Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 42,1 68,0 219,0 13,0 7,4Limit 100,0 - 555,0 50,0 25,0Margin 57,9 - 336,0 37,0 17,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,8 3,0 2,2 2,35Worst Value: Local: 45 18,3 43,5 25,2 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 25,1 17,9 7,2 41,00Remote: 78 21,4 17,3 4,1 47,00Worst Value: Local: 12 16,2 8,7 7,5 337,00Remote: 12 17,0 9,0 8,0 314,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,0 26,8 2,2 496,00Remote: 36-45 30,0 26,7 3,3 500,00Worst Value: Local: 36-45 29,0 26,8 2,2 496,00Remote: 36-45 30,0 26,7 3,3 500,00dB 060120