Title: 360.002 - Tilluft.pdf.pdf
16.213.50.0 +0.08k [dB]4.714.0 +14.114.28.30.0 +0.08.91.5 +0.05.52.60.5 +0.04.214.00.00.1 +0.03.03.0 +0.03.00.0 +0.04.714.0 +15.615.68.00.0 +0.0Lp [dB]20,820,2LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeProductSize161 PLUGESU_SE-*0200DUCT400162 T-BRANCHTCPU_DK-*-*0,0 400/250DUCT250BEND-15MAGIB-C4-*-*250DUCT250BEND-15MAGIB-C4-*-*250DUCT250163 FLOWDAMPER LEO-0-250250DUCT250L [m]0,00,00,00,50,1Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]4301,00,0 Sound in:Attenuation: Addition:4301,01,3 Sound in:Attenuation: Addition:Dividing:4302,40,0 Sound in:Attenuation: Addition:4302,40,2 Sound in:Attenuation: Addition:4302,40,0 Sound in:Attenuation: Addition:4302,4