Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]43.3 187 2 6.22Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]22.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.9 500.0 29.2 36 5.2 500.0 26.4SR 12-36 8.0 500.0 29.2 36 9.3 500.0 26.4MAIN 36-45 6.9 500.0 29.2 36 5.2 500.0 26.4SR 12-36 8.0 500.0 29.2 36 9.3 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.7 466.0 11.9 45 19.9 402.0 10.2SR 78-45 18.8 494.0 11.4 45 20.0 383.0 10.6MAIN 78-45 19.0 500.0 11.3 45 20.4 500.0 8.3SR 78-45 18.8 494.0 11.4 45 20.6 490.0 8.40100806040200250 MHzACR-F (dB)