Title: Data tester Smestad skole - Detaljert.pdf
dB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,9 23,8 3,1 497,00Remote: 36 27,8 23,9 3,9 496,00Worst Value: Local: 36 26,9 23,8 3,1 497,00Remote: 36 27,7 23,8 3,9 497,00PS-ACRF: Pass Worst Margin: Local: 12 71,8 61,2 10,6 1,00Worst Value: Local: 12 18,8 7,3 11,5 496,00Remote: 45 70,8 61,2 9,6 1,00Remote: 12 18,7 7,3 11,4 494,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:05Signature:______________________ Page: 75Copper Certification ReportCable Label: 521.002-UD-202 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:01:49 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: