Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]26.9 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.7 500.0 29.2 36 9.2 477.0 26.8SR 36-45 9.2 467.0 29.9 36 9.1 500.0 26.4MAIN 36-45 8.7 500.0 29.2 36 9.3 497.0 26.4SR 36-45 9.4 500.0 29.2 36 9.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.7 465.0 11.9 45 14.5 2.9 53.1SR 45-78 14.8 465.0 11.9 45 14.5 2.9 53.1MAIN 78-45 14.8 498.0 11.3 45 15.4 484.0 8.5SR 45-78 15.0 498.0 11.3 78 16.1 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.0 48.0 34.9 45 24.4 48.0 32.5SR 36-45 23.7 48.0 34.9 36 24.1 55.3 30.6MAIN 36-45 35.7 500.0 -12.4 36 36.6 497.0 -15.1