Title: +038=370.104-OE004T_01-Multical 801 Energimåler Kamstrup - Installasjons- og brukerguide.pdf
MULTICAL® 80111A10B 11B10A56K29A97A 98ASONOFLO/MAGFLO MkIIIMULTICAL® 80110B (69B)50 51 52V1 (V2)11B (79B)PEMAGFLO Mk IVMULTICAL® 80110B (69B)56 56 56 56V1 (V2)11B (79B)SITRANS F MAGFLOMULTICAL® 80110B44 45 4611B 69BV157 5879BV2Cooling energy E1 = V1 (T1-T2)k E3 = V1 (T2-T1)k15MULTICAL® 801Auxiliary voltage from E+ and E- is added to the passive contact output P of the flow sensor before the signal is connected to the galvanically separated flow sensor input. This permits a cable length of up to 100 m between flow sensor and calculator.The active pulse output of the flow sensor is connected to the galvanically separated flow sensor input directly. This permits a cable length of up to 100 m between flow sensor and calculator.