Title: Luftport - frico_ar3500-no.pdf
Outlet air temp. [°C] 40,1 46,4 41,2 47,5 41,3 47,7Water flow [l/s] 0,18 0,12 0,27 0,17 0,37 0,24Pressure drop [kPa] 11,0 5,0 9,0 4,0 19,0 9,0TypeFan positionAR3510W max min AR3515W max min AR3520W max minAirflow[m3/h] 2000 1000 2800 1400 4000 2000Supply water temperature:70 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 Return water Output temp. [°C] 48,7 37,0 46,2 35,5 45,5 34,4Water flow [l/s] 0,13 0,04 0,16 0,06 0,22 0,08[kW] 11,5 5,7 16,0 8,0 23,0 11,5Pressure drop [kPa] 6,0 1,0 4,0 1,0 8,0 1,0Water temperature: 70/50 °C Room temperature: +18 °COutput *2[kW] 11,5 7,6 17,3 11,1 24,9 15,9Outlet air temp. [°C] 35,4 40,5 36,3 41,4 36,5 41,6Water flow [l/s] 0,14 0,09 0,21 0,13 0,29 0,19Pressure drop [kPa] 7,0 3,0 6,0 3,0 14,0 6,0TypeFan positionAR3510W max min AR3515W max min AR3520W max minAirflow[m3/h] 2000 1000 2800 1400 4000 2000