Title: Hardware Installation Guide.pdf
revision 6 — 301LNL-1200 Output Control Module32 Downstream Devices TotalSingle Reader Interface Module0 1 2 3 4 5 6 7 8 9 * #EOL Termination Required302 — revision 6EOL TerminationIntelligent System ControllerRS-485 Multi-drop 2 or 4 wireDual Reader Interface Module0 1 2 3 4 5 6 7 8 9 * #0 1 2 3 4 5 6 7 8 9 * #EOL Termination RequiredDownstream Communications • Four 2-wire ports • Two 4-wire ports • Combination 2 and 4 wire portsInput/Output Control Module(s)Hardware Installation Guide54Specifications** The LNL-1200 series 2 is for use in low voltage, class 2 circuits only. These specifications are subject to change without notice.Primary Power: - - -12 to 24 VDC ± 10%, 1100mA maximum 12 VDC @ 850mA nominal 24 VDC @ 450mA nominalRelay contacts: 16 Form-C, 5A @ 28 VDC, resistiveInputs: 2 unsupervised, dedicated for cabinet tamper and UPS fault monitoringCommunication: RS-485, 2-wire, 9600 to 115,200 bps async-Cable Requirements: - -