Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]177 282 21 7.6177 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 246.0 35.5 36 0.8 * 247.5 32.8SR 36-450.9 *238.0 35.7 36 0.7 *238.0 33.1MAIN 36-45 0.9 247.5 35.4 36 0.8 247.5 32.8SR 36-45 1.0 245.5 35.5 36 0.8 247.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 18.1 232.0 16.9 36 20.2 129.5 18.9SR 45-36 17.8 223.0 17.2 45 19.3 232.0 13.9MAIN 45-36 18.2 250.0 16.2 36 20.4 250.0 13.2SR 45-36 18.5 246.0 16.4 45 19.3 232.0 13.9010080604020050100150MHzACR-F (dB)2002500100