Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: T4182 Date / Time: 09/11/2013 12:46:50 Headroom 6.4 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]105 159 5 4.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]20.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.7 188.0 37.4 36 8.0 214.0 33.8SR 36-78 6.4 200.5 36.9 36 8.3 200.5 34.3MAIN 12-36 7.8 232.5 35.9 36 8.0 214.0 33.8SR 36-78 7.5 243.0 35.5 36 8.3 226.5 33.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.3 5.1 50.0 12 16.1 2.6 52.8