Title: 1 etg del 2.pdf
Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.8 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.1 249.0 35.4 36 1.0 * 247.5 32.8SR 36-45 1.9 249.0 35.4 36 1.9 241.0 33.0MAIN 36-45 1.1 249.0 35.4 36 1.0 247.5 32.8SR 36-45 1.9 249.0 35.4 36 1.9 242.5 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 19.2 226.5 17.1 12 20.0 4.8 47.7SR 45-12 18.7 132.0 21.8 12 20.4 5.0 47.2MAIN 45-12 19.2 226.5 17.1 12 21.1 230.5 13.9SR 45-12 19.3 224.0 17.2 45 21.2 226.5 14.1010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250