Title: +038=360.000-OU045T_05-PCD2.m4160 PLS SBC - User Manual.pdf
` To avoid reflections, each segment must be terminated at the ends of the cable.  According to the Profibus standard, this must not be done on the device. The  PCD7.T160 termination boxes or standard 9-pole Profibus DP D-Sub connec- tors are suitable for this purpose.` Details can be found in the manual “26- 765 Profibus DP”.User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-2112-6Remove the power supply from the PCD2.M4_. ● Remove all cables (UBS, Ethernet, Profibus, RS-232) that may be present and that may interfere with the removal of the housing.Remove the upper part of the housing. ● Next, insert the spacer supplied (Fig. 2) on the back of the PCD2.F7500 to be  attached. The round end of the spacer must be inserted into the round hole of  the CPU board.PCD7.F75000X816S2X1X7X9X2 MPIX3ExtX6y r o m e My r o m e My r o m e My r o m e MX5RunHaltErrorCPU0 6 5 4 M 2 D C P.Fig. 1Fig. 2OS1Fig. 3t t a BM1CDo not remove