Title: Hardware Installation Guide.pdf
260 — revision 6Hardware Installation GuideUse sufficiently large gauge of wires for the load current as to avoid voltage loss.12 VDCDC STRIKE+ -NCC NONONC+CDIODE 1N4002 (100 V/1A) TYPICAL DIODE CURRENT RATING > 1X STRIKE CURRENT DIODE BREAK DOW N VOLTAGE > 4X STRIKE VOLTAGEAC XFMRAC STRIKENCC NONONCCFOR 24 VAC STRIKE, PANASONIC ERZ-C 07 DK470 MOV SELECTION: CLAMP VOLTAGE > 1.5 X VAC RMS42.1.5PowerFor the LNL-1100 series 2, the power source should be located as close to module as possible.Wire the power input with an 18 AWG (minimum) twisted pair cable.Note:Be sure to observe polarity.+ 12 to 24 VDC -VINGNDrevision 6 — 261LNL-1100 Input Control Module42.2Elevator ControlOnGuard hardware is capable of supporting elevator control for up to 128 floors. An elevator reader has an input/output module that controls the access to floors via an elevator.