Title: +135.01=744.001-UP001T_03-O80 LED brukermanual.pdf
5. Emergency light luminaires should be tested and the results/actions must be recorded in accordance with applicable regulations. Please refer in this respect to EN 50172: a. A function test at least once a month. b. Full load test at least once a year. In the interests of safety, we recommend that a full load test is carried out every three months.c. The details to be recorded are asfollows: i. Date when the facility was put into operation ii. Date for tests iii. Date and comments concerningservicing at the facilityiv. Date of errors which occur at the facility and what measures shouldbe takenv. Date when measures are takenand subsequent test status6. Luminaires with the Self-Test function automatically test themselves according to EN 50172. Any errors are indicated on a bi-colour diode or a set of LEDs. A lighting pattern for the various errors can be found in the accompanying user manual. User manuals can also be downloaded from the ‘Download’ section on our website. Maintenance