Title: 1 etg del 2.pdf
RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: D1032 Date / Time: 10/17/2013 11:53:49 AM Headroom 12.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]86 135 9 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.1 84.3 33.5 36 13.4 99.8 29.3SR 12-36 12.3 84.3 33.5 36 13.0 99.8 29.3MAIN 12-36 12.3 99.8 32.3 36 13.4 99.8 29.3SR 12-36 12.6 99.8 32.3 36 13.0 99.8 29.310080604020NEXT (dB)