Title: 30. Technoporten_Brannalarmutstyr datablad.pdf
192Polyamide 6.6.Light greyWall mounting, 100mm bolt spaceUnit connects to AL_Com only16-26 VDC359μAAll connections are made to screw terminals numbered 1- 8. Terminal 1 2 3 4 5 6 7 8Function AL_Com In (+) AL_Com In (-) AL_Com Out (+) AL_Com Out (-) Input (+) Input (common) Relay contact Relay contactAverage current consumption<60μAPart number116-BN-304DescriptionSingle monitored input/output unitTemperature range25 to +70 CHumidity10% - 95% RH (non-condensing)116-6571-011.6020Membrane gland TSS M20, greyDegree of protection Membrane inlets: PG inlets (PG-13,5):IP54 IP67Optional:116-6571-011.1920Gland IP67ApprovalsSee Autronica’s website116-6371-006.1920Backnut for glandCommunication loopCable terminalsAutronica loop communication protocol (AL_Com)Max 2.5 mm² single core wiresDimensionsCable requirements AL_ComRefer to specification for Autroprime or AutroSafeMaximum input cable length10 mMaximum cable capacitance10nF