Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Isc: 631A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 240A Isc(0.76%): 479A Isc(1.15%): 725ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF050 16C2/003 06.11.2020 10:56Zs(rcd)Z: 0.34ΩIsc: 667A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF050 16C2/003 06.11.2020 11:00Tallberg Elektro A/S Tlf.22796640Side:28GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr.188188189189190190191191192192193193194194195195TEST RAPPORTResultatRCD II: 28.5mAUci: 0.2V t: 104.0ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF050 16C2/003 05.11.2020 11:27R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF051 16C2/003 06.11.2020 14:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF052 16C2/003 06.11.2020 14:11R ISO