Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Isolation voltage: Resistance to interference: acc. to IEC 801-4 Internal current consump- tion: (from +5 V bus) Internal current consump- tion: (from V+ bus) External current consump- tion: Terminals:8, electrically isolated 1 … 500 mA (leakage current max. 0,1 mA) Within the voltage range 5 … 24 VDC, the load resis- tance should be at least 48 Ω. 4 A on 100 % duty cycle Source operation (positive switching) 5 … 32 VDC, smoothed 10 … 25 VDC, pulsed ≤ 0,4 V at 0,5 A Switch-on delay typically 10 µs Switch-off delay typically 50 µs (ohmic load 5 … 500 mA), longer with inductive load, because of the protective diode. 1000 VAC, 1 min 4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 1 … 24 mA typically 15 mA0 mALoad currentPluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²5-42PCD2.A410LEDs and connection terminalsBus connectorBus interfaceOptocouplerA0A2A4A6Output transistors (MOSFET)A1A3A5A7Protective diodesLEDs