Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
SPENNING TRMS Uln: 232V Ulpe: 232V Unpe: 1V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.32ΩIsc: 723A R: 0.32Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ATALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:21GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr.61616262636364646565TEST RAPPORTResultatRCD: UtlřsningsstrřmI: 27.0mAUci: 0.0V t: 203.1ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 521V Rnpe: >30.0MΩ Um: 516VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF031 C16/2/003 / Mal 3 10.03.2022 13:46 (TomekElektriker)KONTINUITET: R200mA LPER: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF034 C16/2/Res 11.03.2022 10:20 (TomekElektriker)SPENNING TRMS Uln: 233V Ulpe: 233V Unpe: 1V f: 53.50HzSYS.: TN/TTColliers Plan 5 / DM3.E2=433.05.02 / XF034 C16/2/Res 11.03.2022 10:21 (TomekElektriker)RCD: Utlřsningstidt: 51.0ms