Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]33.7 147 3 5.06Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 10.5 494.0 29.4 36 10.0 491.0 26.6SR 36-45 9.8 499.0 29.3 36 9.4 475.0 26.9MAIN 12-45 10.5 494.0 29.4 36 10.2 499.0 26.4SR 36-45 9.8 499.0 29.3 36 9.7 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.0 442.0 12.3 45 14.3 2.5 54.3SR 45-78 14.1 429.0 12.6 45 14.4 3.0 52.7MAIN 78-45 14.3 478.0 11.6 45 15.3 478.0 8.6SR 45-78 14.5 478.0 11.6 78 15.8 478.0 8.60100806040200250 MHzACR-F (dB)