Title: etg u1.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]221 346 20 9.2221 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.2 241.5 35.6 36 1.3 241.5 33.0SR 36-450.4 *249.0 35.4 36 0.0 *249.5 32.7MAIN 36-45 1.2 247.5 35.4 36 1.3 248.0 32.8SR 12-36 0.5 250.0 35.3 36 0.0 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 16.6 206.0 17.9 12 19.1 205.0 15.0SR 45-12 16.6 208.0 17.8 45 18.7 49.0 27.4MAIN 45-12 16.6 211.0 17.7 12 19.2 212.5 14.6