Title: 2 etg del2.pdf
Cable ID: D2101 Date / Time: 10/10/2013 01:35:28 PM Headroom 9.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]98 155 11 4.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.0 76.5 34.2 36 13.5 76.5 31.2SR 12-36 9.6 90.0 33.1 36 12.3 90.0 30.1MAIN 12-36 11.1 100.0 32.3 12 13.8 100.0 29.3SR 12-36 9.7 100.0 32.3 36 12.4 100.0 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 20.3 97.3 18.9 36 22.4 97.3 15.9