Title: +038=370.001-RD001._01-Siemens Differanstrykk væske QBE3000-D6.pdf
Differential pressure sensors can be used in conjunction with all devices or systems capable of processing the DC 0...10 V or DC 4...20 mA output signal.The pressure to be monitored acts on a ceramic sensor element. The ceramic element has the following significant advantagesVery low susceptibility to temperature · Resistance to high temperature · No mechanical ageing or creepageThe sensor signal is linearised, temperature-compensated and amplified by the sensor electronics.The differential pressure sensor comprises the following:Sensor cover with DIN 175301-803-A connecting cable and gland · Pressure sensor casing with ceramic element, screw connections and burglarproof screwSensor cover with DIN 175301-803-A connecting cable and gland · Pressure sensor casing with ceramic element, screw connections and burglarproof screwPrinted circuit board · Pressure connections G⅛“, external threaded with unscrewed fittings for copper pipe, 6 mm diameter