Title: Data tester Smestad skole - Detaljert.pdf
dB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 67,2 57,3 9,9 2,20Remote: 12-45 64,8 53,6 11,2 3,40Worst Value: Local: 12-45 22,2 11,0 11,2 457,00Remote: 12-45 22,5 11,0 11,5 457,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,2 23,9 4,3 495,00Remote: 36 28,3 23,8 4,5 499,00Worst Value: Local: 36 28,2 23,9 4,3 495,00Remote: 36 28,3 23,8 4,5 499,00PS-ACRF: Pass Worst Margin: Local: 12 71,9 61,2 10,7 1,00Worst Value: Local: 45 20,4 8,0 12,4 457,00Remote: 45 70,6 61,2 9,4 1,00Remote: 45 21,5 8,1 13,4 453,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:59Signature:______________________ Page: 37Copper Certification Report