Title: økernvn 94.pdf
100150200250MHzLinkWare Version 7.4Cable ID: T4192 Date / Time: 09/11/2013 10:20:57 Headroom 6.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]257 392 14 12.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]6.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.3 229.5 35.9 36 8.7 229.5 33.3SR 12-36 6.8 184.0 37.5 12 7.4 243.0 32.9MAIN 12-36 7.3 229.5 35.9 36 8.7 229.5 33.3SR 12-36 7.7 243.0 35.5 12 7.4 243.0 32.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)