Title: TESEO.pdf
6.1. How to trace3. the3. distribution line3.: trace a horizontal line at the chosen height by means of a stretched plumb line. with the TeSeo system you do not need to give the inclination to collect the condensate as the up-column and the down-column are already equipped at the bottom with a collection and a drain valve.6.2. How to se3.cure3. the3. pipe3.work: The pipework can be supported by several types of ceiling or wall mounted fi- xing plates and brackets. The recommended distance between these fixing brackets is 2 to 4 meters, depen- ding on the weight of the distributed fluid.6.3. Isolation valve3.s: ball valves must be mounted both at the beginning of the line and at the beginning of the branches of the main line. mount a pressure gauge at the beginning of the main line and a safety valve on the air receiver.6.4. Take3.-offs: for the3. down tube3.s: to prevent any impurities fouling the bottom of the hollow bar, we recommendfitting the outlet plates on the sides of the hollow bar.