Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
28.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.6 410.0 31.1 36 7.9 471.0 27.0SR 36-45 5.6 476.0 29.7 36 6.1 475.0 26.9MAIN 36-45 9.0 500.0 29.2 36 8.1 500.0 26.4SR 36-45 5.9 492.0 29.4 36 6.2 491.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.6 447.0 12.2 45 17.8 26.5 33.8SR 45-78 16.9 447.0 12.2 45 17.8 4.9 48.5MAIN 78-45 17.0 496.0 11.3 45 18.8 500.0 8.3SR 45-78 17.4 500.0 11.3 45 18.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.5 54.5 33.2 45 26.5 54.5 30.8SR 12-36 24.4 61.5 31.6 36 23.6 61.5 29.1MAIN 36-45 37.3 500.0 -12.4 36 36.6 500.0 -15.3SR 36-45 34.2 496.0 -12.1 36 34.3 491.0 -14.70804000250 MHzACR-N (dB)