Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs.6-91Analogue combined input/output modules6.12Analogue combined input/output modulesPCD3.W5002 analogue inputs 12 bit + 2 analogue outputs 12 bit, 0…10 V, -10 V…+10 V *)) jumper selectableI/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24?V are disconnected from the power supply.6-92PCD3.W5006.12.1PCD3.W500, analogue inputs/outputs, 2 + 2 channels, 12 bit resolutionApplicationCombined high speed analogue input/output module with 2 voltage inputs and 2 volt- age outputs 0…+10 V (unipolar) or -10…+10 V (bipolar), jumper selectable, All with 12 bit resolution. The module is suitable for precise, high-speed applications.Module overviewPCD3.W500: Module with 2 voltage inputs and 2 voltage outputsTechnical dataInputs Number of input channels: Signal ranges:2 W500: 0…+10 V10…+10 V}