Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Watch-DogSlot A1, A2 F1xx modules communicationSlot C F7xxx modules communicationR T C F vol nvolRegister Timer Counter Flag volatile non volatile1) USB2) COM/PGU o. RS485Serial data interfaces field bus connectionsProfibus DP CAN InterfaceP TX DBPrograms Texts Data blocksS-Net/ MPIEthernet- TCP/IPModem RS 232 “Full Handshaking”1) Connection for the programming unit 2) With PCD2.M5540No changes (e.g. plugging/unplugging I/O modules) should be made with the powerswitched on.To prevent loss of data, batteries should be changed with the power switched on.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-8Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsPCD2 CPUs3.4.2 Hardware and firmware versions for the PCD2.M5_The firmware for the PCD2.M5_ is stored in a Flash EPROM, soldered to the motherboard. A firmware update can be applied by downloading a new version with the PG5. The procedure is as follows: