Title: V20-05-02 VVS-anlegg plan 5 - DM3.pdf
+05 = 320.102 - OE 051 0.100 L/sSTAP/STAD DN20320.102: 54mm 320.102: 54mmLD018T Maks:100 m³/h Kjøling: 750 W 0.060 L/sLD018T Maks:205 m³/h Kjøling: 435 W 0.035 L/s Varme: 300 W 0.007 L/sLD018T Maks:100 m³/h Kjøling: 750 W 0.060 L/s Varme: 280 W 0.007 L/s4370.101: DN 100mm 370.101: DN 100mmSTAP/STAD DN32Alle overstrømningsventiler toalettkjerne: SF002T-125 og kanal ø125 UK=2737LD024T Q: 200 m³/h Varme: 820 W 0.018 L/s+05 = 370.101 - OE 051 0.410 L/s5DN 100 +c 1000Skap tørropplegg6LD022T Maks:80 m³/h Kjøling: 200 W 0.016 L/sLD018T Maks:200 m³/h Kjøling: 500 W 0.040 L/s Varme: 550 W 0.013 L/sLD018T Maks:200 m³/h Kjøling: 470 W 0.037 L/s Varme: 210 W 0.005 L/sLD018T Maks:200 m³/h Kjøling: 470 W 0.037 L/s Varme: 210 W 0.005 L/sLD018T Maks:210 m³/h Kjøling: 300 W 0.024 L/s Varme: 350 W 0.008 L/s7STAP/STAD DN32370.101: DN 100mm 370.101: DN 100mm+05 = 370.101 - OE 052 0.440 L/sLD018T Maks:210 m³/h Kjøling: 300 W 0.024 L/s Varme: 350 W 0.008 L/s