Title: +038=360.000-LC008T_04-Major line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
Table with hypothetical acoustic attenuation of the room and installation for 2-tube system from previous page:CV/CH/NCV models: 12dB: Sizes 102A, 102C, 202A, 202C, 202D, 302A, 302B, 302C 14dB: Sizes 402C, 502C 15dB: Size 602D NCH models: 14dB: Sizes 102A, 102C, 202A, 202C, 202D, 302A, 302B, 302C 16dB: Sizes 402C, 502C, 602D(1) Important: the supply air temperature should not exceed 65°C (CIAT recommendation).PERFORMANCE – 4 TUBE SYSTEM Cold water temperature: 7/12°C, Summer air temperature: 27°C 19° (BH) - Hot water temperature: 70/60°C, Winter air temperature: 20°C.Major LineMotor code(cid:36)(cid:76)(cid:85)(cid:3)(cid:192)(cid:82)(cid:90)(cid:3)(cid:85)(cid:68)(cid:87)(cid:72) (m3/h)Cooling capacity (cid:11)(cid:58)(cid:12)TotalSensibleHeating capacity (cid:58)(cid:54)(cid:82)(cid:88)(cid:81)(cid:71)(cid:3)(cid:83)(cid:82)(cid:90)(cid:72)(cid:85)(cid:3)(cid:47)(cid:58) dB(A)Comfort level ISO or NRV52801 5201 2301 4804933V42451 3501 0901 3804630104X