Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Z-LINEZ: 0.17ΩIsc: 1.38kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 27.11.2020 10:55Zs(rcd)Z: 0.18ΩIsc: 1.27kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 27.11.2020 10:56RCD II: 28.5mAUci: 0.2V t: 15.5ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 30.11.2020 11:59 (ELEKTRIKER)Tallberg Elektro A/S Tlf.22796640Side:44GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.304304305305306306307307308308309309310310TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 27.11.2020 11:53R LOW OhmR: 0.22ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7Ω