Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]29.2 127 2 4.38Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.4 479.0 29.6 36 9.2 498.0 26.4SR 36-45 7.5 474.0 29.7 36 7.9 490.0 26.6MAIN 36-45 9.5 498.0 29.3 36 9.2 498.0 26.4SR 36-45 7.6 490.0 29.4 36 7.9 490.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.4 500.0 11.3 45 14.0 2.6 53.9SR 78-45 15.4 500.0 11.3 45 14.0 2.6 53.9MAIN 78-45 15.4 500.0 11.3 45 16.7 500.0 8.3SR 78-45 15.4 500.0 11.3 45 16.2 500.0 8.30100806040200250 MHzACR-F (dB)