Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
EUROVENT Certific.SkyStarTechnical featureswww.eurovent-certification.com2 pipe units. The following standard rating conditions are used:COOLING Entering air temperature: + 27°C d.b., + 19°C w.b. Water temperature:+ 7/12°CHEATING Entering air temperature: + 20°C Water temperature: + 50°C water flow rate as for the cooling conditionsMODEL Speed m3/h Air flow Cooling total emission (E) kW Cooling sensible emission (E) kW kW Heating (E) l/h Water flow kPa kPa dB(A) dB(A) W A l mmP Cooling (E) P Heating (E)∆ ∆ Sound power Lw (E) Sound pressure Lp (*) Fan (E)Water content DimensionsSK 02 2 420 1,63 1,32 2,12 280 7,0 6,0 40 31 32 0,15 0,81 310 1,27 1,01 1,62 219 4,5 4,0 33 24 25 0,113 610 1,98 1,64 2,64 340 10,0 9,0 49 40 57 0,27SK 12 2 420 2,34 1,75 2,90 402 7,6 6,3 40 31 32 0,15 1,41 310 1,84 1,35 2,22 316 4,9 4,1 33 24 25 0,113 520 2,68 2,04 3,35 461 9,7 8,2 45 36 44 0,20SK 22 2 500 3,34 2,39 3,93 574 9,4 7,3 45 36 44 0,20 2,11 320 2,25 1,57 2,56 387 4,6 3,5 33 24 25 0,11