Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 11.06.2020 16:23Tallberg Elektro A/S Tlf.22796640Side:31GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.212212213213214214215215216216217217TEST RAPPORTResultatZ-LINEZ: 0.60ΩIsc: 382A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 11.06.2020 16:23Zs(rcd)Z: 0.56ΩIsc: 411A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 12.06.2020 09:27RCD tt: 68.1msUc: 0.3V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 12.06.2020 09:28RCD UbUc: 0.2V Rl: 6Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 12.06.2020 09:28RCD II: 28.5mAUci: 0.0V t: 18.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 12.06.2020 12:07