Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 36-45 14.7 476.0 11.7 45 15.8 478.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 40.0 421.0 -7.0 36 40.9 480.0 -13.9SR 36-45 40.1 421.0 -7.0 36 40.3 466.0 -13.0MAIN 36-45 40.8 480.0 -11.1 36 41.0 481.0 -14.0SR 36-78 42.1 496.0 -12.1 36 41.6 496.0 -15.00804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.8 491.0 8.0SR 45 3.7 491.0 8.0MAIN 45 3.8 491.0 8.0SR 45 3.7 491.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA0048.2 m60Insertion Loss (dB)504030201000250 MHz500