Title: Data tester Smestad skole - Detaljert.pdf
1000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,8 3,8 497,00Remote: 36 27,9 23,8 4,1 500,00Worst Value: Local: 36 27,6 23,8 3,8 497,00Remote: 36 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,4 61,2 11,2 1,00Worst Value: Local: 45 20,8 7,2 13,6 500,00Remote: 12 65,1 54,3 10,8 2,20Remote: 45 21,0 7,2 13,8 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:18Signature:______________________ Page: 165Copper Certification ReportCable Label: 521.002-UD-207 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:40:38 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-Panel