Title: 1 etg del 2.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.5 15.6 47.8 36 10.2 18.9 43.4SR 12-36 8.7 15.6 47.8 12 10.5 15.6 45.4MAIN 36-45 14.6 249.5 4.7 36 14.8 249.5 2.1SR 36-45 15.2 249.5 4.7 36 14.1 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.5 27.0 18.8SR 36 3.6 28.4 18.7MAIN 36 10.3 237.5 10.2SR 45 7.2 234.5 10.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1