Title: Aggregatkjøring.pdf.pdf
The air handling unit is built with a complete and fully integrated control system - based on the Access control unit mounted in the control cabinet and the NaviPad control panel with a graphical user interface. The air handling unit can either run stand alone or handled from a building management system. Before shipment the unit has been assembled and has passed a final functional test and inspection. Order-specific parameters are stored in the control unit during this process. The test report is delivered with the air handling unit.Flow chartBT3BP1:BTA2BT2GQ4 BP2:A GQ2QM32STPTPMExtractExhaustMEFEFDVHSFSupplySFVVXOutdoorTTTPPTMBT5BT10BT4GQ1 GQ3BP1:ABP2:BBT1QM31SComponents in red are not deliveredExternal componentsSymbol NameHW I/OSupply air temperatureBT5AI1Normal speedExt. Sig.DI2Reduced speedDI1Unit stopDI3Internal componentsRotor driveTA2BUS Adr. 7Damper motor on/off spring return, supply