Title: Datasheet_LDALI-MS2-BT_LDALI-MS4-BT.pdf
With the built‑in infrared receiver, the room’s lights, sunblinds and HVAC system can be controlled via the optionally available IR remote control L‑RC1. In addi‑ tion to occupancy and lux sensors, the LDALI‑MS2‑BT/LDALI‑MS4‑BT comes with integrated temperature and humidity sensors. In room automation applications, those values can be used to calculate the current dew point. On the back of the sensor, there is a connector for three digital inputs, allowing to connect conven‑ tional switches and push‑buttons, window contacts, dew point sensor, etc. This feature not only saves on additional hardware, but also significantly reduces wir‑ ing costs, as the inputs can be wired inside the room and wires no longer have to be pulled to the I/O modules in the switching cabinet.Furthermore, the LDALI‑MS2‑BT/LDALI‑MS4‑BT can transmit all supported bea‑ con‑types (iBeacon, Eddystone UID beacon or manufacturer specific LOYTEC bea‑ con) for indoor localization.