Title: 30. Technoporten_Brannalarmutstyr datablad.pdf
Response time<= 1 secondOutput relay rating1A 30 VDC resistive loadOutput relay typeDry contact, latching type; keep state on loss of power. No EOL monitoringThresholdShort circuit: 0-235  Activate: 260-1000  Normal: 1200-4800  Open circuit: 5400- Connectors and DIP switches on circuit board0333Autronica Fire and Security AS, N-7483 Trondheim 08 0333-CPD-075248EN 54-17:2005 Short circuit isolators EN 54-18:2005 Input/output devicesAUTRONICA FIRE AND SECURITY ASHead office, Trondheim, Norway Tel: +47 73 58 25 00, fax: +47 73 58 25 01, e-mail: info@autronicafire.no Oil and Gas division, Stavanger, Norway Tel: +47 51 84 09 00, fax: +47 51 84 09 99 Maritime division, Spikkestad, Norway Tel: +47 31 29 55 00, fax: +47 31 29 55 01Visit Autronica Fire and Security AS’ website: www.autronicafire.comSingle Monitored Input/Output Unit – BN-304Descriptions of connection optionsInput configuration A