Title: Hardware Installation Guide.pdf
Isolated, non-switching, regulated DC power805mA for 12VDC 407mA for 24VDCNote:Be sure to observe polarity.320 — revision 6Hardware Installation GuidePower source wiring59.6UL Listed InstallationsFor UL installations, the following must be observed:All field wiring terminals are suitable for single wire only.Use 22 AWG minimum for wiring RS-485.RS-485 4-wire is “Not Evaluated by UL” and therefore cannot be used in UL Installations.The use of AC Strike is “Not Evaluated by UL” and therefore cannot be used in UL installations.Environmental for UL installations: - -Temperature: -10 to +49°C (14 to 120°F) operating Humidity: 85+/-5% at 30+/-2°C (86°F)revision 6 — 321LNL-1200-U Output Control Module60SpecificationsNote:For UL installations, refer to section UL Listed Installations on page 321.The LNL-1200-U is for connection to low voltage, class 2 power-limited circuits only. These specifications are subject to change without notice.