Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 27.11.2020 11:52R LOW OhmR: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 27.11.2020 11:54KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 30.11.2020 11:59 (ELEKTRIKER)Tallberg Elektro A/S Tlf.22796640Side:43GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.298298299299300300301301302302303303TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 255V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF092 16C2/003 30.11.2020 11:42RCD II: 28.5mAUci: 0.3V t: 87.8ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 27.11.2020 10:55SPĆNDINGUln: 237V Ulpe: 237V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF093 16C2/003 27.11.2020 10:55