Title: 2 etg del2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]88 140 10 3.888 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]22.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.0 * 233.0 35.8 36 0.7 * 233.5 33.2SR 12-36 5.3 223.0 36.2 36 6.9 152.5 36.3MAIN 36-45 1.1 248.5 35.4 36 0.7 249.0 32.7SR 12-36 5.3 223.0 36.2 36 7.5 245.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.3 247.5 16.3 36 18.5 245.5 13.4SR 36-45 17.7 247.5 16.3 45 18.4 3.4 50.6MAIN 45-36 17.3 247.5 16.3 36 18.5 245.5 13.4SR 36-45 17.7 247.5 16.3 45 20.0 247.5 13.3010080604020050100150MHzACR-F (dB)2002500100806040