Title: 1 etg del 2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]264 414 25 11.1264 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.4 250.0 35.3 36 1.3 246.5 32.8SR 36-450.3 *249.0 35.4 36 0.9 *249.0 32.7MAIN 36-45 1.4 250.0 35.3 36 1.3 246.5 32.8SR 36-45 0.3 249.0 35.4 36 0.9 249.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 11.2 52.0 29.9 36 13.9 43.8 28.4SR 45-36 11.2 52.0 29.9 36 13.7 51.5 27.0MAIN 36-45 13.8 249.5 16.2 36 15.5 242.5 13.5