Title: Eurotester målerestultat.pdf
Bytesteinen 1 / =433.202 / SIKRING38 30.03.2021 14:51:44Testet av: Andreas PedersenSide:14GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr.909091919292939394949595TEST RAPPORTResultatR ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING38 30.03.2021 14:51:59R LOW OhmR: 0.37ΩR+: 0.4Ω R-: 0.4Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING39 30.03.2021 15:04:24RCD II: 21.0mAUc: 9.2V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING40 30.03.2021 15:05:05RCD II: 22.5mAUc: 9.5V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING41 30.03.2021 14:55:02Z-LINEZ: 0.37ΩIsc: 622A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 236A Isc(0.76%): 473A Isc(1.15%): 715ABytesteinen 1 / =433.202 / SIKRING41 30.03.2021 14:55:18RCD II: 22.5mAUc: 8.4V Idn: 30mA type: AC Ulim: 50V