Title: 2 etg del2.pdf
SR 36-45 18.5 250.0 16.2 45 19.0 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.7 11.3 51.1 36 10.8 12.6 47.6SR 12-36 14.8 11.3 51.1 36 14.7 12.6 47.6MAIN 36-45 12.2 250.0 4.7 36 11.6 250.0 2.0SR 12-36 19.6 246.0 5.1 36 19.1 246.0 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.8 12.5 20.5SR 45 3.1 15.4 20.1MAIN 45 8.3 222.0 10.5SR 36 4.2 246.0 10.1010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030