Title: Romtermostat møterom.pdf
N.B. : Without the relevant linearity, the EGT338F101 room setpoint adjuster is not suitable for useas a setpoint transmitter for 0...10 V.EGT 338 F601:A 47 Q potentiometer is installed in series with the measuring resistor for changing the measurement by +4 K. The setpoint can be corrected with or without room temperature influence depending on whether an equitherm controller is connected.Engineering and fitting notesThe temperature sensor should not be exposed to direct sources of heat, the effects of radiation or draughts. There is an error of approx. 1 K with a temperature difference of 5 K between wall and air at a distance of approx. 1 m.Setpoint adjustmentFixed setting A fixed individual room setpoint needs to be set in different application cases. After this has been doneusing the setpoint knob, the knob is removed. The transparent cover of the EGT 338 (with opening for setpoint adjuster) is replaced with a closed transparent cover (accessory).