Title: økernvn 94.pdf
SR 36-45 20.8 98.5 18.7 45 23.0 98.8 15.701008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 19.9 19.9 35.1 12 21.8 18.0 33.2SR 12-36 20.8 21.6 34.1 12 22.7 18.0 33.2MAIN 12-36 25.2 100.0 11.9 36 26.5 100.0 8.9SR 12-36 26.1 98.0 12.3 36 27.9 98.0 9.301008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 5.6 17.9 19.0SR 36 5.5 23.4 18.3MAIN 45 7.4 89.3 12.5SR 36 8.8 98.5 12.101008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 4.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002180 ft60Insertion Loss (dB)