Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 30,8 28,3 2,5 447,00Remote: 36-45 29,8 26,7 3,1 500,00Worst Value: Local: 36-45 29,3 26,7 2,6 498,00Remote: 36-45 29,8 26,7 3,1 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,8 11,0 10,8 457,00Remote: 12-45 22,6 11,1 11,5 451,00Worst Value: Local: 12-45 21,8 11,0 10,8 457,00Remote: 12-45 22,5 11,0 11,5 455,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,3 25,6 3,7 442,00Remote: 36 28,5 23,8 4,7 500,00Worst Value: Local: 36 28,1 23,8 4,3 500,00Remote: 36 28,5 23,8 4,7 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,1 60,0 12,1 1,15Worst Value: Local: 45 21,1 8,0 13,1 457,00Remote: 12 71,8 60,0 11,8 1,15