Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12 15,8 8,0 7,8 444,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,5 26,7 1,8 500,00Remote: 36-45 29,8 26,7 3,1 500,00Worst Value: Local: 36-45 28,5 26,7 1,8 500,00Remote: 36-45 29,8 26,7 3,1 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 67,8 57,3 10,5 2,20Remote: 45-12 67,8 57,3 10,5 2,20Worst Value: Local: 12-36 22,2 10,4 11,8 492,00Remote: 12-36 22,4 11,2 11,2 446,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,6 24,0 2,6 493,00Remote: 36 27,9 23,9 4,0 494,00Worst Value: Local: 36 26,6 24,0 2,6 493,00