Title: Tørrsprinkler.pdf
The compressed Spring is then able to expand and push the Water Tube as well as the Guide Tube outward. This action simultaneously pulls inward on the Yoke, withdrawing the Plug with Sealing Assembly from the Inlet, allow- ing the sprinkler to activate and flow water. Design Criteria TYCO Series DS-1 5.6K Pendent, Upright, and Horizontal Sidewall, Stan- dard Response, Standard Coverage Dry-type Sprinklers are intended for use in fire sprinkler systems designed in accordance with the standard instal- lation rules recognized by the appli- cable listing or approval agency (for example, UL Listing is based on NFPA 13 requirements). For more information on LPCB Approval, contact Johnson Controls at the following office:Kopersteden 1 7547 TJ Enschede The Netherlands Tel: +31-(0)53-428-4444 Fax: +31-(0)53-428-3377Sprinkler Fittings Install 1 in. NPT Series DS-1 Dry-type Sprinklers in the 1 in. NPT outlet or run of the following fittings: