Title: 1 etg del 2.pdf
Cable ID: T1148 Date / Time: 10/21/2013 08:05:15 AM Headroom 11.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]194 308 22 8.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.5 82.3 33.7 36 15.6 94.3 29.7SR 12-36 11.8 94.3 32.7 36 14.0 94.3 29.7MAIN 12-36 13.5 94.3 32.7 36 15.6 94.3 29.7SR 12-36 12.0 99.3 32.4 36 14.0 94.3 29.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 22.8 64.8 22.4 45 24.9 90.5 16.5