Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Sikringstype: C SIKRING I: 16A SIKRING T: 35ms dU_lim: 4.5% Isc: 214A Z: 1.08Ω Zref: ___ΩOBJEKT / Plan 10 / FUSE038 06.02.2020 15:02RCD AUTOt : 54.7ms t : 65.2ms t : 30.2ms t : 29.4ms t : >300ms t : >300ms I I: 28.5mA : 28.5mAUc: 1.6V Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE038 07.02.2020 09:22KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE039 06.02.2020 14:50Z-LINEZ: 0.92ΩIsc: 250A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE039 06.02.2020 15:04TEST RAPPORTSide:11GODKJENTMISLYKKESMISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTGODKJENTGODKJENTGODKJENTNr.686869697070717172727373ResultatRCD AUTOt : 58.1ms t : 66.8ms t : 30.1ms t : 28.7ms t : >300ms t : >300ms I I: 28.5mA : 28.5mAUc: 0.1V Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE039 06.02.2020 14:38Zs(rcd)Z: 0.86ΩIsc: 269A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A