequency are out of toleranceCheck input power source.Check the building wiring and input cable.Check if the input breaker is closed.Batteries not fully charged / battery defect Charge the batteries for at least 12 hoursand then check capacity.21. TECHNICAL SPECIFICATIONModels66 (LB)1010 (LB)Nominal PowerVA/W6000/540010000/9000Input/Output phases1/11/1Electrical Specifications - InputMains voltage (Vin)Vin220/230/240 V; 1 Ph (L/N) + PE, 3-wireInput frequencyHz50/60Input power factor≥ 0.99THDI< 5 % with full loadElectrical Specifications - OutputOutput VoltageV208/220/230/240 V ±1 %; 1 Ph (L/N) + PE, 3-Wire Output power must derating to 90 % when the output voltage rate be set with 208 V, and 80 % for 200 VFrequencyHz