Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E6.433.09.03 / XF038 C16/2 15.06.2020 12:46R LOW OhmR: 0.22ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF038 C16/2 16.06.2020 08:31SPĆNDINGUln: 231V Ulpe: 231V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF039 C16/2 15.06.2020 08:39SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.1HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF039 C16/2 15.06.2020 08:39Z-LINEZ: 0.36ΩIsc: 635A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF039 C16/2 15.06.2020 08:40Zs(rcd)Z: 0.32ΩIsc: 708A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF039 C16/2 15.06.2020 08:40Tallberg Elektro A/S Tlf.22796640Side:10GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.7272737374747575767677777878TEST RAPPORTResultatRCD UbUc: 0.4V