Title: Ø94, Medistim - innregulering ventilasjon, tilluft U1.pdf
TILLUFTMÅLEPROTOKOLLANLEGG:SYSTEM NR.:PLAN:ETGROM/GRENNR. U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1 U1NAVN/NR T1 T2 T3 T4 T5 T6 T7 T8 T9 T10 T11 T12 T13 T14 T15 T16 T17 T18 T19 T20 T21 T22 T23 T24SUMANMERKNINGERLUFT KONTROLLLUFT KONTROLLØKERNVEIEN 94DATO:FREKVENS / TRYKK:U1 ETGSIGNATURKANALPROSJEKTERTMÅLTFORHOLDTempØ.DIM.C[m3/h] 150 150 250 250 150 150 120 250 500 200 200 200 200 250 150 150 200 150 150 100 100 120 120 120[m3/h] 155 158 255 251 155 152 123 257 300 120 280 211 208 251 154 151 208 154 156 90 90 96 97 96[%] 103 % 105 % 102 % 100 % 103 % 101 % 103 % 103 % 60 % 60 % 140 % 106 % 104 % 100 % 103 % 101 % 104 % 103 % 104 % 90 % 90 % 80 % 81 % 80 %4380416895 %12.03.2013H.FANMERKNING