Title: +038=433.000-NI003._05-Testrapport elektriske anlegg - DM3.E3.433.09.02, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 10.06.2020 14:58R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 15.06.2020 09:07RCD II: 28.5mAUci: 0.1V t: 107.5ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 15.06.2020 09:13SPĆNDINGUln: 233V Ulpe: 233V Unpe: 1V f: 50.0HzDM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 15.06.2020 09:16Tallberg Elektro A/S Tlf.22796640Side:7GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.525253535454555556565757TEST RAPPORTResultatZ-LINEZ: 0.35ΩIsc: 666A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 15.06.2020 09:17Zs(rcd)Z: 0.31ΩIsc: 738A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E3.433.09.02 / XF028 C16/2 15.06.2020 09:20RCD Ub