Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
678----9E110W400A400W200 / W220The module can be installed on sockets 1…4 (top) on the PCD2.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-45Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.G4106.7.2 PCD2.G410, multi-functional I/O module with elect. isolated digital I/OApplicationCombined module with digital and analogue inputs and outputs. This module is designed to extend the range of uses for the PCD. The functions and the technical specification are based on the existing PCD2 modules.This module cannot be installed in the PCD1.The technical details should be taken from the descriptions of these modules.Number and type of inputs/outputs16 digital inputs, electrically isolated, I0…I15, (addresses 0…15).Tech. data as for PCD2.E610, Source or sink operation selectable via "Q/S" jumper.64 relay outputs, O16…O19 (addresses 16…19),