Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Output for the connection of signalling devices which warn building inhabitants of the actual discharge of the extinguishing agent.It will activate on activation of the electrovalve.Note:The functions shown in the table, with the exception of the “VALVE” output, can be replicated on the input/output devices of the loop or IFM internal modules.3.11IFMNET, internal network connection moduleThe IFMNET module allows you to connect two or more control panels in a Hornet+ network by means of two RS485 communication ports (A and B).In cases where a fiber optic cable is used over long BUS lengths, it is necessary to use a RS485/fiber converter (non-INIM brand product). The module has a 12V output for the power supply to the converter in use.26Description of the Previdia Max system partsInstallation manualIFMNET comes with:3 screws for securing the module to the grounding bar • Instructions manual[A]Status LEDABCDE[B]Mini USB portG[C]Port-A