Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]26.0 113 2 3.97Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]29.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.3 478.0 28.9 36 6.7 468.0 26.5SR 12-36 8.4 399.0 31.4 36 9.7 460.0 26.9MAIN 36-45 7.5 492.0 28.2 36 7.6 497.0 25.1SR 12-36 9.2 497.0 28.0 36 10.0 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.9 7.1 48.2 45 21.5 500.0 8.3SR 78-45 19.9 7.1 48.2 45 21.9 6.0 46.7MAIN 36-45 23.0 500.0 11.3 45 21.5 500.0 8.3