Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 27.11.2020 11:46R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF021 16C2/003 27.11.2020 11:46KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF022 16C2/003 30.11.2020 09:33RCD II: 28.5mAUci: 0.2V t: 37.9ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF022 16C2/003 30.11.2020 09:34SPĆNDINGUln: 235V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF022 16C2/003 30.11.2020 09:34Z-LINEZ: 0.48ΩIsc: 478A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF022 16C2/003 30.11.2020 09:34Tallberg Elektro A/S Tlf.22796640Side:6GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.4141424243434444454546464747TEST RAPPORTResultatZs(rcd)