Title: 370.02-SB401 - Siemens VXF40.80-100.pdf
Before disposal the valve must be dismantled and separated into its various constituent materials. Legislation may demand special handling of certain components, or it may be sensible from an ecological point of view. Current local legislation must be observed.The technical data given for these applications is valid only in conjunction with the Siemens actuators as detailed under "Equipment combinations", page 3. All terms of the warranty will be invalidated by the use of actuators from other manufacturers.7/103-port seat valves PN16 with flanged connectionCA1N4430en 2013-09-06Technical dataFunctional dataIndustry standardsMaterialsDimensions / Weight8/10Siemens Building TechnologiesPN class Working pressurePN 16 to ISO 7268 to ISO 7005 within the permissible "medium temperature" range according to the diagram on page 6Flow characteristicthrough-port 0…30 %bypass Leakage rate30…100 % 0…100 %linear equal percentage; ngl = 3 to VDI / VDE 2173 1) linear