Title: 360.001 - Tilluft.pdf
25.73.0 +23.826.30.0 +23.828.23.0 +23.827.60.3 +23.88k [dB]36.00.0 +9.536.036.00.0 +9.536.01.5 +6.414.320.220.20.0 +16.821.83.0 +16.820.90.0 +16.822.33.0 +16.821.20.3 +16.8Lp [dB]LocationLevelTeknisk etasjeTeknisk etasjeTeknisk etasjeTeknisk etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje3. etasjeNodeTypeBEND-90DUCTBEND-30DUCTBEND-30DUCTBEND-90DUCTDUCT185 TAPMAGIB-C4-*-*MAGIB-C4-*-*MAGIB-C4-*-*MAGIB-C4-*-*MAGIO-RC-*ProductSize315315315315315315315315315315/250Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]16806,06,416806,016806,00,316806,016806,00,816806,016806,00,516806,00,316806,04602,635,2 Sound in:Attenuation: Addition:8,6 Sound in:Attenuation: Addition:2,2 Sound in:Attenuation: Addition:0,5 Sound in:Attenuation: Addition:2,2 Sound in:Attenuation: Addition:1,1 Sound in: