Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]33.7 147 3 5.13Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.6 477.0 29.7 36 5.9 481.0 26.8SR 12-36 8.3 462.0 30.0 36 8.4 500.0 26.4MAIN 36-45 6.1 500.0 29.2 36 5.9 481.0 26.8SR 12-36 8.6 500.0 29.2 36 8.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.5 450.0 12.2 45 19.0 468.0 8.8SR 78-45 17.4 445.0 12.3 45 19.3 469.0 8.8MAIN 78-45 17.6 460.0 12.0 45 19.0 468.0 8.8