Title: 2 etg del2.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.9 115.5 20.8 36 6.4 249.5 2.1SR 36-45 5.6 247.5 4.9 36 5.6 236.5 3.4MAIN 12-36 7.2 248.5 4.8 36 6.4 249.5 2.1SR 36-45 5.6 248.5 4.8 36 5.7 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.0 3.9 21.0SR 45 3.7 3.9 21.0MAIN 45 6.6 221.0 10.6SR 36 6.2 222.0 10.5010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1