Title: 10 FDV - SUPERFIRE EI60.pdf.pdf
Specimen nr 8590A 60 minutes(e) 60 minutes(e) 60 minutes(e) 60 minutes(e) 60 minutes(e) 60 minutes(e) 60 minutes(e) 60 minutes(e) 60 minutes(e)(e): End of the assessment of the specimen. Without failure.From the minute 19 to the minute 125, the tolerance of the heating curve stays above the limit stated by the standard, this situation being considered as more unfavourable and, therefore, in favour of safety.4.- CLASSIFICATION AND FIELD OF APPLICATION4.1.- CLASSIFICATION STANDARDThis classification has been carried out in accordance with the paragraph 7.5.5 of the standard EN 13501-2:2007+A1:20094.2.- CLASSIFICATIONThe element “BACH SUPER FIRE” is classified according to the following combination of performance parameters and classes. Other classifications are not admitted.Fire Resistance ClassificationEI2 604.3.- FIELD OF APPLICATION