Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 27,0 23,9 3,1 495,00Worst Value: Local: 36 27,9 23,9 4,0 495,00Remote: 36 27,0 23,9 3,1 495,00PS-ACRF: Pass Worst Margin: Local: 12 22,0 9,8 12,2 373,00Worst Value: Local: 45 21,3 8,1 13,2 450,00Remote: 45 73,2 61,2 12,0 1,00Remote: 36 21,2 7,2 14,0 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:03Signature:______________________ Page: 64Copper Certification ReportCable Label: 521.002-UD-161 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 13:42:03 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4