Title: Data tester Smestad skole - Detaljert.pdf
Remote: 45 26,6 23,8 2,8 500,00Worst Value: Local: 36 27,6 23,8 3,8 498,00Remote: 45 26,6 23,8 2,8 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,1 61,2 10,9 1,00Worst Value: Local: 12 20,0 7,5 12,5 484,00Remote: 12 72,6 61,2 11,4 1,00Remote: 36 19,7 7,2 12,5 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:58Signature:______________________ Page: 24Copper Certification ReportCable Label: 521.002-UD-036 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 14:16:02 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4