Title: 2 etg del2.pdf
20100050100150200250MHz100NEXT @ Remote (dB)806040202500050100150200250MHz100ACR-F @ Remote (dB)806040202500050100150200250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 8.1Cable ID: T2090 Date / Time: 10/11/2013 08:05:14 AM Headroom 11.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]125 199 15 5.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.6 100.0 20.4Worst Case Margin Worst Case Value