Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.2 499.0 29.3 36 6.6 500.0 26.4SR 12-36 7.7 499.0 29.3 36 8.1 500.0 26.4MAIN 12-36 7.3 500.0 29.2 36 6.6 500.0 26.4SR 12-36 7.8 500.0 29.2 36 8.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.8 350.0 14.4 45 21.5 406.0 10.1SR 78-45 19.6 350.0 14.4 45 21.3 396.0 10.3MAIN 45-78 20.7 396.0 13.3 45 21.5 406.0 10.1SR 78-45 20.6 396.0 13.3 45 21.3 396.0 10.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.4 26.4 42.3 36 20.4 26.4 39.9SR 36-45 17.2 26.4 42.3 36 19.0 29.0 38.8MAIN 12-36 29.3 500.0 -12.4 36 28.7 500.0 -15.3SR 12-36 29.8 500.0 -12.4 36 30.2 500.0 -15.30804000250 MHzACR-N (dB)