Title: økernvn 94.pdf
SR 45-12 19.0 5.4 49.6 12 19.7 4.3 48.6MAIN 36-12 20.4 222.5 17.2 12 22.2 250.0 13.2SR 12-36 20.8 222.5 17.2 36 21.6 225.5 14.1010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 21.3 60.5 31.2 12 20.8 53.3 30.6SR 12-36 16.2 60.5 31.2 36 16.7 64.5 27.8MAIN 12-36 27.1 215.5 8.2 12 27.8 215.5 5.6SR 36-45 22.7 249.0 4.8 36 22.1 245.5 2.5010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.6 245.0 10.1SR 36 5.2 192.0 11.2MAIN 36 4.6 245.0 10.1SR 36 5.2 192.0 11.2010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active