Title: Simployer - Data testrapport =514.204-FS001.pdf
Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]33.8 173 12 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.5 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 7.6 249.0 33.1 3,6 10.3 249.0 30.2SR 4,5-7,8 9.5 207.5 34.5 7,8 11.4 207.5 31.6MAIN 1,2-3,6 7.6 249.0 33.1 3,6 10.3 249.0 30.2SR 4,5-7,8 9.5 207.5 34.5 7,8 11.4 207.5 31.6PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 16.4 229.0 16.1 4,5 17.1 4.6 47.0SR 7,8-4,5 16.5 210.0 16.8 4,5 17.3 4.0 48.2MAIN 7,8-4,5 16.4 236.5 15.8 4,5 17.7 237.5 12.7