Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.6262636364646565666667676868TEST RAPPORTResultatZ-LINEZ: 0.81ΩIsc: 284A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF026 16C2/003 30.11.2020 10:47Zs(rcd)Z: 0.82ΩIsc: 282A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF026 16C2/003 30.11.2020 10:52RCD II: 28.5mAUci: 0.1V t: 17.7ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF026 16C2/003 30.11.2020 11:53 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF026 16C2/003 27.11.2020 11:55R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF026 16C2/003 27.11.2020 11:55KONTINUITET R: 0.1ΩGrenseverdi: 0.7Ω