Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
BLE24 , BLE24-ST AC 24V 50/60Hz DC 24VBLE230AC 220-240V 50/60 HzPower demand: - for spring tensioning - for spring holding Sizing (apparent power) Appliance class Ingress protection ratingAuxiliary circuit breaker:12 W 0,5W 18 VA III IP 54 2xSPDT 6(3) A, 250V 3°, 87°8 W 0,5 W 15 VA II IP 54 2xSPDT 6(3) A, 250V 3°, 87°7.5 W 0,5 W 9 VA III IP 54 2xSPDT 3A, AC 250V 3°, 87°5 W 1 W 12 VA II IP 54 2xSPDT 3A, AC 250V 3°, 87°activation position [degrees] Torque: - motor - locking Cable connection: - motor (L = 0.9 m) - auxiliary circuit breaker Movement time: (0-90°) - motor Operating temperature range Sound pressure level: - motor Technical specifications - Actuatorsactivation position [degrees] Torque: - motor - locking Cable connection: - motor (L = 0.9 m) - auxiliary circuit breaker Movement time: (0-90°) - motor Operating temperature range Sound pressure level: - motor Technical specifications - ActuatorsPower supply40 Nm 50 Nm3x0,75 mm2 6x0,75 mm260s30 ...+50°Cmax 62 dB (A)