Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
OBJEKT / Plan 10 / FUSE028 10.02.2020 13:22SPÆNDINGUln: 230V Ulpe: 230V Unpe: 2V f: 49.9HzOBJEKT / Plan 10 / FUSE028 10.02.2020 13:22Z-LINEZ: 0.81ΩIsc: 285A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE028 10.02.2020 13:23Zs(rcd)Z: 0.41ΩIsc: 564A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE028 10.02.2020 13:23RCD II: 28.5mAUci: 0.1V t: 27.8ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE028 06.02.2020 09:12R LOW OhmR: 0.01ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE029 10.02.2020 13:12TEST RAPPORTSide:4GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.2626272728282929303031313232ResultatSPÆNDINGUln: 231V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE029 06.02.2020 09:10R LOW OhmR: 0.08Ω