Title: Simployer - Data testrapport =514.204-FS001.pdf
Test Summary: PASSModel: DTX-ELT Main S/N: 9862060 Remote S/N: 9862059 Main Adapter: DTX-CHA001 Remote Adapter: DTX-CHA00134.0 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD22 Date / Time: 28/01/2022 10:24:00 Headroom 7.9 dB (NEXT 3,6-4,5) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]36.9 190 14 7.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]24.6 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 7.9 175.0 35.8 3,6 9.5 169.5 33.1SR 3,6-7,8 8.9 194.5 35.0 7,8 9.0 206.5 31.6