Title: +038=310.101-SC020T_02-FDV-dokumentasjon - Danfoss AS - VA_VVS 5640952 med flere - Danfoss spoler.pdf
y In accordance with: - RoHS 2011/65/EU - LVD 2014/35/EUVoltageIndustrial plug size DIN 11 1) Protects against voltage peaks[V AC] 24[V DC] 24Suitable for coil types AB, ACLED colour RedBuilt-in VDR1) resistor YesCode no. 042N0267Technical dataDesign Supply voltage variation Power consumption Approval Enclosure Max. operating current Contact resistance Protection against wrong polarity Cable diameter Wire cross section Ambient temperatureMaterialsIndustrial form ±10% Max. 5 mA CSA IP65 (IEC 60529) 1.5 A clamping contact ≤ 4m Ω Yes 5 – 6 mm and 6 – 9 mm Max. 1 mm2 -25 – 60 °C / -13 – 140 °F Contacts: Terminal block: Flat gasket: Housing: Wire holder:CuZn, Cu/Sn-plated PA6 + 30% FG, black NBR LABS-fre PA6 PA6.6 + 50% FG P7,5 blackDimensions and weightWeight 0.027 kg / 0.059 lbsIC.PD.600.1A.02 | 22Universal electronic multi-timer Type ET 20 M