Title: 1 etg del 2.pdf
SR 36-45 13.7 181.5 19.0 36 15.5 209.0 14.8MAIN 45-36 13.2 246.0 16.4 36 15.1 248.0 13.3SR 36-45 13.7 246.0 16.4 36 16.3 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.1 18.0 46.3 12 9.6 17.9 44.0SR 12-36 8.6 17.9 46.3 12 10.3 17.9 44.0MAIN 36-45 11.2 245.5 5.1 36 11.1 245.5 2.5SR 36-45 12.0 250.0 4.7 36 11.9 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.0 10.9 20.8SR 45 3.5 12.4 20.5MAIN 36 7.2 229.0 10.4SR 45 6.2 189.5 11.260500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active