Title: +038=433.000-NI003._27-Testrapport Elektriske Anlegg Pactum Plan 10 UF 433.10.01.pdf
TEST RAPPORTBruker:Teststed:Tallberg Elektro A/S Stanseveien 4Pactum Dronning Maudsgate1-3Instrument dataType:EUROTEST COMBOSer.Nr.:13250825Modell:MI 3125BTProdusent:Metrel d.d.Nr. 11ResultatDronningMaudsgat / 433.10.01 Plan10 / SIKRING25 13.02.2020 09:46SPÆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0Hz22DronningMaudsgat / 433.10.01 Plan10 / SIKRING25 13.02.2020 09:46Z-LINEZ: 0.47ΩIsc: 490A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A33DronningMaudsgat / 433.10.01 Plan10 / SIKRING25 13.02.2020 09:50Z-LINE dUdU: 3.3%Sikringstype: C SIKRING I: 16A SIKRING T: 35ms dU_lim: 4.0% Isc: 490A Z: 0.47Ω Zref: ___Ω44DronningMaudsgat / 433.10.01 Plan10 / SIKRING25 13.02.2020 09:51Zs(rcd)Z: 0.40ΩIsc: 574A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A55DronningMaudsgat / 433.10.01 Plan10 / SIKRING25 13.02.2020 09:52Side:1Rapport opprettet08.03.2022GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*