Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.0 436.0 30.5 36 10.1 474.0 26.2SR 36-45 10.7 453.0 30.1 36 10.3 496.0 25.2MAIN 36-45 10.5 499.0 27.9 36 10.8 499.0 25.0SR 36-45 11.3 499.0 27.9 36 10.4 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 16.2 6.3 49.3 45 14.8 2.5 54.3SR 36-45 16.2 6.3 49.3 45 14.8 2.6 53.9MAIN 78-45 16.4 500.0 11.3 45 16.8 500.0 8.3SR 45-78 16.8 500.0 11.3 45 17.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.4 58.0 32.4 36 24.5 62.3 28.9SR 36-45 22.2 58.0 32.4 45 24.1 58.0 29.9MAIN 36-45 38.2 499.0 -12.3 36 38.5 499.0 -15.2SR 36-45 39.0 499.0 -12.3 36 38.1 497.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)