Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF090 16C2/003 30.11.2020 11:53RCD II: 28.5mAUci: 0.2V t: 17.7ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 26.11.2020 13:53SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 26.11.2020 13:53Z-LINEZ: 0.43ΩIsc: 531A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 26.11.2020 13:53Zs(rcd)Z: 0.46ΩIsc: 505A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 26.11.2020 13:53RCD II: 28.5mAUci: 0.1V t: 102.1ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF091 16C2/003 27.11.2020 11:42KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩTallberg Elektro A/S Tlf.22796640Side:42GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 290290291291292292