Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare Version 9.0Cable ID: UD14 Date / Time: 05/19/2022 11:55:29 AM Headroom 7.6 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 6A F/UTP Calibration Date: 12/10/2013Operator: BENDIK Software Version: V3.0 Build 6 Limits Version: V3.0 NVP: 74.0%Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 12] [Pair 36] [Pair 36] [Pair 36]15.5 72 2 3.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]33.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.6 480.0 29.6 45 8.3 480.0 26.8SR 36-45 9.8 487.0 29.5 36 10.3 494.0 26.5MAIN 12-45 7.6 480.0 29.6 45 8.3 480.0 26.8