Title: økernvn 94.pdf
Cable ID: D4130 Date / Time: 09/10/2013 10:17:01 Headroom 10.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]235 372 26 10.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.4 51.3 37.1 36 20.2 51.3 34.1SR 12-36 10.4 100.0 32.3 36 13.0 96.3 29.6MAIN 36-45 20.9 99.5 32.3 36 21.8 99.3 29.4SR 12-36 10.4 100.0 32.3 36 13.0 99.5 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.6 66.3 22.2 12 23.6 80.8 17.5