Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 41,8 68,0 217,0 12,0 7,4Limit 100,0 - 555,0 50,0 25,0Margin 58,2 - 338,0 38,0 17,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,0 2,3 1,90Worst Value: Local: 36 17,8 43,6 25,8 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 26,1 18,5 7,6 31,50Remote: 12 20,0 14,8 5,2 84,00Worst Value: Local: 78 15,6 8,0 7,6 457,00Remote: 36 17,3 8,0 9,3 500,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):