Title: 2 etg del2.pdf
200250MHzLinkWare Version 8.1Cable ID: D2307 Date / Time: 10/10/2013 02:40:32 PM Headroom 14.7 dB (NEXT 36-45) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]86 137 10 3.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 97.0 32.5 36 15.4 81.0 30.8SR 36-45 18.6 97.0 32.5 36 18.2 81.0 30.8MAIN 36-45 14.7 97.0 32.5 36 15.7 96.0 29.6SR 36-45 18.6 97.0 32.5 36 18.2 81.0 30.810080604020NEXT (dB)