Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 36-45 10.2 464.0 29.6 36 9.6 465.0 26.7SR 36-45 5.5 468.0 29.4 45 7.0 472.0 26.3MAIN 36-45 11.3 500.0 27.8 36 10.4 497.0 25.1SR 36-45 5.7 473.0 29.1 45 7.1 477.0 26.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 3.9 53.5 45 13.6 2.3 55.2SR 36-45 14.6 3.8 53.8 45 13.6 3.8 50.8MAIN 36-45 15.6 471.0 11.8 45 17.2 499.0 8.3SR 36-45 15.6 472.0 11.8 45 17.0 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.3 69.3 29.9 36 26.4 82.3 24.8SR 12-45 25.9 63.3 31.2 45 27.1 64.0 28.5MAIN 36-45 39.2 500.0 -12.4 36 38.9 500.0 -15.3SR 36-45 35.3 500.0 -12.4 45 36.5 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 8.0 493.0 8.0SR 12 6.6 475.0 8.0MAIN 12 8.0 493.0 8.0SR 12 6.6 475.0 8.040010080250 MHzRL (dB)