Title: Ahlsell.pdf
N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 16.5 3.5 61.7 3,6 18.0 3.5 58.7SR 3,6-7,8 18.9 7.6 54.9 3,6 19.0 7.3 53.0MAIN 3,6-4,5 49.9 500.0 -17.1 3,6 51.0 499.0 -19.9SR 3,6-4,5 48.6 487.0 -16.1 3,6 49.6 487.0 -18.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 3,6 7.5 357.0 8.5SR 3,6 6.5 477.0 8.0MAIN 3,6 8.0 478.0 8.0SR 3,6 6.5 477.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Ahlsell Site: Not Set Floor: Not Set Rack: Not Set Untitled1Building: Not Set Room: Not Set Patch: Not SetPage 22Test Summary: PASSRemote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 25050959.5 m60Insertion Loss (dB)5040