Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
mWCP1PuVariable flow rate: Constant regulation of the temperature differenceVariable flow rate: Constant regulation of the temperature differenceThe regulation maintains a constant temperature difference whatever the load rate of the unit by reducing the flow rate to the minimum acceptable limit. This control mode is suitable for most comfort applications.P ΔP2mp AVPauriamp " ble sPuAm"ppeBedNominal flow ratem3/hThis provides energy savings of around 66% for the pump in each of these last two operating modes12Water chillersHeat pumpDYNACIAT LGTechnical characteristicsDYNACIAT LG080090100120130150180200240260300HeatingNominal capacitykW303538445156707789101114Standard unit Full load performances*HW1COPkW/kW5,485,485,445,475,435,455,495,405,465,425,47Nominal capacitykW29333643495468748597108HW2COPkW/kW4,314,334,324,334,37