Title: V67--02 Oppleggskjema kjøling.pdf
Tak 41.70 mPlan 11 38.25 mPlan 1035.07 mPlan 0931.97 mPlan 0828.17 mPlan 0725.07 mPlan 0621.97 mPlan 0518.87 mPlan 0415.77 mPlan 0312.67 m1360.008 24,2 kW, 4157 l/h360.00724,2 kW, 4157 l/h360.00624,2 kW, 4157 l/h360.00524,2 kW, 4157 l/h360.00424,2 kW, 4157 l/hAkse C-D DN 100370.104DN 1001+08=360.008-OE902MM 54+07=360.007-OE902MM 54+06=360.006-OE902MM 54+05=360.005-OE902MM 54+04=360.004-OE902MM 54ParetoParetoParetoParetoBainSølvfunnSeasport2TianleiSeasport3370.101 Kombibaffel og reserver (nord / akse A) -Beregnet behov bafler plan 3-10 v/ 100% samtidighet 55 kW (15 / 18°C) -Planlagt EF-rom 2 kW (15 / 18°C) 4370.101 Kombibaffel og reserver (syd / akse D) -Beregnet behov bafler plan 3-10 v/ 100% samtidighet 68 kW (15 / 18°C)+11=370.101-OE111 0.483 L/sDN32DN40+11=370.101-OE114 0.664 L/sMM 42MM 42Pareto6,1 kW, 1734 l/h8,3 kW, 2387 l/hPareto+10=370.101-OE101 0.358 L/sDN25DN32