Title: DOCA0005EN-12.pdf
– by Internal Clock: the device clock controls the active tariff. If you set the Control Mode to by Internal Clock, you must also configure the schedule. Set the time when each tariff period starts, using the 24 hour clock format (00:00 to 23:59). The start time of the next tariff is the end time of the current tariff. For example, T2 start equals the end of T1.Overload AlarmAlarmDisableEnableSelect whether or not the Overload Alarm is enabled: – Disable: the alarm is disabled.– Enable: the alarm is enabled. If you enabled the Overload Alarm,you must also configure the Pick Up Value in kW from 1 - 9999999.Select how the digital output functions: – Disable: the digital output is disabled.– for Alarm: the digital output is associated with the overload alarm.Digital OutputDO FunctionDisablefor Alarmfor Pulse (kWh)The meter sends a pulse to the digital output port when the alarm is triggered.