Title: +038=360.000-LC008T_04-Major line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
The fan motor assembly is equipped with an asynchronous motor or an HEE motor with a 230V (50/60 Hz) closed and tropicalised power supply, with a protected shaft and internal automatic overload protection as standard on the winding. The impellers will be HEE type in ABS, class V0 with a diameter of 160 mm to ensure high acoustic and air flow performance. The fan motor assembly will be sized to meet the requirements of installations needing up to 50 Pa of operating pressure. The impellers of the unit will be in ABS, class V0 and designed for optimum performance. They will be split unit type, therefore easily removed, enabling the maintenance operator to replace only the defective part if necessary (motor or impeller)..The asynchronous motor has 5 speeds connected to the electrics box of the unit for optimised selection on site.The asynchronous motor has 5 speeds connected to the electrics box of the unit for optimised selection on site.