Title: +038=433.002-FS034._06-Tavlebyggeren Eaton FDV.pdf
Built-in depthmm70Suitable for ﬂush-mounted installationNoAnti-nuisance tripping versionYesDegree of protection (IP)IP20Connectable conductor cross section solid-coremm²1 - 25Connectable conductor cross section multi-wiredmm²1 - 2508/15/2020Eaton Industries GmbH http://www.eaton.eu © 08/2020 by Eaton Industries GmbH Eaton Y7-300501 ED2020 V71.0 EN2 / 2sg00719_rDescription(cid:129) High-quality residual current device /miniature circuit breaker combination,line voltage-dependent(cid:129) Increased protection in applications with1-phase frequency converter due to thedetection of mixed frequencies (type F)(cid:129) Reduction of nuisance tripping (type F or G/A)thanks totime delayed trippingincreased current withstand capability3 kA(cid:129) Higher load rating with DC residual currentsup to 10 mA (Type F)(cid:129) Contact position indicator red - green(cid:129) The -OL types are speciﬁ cally designed to