Title: bn305_cgb.pdf
Number of addresses: 2S1.1 OFFS1.2 OFFS1.3 ONS1.4 OFFApplication include: • Manual input for Pre Alarm • •Pre Alarm input from a detector with relay output Sprinkler contacts, etc.Function: Delayed Alarm condition signalling input unit with feedback function. Input delay 2 seconds. Configurable delays for entering Pre Alarm and Alarm condition. Default delays: Pre Alarm 10 seconds, Alarm 20 seconds.The relay contact will follow the state of the input.Number of addresses: 2Application include: •Sprinkler contacts, etc.Autronica Fire and Security AS | Tel.: +47 90 90 55 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 5Dual Monitored Input/Output Unit – BN-305Function FFunction HS1.1 ONS1.2 OFFS1.3 ONS1.4 OFFS1.1 ONS1.2 ONS1.3 ONS1.4 OFFFunction: Fault, Pre Alarm and Alarm condition.Function: Alarm condition signalling input and independent relay output function.Number of addresses: 2Number of addresses: 4Applications include: