Title: Sidewall (1).pdf
(a) For coverage area dimensions less than or between those indicated, use the minimum required flow for the next highest coverage area for which hydraulic design criteria are stated.(b) Requirement is based on minimum flow in GPM (LPM) from each sprinkler. The associated residual pressures are calculated using the nominal K-factor. Refer to Hydraulic Design under the Design Criteria section.For NFPA 13 residential applications, the greater of 0.1 gpm/ft2 over the design area or the flow in accordance with the criteria in this table must beused.The Width x Length dimension refers to the Width (backwall where the sprinkler is located) times the Length (horizontal throw of sprinkler).TABLE B DRY PIPE SYSTEM SERIES LFIl RESIDENTIAL HORIZONTAL AND RECESSED HORIZONTAL SIDEWALL SPRINKLERS (TY1334) NFPA 13D, 13R, AND 13 HYDRAULIC DESIGN CRITERIA(cTFP410Page 6 of 6InstallationThe TYCO RAPID RESPONSESeries LFIl Residential Horizontal