Title: 564 6131_50-51-xxx-500 Tilstedeværelsesdetektor tak 360 hvit korridor.pdf
Length of the detection range L1 (longitudinal to the alarm unit) times the width B1 Max. 18 m x 2.5 m Max. 20 m x 3 m Max. 20 m x 3 mLength of the detection range L2 (crosswise to the alarm unit) times the width B1 Max. 24 m x 2.5 m Max. 30 m x 3 m Max. 30 m x 3 mThe device can be mounted either in the ceiling via hollow-wall mounting (steps 1 - 4) or on the ceiling via the optionally available surface-mounted housing (6131/39-xxx-500). It can additionally be mounted on a flush-mounted box via an optionally available intermediate ring (6131/38-xxx-500). Mounting instructions are enclosed with the surface-mounted housing and the intermediate ring.CAUTION The arrows on the device must be aligned in a longitudinal direction to the corridor.6131/50-xxx-500 6131/51-xxx-500 PM/Ax.24.x.124 V DCDE EN FR NL IT+www.busch-jaeger- catalogue.com/ 6132-0-0413,artikel.htmlAnschlussAnschluss des integrierten KNX-Busankopplers: – Präsenzmelder an dessen Rückseite über die beiliegende