Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 78-45 14.8 391.0 13.4 45 14.6 3.9 50.5SR 45-78 14.9 391.0 13.4 45 14.4 2.5 54.3MAIN 78-45 15.3 420.0 12.8 45 16.3 443.0 9.3SR 45-78 15.3 420.0 12.8 45 16.9 464.0 8.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 17.5 31.5 40.2 45 18.5 31.8 37.7SR 36-45 16.2 31.5 40.2 36 17.8 31.5 37.8MAIN 12-45 33.3 499.0 -12.3 12 34.4 499.0 -15.2SR 36-45 34.2 500.0 -12.4 36 33.6 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.9 496.0 8.0SR 12 5.4 499.0 8.0MAIN 12 7.9 496.0 8.0SR 12 5.4 499.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS