Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
8 analogue inputs 10 bit, 0…10V 8 analogue inputs 10 bit, 0…20mA 8 analogue inputs 10 bit, Pt/Ni1000 8 analogue inputs 12 bit, 0…10V 8 analogue inputs 12 bit, 0…20mA 8 analogue inputs 12 bit, 0…10V, 0…20mA, Pt/Ni1000 *) 8 analogue inputs 12 bit, Pt/Ni 100 8 analogue inputs 12 bit, resolution ‹ 0.1 °C, Pt1000) jumper selectableI/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24?V are disconnected from the power supply.6-57PCD3.W2x06.8.1PCD3.W2x0, analogue inputs, 8 channels, 10 bit resolutionApplicationWith its short conversion time of <50 µs, this module is universally suitable for recording analogue signals. The only limitations are with weak signals, as with Pt100 resistive temperature sensors, or with thermocouples.Module overviewPCD3.W200 PCD3.W210 PCD3.W220 PCD3.W220Z03 PCD3.W220Z12