Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 58,4 68,0 303,0 17,0 10,1Limit 100,0 - 555,0 50,0 25,0Margin 41,6 - 252,0 33,0 14,9Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,2 3,1 1,9 3,10Worst Value: Local: 36 24,7 43,7 19,0 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 18,7 13,3 5,4 118,50Remote: 12 24,1 18,3 5,8 35,25Worst Value: Local: 78 14,8 8,0 6,8 495,00Remote: 36 16,0 8,0 8,0 499,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 30,3 28,3 2,0 447,00Remote: 36-45 29,6 26,7 2,9 500,00Worst Value: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 29,6 26,7 2,9 500,00dB 0501000Local250500 MHzdB 0