Title: +038=249.001-#####._05-Lydtest plan 10 og 11 Pareto - Flere rom - Multiconsult.pdf
30125048,0160049,8200052,5250052,520315053,4400054,7500056,8106312525050010002000Hz 4000Frequency, f, Hz Rating according to ISO 717-1 R'w Evaluation based on field measurement results obtained in one-third-octave bands by an engineering method.(C;Ctr) =44(2;8) dBC50-3150 = Ctr,50-3150 =312dB C50-5000 = dB Ctr,50-5000 =212dB C100-5000 = dB Ctr,100-5000 =18dBdBName of test institute:Multiconsult Norge ASNo. of test report:Date:4/27/2020Signature:SUVApparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation between roomsClient: Description:Probea AS Luftlyd horisontaltDate of test:4/27/2020Object:Møterom 11-007 - Møterom 11-006 Etter tiltak; tette himling og fuge mellom vegg og vinduprofilSource room:Receiving room:Condition:Condition:Type:Type:Location:Location:Frequency range according to theArea of common partition:17,29m²