Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
SIKRING T: 35msIsc lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT * 12.03.2020 14:19RCD I GODKJENTI: 28.5mAUci: 0.3Vt: 87.6msIdn: 30mAtype: ACH,Ulim: 25Vr_bronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT* | 1i2403.2020 15:16KONTINUITET GODKJENTR: 0.2QGrenseverdi:1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 042 GODKJENT * |#12608422020, | 15:15R LOW Ohm GODKJENTR: 0.10QR+: 0.1QR: 0.1QGrenseverdi: 1.0QTEST RAPPORTr. ResultatR ISO GODKJENTR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQSPENDINGUln: 233VUlpe: 233VUnpe: 0Vf: 50.0HzZ=LINE GODKJENTZ: 0.49QIsc: 465ASikringstype: CSIKRING T: 16ASIKRING T: 35msIsc_lim: 160.0AZs (red) GODKJENTZ: 0.36QIsc: 636ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0AI a GODKJENT28.5mAUci: 0.1Vt: 18.1msIdn: 30mAtype: ACHN,Ulim: 25VKONTINUITETR: 0.20QGrenseverdi: 1.0QR LOW Chm GODKJENTR: 0.10QR+: 0.1QR: 0.1Q