Title: +038=370.001-RD001._01-Siemens Differanstrykk væske QBE3000-D6.pdf
For remote mounting, the sensor can be operated together with the AQB pressure mounting kit in ambient temperatures of up to 70 °C for medium temperatures of up to 180 °C. Care must be taken in this case to ensure that the cooling efficiency of the copper pipe is not reduced by additional heat sources or by restrictions to the air circu- lation.3/6Differential Pressure Sensor QBE3000-D.. / QBE3100-D..CE1N1922en 2018-11-19DisposalTechnical dataProduct dataDegree of protectionConnections4/6Siemens Building TechnologiesThe device is considered an electronic device for disposal in accordance with the Euro- pean Guidelines and may not be disposed of as domestic garbage.Dispose of the device via the channels provided for this purpose. · Comply with all local and currently applicable laws and regulations.Power supplyLow voltage (SELV)Operating voltage QBE3000-D..AC 24 V ± 15 %, 50/60 Hz or DC 18...33 VPower consumpt. (at nom. pressure)< 5 mA at AC 24 V