Title: Økernveien 94 Sprinklerberegning U2.pdf
1(eu.TeeScr-Run); 3.5450.84 1.940.0071 0.020.02 0n15 n17120 0.10161(eu.TeeScr-Run); 3.5440.48 1.890.0068 0.020.02 0n13 n15120 0.10161(eu.TeeScr-Run); 3.5434.73 1.870.0066 0.020.02 0n11 n13120 0.10161(eu.TeeScr-Run); 3.5431.79 1.850.0065 0.020.02 0n9 n11120 0.10161(eu.TeeScr-Run); 3.5429.28 1.840.0065 0.020.02 0n7 n9120 0.10161(eu.TeeScr-Run); 3.5424.59 1.820.0063 0.020.02 0n5 n7120 0.10161(eu.TeeScr-Run); 3.5415.82 1.790.0061 0.020.02 0n3 n5120 0.10161(eu.TeeScr-Run); 3.5401.25 1.720.0057 0.020.01 0n1 n3120 0.10161(eu.90s); 1.91 2.9379.08 1.630.0051 0.010.01 0n25 n1120 0.10161(eu.90s); 1.98.3 10.2379.08 1.630.0051 0.050.01 0n26 n25120 0.10161(eu.TeeScr-Run); 5379.08 1.630.0051 0.030.01 0n27 n26120 0.10161(eu.90s); 1.96 7.9460.85 1.980.0074 0.060.02 0n30 n27120 0.10161(eu.90s); 1.914 15.9460.85 1.980.0074 0.120.02 0n31 n30120 0.1016