Title: 1 etg del 2.pdf
SR 12-36 23.7 99.8 23.4 12 24.1 86.3 23.3MAIN 36-45 24.8 248.5 4.8 36 24.6 248.0 2.2SR 36-78 30.8 247.5 4.9 36 30.5 248.0 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.4 132.5 12.8SR 36 3.4 145.0 12.4MAIN 36 6.8 247.0 10.1SR 36 4.4 248.5 10.060500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94