Title: +175=324.001_KA001_Ventilmotor kjølebatterier 36.01 og .02 - AVM115.Produktinformasjon.pdf
formed automatically, either by using the manual adjustment and moving to 100% stroke or by con- necting the voltage to terminals MM/N and 01. When dismantling, first the actuator and valve spindles are released, then the cap nut. The device is delivered ex works in the middle position. The concept of synchronous motor and magnetic coupling enables parallel operation of multiple valve actuators of the same type. The maximum accessory equipment for an actuator is 1 auxiliary change-over contact or 1 potentiom- eter. The auxiliary contact accessory is screwed onto the top cover of the actuator. To be able to make the mechanical connection, you first have to remove the indicator knob. A new indicator can be seen on the cover of the accessory.!Beware of injury Opening the housing creates a risk of injury. ►The housing must not be opened.Additional technical data