Title: 1 etg del 2.pdf
100ACR-N @ Remote (dB)806040202500050100150200250MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 8.1Cable ID: D1011 Date / Time: 10/21/2013 12:41:07 PM Headroom 6.9 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]147 225 8 6.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]16.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.9 130.5 40.0 36 8.1 119.0 38.1SR 12-36 7.8 245.5 35.5 12 8.5 245.0 32.9MAIN 36-78 8.1 230.5 35.9 36 8.6 249.0 32.7SR 12-36 7.8 245.5 35.5 12 8.5 245.5 32.810080