Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD08 Date / Time: 05/19/2022 11:11:02 AM Headroom 5.8 dB (NEXT 36-78) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 12] [Pair 36] [Pair 36] [Pair 36]21.7 100 2 3.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.8 498.0 29.3 36 9.9 498.0 26.4SR 36-78 5.8 271.0 34.8 36 8.0 219.0 33.7MAIN 36-45 8.8 498.0 29.3 36 9.9 498.0 26.4SR 36-78 7.3 385.0 31.7 36 9.6 498.0 26.4100806040