Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
The PCD3.A810 occupies 16 addresses, of which 8 are used:Address + BA Data read (inputs)0 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15Switch state: Output 0 Switch state: Output 1 Switch state: Output 2 Switch state: Output 3Switch: Output 0 (0=auto;1=man) Switch: Output 1 (0=auto;1=man) Switch: Output 2 (0=auto;1=man) Switch: Output 3 (0=auto;1=man)Data write (outputs) Output 0 Output 1 Output 2 Output 3No FBs or FBoxes are required; the module can be addressed in the same way as a normal relay module. At addresses 0…3, the relay outputs are written to and the effective switch state of the outputs is read back. The effective switch state is displayed at these addresses in manual operation also. However, the display of the switch state does not indicate whether the external relay supply is present - just as with normal output modules. The operating mode (Auto or Manual) for each channel can be read at input addresses 8…11; "0” = Auto; “1” = Man.6-45PCD3.A810