Title: Luftport - frico_ar3500-no.pdf
11SIReB Basic - Parallel connectionAR3500 WSIReB1SD230Pot. Unit IDC2 X5C1 X4ROOM X3ACTUATOR SUPPLY230V~N L PEPEN LSIReB1SD230Pot. Unit IDC2 X5C1 X4ROOM X3ACTUATOR SUPPLY230V~N L PEPEN LSIReB1SD230SIReRTX (optional)SIReUB1Pot. Unit IDC2 X5C1 X4ROOM X3ACTUATOR SUPPLY230V~N L PEPEN LWiring diagrams for SIReAC Competent and SIReAA Advanced, see manuals for SIRe.12Output charts water AR3500AR3500W Standard coilTypeFan positionAR3510W max min AR3515W max min AR3520W max minAirflow[m3/h] 2000 1000 2800 1400 4000 2000Supply water temperature:80 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 Output Return water temp. [°C] 44,5 33,6 42,2 32,4 41,0 31,0Water flow [l/s] 0,08 0,03 0,10 0,04 0,14 0,06[kW] 11,5 5,7 16,0 8,0 23,0 11,5Pressure drop [kPa] 2,0 0,6 2,0 0,4 4,0 1,0Water temperature: 80/60 °C Room temperature: +18 °COutput *2[kW] 14,9 9,6 21,9 14,0 31,4 20,0