Title: Data tester Smestad skole - Detaljert.pdf
Margin 39,1 - 239,0 33,0 14,3Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,2 3,0 1,8 2,35Worst Value: Local: 45 25,7 43,8 18,1 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 23,8 17,2 6,6 48,25Remote: 12 20,7 17,5 3,2 44,25Worst Value: Local: 12 16,7 8,7 8,0 339,00Remote: 78 14,2 8,0 6,2 452,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,0 26,7 2,3 499,00Remote: 36-45 29,9 26,7 3,2 500,00Worst Value: Local: 36-45 29,0 26,7 2,3 499,00Remote: 36-45 29,9 26,7 3,2 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,5 10,2 10,3 499,00