Title: Data tester Smestad skole - Detaljert.pdf
Insertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,5 3,0 2,5 1,75Worst Value: Local: 36 14,5 43,7 29,2 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 14,7 10,1 4,6 247,50Remote: 12 21,6 17,2 4,4 47,50Worst Value: Local: 12 14,7 10,1 4,6 247,50Remote: 12 17,3 9,9 7,4 255,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,5 26,7 2,8 499,00Remote: 36-45 29,6 26,7 2,9 499,00Worst Value: Local: 36-45 29,5 26,7 2,8 499,00Remote: 36-45 29,6 26,7 2,9 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-12 24,0 13,0 11,0 364,00Remote: 12-36 23,9 13,0 10,9 364,00