Title: Ekspansjonskar.pdf
Hst ≤ 7 m ≥ p0 = 1,0 bar Eldre radia- Nye radia- torer torer 90 | 70 70 | 50Nye radia- torer 70 | 50Nye radia- torer 90 | 70 Nominelt volum VN [liter] 18 18 25 35 35 50 50 80 80 80 80 140 140 200 300 300 400 500 500 600 800 800 1000 150018 25 25 35 35 50 50 80 80 80 140 140 200 200 300 300 400 500 600 800 800 1000 1000 150025 25 35 50 50 80 80 80 140 140 140 140 200 300 400 400 600 800 800 1000 1500 1500 1500 200018 18 25 25 35 35 50 50 80 80 80 80 140 200 300 300 300 400 500 600 600 800 800 1500psv = 3,0 bar Hst ≤ 12 m ≥ p0 = 1,5 bar Nye radia- torer 90 | 70Eldre radia- torer 90 | 70Nye radia- torer 70 | 5035 35 50 80 80 80 140 140 140 200 200 200 300 400 500 600 800 1000 1500 1500 1500 2000 2000 300025 35 35 50 50 80 80 80 140 140 140 140 200 300 400 400 500 800 800 1000 1000 1500 1500 200025 25 35 35 50 50 80 80 80 140 140 140 200 300 300 400 500 600 800 800 1000 1000 1500 2000Eksempel Q = 200 kW psv = 3 bar Hst = 7 m Radiatorer 90 | 70 °C