Title: 36 Siemens GDB181-MO.pdf.pdf
Set address “5”: 1. Enter addressing mode 2. Set 1-digits: Press button 5-times à LED flashes green per button press 3. Store address: press button until LED shines redà address is stored and displayed 1x for confirmation1 Note: If button is released before LED shines yellow, the address is discarded.11 / 40VAV Compact Controller Modbus RTUA6V10631862_en--_d 2019-09-13Internal diagram (Applies to all types)Power supply and bus cable (color coded and labeled)Note12 / 40Siemens Smart InfrastructureThe VAV Compact Controller is supplied with two prewired connecting and communication cables.Tool = Configuration and maintenance interface (7-pin)Core designation Core colorTerminal codeDescriptionCable 1: Power / black sheathing1red (RD)GSystem voltage AC 24 V2black (BK)G0System neutral AC 24 VCable 2: Communication / blue sheathing6violet (VT)REFReference8grey (GY)+Bus (Modbus RTU)9pink (PK)Bus (Modbus RTU)