Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
It is sometimes recommended to separate the unit from its support and the support from the wall or the ground, using joints made of noise-absorbing materials or vibration absorbers (not supplied). In these cases, users should comply with the manufacturers’ recommendations for their choices and installations. TECUMSEH is not responsible for the choice of vibration absorbers or their absorption capacity.■ 2.1. Serial label for the WINTSYS® rangeSee annex 1■ 2.2. Safety feature All units are delivered with a switch-disconnector fitted with a handle that is lockable in the ON or OFF position and a HP/LP adjustable pressure switch with automatic (factory setting) or manual reset. The choice of reset is made using a switch (see annex 7). The pressure switch has a 16 A breaking capacity.■ 2.3. Refrigeration diagrams See annex 2