Title: økernvn 94.pdf
Site: OKERNVEIEN 94Cable ID: T3032 Date / Time: 09/12/2013 02:40:24 Headroom 12.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]145 229 16 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.9 40.5 38.7 36 15.2 99.5 29.3SR 12-36 12.9 67.8 35.1 36 14.2 99.3 29.4MAIN 12-36 14.2 99.5 32.3 36 15.2 99.5 29.3SR 12-36 13.1 99.3 32.4 36 14.2 99.3 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 20.0 94.3 19.1 36 22.3 94.3 16.1