Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 36-45 15.9 4.3 52.7 45 14.4 3.0 52.7SR 45-36 15.9 4.3 52.7 45 14.3 2.6 53.9MAIN 78-45 16.4 500.0 11.3 45 17.5 500.0 8.3SR 45-78 16.5 500.0 11.3 78 18.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.1 67.0 30.3 45 26.1 67.3 27.8SR 36-45 24.0 71.3 29.5 36 24.7 72.0 26.8MAIN 36-78 36.7 494.0 -12.0 36 37.0 494.0 -14.9SR 36-45 38.7 500.0 -12.4 36 38.7 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.9 493.0 8.0SR 12 5.7 493.0 8.0MAIN 12 7.9 493.0 8.0SR 12 5.7 493.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS