Title: Data tester Smestad skole - Detaljert.pdf
Worst Margin: Local: 12-45 69,1 59,3 9,8 1,75Remote: 45-12 67,7 57,3 10,4 2,20Worst Value: Local: 12-45 22,7 10,4 12,3 489,00Remote: 45-12 23,2 10,4 12,8 489,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,8 3,8 500,00Remote: 36 27,9 23,8 4,1 500,00Worst Value: Local: 36 27,6 23,8 3,8 500,00Remote: 36 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,6 61,2 11,4 1,00Worst Value: Local: 12 22,1 7,5 14,6 486,00Remote: 12 72,1 61,2 10,9 1,00Remote: 12 21,7 7,4 14,3 489,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:58Signature:______________________ Page: 26Copper Certification ReportCable Label: 521.002-UD-025 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name: