Title: 40 Bender brukermanual.pdf.pdf
Fault 1/1CT connectionAddr.: 2 Chan.: 4The "CT fault" is displayed in the same way as „Device error display (channel- related)“ on page 83.Possible causes:   Measuring current transformer defective.   Power supply cable interrupted.   Power supply cable short-circuited.   Failure of the power supply unit AN420 or AN110 when W…AB seriesmeasuring current transformers are used.7.3.4 External alarm LED "ALARM 2“ lights up. The programmed common alarm relay switches.Possible causes:   Alarm message from an external device.   Device failure84RCMS460-490_D00067_03_M_XXEN/12.20178. Data8.1 StandardsObserve the applicable national and international standards. The RCMS… se- ries corresponds to the following device standards:   DIN EN 62020 (VDE 0663):2005-11   IEC 62020 (2003-11) Ed. 1.1. The operating manuals for the individual system components provide you with information about the standards that apply to that particular device.