Title: økernvn 94.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.9 25.1 42.5 36 12.8 31.5 37.4SR 12-36 17.4 25.0 42.6 36 17.0 25.1 40.1MAIN 36-45 17.8 247.5 4.9 36 16.7 243.5 2.7SR 36-78 22.7 248.0 4.9 36 23.8 248.0 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.7 14.1 20.3SR 36 3.2 26.9 18.9MAIN 36 9.1 243.0 10.1SR 36 7.1 250.0 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4