Title: Data tester Smestad skole - Detaljert.pdf
601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 67,9 57,3 10,6 2,20Remote: 12-45 67,9 57,3 10,6 2,20Worst Value: Local: 12-45 22,1 11,2 10,9 444,00Remote: 12-36 22,1 10,5 11,6 482,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,8 3,3 499,00Remote: 36 29,6 23,8 5,8 500,00Worst Value: Local: 36 27,1 23,8 3,3 499,00Remote: 36 29,6 23,8 5,8 500,00PS-ACRF: Pass Worst Margin: Local: 45 71,3 60,0 11,3 1,15Worst Value: Local: 45 21,8 8,5 13,3 430,00Remote: 45 71,5 61,2 10,3 1,00Remote: 12 21,4 8,3 13,1 442,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:13Signature:______________________ Page: 130Copper Certification Report