Title: +038=360.000-OU045T_05-PCD2.m4160 PLS SBC - User Manual.pdf
User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-214-5On-board4.6X6 / X7 – Dual Ethernet (Switch)Dual Ethernet port with integrated switch 10/100M.4.7X8 – Digital interruptive inputsFour digital inputs configurable interruptive functions.Connector inscription252423222120SignalDI_IX3DI_IX2DI_IX1DI_IX0––4.8X9 – Communication port Slot ‘C’A hole is foreseen in the housing for the SUBD connector of module PCD2.F7500.4.9M1 – Memory SlotSlot for memory modules like PCD7.R610 for example.4.10BAT – Battery module slotSlot for PCD3 battery module.User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-214-65Power supplySupply voltage: 24 VDC –20 % … +25 %Power consumption: Typically 15 WCapacity of internal 5V / V+ bus: 800 mA / 250 mAConnection terminalsPCD2.M4x60X49 8 7 6 5 4 3 2 1 0D /D – WDWD – – + + +LNP o w ers u p ply+24 VDC –L N