Title: FDV-DOKUMENTASJON.pdf
3) Up to 95 mm² can be connected depending on the cable manufacturer. Al circular conductor Tunnel terminal Solid mm2 1 x 16 Stranded Stranded mm2 1 x (25 - 95) Bolt terminal and rear-side connection Direct on the switch Solid mm2 1 x (10 - 16)2 x (10 - 16) Stranded mm2 1 x (25 - 35)2 x (25 - 35) Cu strip (number of segments x width x segment thickness) Box terminal min. mm 2 x 9 x 0.8 max. mm 9 x 9 x 0.8 Copper busbar (width x thickness) mm Bolt terminal and rear-side connection Screw connection M6 Direct on the switch min. mm 12 x 5 max. mm 16 x 5 Control cables mm2 1 x (0.75 - 2.5)2 x (0.75 - 1.5) Design veriﬁcation as per IEC/EN 61439 Technical data for design veriﬁcation Rated operational current for speciﬁed heat dissipation In A 63 Equipment heat dissipation, current-dependent Pvid W 14.17 Operating ambient temperature min. °C