Title: Installasjonsmanualer.pdf
1.1 kVA 24 VDC (NRT2-B1100) • 1.7 kVA 48 VDC (NRT2-B2200) • 2.2 kVA 48 VDC (NRT2-B2200) • 3.3 kVA 72 VDC (NRT2-B3300)the UPS has been shut down completely and all isolation switches are OFF; • switches upstream of the UPS are OFF.When connecting the UPS to the battery extension, use only the cable provided with the equipment.Any wiring error that results in the polarity of the battery being inverted can cause permanent damage to the equipment.Set the switch on the back of the battery extension module to the OFF position.Connect the battery extension module to the UPS.Set the switch on the back of the battery extension module to the ON position.Set the number of EBM connected to the UPS on setting menu.14 NETYS RT 1.1-3.3 kVA - Ref.: IOMNETRTXX0B-EN 01Switch ON-OFFX X - T R T E N W R D 2 5 01100 VAConnection of multiple batteriesMax EBMwith additional chargerNRT2-U11002/NRT2-U17002up to 10