Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
The module is set up to use blind systems with integrated limit switches. Suppressors should be fitted externally. The module can be operated by the Saia PCD® via an FBox or via the inputs (blind/light switches) on the module. The choice of function and initialisation with the various times is handled exclusively by the F-Box, and must be carried out after activation.6-49PCD3.A860Shade function, short move functionIf a key (or ext. Input 0 / Input 1) is activated briefly, the corresponding relay switches on for the "short move time". If the key/input is activated for longer than the "short move time", the output will stay on for as long as the key is pressed.During a short move, the relay cannot be interrupted by any further input or key activation on the module.InputOutputshort move timeInputOutputshort move timeShade function, hold function