Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 36]33.7 146 2 4.90Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]26.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.5 499.0 29.3 36 5.8 500.0 26.4SR 12-36 6.2 447.0 30.3 36 6.4 500.0 26.4MAIN 36-45 6.5 499.0 29.3 36 5.8 500.0 26.4SR 12-36 6.5 500.0 29.2 36 6.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.6 460.0 12.0 45 19.5 451.0 9.2SR 78-45 17.3 460.0 12.0 45 18.7 461.0 9.0MAIN 45-78 18.0 500.0 11.3 45 19.6 498.0 8.3SR 78-45 17.7 500.0 11.3 45 19.2 500.0 8.30100806040200250 MHzACR-F (dB)