Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF055 Date / Time: 27-02-2020 20:57:42 Headroom 10.1 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]22.4 97 1 3.48Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 11.1 467.0 29.4 36 10.6 473.0 26.3SR 12-45 10.1 421.0 30.9 36 10.2 463.0 26.8MAIN 36-45 12.1 499.0 27.9 36 10.9 500.0 25.0SR 36-45 11.0 498.0 27.9 36 10.7 500.0 25.010080604020NEXT (dB)