Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
1= T =8 = Surface Result Average Min Max Min/average Min/max Visual task area 6 Perpendicular illuminance (adaptive) [Ix] 491 418 532 0.85 0.79Surrounding area: 0.500 mSurrounding area 6 Perpendicular illuminance (adaptive) [Ix] 394 295 485 0.75 0.61 Background area 5 Perpendicular illuminance (adaptive) [Ix] 210 158 258 0.75 0.61Wall zone: 0.500 mDIALux Page 35Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Mate 6_1/ Visual task area 6 / Perpendicular illuminance (adaptive)/ENTSKFalse colors [Ix]295 500 IxScale: 1:25Value grid [Ix]1453 470 490 504 515 523 526 524 519 506 494 485 T T T T1461 476 496 510 521 529 (532),530 ,524 513 501 491 T T T1456 472 1492 506 516 524 528 526 519 509 497 487 T T T T1441 454 474 487 497 505#07 506 500 ;490 478 471 T T TScale: 1:25479 481 475 464 444 4 + 4 4 + 4 4The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 36