Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The procedure for installing plug-in tap-off units without automatic clamping system is described in instruction sheets available on the Schneider Electric website. The list of instruction sheets can be found in the following table:Device installed in plug in-tap-off unit without automatic clamping systemTap-off unit ratingCatalogue numberInstruction sheetCompact NSX circuit breaker160 AKSB160DC•••AAV16555250 AKSB250DC•••AAV16555400 AKSB400DC•••AAV16555Isolator for blade-type fuses160 AKSB160SE•AAV16543250 AKSB250SE•AAV16546400 AKSB400SE•AAV16546Follow this procedure to install plug-in tap-off units without automatic clamping system:StepAction1Open or remove the tap-off unit cover.2Install the protection device in the tap-off unit.3Remove the IP protection on the outlet of the run component.4Prepare the output cable glands and connect the cables to the tap-off unit.5