Title: ECY-303_SP.pdf
Maximum number of standard room devices supported per controller combined14excluded, no USB peripheralsFull Load Power Consumption 36VA; external 24VAC loadsexcludedAllure EC-Smart-Vue Series2 4 Allure EC-Smart-Comfort 4 SeriesFrequency Range 50 to 60HzOvercurrent Protection Field replaceable fuseFuse Type 2A, fast-acting, 5 × 20mm(GMA-2A)Allure EC-Smart-Air Series2 4 EC-Multi Sensor 4 4ECx-Light-4 / ECx-Light-4D / ECx-Light-DALI1.24VDC does not support DO (triac outputs).CommunicationsEthernet Connection Speed 10/100 MbpsCable Type Cat 5e, 8 conductor twisted pair(unshielded)Addressing IPv4 or HostnameECx-Blind-4 / ECx-Blind-4LV 4 4Maximum number of Bluetooth low energy room devices per controller combined 3 Allure UNITOUCH™ 2 EC-Multi-Sensor-BLE 4BACnet Profile BACnet Building Controller (B-BC)), AMEV AS-A and AS-BBACnet Listing BTL, WSP B-BCBACnet Interconnectivity BBMD forwarding capabilities BACnet Transport Layer IPWeb Server Protocol HTML5