Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
Protection class IP rating auxiliary switch: – activation point [degrees] Torque: - motor - spring Wire connection: – motor (length: 0.9 m) – auxiliary switch Movement time (0–90°): - motor - return spring Working temperature range Sound pressure level: - motor - springIII IP 54 2 x PDT 3(0.5) A AC 250V 5, 804 Nm 3 Nm2 x 0.75 mm2 6 x 0.75 mm260 s ≈ 20 s −30 ...+55°Cmax 43 dB (A) ~ 62 dB (A)II IP 54 2 x PDT 3(0.5) A AC 250V 5, 804 Nm 3 Nm2 x 0.75 mm2 6 x 0.75 mm260 ≈ 20 s −30 ...+55°Cmax 43 dB (A) ~ 62 dB (A)III IP 54 2 x SPDT 3(0.5) A, 250 V 5, 809 Nm 7 Nm2 x 0.75 mm2 6 x 0.75 mm260 s ≈ 20 s −30 ...+55°Cmax 55 dB (A) ~ 67 dB (A)II IP 54 2 x SPDT 3(0.5) A, 250 V 5, 809 Nm 7 Nm2 x 0.75 mm2 6 x 0.75 mm260 s ≈ 20 s −30 ...+55°Cmax 55 dB (A) ~ 67 dB (A)Connection diagram for the BF24-Tand BF230-T actuatorsConnection diagram for the BFL24-T, BFL230-T, BFN24-T, BFN230-T, BF24-TN and BF230-TN actuators