Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 35,6 68,0 185,0 10,0 6,5Limit 100,0 - 555,0 50,0 25,0Margin 64,4 - 370,0 40,0 18,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 2,05Worst Value: Local: 36 15,1 43,6 28,5 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 22,4 16,0 6,4 63,00Remote: 78 20,4 16,5 3,9 56,75Worst Value: Local: 78 15,4 8,0 7,4 415,00Remote: 36 16,3 8,0 8,3 472,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass