Title: 2 etg del2.pdf
Cable ID: D2017 Date / Time: 10/10/2013 11:56:12 AM Headroom 5.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 36] [Pair 36] [Pair 45]88 134 5 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.9 165.5 38.3 36 8.6 234.5 33.2SR 12-36 5.5 226.0 36.1 12 6.8 226.0 33.4MAIN 36-78 8.1 234.5 35.8 36 8.6 234.5 33.2SR 12-36 5.5 226.0 36.1 12 6.8 226.0 33.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.4 4.6 50.9 12 17.3 3.1 51.3