Title: 91879 FDV F13 Kafe.pdf
RCD/MCB,32A,30mA,miniaturecircuit-breakertripcurveC,3p,residual currentcircuit-breakertripcharacteristic:APartno. Articleno.PKPM3-32/3/C/003-A 136564Deliveryprogram Basic functionCombined RCD/MCB devicesNumber of poles3 poleTripping characteristicCApplicationSwitchgear for residential and commercial applicationsRated currentInA32Rated switching capacity according to IEC/EN 61009kA10Rated fault currentIΔNA0.03TypeType ATrippingAnon-delayedProduct rangePKPM3SensitivityPulse-current sensitiveImpulse withstand currentPartly surge-proof 250 ATechnicaldata Electrical SensitivityPulse-current sensitiveDesignverificationasperIEC/EN61439 Technical data for design verificationRated operational current for specified heat dissipationInA32Heat dissipation per pole, current-dependentPvidW0Equipment heat dissipation, current-dependentPvidW12.8Static heat dissipation, non-current-dependentPvsW0Heat dissipation capacity