Title: 40 Bender brukermanual.pdf.pdf
If the RCMS… is used as a means of protection to ensure personnel and fire protection, the PRESET function must not be used! There is the risk that the selected response values are too high.WARNINGMake sure that all existing insulation faults are eliminated before using the preset function! There is the risk that the selected response values are too high.RCMS460-490_D00067_03_M_XXEN/12.20175758Presetting is carried out for all measuring channels on this device. Exceptions:   When a channel is disabled, the set response value does not change.   When the current measured value is 0 mA, the smallest possibleresponse value is set: – Type A measuring current transformer : 6 mA – Type B measuring current transformer : 10 mA  If the PRESET routine determines a value that exceeds the maximum response value (type A: 20 A, type B: 10 A) the highest possible response value is set.