Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-73Saia-Burgess Controls Ltd.Input/output (I/O) modulesAnalogue output modules, electrically isolated6.11 Analogue output modules, electrically isolatedPCD2.W605 PCD2.W615 PCD2.W6256 analogue outputs 10 bit resolution, 0..10 V 4 analogue outputs 10 bit resolution, 0..10 V 6 analogue outputs 10 bit resolution, 0..10 VGalvanic separation of outputs to PCD, channels themselves not separatedI/O modules and I/O terminal blocks may only be plugged in and removed when the PCD and the external +24 V are disconnected from the power supply.6Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-74Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W6x56.11.1 PCD2.W6x5, analogue outputs,electrically isolated, 6 (4) channels, 10 bit resolutionApplication