Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD02 Date / Time: 05/19/2022 08:57:13 AM Headroom 9.2 dB (NEXT 36-78) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 45] [Pair 12] [Pair 12] [Pair 36]33.9 157 4 6.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]25.0 496.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.5 470.0 29.8 45 10.4 480.0 26.8SR 36-78 9.2 190.5 37.3 36 10.7 190.5 34.7MAIN 36-45 9.7 500.0 29.2 45 10.6 500.0 26.4