Title: Hardware Installation Guide.pdf
Wire the J1 interface using a 24 AWG (minimum) cable at a maximum of 500 feet.The reader power is a maximum of 80 mA. If the reader requires additional current, connect the reader power to a +12 VDC terminal on the Single Reader Interface Module.If you are connecting the reader to a dual reader interface module, each wire should be attached to the associated connection on the Dual Reader Interface Module board (LNL-1320).All readers that have a buzzer will beep during pre-alarm when in extended held open mode. This includes primary and alternate readers. If the reader has two-wire LED control, this feature is disabled. The reader starts beeping at pre-alarm time and continues to do so until the door is closed or the held open time is hit.revision 6 — 331LNL-1300 Single Reader Interface ModuleReader/Single Interface Module Downstream WiringBlack - GNDOrange - BZRBrown - LEDWhite - CLK/D1Green - DAT/D0Red - +12V62.1.5Open Supervised Device Protocol