Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ001 NZM1/4 16.06.2020 08:47SPĆNDINGU12: 400V U13: 399V U23: 400V f: 50.0Hz : 1.2.3DM1-3. Plan 9 / DM1.E5.433.09.04 / XQ002 NZM1/4 15.06.2020 11:35Tallberg Elektro A/S Tlf.22796640Side:2GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.131314141515161617171818TEST RAPPORTResultatRCD II: 28.5mAUci: 0.0V t: 107.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM1.E5.433.09.04 / XQ002 NZM1/4 15.06.2020 11:35Z-LINEZ: 0.31ΩIsc: 746A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XQ002 NZM1/4 15.06.2020 11:36Zs(rcd)Z: 0.26ΩIsc: 873A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XQ002 NZM1/4 15.06.2020 13:09R LOW OhmR: 0.11ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XQ002 NZM1/4 10.06.2020 15:07R ISOR: >200MΩ Um: 263V