Title: Aggregatkjøring.pdf.pdf
The Navipad control panel with 7” capacitive touch panel and 3 m cable must be connected to the Access control unit in the control cabinet. All normal handling and configuration is carried out from the graphical user interface on the NaviPad control panel. The protection class of the NaviPad control panel is IP 54 and 0-50 C° permitted temperature. The NaviPad enclosure is not UV resistant and the NaviPad is not for outdoor mounting. Communication between the panel and the controller in the cabinet is possible with up to 100 meters of cable. The installer must use Standard PDS LAN network cable AWG23 (path cable) for extension. If several units are connected to a local network (on the same subnet), the NaviPad will be able to connect and monitor up to nine units. Please see separate instruction for details If more units are connected to a local network (same subnet), the panel will be able to connect and handle up to nine units. Please see separate instruction for detailsSchedules