Title: Data tester Smestad skole - Detaljert.pdf
Insertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,0 2,3 2,20Worst Value: Local: 45 16,9 43,6 26,7 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 13,0 8,0 5,0 500,00Remote: 78 20,7 13,5 7,2 112,00Worst Value: Local: 12 13,0 8,0 5,0 500,00Remote: 36 17,3 8,0 9,3 467,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,1 26,7 2,4 498,00Remote: 36-45 28,6 26,7 1,9 500,00Worst Value: Local: 36-45 29,1 26,7 2,4 498,00Remote: 36-45 28,6 26,7 1,9 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,0 10,4 10,6 491,00Remote: 45-12 67,9 57,3 10,6 2,20