Title: Simployer - Data testrapport =514.204-FS001.pdf
Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]60.4 311 23 10.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]17.8 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 8.8 57.5 44.0 3,6 9.8 57.3 41.2SR 3,6-7,8 9.2 23.1 50.6 3,6 9.8 72.8 39.5MAIN 1,2-3,6 10.9 248.5 33.2 3,6 11.3 245.0 30.3SR 3,6-7,8 9.7 243.0 33.3 7,8 11.3 246.0 30.3PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 15.8 223.5 16.3 4,5 17.3 226.5 13.2SR 7,8-4,5 15.8 225.5 16.2 4,5 18.0 226.5 13.2MAIN 7,8-4,5 16.0 236.5 15.8 4,5 17.3 234.0 12.9