Title: økernvn 94.pdf
SR 36-45 11.7 21.4 44.4 36 13.4 21.3 42.0MAIN 12-45 18.5 224.0 7.3 12 17.5 224.0 4.7SR 12-36 17.8 250.0 4.7 12 17.7 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 0.7 *29.6 18.6SR 45 0.0 *29.6 18.6MAIN 36 4.2 246.0 10.1SR 36 5.1 249.5 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94