Title: Data tester Smestad skole - Detaljert.pdf
Margin 44,8 - 268,0 34,0 15,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 1,1 3,0 1,9 2,80Worst Value: Local: 45 23,3 43,6 20,3 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 13,8 8,0 5,8 419,00Remote: 78 20,3 14,9 5,4 81,00Worst Value: Local: 78 13,8 8,0 5,8 419,00Remote: 78 15,6 9,8 5,8 266,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,0 26,7 2,3 499,00Remote: 36-45 30,1 26,7 3,4 497,00Worst Value: Local: 36-45 29,0 26,7 2,3 499,00Remote: 36-45 30,1 26,7 3,4 497,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,5 11,3 10,2 443,00