Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]24.1 105 2 3.77Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.7 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.4 471.0 29.2 36 9.1 471.0 26.4SR 36-45 7.4 448.0 30.3 36 8.2 448.0 27.5MAIN 36-45 10.1 500.0 27.8 36 9.6 496.0 25.2SR 36-45 8.5 500.0 27.8 36 9.0 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.3 3.8 53.8 45 13.7 2.3 55.2SR 36-45 15.3 3.8 53.8 45 13.8 2.6 53.9MAIN 78-45 16.4 500.0 11.3 45 17.3 493.0 8.4SR 78-45 16.6 500.0 11.3 45 17.4 498.0 8.30100806040200250 MHzACR-F (dB)