Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
PCD3.W500 module, fully equipped (with additional module plugged on) Apart from the bus connector, DC-DC converter and terminals, the base module carries the two input channels with the 2-pole jumper for unipolar or bipolar operation and a number of preset potentiometers, which cannot be adjusted by the user. The plug-on module contains the two analogue outputs with the two 3-pole jumpers for the individual unipolar or bipolar operation of each output. The module also works without the plug-on module.Changing the jumpers On this circuit board there are components that are sensitive to electrostatic discharges. For further information, refer to Appendix, "Icons"6-95PCD3.W500Block diagram+/- 10 VRef. 2.5 VInput 0Prot. EMCDiff.V Adj.Mux./4 /8ANBusInput 1Prot. EMCDiff.Output 0Prot. EMCx2 x4Diff. x2ANBusOutput 1Prot. EMCx2 x4Diff. x2ANBus+/- 10 VRef. 2.5 VProgrammingReset