Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]34.0 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.6 458.0 29.8 36 8.3 458.0 27.0SR 36-78 7.8 474.0 29.1 36 7.9 465.0 26.7MAIN 36-45 9.3 498.0 27.9 36 9.4 498.0 25.1SR 36-78 8.0 482.0 28.7 36 8.0 473.0 26.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.4 4.5 52.2 45 14.5 2.6 53.9SR 36-45 16.3 161.5 21.1 45 14.4 2.6 53.9MAIN 36-45 16.5 477.0 11.7 45 19.0 477.0 8.7SR 45-36 16.5 477.0 11.7 45 18.8 470.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 32.7 181.0 13.6 45 32.9 174.5 11.7SR 36-45 31.8 175.5 14.2 45 31.9 174.5 11.7MAIN 36-45 42.1 498.0 -12.3 36 42.2 498.0 -15.1