Title: Data tester Smestad skole - Detaljert.pdf
Overall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 36,4 68,0 189,0 11,0 6,5Limit 100,0 - 555,0 50,0 25,0Margin 63,6 - 366,0 39,0 18,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,7 3,1 2,4 3,10Worst Value: Local: 36 15,4 43,6 28,2 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 12,3 8,0 4,3 458,00Remote: 78 18,1 12,4 5,7 143,00Worst Value: Local: 78 12,3 8,0 4,3 458,00Remote: 36 16,3 8,0 8,3 479,00dB -2030800Local250