Title: fireray5000_igb.pdf
Installation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 14How to change Compensation Level:3.2.2 Manual Fire and Fault TestsAfter installation or cleaning, it is recommended that a manual Fire and Fault Test is performed:Fire Test: Cover the Reflector slowly so that it takes longer than 2 seconds to coer. The System Controller will signal Fire to the Fire Control Panel.Fault Test: Cover the Reflector completely within 2 seconds. The System Controller will signal Fault back to the Fire Control Panel.Installation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 15In UseTroubleshooting4. Troubleshooting4.1 Error Codes4.1.1 Detector Not Found