Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: T4189 Date / Time: 09/11/2013 12:17:54 Headroom 7.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]191 293 11 8.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.3 232.5 35.9 36 7.1 232.0 33.2SR 45-78 7.3 235.0 35.8 45 9.0 235.0 33.2MAIN 12-36 7.4 234.5 35.8 36 7.1 232.0 33.2SR 45-78 7.3 235.0 35.8 45 9.0 235.0 33.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)