Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
323 318 284 245 207292 282 254 211 183258 244 217 187 156217 211 185 163 (134Scale: 1:50The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 80Dronning Mauds gate 1310. og 11. etasjeSite 1/ Building 1/ Storey 10 / Washroom / Room summary8/28/2019WashroomClearance height: 2.900 m, Reflection factors: Ceiling 70.0%, Walls 49.8%, Floor 20.0%, Light loss factor: 0.80WorkplaneSurface1 Workplane (Washroom) Perpendicular illuminance (adaptive) [Ix] 207 (= 200) Height: 0.000 m, Wall zone: 0.200 mAverage (Target) Min Max Min/average Min/max115 301 0.56# Luminaired(Luminaire) [Im]Power [W]Luminous efficacy [Im/W]6 iGuzzini illuminazioneQ497 Laser Blade XSDownlight HC 12.4W1 iGuzzini illuminazione S.p.A - QA85+QB22_B66J iN60 LED: Down LO 1824 plate - DALI - General Light - LED Warm - L 1196 - 15W 2400Im - 3000K - Initial module - Frame Down - General Light - L 1208