Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Follow these general rules for installing supports:  No run component must be left unsupported.  For easier leveling, always use at least two supports for each run component wherever possible.  The supporting capacity of the support must be at least the weight of the run component plus 90 kg, inaccordance with IEC 61439-6. Components at the terminal ends of the run must be supported by separate supports. The weight of endcomponents must not be carried by transformers or switchboards. Vertical branches must be always supported as close as possible to the elbow angle.  Elbows and zed units must be supported individually.  Supports must be installed close to joint blocks. However, a support must never be positioned directlyunder a joint block.Edgewise horizontal installation:Flatwise horizontal installation:Supports for Edgewise Installation