Title: +038=360.021-#####._06-360.021 Gold RXF-12 Ventilasjonsaggregat Swegon - Installasjonsanvisning.pdf
Independent contact, max. 5 A/AC1, 2 A/AC3, 250 VAC. Closes when the unit is operating.28,29,30Damper control24 VAC. 28= Controlled 24 VAC (G), 29= 24 VAC (G), 30= 24 VAC (G0).31,32Control voltage24 VAC control voltage. Terminals 31-32 are loaded with a total of 16 VA. Opened by means of the safety isolating switch.33,34Reference voltageOutput for constant 10 VDC. Max. permissible load: 8 mA.35,36,37,38Control, recirculation damperThe recirculation damper can be loaded with max. 2 mA at 10 VDC. 35= 24 V AC (G), 36= 24 V AC (G0), 37= 0-10 V DC control signal, 38= 0-10 VDC feedback signal.The max permissible common load on terminals 31-32, outputs for Heat/Cool and damper output (terminals 28-30) is 50 VA.212214.Respektive anslutning får belastas med max 16 VA.ABSDDigitala ingångar, plint 4-17, är av typ klenspänning. Analog ingång, plint 18-19 har ingångsimpedans 66 kΩ.PlintFunktionKommentar1,2,3Anslutningar för EIA-485