Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
GODKJENTGODKJENT*Nr.2626272728282929303031313232ResultatSPÆNDINGUln: 231V Ulpe: 229V Unpe: 2V f: 50.0HzOBJEKT / Plan 10 / FUSE029 06.02.2020 09:10R LOW OhmR: 0.08ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE029 10.02.2020 08:55Z-LINEZ: 0.82ΩIsc: 281A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE029 06.02.2020 12:36R ISOR: 9.83MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩOBJEKT / Plan 10 / FUSE031 10.02.2020 13:16SPÆNDINGUln: 226V Ulpe: 228V Unpe: 2V f: 49.9HzOBJEKT / Plan 10 / FUSE031 10.02.2020 13:17Z-LINEZ: 0.74ΩIsc: 310A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE031 10.02.2020 13:17RCD II: 28.5mAUci: 0.2V t: 107.7ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE031 06.02.2020 09:08TEST RAPPORTSide:5GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.3333