Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
Technical DataEXBF B 001 2 ...0 N 000EXBF A 001 2 ...0 N 000Supply24 V AC ±20% 50/60 Hz / 24 VDC-10/+20%230 V AC ±14% 50/60 Hzpower requirement: -during spring tensioning -during sustaining7 W 2 W8 W3 Wsizing (apparent power)10 VA12,5 VAprotection classIP 66auxiliary switch: - point of activation2 x SPDT 6A (3) max 250 V AC 5(cid:176) , 80(cid:176)torque:motor - springrotation angle18 Nm 12 Nm 95(cid:176) (including the initial spring tensioning 5(cid:176) )running time : (90°C) - motorreturn springambient temperature150 s » 20 s -20 ...+50°Cweight10 kgFigure 14. Connection diagram for EDELWEISS EXBF B 001 2 ...0 N 000 and EDELWEISS EXBF A 001 2 ...0 N 000 actuators.MERCOR SA – The company reserves the right to make modifications and changes17/21mcr WIP multi-plane fire dampers GRUNER actuatorsTechnical data229-024-05-S2 (229TA-024-05-S2) 229-230-05-S2 (229TA-230-05-S2)Supply24 VAC (50/60Hz) / DC ± 20%230 VAC (50/60 Hz) ± 15%