Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Isc: 610A R: 0.38Ω Xl: 0.02Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.1V t: 64.5ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 521V Rnpe: >30.0MΩ Um: 523VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF028 C16/2/003 / Mal 2 10.03.2022 13:42 (TomekElektriker)TALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:17GODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*Nr.505051515252TEST RAPPORTResultatKONTINUITET: R200mA LPER: 0.18ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF029 C16/2/003 / Mal 1 10.03.2022 11:28 (TomekElektriker)SPENNING TRMS Uln: 235V Ulpe: 235V Unpe: 1V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.47ΩIsc: 485A R: 0.47Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A