Title: Data tester Smestad skole - Detaljert.pdf
Worst Margin: Local: 12-45 23,5 12,5 11,0 385,00Remote: 45-12 23,6 12,5 11,1 385,00Worst Value: Local: 12-45 21,7 10,4 11,3 492,00Remote: 45-12 22,0 10,4 11,6 492,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 33,1 29,4 3,7 344,00Remote: 45 27,9 23,8 4,1 500,00Worst Value: Local: 45 27,8 23,8 4,0 497,00Remote: 45 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 24,3 12,0 12,3 289,00Worst Value: Local: 45 21,2 7,4 13,8 492,00Remote: 45 72,6 61,2 11,4 1,00Remote: 12 20,5 7,2 13,3 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:19Signature:______________________ Page: 168Copper Certification ReportCable Label: 521.002-UD-195 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name: