Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]23.4 101 1 3.59Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 4.9 466.0 29.5 36 6.3 475.0 26.2SR 36-45 5.1 457.0 29.9 36 6.3 459.0 27.0MAIN 36-45 6.0 496.0 28.0 36 7.1 500.0 25.0SR 36-45 5.7 497.0 28.0 36 6.8 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.2 494.0 11.4 45 17.5 3.9 50.5SR 78-45 16.9 494.0 11.4 45 17.5 4.3 49.7MAIN 45-78 17.3 499.0 11.3 78 19.0 499.0 8.3SR 78-45 17.0 499.0 11.3 45 18.3 500.0 8.30100806040200250 MHzACR-F (dB)