Title: økernvn 94.pdf
Cable ID: T4180 Date / Time: 09/11/2013 12:45:34 Headroom 7.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]112 171 6 5.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]20.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.2 248.0 35.4 36 7.9 247.5 32.8SR 36-78 7.8 205.0 36.8 45 9.1 231.5 33.3MAIN 36-78 7.2 248.0 35.4 36 7.9 247.5 32.8SR 36-78 7.8 205.0 36.8 45 9.1 231.5 33.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.1 189.0 18.7 12 17.8 3.3 51.0