Title: Bytesteinen 1 - =514.202-FS001.pdf
Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]37.6 192 13 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.0 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 7.7 105.5 39.5 3,6 9.8 100.0 37.1SR 1,2-3,6 8.9 231.5 33.7 3,6 9.5 63.8 40.4MAIN 3,6-7,8 8.0 216.0 34.2 3,6 9.9 216.5 31.2SR 1,2-3,6 8.9 247.0 33.2 4,5 9.8 242.5 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 13.6 185.5 17.9 4,5 15.3 3.3 50.0SR 7,8-4,5 13.5 196.5 17.4 4,5 15.3 4.5 47.2MAIN 7,8-4,5 14.4 217.0 16.5 4,5 16.1 217.0 13.5