Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
22.4 97 1 3.43Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.1 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.3 459.0 29.8 36 8.2 469.0 26.5SR 12-36 7.3 405.0 31.2 36 8.7 458.0 27.0MAIN 12-36 10.3 498.0 27.9 36 9.2 498.0 25.1SR 12-36 8.6 500.0 27.8 36 9.5 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.0 6.0 49.7 45 20.7 5.3 47.8SR 45-78 19.0 6.1 49.5 45 20.7 5.1 48.0MAIN 45-36 22.4 500.0 11.3 45 22.7 496.0 8.3SR 36-45 22.3 500.0 11.3 45 22.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.7 83.5 27.1 45 24.3 83.3 24.6SR 36-45 25.4 83.5 27.1 36 26.3 83.5 24.5