Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 45-78 14.5 478.0 11.6 78 15.8 478.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.3 44.5 35.9 45 20.9 44.5 33.5SR 36-45 19.3 44.5 35.9 45 21.0 44.5 33.5MAIN 12-45 37.2 494.0 -12.0 36 37.2 499.0 -15.2SR 36-45 36.7 499.0 -12.3 36 36.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.8 460.0 8.0SR 12 6.0 491.0 8.0MAIN 12 7.8 460.0 8.0SR 12 6.0 491.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00433.7 m60Insertion Loss (dB)504030201000250 MHz500100