Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
a residual current device is installed on the UPS input line (optional), this must be located upstream of the power distribution unit.Electrical requirementsUPSThermal-magnetic switch on inputInput leakage currentCable section1 kVA10 C< 3.5 mAaccording to IEC2 kVA16 C< 3.5 mAaccording to IEC3 kVA20 C< 3.5 mAaccording to IECITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 004. REAR VIEWConnection to the mains power supply and to the load(s) must be made using cables of suitable cross section, in accordance with current standards.If not already provided, install a PDU panel allowing isolation of the mains supply upstream of the UPS. The panel must be equipped with an automatic switch rated high enough to handle the current draw on full load, and with a residual current device.EPO (Emergency Power Off)USB serial portRS232 serial connectorSlot for optional communication cardsFanBattery extension socketOutput sockets OUT 230 V~ 3 x IEC 320Input protection