Title: DOCA0005EN-12.pdf
– by Digital Input: the digital input is associated with the multi-tariff function. Asignal to the digital input changes the active tariff.– by Internal Clock: the device clock controls the active tariff. If you set the Con- trol Mode to by Internal Clock, you must also configure the schedule. Set the time when each tariff period starts, using the 24 hour clock format (00:00 to 23:59). The start time of the next tariff is the end time of the current tariff. For example, T2 start equals the end of T1.Select whether or not the Overload Alarm is enabled: – Disable: the alarm is disabled.– Enable: the alarm is enabled. If you enabled the Overload Alarm, you mustalso configure the Pick Up Value in kW from 1 - 9999999.45Front panel display and meter setupiEM3000 series user manualSectionParameterOptionsDescriptionSelect how the digital output functions: – Disable: the digital output is disabled.Disable– for Alarm: the digital output is associated with the overload alarm. The meter