Title: Installasjonsmanualer.pdf
WARNING! If problems should persist or reoccur frequently after following the procedures indicated in this section, contact the SOCOMEC After Sales Service, providing a full description of the current difficultyProblemPossible causeSolution"UPS not powered up (no alarm, no display)No mains presentCheck if mains is present or distribution switch are closedThe ON/TEST button has not been pressed. Press the ON/TEST button to switch the UPS on.Shutdown due to flat battery and no mains power.Wait for mains power to be restoredThermal switch on the rear panel has been tripped.Reduce the load connected to the UPS, then reset the thermal-magnetic switch.Faulty UPSContact SOCOMEC After Sales Service if the solu- tions indicated above do not solve the problem.UPS does not guar- antee the expected backup time.UPS internal batteries not completely charged.UPS in overload.Recharge the batteries for a minimum of 8 hours.Disconnect non-essential loads.Depleted batteries.