Title: 2 etg del2.pdf
806040200050100150200250MHz100ACR-F @ Remote (dB)806040200050100150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz100RL @ Remote (dB)806040200050100150200250MHzLinkWare Version 8.1Cable ID: T2228 Date / Time: 10/11/2013 08:44:12 AM Headroom 2.2 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]61 96 6 2.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]25.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 3.0 242.0 35.6 36 2.9 248.0 32.8