Title: 2 etg del2.pdf
Cable ID: T2019 Date / Time: 10/11/2013 08:19:08 AM Headroom 5.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]88 135 5 4.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]21.9 249.0 30.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.2 206.0 36.7 36 7.0 206.0 34.1SR 12-36 5.7 218.0 36.3 12 7.5 218.5 33.7MAIN 36-78 5.2 206.0 36.7 36 7.7 241.0 33.0SR 12-36 5.7 218.0 36.3 12 7.5 218.5 33.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.7 6.1 48.4 12 19.0 3.6 50.0