Title: +038=310.101-##047._01-FDV DrM vanning tak.pdf
10. Select a wire gauge that meets electrical specifications. Multi-strand, direct-burial wire is recommended. Refer to local building codes for additional requirements. 11 11. Use a watertight connector to connect one lead on each valve to a common wire (A). Either lead may be used. All valves on the same controller can share the same common wire.Use a watertight connector to connect the second lead on each valve to a power wire (B). Each power wire must be run separately to the controller.12. Connect the shared common wire (A) to the common 12 terminal on the controller. Connect one power wire from each valve (B) to a station terminal on the controller.Operate Valve Manually13 13 To open the internal bleed, turn the solenoid handle (A) counterclockwise ¼ to ½ turn. Be sure to re-tighten the solenoid completely. Always use the solenoid handle, which is designed to shut the valve off completely and keep it from “weeping.”