Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 15.06.2020 13:36R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 15.06.2020 13:37R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 15.06.2020 13:38Tallberg Elektro A/S Tlf.22796640Side:18GODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESMISLYKKESNr.133133134134135135136136137137138138139139140140141141TEST RAPPORTResultat R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 15.06.2020 13:35KONTINUITET R: 2.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 15.06.2020 13:36KONTINUITET R: 2.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 10:25KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 10:25R LOW OhmR: 0.01Ω