Title: Hardware Installation Guide.pdf
ISC panels can be multidropped on the RS-485 line using this configuration. Follow typical EOL termination5 1 J6 1 J7 1 J8 1 J5 1 U6 1 UJ10J128 J7 J7 1 UG E M 2J64W 2W1 JN SJ4J9485 232CJ2J3V E RB523237Intelligent System ControllerM U H T LIIV 3N P5 2 3 2 R BDB 25 Pin FemaleDB 9 Pin Male 9 or 25 Pin Connector Workstation (PC)C D C AC AD N G2 NID N G1 NI40.13Dial-Up Configuration for the ISCRefer to the following diagram for dial-up configuration. Note: ALL DIAL-UP PANELS MUST BE SET TO ADDRESS 1 OR DIAL-BACK CAPACITY WILL FAIL. Modem DIP Switches 1, 3, 4, 5, and 8 should be ON. DIP Switches 2, 6, and 7 should be OFF.revision 6 — 237ISC Communications9Vac (1000mA) Power SupplyModem-controller cable, part #HOC-56KEXTIntelligent System ControllerACDCAC5 8 4W 4GND2 3 2W 2GND9 J4 1 JIN2J1GNDA B CIN1J 3J 2J 42 MEG6 JU17LITHIUM 3V BR2325PNREVSN238 — revision 6J8