Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 16.9 494.0 11.4 45 17.5 4.3 49.7MAIN 45-78 17.3 499.0 11.3 78 19.0 499.0 8.3SR 78-45 17.0 499.0 11.3 45 18.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 24.7 110.0 22.6 45 25.7 110.0 20.1SR 36-78 24.9 79.5 27.8 36 25.6 80.5 25.1MAIN 36-45 34.9 496.0 -12.1 36 36.3 500.0 -15.3SR 36-45 34.7 497.0 -12.2 36 36.0 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.3 500.0 8.0SR 45 6.8 459.0 8.0MAIN 45 7.3 500.0 8.0SR 45 6.8 459.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS