Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 43,0 68,0 223,0 12,0 7,5Limit 100,0 - 555,0 50,0 25,0Margin 57,0 - 332,0 38,0 17,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,8 3,0 2,2 2,80Worst Value: Local: 45 18,3 43,5 25,2 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 17,3 9,7 7,6 269,00Remote: 12 22,2 14,4 7,8 91,00Worst Value: Local: 78 16,1 8,0 8,1 437,00Remote: 12 17,4 8,5 8,9 353,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass