Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 27.11.2020 11:56R LOW OhmR: 0.13ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 27.11.2020 11:56KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 30.11.2020 11:58 (ELEKTRIKER)Tallberg Elektro A/S Tlf.22796640Side:40GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.277277278278279279280280281281282282283283TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 27.11.2021 10:42ISOLASJON: ALLERln: >30.0MΩ Um: 1046V Rlpe: >30.0MΩ Um: 1066V Rnpe: >30.0MΩ Um: 1058VUiso: 1000V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF090 16C2/003 26.11.2020 13:48SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0Hz