Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
Total emissionAir (°C) K K K25-18 26-18.5 28-20 Water (°C) 0,82 0,56 0,350,89 0,63 0,411,11 0,82 0,527/12 °C 10/15 °C 14/18 °CSensible emission Air (°C) K K K25-18 26-18.5 28-20 1,06 0,94 0,9 0,78 0,72 0,580,9 0,72 0,5Note:the correction factors are indicative, as they are average values.31SkyStar ECM SkyStar ECMSkyStarEmission of 4 pipe units with standard and enhanced cooling batteryCooling emission of 2 battery units (4 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.ECM Mod.SK 14SK 26SK 36SK 44SK 56Speed VdcHigh Med Low High Med Low High Med Low High Med Low High Med Low10 5 1 10 5 1 10 5 1 10 5 1 10 5 1Air flowm3/h 535 380 310 710 445 310 880 610 360 1165 870 630 1770 1130 710EWT 5 - LWT 10°C Total emission kW 3,32 2,61 2,20 4,72 3,35 2,47 5,46 4,24 2,82 7,79 6,29 5,10 11,83 8,53 5,87Water flow l/h 572 448 378 812 576 425 940 729 486 1341 1081 877 2035 1467 1010