Title: økernvn 94.pdf
Cable ID: D3182 Date / Time: 09/12/2013 11:59:58 Headroom 11.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]168 265 18 6.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.1 66.3 35.2 36 13.3 94.0 29.7SR 12-36 18.9 23.3 42.6 12 20.4 21.1 40.3MAIN 12-36 11.4 99.5 32.3 36 13.5 99.8 29.3SR 12-36 21.9 99.5 32.3 36 21.1 90.0 30.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 25.0 6.5 42.4 45 24.7 4.0 43.6