Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD59 Date / Time: 28/01/2022 13:23:34 Headroom 8.5 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]53.5 275 20 9.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.9 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 8.5 59.0 43.8 4,5 10.6 59.0 41.0SR 4,5-7,8 10.0 183.5 35.4 3,6 11.8 53.3 41.8MAIN 4,5-7,8 8.8 248.5 33.2 7,8 11.3 248.5 30.2SR 1,2-3,6 11.3 233.0 33.6 3,6 12.1 243.0 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)