Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 498.0 29.3 36 6.6 495.0 26.5SR 12-36 8.2 500.0 29.2 36 7.4 500.0 26.4MAIN 12-36 8.0 498.0 29.3 36 6.7 500.0 26.4SR 12-36 8.2 500.0 29.2 36 7.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.1 500.0 11.3 45 21.2 500.0 8.3SR 45-78 20.4 500.0 11.3 45 21.5 500.0 8.3MAIN 78-45 20.1 500.0 11.3 45 21.2 500.0 8.3SR 45-78 20.4 500.0 11.3 45 21.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.8 27.8 41.7 45 21.4 27.8 39.3SR 36-45 19.2 27.5 41.8 36 21.0 30.3 38.3MAIN 36-45 31.0 500.0 -12.4 36 29.9 500.0 -15.3SR 12-36 31.3 500.0 -12.4 36 30.6 500.0 -15.30804000250 MHzACR-N (dB)