Title: +038=370.104-OE004T_01-Multical 801 Energimåler Kamstrup - Installasjons- og brukerguide.pdf
2.1 Direct sensors The short, direct sensors up to DN25 can be mounted in special ball valves with built-in M 10 socket for the short direct sensor. They can also be mounted in installations with standard angle tee-pipes. Kamstrup supply R½ and R¾ brass nipples, which fit our short, direct sensor. Make sure that the tip of the temperature sensor reaches at least the center of the flow pipe. The short direct sensor can also be direct mounted in all Kamstrup flow sensors with G¾B, G1B, G5/4B and G2 thread on the meter case. Fasten the sensors’ brass unions lightly (approx. 4 Nm) using a 12 mm face wrench and seal the sensors with seal and locking wire.Kamstrup A/S • 5512603_C1_GB_03.20167MULTICAL® 801