Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
I n s t a l l a t i o n P r o c e d u r eInstallation Procedure7 Adjust the unit to the appropriate position, taking intoaccount the installation area for the front panel.Place the pattern sheet on the indoor unit.Adjust the space between the ceiling and the indoor unit by using a dimension gauge.Fix the indoor unit securely after adjusting the level of the unit by using a leveller.Remove the pattern sheet, connect the other cables. and install the front panel.CeilingIndoor unitGauge of dimensionsFor the recessed installation of the square panel: 11.5 mm For the recessed installation of the circular panel: 41.5 mmStep 5 Purging inert gas from the indoor unitThe indoor unit comes with nitrogen gas (inert gas) charged at the factory. Therefore, all inert gas must be purged before connecting the assembly piping.Unscrew the pinch pipe at the end of each refrigerant pipe.InsulatorGas sideLiquid sideNOTE