Title: økernvn 94.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.0 246.5 5.0 36 7.2 245.0 2.5SR 36-45 6.9 242.5 5.4 36 6.9 249.0 2.1MAIN 36-45 7.0 250.0 4.7 36 7.4 250.0 2.0SR 36-45 7.0 249.0 4.8 36 6.9 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.7 25.4 19.0SR 36 4.4 14.8 20.2MAIN 45 9.5 227.5 10.4SR 45 8.2 225.0 10.506050050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4