Title: økernvn 94.pdf
SR 36-45 13.8 164.5 19.9 36 15.7 77.8 23.4MAIN 45-36 14.7 248.0 16.3 45 16.6 241.5 13.5SR 36-45 14.6 248.0 16.3 45 16.1 248.0 13.3010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 12.1 43.8 35.7 45 14.3 44.0 33.2SR 36-45 14.5 48.8 34.3 36 15.0 42.8 33.6MAIN 36-78 26.8 249.5 4.7 36 26.1 237.0 3.3SR 36-45 24.4 247.0 5.0 36 25.1 247.5 2.3010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 3.3 31.8 18.5SR 78 4.8 31.8 18.5MAIN 36 6.5 248.0 10.1SR 12 6.9 120.0 13.2010080050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040200050100150MHzProject: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASS