Title: +038=310.000-NI024T_01-Innreg. protokoll OAR.xlsx
360.021 1.07 1 5.23 2.6 DN50 1.07 Sekundær side 360.021 1.01 1 4.2 2.7 DN50 1.01 Primær side 360.022 0.045 0.04 32.7 0.8 DN 20 1.125 Pumpe 1,1 meter 360.023 0.05 0.04 10.2 0.9 DN20 1.25 Pumpe 1,1 meter 360.024 0.05 0.04 9.3 0.9 DN20 1.25 Pumpe 1,2 meter 360.025 0.048 0.04 10.5 0.6 DN20 1.2 Pumpe 1,02 meter 360.026 0.04 0.036 9.5 0.5 DN 20 1.111111 Pumpe 1,02 meter 360.027 0.36 0.31 6.17 2 DN32 1.16129 Pumpe 2 meter 360.028 - 360.029 - 360.030 0.047 0.04 10.4 0.5 DN20 1.175 Pumpe 1,02 - - Olav V gt plan 5 (McKinsey) - 370.101 SV 503 0.51 0.32 14.1 2 DN32 1.59375 Akse A 8 stk baffler 0,04l/s 370.101 SV 504 0.35 0.24 11.9 2 DN 25 1.458333 Akse D 6 stk baffler 0,04 l/s 370.101 SV 502 0.42 0.4 28.9 1.3 DN 32 1.05 Pumpe 1,5 meter Datarom 370.101 SV 501 1.84 1.2 9.5 3 DN 50 1.533333 Baffler 20 stk og datarom 370.101 SV 505 0.75 0.44 11.6 4 DN 25 1.704545 Baffler mot bakgård 11 stk 370.101 SV 506 0.89 0.52 15.8 4 DN 25 1.711538 Baffler mot Olav V gt 13 stk 310.101 SV 501 0.43 0.4 503 0.6 DN 25 1.075 Backup vann