Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
System water volume - exchanger water flow rate The Connect Touch control is equipped with anticipation logic making it highly flexible in adjusting operation to parameter drift, particularly on hydraulic systems with low water volumes. By adjusting compressor running times, it prevents short cycle protection cycles from starting and, in most cases, eliminates the need for a buffer tank.Cooling mode (Evaporator) - Chilled water temperature = 12°C/7°C - Hot water temperature = 30°C/35°CHeating mode (Condenser) - Chilled water temperature = 10°C/7°C - Hot water temperature = 30°C/35°CNote: The minimum volumes of chilled water are calculated for EUROVENT rated conditions:This value is applicable for most air conditioning applications (unit with fan coil units)Note: For installations running with a low volume of water (unit with air handling unit) or for industrial processes, the buffer tank is essential.■ Minimum system water volume and exchanger water flow rateDYNACIAT LG080090100120