Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
DM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 05.11.2020 12:31RCD II: 28.5mAUci: 0.1V t: 84.4ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 06.11.2020 13:18R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 05.11.2020 11:14KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF031 16C2/003 05.11.2020 11:26R LOW OhmR: 0.25ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF032 16C2/003 05.11.2020 12:33SPĆNDINGU12: 235V U1pe: 235V U2pe: 0V f: 49.9HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF032 16C2/003 05.11.2020 12:57Z-LINEZ: 0.61ΩIsc: 378A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 144A Isc(0.76%): 287A Isc(1.15%): 435ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF032 16C2/003 05.11.2020 12:57Tallberg Elektro A/S Tlf.22796640Side:13GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*