Title: +038=433.002-FS029._06-Eaton Tavlebyggeren Produktblad.pdf
Accessories: Auxiliary switch for subsequent installationTripping signal switch for subsequent installation Shunt trip releaseZP-IHK ZP-WHK ZP-NHK ZP-ASA/..286052 286053 248437 248438, 2484394EATON CORPORATION xxxxx+xxxx-xxxxENCombined RCD/MCB Devices NdRBM, Technical DataLocal Indication RCDgreenSelf check (power ON) 2 sI  50% InredI = 30-50% InamberI  30% IngreenService Mode (measuring of residual current I) Pressing test button twice to activate Service-Modepress (0,1 - 0,4 s)release (0,1 - 0,4 s)press (0,1 - 0,4 s)Measurement delimiter Measurement delimiter ON time 10 mA measurement color 1 mA measurement color Double-pressing test button to activate Service Mode Time duration of Service ModeLamp test2 s ––>redambergreenred100 mAProtective Devices1.5red 400 ms amber green press (0.1-0.4 s) -> release (0.1-0.4 s) -> press (0.1-0.4 s) 4 min (during activated Service Mode all protection functions are still working)2 s ––>amberambergreen