Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Uc: 0.1V Rl: 2Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 15.06.2020 12:47R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF037 C16/2 16.06.2020 09:53R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF038 C16/2 15.06.2020 08:57RCD II: 28.5mAUci: 0.1V t: 87.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF038 C16/2 15.06.2020 08:58Z-LINEZ: 0.45ΩIsc: 508A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATallberg Elektro A/S Tlf.22796640Side:9GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 6565666667676868696970707171TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E6.433.09.03 / XF038 C16/2 15.06.2020 08:58Zs(rcd)Z: 0.39ΩIsc: 584A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A