Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Site 1/ Building 1/ Storey 10 / Toilet 3 / Room summaryToilet 3Clearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Toilet 3) Perpendicular illuminance (adaptive) [Ix] 203 (= 200) 155 236 0.76 0.66 Height: 0.000 m, Wall zone: 0.300 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 1 iGuzzini illuminazione - Q510 Laser Blade XS - Downlight HC 23.1W 1452 231 62.9 Total via all luminaires 1452 231 62.9Lighting power density: 4.23 W/m? (Floor area of room 5.46 m? ), Lighting power density: 7.67 W/m? = 3.78 W/m?/100 Ix (Area of working plane 3.01 m?)Consumption: 19 kWh/a of maximum 200 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 70