Title: 2 etg del2.pdf
150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz100RL @ Remote (dB)806040200050100150200250MHzLinkWare Version 8.1Cable ID: D2018 Date / Time: 10/10/2013 11:56:53 AM Headroom 4.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]88 134 5 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 4.3 250.0 35.3 36 6.1 250.0 32.7SR 36-78 6.4 250.0 35.3 36 7.2 250.0 32.7