Title: 370.011 LE001_LF001 (slave-backup maskin dersom master svikter).pdf
Circuito frigorifero in rame coibentato equipaggiato di valvola di espansione elettronicaRefrigerant type Circuits number Coils Compressors Compress.type :[n] [n] [n] Scroll .R410a 1 1 1Internal volume of the circuit Total power input Nominal capacity[dm3] [kW] [Hp]1 x 4,80 2,9 4FRIGORIFIC CIRCUIT PERFORMANCESPerformance are declared according EN 14511 (at gross of the heat generated by the fan)100 % recirculation Re-suction air Re-suction air Evaporating temperature Total cooling capacity: EER (Energy Effinciency Ratio)[°C] [%] [°C] [kW]50,0WB [°C]24,0 17,0 10,6 11,4 3,34[°C] [%] [°C] [kW]Discharge air Discharge air Condens.temper. : Sens.cooling capacity: EER = total cooling capacity / compressors + fans power input. Air cooled condensers excluded.13,6 92,8 45,0 10,6VENTILATING SECTIONPlug fan EC type, air flow control according cooling capacity EC type plug fan for supply air flow regualtion inAvailable static pressure : Total air flow : Fan[Pa] [m3/h] [n]