Title: 1 etg del 2.pdf
MAIN 12-36 10.2 17.5 46.6 12 11.8 17.4 44.3SR 12-36 9.7 24.4 42.9 12 11.6 17.4 44.3MAIN 36-45 16.3 250.0 4.7 36 16.8 250.0 2.0SR 36-45 15.2 250.0 4.7 36 15.2 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.3 22.5 19.2SR 45 4.6 10.1 21.0MAIN 45 5.7 208.5 10.8SR 45 5.4 224.5 10.5010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94