Title: Ahlsell.pdf
Cable ID: UD 47 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/11/2022 06:03:42 AM Operator: Pam Headroom 10.1 dB (NEXT 3,6-4,5) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505095Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 3,6] [Pair 4,5] [Pair 4,5] [Pair 3,6]16.1 80 2 6.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]33.4 487.0 43.1Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 10.5 493.0 26.9 4,5 11.5 493.0 24.0SR 3,6-4,5 10.1 500.0 26.7 3,6 10.5 493.0 24.0MAIN 3,6-4,5 10.5 493.0 26.9 4,5 11.5 493.0 24.0SR 3,6-4,5 10.1 500.0 26.7 3,6 10.6 499.0 23.810080604020NEXT (dB)