Title: 2 etg del2.pdf
259 410 29 11.2259 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.0 * 249.5 35.4 36 1.1 235.0 33.2SR 12-36 6.5 241.0 35.6 36 6.7 241.0 33.0MAIN 36-45 1.0 250.0 35.3 36 1.1 250.0 32.7SR 12-36 6.5 241.0 35.6 36 6.7 241.0 33.010080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 12.8 246.0 16.4 36 14.8 245.5 13.4SR 45-36 13.0 50.0 30.2 45 14.4 37.8 29.7MAIN 45-36 12.8 246.0 16.4 36 14.8 245.5 13.4SR 36-45 13.4 246.0 16.4 45 14.8 246.0 13.4010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz