Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
3830.6 m 136 136 0 0 0Cable ID: =521.03.04-UF001 Date / Time: 14-08-2020 07:43:25 Headroom 6.0 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]12.2 52 0 2.00Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]35.4 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.0 450.0 30.2 36 7.0 459.0 27.0SR 12-36 7.8 460.0 29.7 36 7.9 460.0 26.9MAIN 12-36 7.3 500.0 27.8 36 7.6 499.0 25.0SR 12-36 8.6 499.0 27.9 36 8.3 500.0 25.010080604020NEXT (dB)