Title: Ahlsell.pdf
SR 4,5-7,8 17.1 78.3 26.3 7,8 17.9 1.0 61.2MAIN 4,5-1,2 19.2 498.0 10.2 1,2 19.3 499.0 7.2SR 3,6-1,2 19.3 500.0 10.2 1,2 20.1 500.0 7.20100806040200250 MHzACR-F (dB)N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 1,2-7,8 14.1 5.9 57.2 1,2 15.2 5.9 54.9SR 1,2-7,8 14.1 14.9 48.4 7,8 15.5 14.9 46.0MAIN 3,6-4,5 38.9 491.0 -16.4 3,6 40.7 496.0 -19.7SR 1,2-7,8 34.9 496.0 -16.8 1,2 36.9 496.0 -19.70804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 4,5 7.6 33.5 18.4SR 4,5 6.8 33.5 18.4MAIN 4,5 9.0 487.0 8.0SR 4,5 8.1 404.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Ahlsell Site: Not Set Floor: Not Set Rack: Not Set Untitled1Building: Not Set Room: Not Set Patch: Not SetPage 3