Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
TEST RAPPORTBruker:Teststed:Tallberg Elektro A/S Stanseveien 4UF+DM1.E5.433.09.04 Dronning Mauds gate 1-3Instrument dataType:EUROTEST COMBOSer.Nr.:13250825Modell:MI 3125BTProdusent:Metrel d.d.Nr. 11ResultatDM1-3. Plan 9 / DM1.E5.433.09.04 / XQ000 NZM2/4 15.06.2020 08:29Z-LINEZ: 0.25ΩIsc: 911A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A22DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ000 NZM2/4 15.06.2020 08:29Zs(rcd)Z: 0.21ΩIsc: 1.10kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A33DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ000 NZM2/4 10.06.2020 15:06R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩ44DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ000 NZM2/4 16.06.2020 08:39SPĆNDINGU12: 401V U13: 400V U23: 401V f: 50.0Hz : 1.2.355DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 15.06.2020 11:37Z-LINEZ: 0.42ΩIsc: 552A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A66