Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 12] [Pair 45] [Pair 36] [Pair 45]35.1 152 2 5.24Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]26.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.3 466.0 29.9 45 8.3 492.0 26.5SR 36-45 8.6 498.0 29.3 36 9.5 500.0 26.4MAIN 36-45 8.6 492.0 29.4 45 8.3 492.0 26.5SR 36-45 8.6 498.0 29.3 36 9.5 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.6 412.0 12.9 45 14.4 3.8 50.8SR 78-45 14.5 412.0 12.9 45 14.3 2.9 53.1MAIN 45-78 15.1 451.0 12.2 78 16.5 477.0 8.7SR 78-45 15.0 451.0 12.2 45 16.6 467.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.2 44.0 36.1 45 20.6 40.3 34.8