Title: 20320REG Spenningsforsyner 320mA..pdf
Output with integrated choke for supplying KNX bus lines - Output DC 30 V for supplying additional devices - Nominal current can be subdivided to outputs as desired - Reset button - Short-circuit proof - Overvoltage proof - No-load protection - Suitable for operation in systems with emergency power supply - Floating signal contact for operating and diagnostic message - Can be connected in parallel with identical power supply (until the maximum short- circuit current is reached)Technical dataAC 200 ... 240 V ~Rated voltage:Mains frequency:50/60 Hzmax. 1.8 WPower loss (max. load on all outputs):Efficiency:approx. 84 %DC 240 ... 250 VRated voltage:KNXKNX medium:TP 256DC 28 ... 31 V SELVBus output voltage:Output current:320 mA (all outputs)Short-circuit current:max. 1 AParallel operation with identical power supply:yesSignal outputSwitching voltage AC:AC 12 ... 230 V ~DC 2 ... 30 VSwitching voltage DC:Switching current:5 mA ... 2 A−5 ... +45 °C