Title: +135.01=315.002-UZ002T_01-Manual320.pdf
Make sure that the item is installed by a competent installer.320 IF - Inlets & outlet connections: 1” BSP female thread.Shut off the main water supply.320 F - Inlet & outlet adaptors 1” BSP female thread.Observe all local plumbing and building codes.320 M - Inlet & outlet adaptors 3/4” BSP male thread.Provided that the thermostatic mixing valve is installed, commissioned, operated within the specification limits and maintained according to this Manual, the risk of malfunction, if not eliminated, is considerably reduced.TemperatureMinimum Cold Water Temperature: 1°C - 25°CMaximum Hot Water Temperature: 70°CFactory Preset Outlet Temperature: 43°CSafetyOptimum Thermostatic Control Range: 35°C - 50°CFlow RatesThe use of the word ‘failsafe’ to describe the function of a thermostatic mixing valve is both incorrect and misleading. In keeping with every other mechanism it cannot be considered as being functionally infallible.