Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 36]31.6 137 2 4.61Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]27.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.0 469.0 29.8 36 6.3 499.0 26.4SR 12-36 7.5 499.0 29.3 36 7.6 499.0 26.4MAIN 36-78 7.5 499.0 29.3 36 6.3 499.0 26.4SR 12-36 7.5 499.0 29.3 36 7.6 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.2 461.0 12.0 45 19.2 496.0 8.3SR 45-78 19.3 461.0 12.0 45 19.7 500.0 8.3MAIN 78-45 19.5 496.0 11.3 45 19.2 496.0 8.3SR 45-78 19.7 496.0 11.3 45 19.7 500.0 8.30100806040200250 MHzACR-F (dB)