Title: etg u1.pdf
Cable ID: D0073 Date / Time: 10/22/2013 01:00:58 PM Headroom 1.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]105 165 10 4.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]21.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 1.3 249.0 35.4 36 2.7 249.0 32.7SR 36-45 8.9 64.0 45.0 36 9.7 249.0 32.7MAIN 12-36 1.3 249.0 35.4 36 2.7 249.0 32.7SR 12-36 9.4 249.0 35.4 36 9.7 249.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 16.6 99.0 24.3 12 18.0 99.0 21.3