Title: EDM_AQAR32_01-S-2GB.pdf
Control panel Theunitsarefittedwithanexternalcontrolpanelthatdisplaysthe operating parameters and alarms.Standard unit : Unit without pump, the hydraulic circuit contains the following components : supplied loose waterfilter,mountedwaterflowswitch,watersafety valve,automaticairvent,optionalfield-installed in/out 3/8" water valves. All water piping is covered with thermal insulation.1P-SP/1P-HP : One pump unit has the sameequipment as Standard unit, with additional single pump. Version 1P-SP (standard pressure pump) provides an available static pressure to the user in nominal conditions around 100-150 kPa. Version 1P-HP (high pressure pump) provides an available static pressure to the user in nominal conditions around 150-200 kPa.The control panel is accessible from exterior without removing any parts, nor shutting down the unit, because it is placed on an external panel.