Title: 2 etg del2.pdf
Cable ID: T2106 Date / Time: 10/11/2013 08:40:41 AM Headroom 13.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 45]58 92 7 2.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.2 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.7 85.0 33.5 36 14.7 85.0 30.5SR 12-36 16.6 85.0 33.5 36 17.1 85.0 30.5MAIN 12-36 13.7 85.0 33.5 36 14.9 96.3 29.6SR 12-36 17.4 96.3 32.6 36 17.4 96.0 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 25.9 6.9 41.9 12 26.0 4.1 43.3