Title: Hardware Installation Guide.pdf
Addresses assigned to input/output panels do not need to be consecutive. On the first panel, the inputs/ outputs represent the first sixteen floors (e.g.: Input 1 = first floor, Input 2 = second floor, etc.). The second panel represents the next sixteen floors (floor 17 through 32), etc.revision 6 — 319LNL-1200-U Output Control ModuleOverview of Elevator ControlAccess Control SystemIntelligent System ControllerMaximum: 4000 feet (1219.2 meters) 5 conductorsOutput Control ModuleInput Control ModuleSingle Reader InterfaceSingle Reader Interface ModuleSingle Reader InterfaceUp to 128 Outputs - eight Output Control ModulesUp to 128 Inputs - eight Input Control ModulesElevator Control RoomElevator Reader (inside cab)59.5Power and CommunicationsThe Output Control Module requires a 12 to 24 VDC ± 10% power source for its input power.Wire the Power In input with 18 AWG (minimum) twisted pair cable.Power SourceRequirementsCurrentDC power source