Title: +038=433.002-FS034._06-Tavlebyggeren Eaton FDV.pdf
Connection diagram 2-polesDimensions (mm)6EATON CORPORATION xxxxx+xxxx-xxxxENProtective Devices Combined RCD/MCB Devices NdRBM, Technical Data1.7Tripping Characteristic NdRBMTripping Characteristic NdRBM, Characteristics B, C and DTripping Characteristic NdRBM, -OL Type 10,13,15, 20 ATripping Characteristic acc. to EN 61009Tripping Characteristic -OL Type 15A, 20Aconventional non-tripping currentconventional tripping current] s [e mi tg n p p i r Ti7EATON CORPORATION xxxxx+xxxx-xxxxEN1.8Protective Devices Combined RCD/MCB Devices NdRBM, Technical DataInternal Resistance NdRBMType B At room temperature (single pole) In [A] 10 13 16 * 50HzR* [m] 17.9 12.3 7.6Type C At room temperature (single pole) In [A] 6 10 13 16 20 25 * 50HzR* [m] 28.5 17.7 9.0 6.7 5.5 3.0Type D At room temperature (single pole) In [A] 6 10 13 16 20 25 * 50HzR* [m] 28.5 14.9 9.0 6.7 5.5 3.0Power Loss at In NdRBMType B (entire unit) In [A] 10 13 16 * 50Hz and ambient temperature