Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
[Pair 12] [Pair 45] [Pair 45] [Pair 45]18.0 78 1 2.79Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.6 491.0 41.2Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.7 474.0 29.1 36 5.9 461.0 26.9SR 36-45 5.6 474.0 29.1 36 6.8 461.0 26.9MAIN 36-45 7.3 500.0 27.8 36 6.8 500.0 25.0SR 36-45 6.2 487.0 28.5 36 8.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.8 8.9 46.3 45 21.1 35.0 31.4SR 45-78 19.8 8.9 46.3 45 21.1 35.0 31.4MAIN 36-12 21.8 463.0 11.9 36 24.4 500.0 8.3SR 12-36 21.7 463.0 11.9 36 23.1 463.0 8.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 32.0 145.0 17.8 78 32.2 145.5 15.2