Title: økernvn 94.pdf
Cable ID: T3109 Date / Time: 09/11/2013 05:44:29 Headroom 1.1 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]175 277 19 7.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.7 234.0 35.8 78 7.6 234.0 33.2SR 36-45 1.1 249.5 35.4 36 1.1 238.0 33.1MAIN 36-78 7.7 234.0 35.8 78 7.6 234.0 33.2SR 36-45 1.1 249.5 35.4 36 1.1 238.0 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 12.6 70.3 27.3 36 15.2 66.3 24.8