Title: V20-09-02 VVS-anlegg plan 9 - DM3-1.pdf
+09 = 320.102 - OE 091 0.104 L/s28 mm +c 274028 mm +c 2750WISE IAQWISE RTA22 mm +c 282018 mm +c 282022 mm +c 282018 mm +c 2820Åpent kontorlandskap 9-018LD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sSTAP/STAD DN 20Åpent kontorlandskap 9-120Opp 35 mm Opp 35 mm+09 = 320.102 - OE 094 0.178 L/s28 mm +c 270028 mm +c 270022 mm +c 2820 22 mm +c 282028 mm +c 2820 28 mm +c 2820LD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/sNed 320.102: 54 mmNed 320.102: 54 mmLD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/s3456DN 657LD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/sSTAP/STAD DN 4054 mm +c 282054 mm +c 2820Opp/ned 370.101: DN 100Opp/nedSF002T-125