Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
34.9 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.8 463.0 29.6 36 6.0 461.0 26.9SR 36-45 7.0 471.0 29.2 36 7.3 461.0 26.9MAIN 36-45 6.9 498.0 27.9 36 6.9 497.0 25.1SR 36-45 7.9 498.0 27.9 36 8.1 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.9 5.9 49.9 45 21.1 5.0 48.3SR 45-78 18.9 5.9 49.9 45 21.2 20.4 36.1MAIN 36-12 22.1 463.0 11.9 36 24.4 462.0 8.9SR 12-36 21.9 463.0 11.9 36 24.2 463.0 8.90100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 33.5 209.5 10.6 36 35.3 209.0 8.0SR 12-36 34.6 209.5 10.6 12 36.0 255.0 3.7MAIN 36-45 40.7 498.0 -12.3 36 40.5 497.0 -15.1SR 36-45 41.7 498.0 -12.3 36 41.7 497.0 -15.10804000250 MHzACR-N (dB)