Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Restrictions (not applicable with cables, hardware version B)For the I/O connectors set out below, the following restrictions must be observed:…on the PCD3.Mxxxx CPUs:If a PCD3.K106/116 cable is used to connect to the next module holder, do not plug module into Slot 3 (far right).The Ethernet cable can be plugged in, but (depending on the RJ-45 cable) may touch the I/O connection to the module if in Slot 0.…on the PCD3.Cxxx module holders:No restriction, where the PCD3.K010 connector is used to connect to other module holders (the supply connector can also be plugged in to the C200 with no problems).If a PCD3.K106/116 cable is used to connect from the preceding module holder or to the next module holder, do not plug the module into Slot 0 (far left) and do not plug into Slot 3 (far right).…on PCD3.T76x head stations:All angled Profibus connectors with max. height 40 mm can be used, e.g.●