Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Failure to follow these instructions can result in death, serious injury, or equipment damage.OverviewThe frequency and the level of maintenance of the Canalis KT system depend on the criticality of the application and the environmental conditions. The recommendations in this section concern only the busbar trunking system. For all devices fitted in tap-off units, the recommendations of the manufacturer must be complied with.Basic Maintenance ProceduresBasic maintenance must be performed every year, for all types of applications, and under all conditions.Carry out the following procedures for basic maintenance:  Inspect the external appearance of the components, accessories, and supports.  Check for deformation, damage, or dirt.  Check for dislocation, bending, misalignment, and other abnormalities of the connecting covers,hangers, and plug-in units. Check if the joint blocks or terminals are discoloured, corroded or pitted, or show signs that they havebeen exposed to high temperatures.