Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]38.3 166 2 5.76Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]24.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.8 36.5 48.9 36 10.1 466.0 27.1SR 12-36 6.5 500.0 29.2 36 7.4 500.0 26.4MAIN 12-36 9.8 498.0 29.3 36 10.2 500.0 26.4SR 12-36 6.5 500.0 29.2 36 7.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.9 6.6 48.8 45 17.8 500.0 8.3SR 45-78 18.8 426.0 12.6 45 17.7 500.0 8.3MAIN 45-12 19.0 500.0 11.3 45 17.8 500.0 8.3