Title: +038=433.002-FS031._02-Eaton Tavlebyggeren Produktblad.pdf
Rated service short-circuit breaking capacity according to IEC/EN 60898-1Ics7,5 kAOperational switching capacitykA7.5CharacteristicB, C, D, K, S, ZMax. back-up fuseA gL/gG 125Selectivity Class3lifespanLifespanOperations> 10000Direction of incoming supplyas requiredMechanical Standard front dimensionmm45Enclosure heightmm80Mounting width per polemm17.5MountingIEC/EN 60715 top-hat railDegree of ProtectionIP20, IP40 (when ﬁtted)Terminals top and bottomTwin-purpose terminalsTerminal protectionFinger and back-of-hand proof to BGV A2Terminal capacities2 mm2 mm1 x 252 mm2 x 10Thickness of busbar materialmm0.8 … 2Mounting positionAs requiredDesign veriﬁcation as per IEC/EN 61439 Technical data for design veriﬁcationRated operational current for speciﬁed heat dissipationInA32Heat dissipation per pole, current-dependentPvidW0