Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]33.4 145 2 5.05Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.3 128.5 40.1 36 7.6 146.5 36.6SR 12-36 8.4 458.0 30.1 36 8.6 460.0 27.2MAIN 12-36 8.4 500.0 29.2 36 9.4 500.0 26.4SR 12-36 9.0 500.0 29.2 36 8.9 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.0 6.9 48.5 45 19.0 500.0 8.3SR 78-45 18.9 496.0 11.3 45 18.2 496.0 8.3MAIN 45-78 19.5 496.0 11.3 45 19.0 500.0 8.3