Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The continuity of the PE conductors is established by the enclosure of the run component. You must check the correct position of the components, joint blocks, and PE conductors and the continuity of the PE conductors through the joint block:CorrectIncorrectPE Protective earth conductor L Fishplate30QGH3492101-01 11/2018Supports and Run ComponentsChecking the Alignment of the Joint Block and CoversNOTICELOSS OF IP55 PROTECTION RATINGThe joint block and the gaskets of the top and bottom covers must be correctly aligned for the system to conform to IP55 protection rating standards.Failure to follow these instructions can result in equipment damage.The alignment must be checked on both the joint block and the cover:  Check the alignment of the joint block:CorrectIncorrect Check the alignment of the cover gaskets:CorrectIncorrectQGH3492101-01 11/201831Supports and Run ComponentsRules for Tightening the Bolts of the Joint Block