Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]19.2 83 1 3.09Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.2 395.0 31.5 36 7.6 463.0 26.8SR 36-45 7.6 496.0 28.0 36 7.7 439.0 27.7MAIN 12-36 6.5 462.0 29.6 36 8.7 499.0 25.0SR 36-45 7.6 496.0 28.0 36 8.2 495.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.4 4.3 52.7 45 17.0 41.5 29.9SR 45-78 16.4 4.3 52.7 45 16.9 3.9 50.5MAIN 78-45 17.5 497.0 11.3 78 18.9 500.0 8.3SR 78-45 17.9 500.0 11.3 36 18.5 498.0 8.30100806040200250 MHzACR-F (dB)