Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,1 2,4 2,95Worst Value: Local: 36 16,3 43,5 27,2 495,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 23,2 15,6 7,6 68,75Remote: 12 14,4 8,0 6,4 500,00Worst Value: Local: 36 16,6 8,0 8,6 494,00Remote: 12 14,4 8,0 6,4 500,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,2 26,8 2,4 495,00Remote: 36-45 29,9 26,7 3,2 500,00Worst Value: Local: 36-45 29,2 26,8 2,4 495,00Remote: 36-45 29,9 26,7 3,2 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,2 10,2 10,0 500,00Remote: 45-12 20,4 10,2 10,2 500,00