Title: økernvn 94.pdf
Cable ID: D4131 Date / Time: 09/10/2013 02:25:53 Headroom 12.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]77 123 9 3.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.5 92.5 32.9 12 15.0 92.5 29.9SR 12-36 12.3 92.5 32.9 36 14.3 92.5 29.9MAIN 12-36 12.5 92.5 32.9 12 15.0 92.5 29.9SR 12-36 12.5 96.5 32.6 36 14.5 96.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.4 5.0 44.6 36 25.1 3.8 44.1