Title: 360.002 - Tilluft.pdf.pdf
22.213.0 +23.824.023.80.0 +0.024.60.2 +7.224.624.60.3 +23.326.82k [dB]21.50.7 +0.020.91.5 +0.03.016.40.0 +0.016.511.0 +18.218.417.90.0 +0.023.50.2 +6.223.423.40.3 +22.225.74k [dB]15.90.7 +0.015.31.5 +0.03.011.00.0 +0.011.312.0 +15.815.912.40.0 +0.019.60.2 +2.219.619.60.3 +18.221.88k [dB]9.50.7 +0.09.31.5 +0.03.05.50.0 +0.06.514.0 +7.07.16.80.0 +0.013.20.2 +0.013.313.30.3 +11.215.2Lp [dB]24,8LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeProductSizeDUCT315136 FLOWDAMPER LEO-0-315315DUCT315SILENCERLKR-315-1200315DUCT315BEND-90MAGIB-C4-*-*315DUCT315137 FIREDAMPER FKR-EU/DE/315/315DUCT315138 T-BRANCHTCPU_DK-*-*0,0 315/315L [m]0,30,00,00,90,5Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]13004,60,2 Sound in: