Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 36] [Pair 36] [Pair 45]18.0 78 1 2.87Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.6 464.0 29.6 36 8.1 470.0 26.4SR 12-45 8.6 325.0 33.3 45 9.3 453.0 27.3MAIN 36-78 9.4 497.0 28.0 36 9.1 497.0 25.1SR 36-45 10.6 498.0 27.9 36 10.5 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.7 412.0 12.9 45 14.5 28.1 33.3SR 36-45 15.6 412.0 12.9 45 14.5 31.5 32.3MAIN 36-45 15.8 469.0 11.8 36 18.6 490.0 8.4SR 36-45 15.7 468.0 11.8 45 18.2 468.0 8.80100806040200250 MHzACR-F (dB)