Title: Data tester Smestad skole - Detaljert.pdf
Insertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,1 2,2 2,95Worst Value: Local: 45 19,7 43,6 23,9 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 21,1 15,7 5,4 68,00Remote: 12 19,5 14,4 5,1 91,50Worst Value: Local: 12 14,7 9,1 5,6 307,00Remote: 12 14,3 8,0 6,3 423,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,8 26,7 2,1 499,00Remote: 36-45 29,5 26,7 2,8 500,00Worst Value: Local: 36-45 28,8 26,7 2,1 499,00Remote: 36-45 29,5 26,7 2,8 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 68,4 57,3 11,1 2,20Remote: 45-12 68,4 57,3 11,1 2,20