Title: +135.01=744.001-UP001T_03-O80 LED brukermanual.pdf
Connection The supply cable must be of a quality that can withstand exposure to UV radiation and heat from the luminaires and light sources. Even if temperature conditions inside the luminaires are within the requirements, it may be that the power cable is not of a sufficient quality to withstand this. The supply cable must be protected from direct radiation from the florescent light sources by means of lightproof casing or similar. If the supply cable is routed through the luminaire, both possible UV radiation and the impact of heat from the luminaire components on the cable needs to be taken into account.Outdoor use requires suitable flexible cables assuring the water tightness through the cable inlet. For easy maintenance of outdoor products we recommend to lubricate the screw threads with silicone grease.Megger Test The luminaires can be megger tested with a maximum of 500V DC. The voltage is applied between the earth and the paired phases. Please note: Disconnect4