Title: 40 Bender brukermanual.pdf.pdf
If the measuring channel settings only differ slightly, we recommend to proceed as follows: - first set all the measuring channels (1…12) to the same value - then modify the setting of an individual measuring channel.1. Factor (for measuring current transformers) Setting of a factor to adapt the RCMS… to connected measuring current transformers. The following factor setting ranges are available depending on the CT type and the application. When the channel is disabled, this setting menu has no function (display: --). Select: *1 For Bender measuring current transformers (W…, WR…, WS…, WF…, W…AB). For measuring current transformers with a different transfor- mation ratio (e.g. if third-party measuring current transform- ers are connected via a Bender measuring current transformer). If the conductor to be monitored is wound through the meas- uring current transformer several times in order to amplify the signal.