Title: +038=320.103-OE009T_02-Multical 801 Energimåler Kamstrup - Produktdatablad.pdf
Application types MULTICAL® 801 operates with 9 different energy formulas, E1...E9, that are all calculated in parallel in connection with each integration no matter how the meter is configured. The energy types E1 to E9 are calculated as follows: E1=V1(T1-T2)k E2=V2(T1-T2)k E3=V1(T2-T1)k E4=V1(T1-T3)k E5=V2(T2-T3)k Outlet energy or tapping from outlet E6=V2(T3-T4)k E7=V2(T1-T3)k E8=m³xT1 E9=m³xT2 This renders MULTICAL® 801 capable of calculating the heat and cooling energy of most appli- cations, both closed and open systems. All energy types are data logged and can be displayed independent of configuration.