Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
) jumper selectableI/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24?V are disconnected from the power supply.6-77High-speed output module with 4 output channels of 8 bits each. Different output signals can be chosen with the aid of jumpers. Suitable for processes in which a large number of actuators have to be controlled, such as in the chemical industry and building automation.Module overviewPCD3.W400: Single signal module with 4 output channels of 8 bits each. 0…10 VPCD3.W410: General purpose module with 4 output channels of 8 bits each. Signals can be selected from 0…10 V, 0…20 mA or 4…20 mA.Technical dataNumber of output channels: Signal ranges:4, short circuit protected W400 0…10 V W410 0…10 V*) 0…20 mA 4…20 mA}selectable with jumpersResolution (digital representation): Conversion time D/A: Load impedance:Accuracy (of output value):Residual ripple: