Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
Manual bypassFuse HolderITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0023H S I L G N E24FanInput protection (magneto-thermal)Input and output terminal boardITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 00USB serial portITYS 10 kRS232 serial connector13. REAR VIEWEPO (Emergency Power Off)Dry contactSlot for optional communication cardsParallel portManual bypassFuse Holder14. CONNECTIONSThe installation and the system must comply with national plant regulations. If a dif- ferential switch is installed on the mains power switch (optional), it must be inserted upstream from the distribution panel.UPSMainsOutputCAUTION! Use selective type differentials. Any current dispersed by the loads will be summed to that of the UPS. The differential protection must be regulated in cases of loads with high current dispersion.ø (mm²) ≥ 6UPS6 kVAø (mm²)≥ 6≥ 1010 kVA≥ 1014-114-2NA14-3NL+NLOUTPUT OUTPUTBATTERY BATTERYINPUT INPUT6 to 10 kVA14-4