Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]17.3 75 1 2.84Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]33.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.0 464.0 29.6 45 9.1 450.0 27.4SR 36-78 10.3 498.0 27.9 45 10.3 288.0 31.7MAIN 12-45 9.7 491.0 28.3 36 9.8 497.0 25.1SR 36-78 10.3 498.0 27.9 78 11.8 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.8 3.9 53.5 45 15.2 2.6 53.9SR 78-45 15.7 3.9 53.5 45 15.3 2.9 53.1MAIN 45-78 20.7 500.0 11.3 45 22.4 495.0 8.3SR 78-45 20.4 498.0 11.3 45 21.7 498.0 8.30100806040200250 MHzACR-F (dB)