Title: 1 etg del 2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]189 300 21 8.0189 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.0 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.8 * 244.5 35.5 36 0.8 * 248.0 32.8SR 36-45 8.3 67.3 44.6 36 9.5 206.0 34.1MAIN 36-45 0.8 244.5 35.5 36 0.8 248.0 32.8SR 36-78 9.9 247.5 35.4 36 10.1 247.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.2 240.0 16.6 36 17.5 162.5 17.0SR 45-36 14.6 249.0 16.3 36 16.9 160.5 17.1MAIN 36-45 15.2 249.5 16.2 45 17.5 249.0 13.3