Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
ValVe with MicroMetric lockshield ValVe3 ways2 waysValVe with siMplified kit3 ways2 waysTechnical data:Valves characteristicsRated pressure:Max. ambient temperature:Max. water flow temperature:16 bar50 °C110 °CBattery typeECM Model2 way valvesKvs m3/h∆pmax kPa *Valve ** connection3 way valvesKvs m3/h∆pmax kPa *Valve ** connectionPower:Rating:Protection:230 V - 50/60 Hz3 VAIP 43Main12 - 22 - 3214 - 26 - 3642 - 5244 - 562,85,250603/4"1"2,54,550503/4"1"Travel time:Max. glycol content of water:approx. 3 min.50%Auxiliary14 - 26 - 3644 - 562,8503/4"2,5503/4"maximum pressure difference for valve to close Note: 3 way valves with simplified kit and 1” connection have conical seal. ** external thread, flat sealmaximum pressure difference for valve to close Note: 3 way valves with simplified kit and 1” connection have conical seal. ** external thread, flat seal∆p - kPap o r d