Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD20 Date / Time: 28/01/2022 10:22:47 Headroom 2.4 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]34.0 175 13 6.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.4 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 8.1 57.0 44.1 4,5 9.1 43.5 43.3SR 4,5-7,8 2.4 197.0 34.9 7,8 4.6 200.0 31.9MAIN 1,2-3,6 10.3 237.5 33.5 3,6 11.7 244.0 30.3SR 4,5-7,8 2.9 241.5 33.4 7,8 5.8 241.5 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)