Title: Bytesteinen 1 - =514.202-FS001.pdf
Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]30.8 157 10 5.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]26.9 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 7.1 217.5 34.2 7,8 8.1 217.5 31.2SR 1,2-3,6 8.0 223.5 34.0 1,2 8.3 223.5 31.0MAIN 4,5-7,8 7.1 217.5 34.2 7,8 8.3 228.5 30.8SR 1,2-3,6 8.0 224.0 33.9 1,2 8.3 223.5 31.0PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 13.7 236.5 15.8 4,5 15.6 3.5 49.4SR 7,8-4,5 13.8 2.8 54.5 4,5 15.5 3.1 50.4MAIN 7,8-4,5 14.0 246.5 15.4 4,5 15.9 248.0 12.4