Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Technical dataSignal ranges:see module overviewGalvanic separation:noResolution (digital representation):10 bits (0…1023)Measuring principle:non-differential, single-endedInput resistance:0…10 V: 200 kΩ / 0.15 % 0…20 mA: Pt/Ni1000: NTC 10:125 Ω / 0,1 % 7.5 kΩ / 0.1 % 10 kΩ / 0,1 %Maximum measurement current for resistance measurement with W220:1.5 mAAccuracy (of measured value):± 3 LSBRepeating accuracy (under same conditions):within 1 LSBTemperature error:± 0.3% ( ± 3 LSB),(over temperature range from 0°…+55°C)Conversion time A/D:Overvoltage protection:<50 μs W200/220:± 50 VDCOvercurrent protection:W210:± 40 mABurst protection: (IEC1000-4-4)± 1 kV, with unshielded cables ± 2 kV, with shielded cablesTime constant of input filter:W200: typically 5 ms typically 1 ms W210: W220 : typically 10 msInternal current consumption: (from +5 V bus)8 mA (W200/210/220)Internal current consumption: (from V+ bus)5 mA (W200/210) 16 mA (W220)