Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E6.433.09.03 / XF036 C16/4 16.06.2020 09:45R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 15.06.2020 08:32Z-LINEZ: 0.52ΩIsc: 443A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 15.06.2020 08:33Zs(rcd)Z: 0.47ΩIsc: 490A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 15.06.2020 09:00Tallberg Elektro A/S Tlf.22796640Side:8GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.595960606161626263636464TEST RAPPORTResultatRCD II: 28.5mAUci: 0.1V t: 37.6ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 15.06.2020 09:01SPĆNDINGUln: 231V Ulpe: 231V Unpe: 1V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 15.06.2020 09:02RCD Ub