Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 17,5 8,0 9,5 451,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 29,7 26,7 3,0 498,00Worst Value: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 29,7 26,7 3,0 498,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,7 10,2 11,5 500,00Remote: 12-36 21,7 10,5 11,2 484,00Worst Value: Local: 12-45 21,7 10,2 11,5 500,00Remote: 12-45 21,6 10,2 11,4 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,2 23,8 3,4 499,00Remote: 36 28,6 23,8 4,8 499,00Worst Value: Local: 36 27,2 23,8 3,4 499,00Remote: 36 28,6 23,8 4,8 499,00