Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Each with a changeover contact protected with 2 varistors. Tech. data as for PCD2.A200. The 24 V supply to the relay coils is via the screwless terminals “Uext”, located next to the 4 relays.4 analogue outputs, with 8 bit resolution, O32...O35 (base addr 32 *, channels 0...3)Each channel selectable with "U/I" jumper for voltage 0...10 V or current 0...20 mA. Tech. data as for PCD2.W410.4 analogue (cid:76)(cid:81)tputs, with 10 bit resolution, (cid:44)48...(cid:44)51 (base addr 48 *, channels 0...3)Each channel can be configured separately with the jumper combinations shown for voltage 0…10 V (“U”), current 0...20 mA (“I”) or for resistive temperature sensors Pt/Ni1000 (“T”) for a temperature range from -20…+100°C. Tech. data as for PCD2.W2xx.Internal current consumption from +5 V busV+ Bus10 … 50 mA 10 … 40 mA24 V connection (Uext):This is located next to the 4 relays as screwless terminal “Uext”. The 24 V supply is common to the relay coils and the external supply to the analogue outputs.