Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
3. Using the screws supplied with the module and the appropriate holes (paragraph 3.3 - [D] and paragraph 3.4 - [H]), mount the FPMCPU module to the front plate. Ensure that the module speaker is properly positioned on the front plate (paragraph 3.3 - [E]).4. Complete the wiring of the FPMCPU module (refer to paragraph 5.3 and paragraph 5.16).4. Complete the wiring of the FPMCPU module (refer to paragraph 5.3 and paragraph 5.16).5. Attach the front plate with the wired module to the enclosure by means of the appropriate holes (paragraph 3.3 - [C]).5. Attach the front plate with the wired module to the enclosure by means of the appropriate holes (paragraph 3.3 - [C]).5.3Mounting FPM modules to the front plateThe front-plate modules (FPMCPU, FPMNUL, FPMLED, FPMLEDPRN, FPMEXT) can be mounted to one of the apertures on the cabinet front plate (paragraph 3.1 - [B]). The FPMCPU module can also be mounted to front plate of the PRREP repeater enclosure (paragraph 3.3 - [B]).