Title: 30. Technoporten_Brannalarmutstyr datablad.pdf
Application include:  Monitoring of associated equipment for faults  Monitoring of detectors with relay contactsFunction: Alarm condition signalling input unit with feedback function. The relay contact will follow the state of the input.Function DNumber of addresses: 1S1.1 S1.2 S1.3 S1.4 OFF OFF ONONApplication include:  Fire Alarm push buttons  Flame, heat or beam detectors with relay contactsFunction: Uncommitted input.Number of addresses: 1Function BS1.1 S1.2 S1.3 S1.4 ON OFF OFF OFFFunction: Pre Alarm condition signalling input unit with feedback function. The relay contact will follow the state of the input.Applications: A typical application is monitoring of the power fault contact in the power supply or a fire pump. This unit can be used for:  Monitoring of water level detection systems  Monitoring of smoke control damper systems  Monitoring of extinguishing systems  General Alarm Push Button (GAPB)Number of addresses: 1The relay contact will follow the state of the input.