Title: +175=737.001_IK001_Brukermanual for Refra varmepumpe.Produktinformasjon.pdf
In these cases it is preferable to install relief devices, which lead the refrigerant to the low-pressure side of the plant (emission reduction).Liquid flow and pressure drop in the evaporator Coolant flow through the evaporator and condenser should be adjusted based on the minimum and maximum values given in the tables of technical data. Consumption is below the lower acceptance threshold gives rise to a laminar flow and, consequently, reduce performance, improper functioning of the TRV, as well as the likely trigger automatic protection for low temperature. Unacceptable increase in consumption is the cause of the destruction of joints and pipe liquid loop evaporator.