Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
9.5…2,431 Hz 19…4,864 Hz 38…9,727 Hz 76…19,454 Hz 0.6…1224 kHz/s, non-linear range division, dependent on selected frequency range with symmetrical acceleration and braking ramps All data in this module are volatile (non-volatile Saia PCD® registers are available).Digital inputs Number of inputs: Terminal 0 = I0 Terminal 1 = I1 Terminal 2 = I2 Terminal 3 = I3 Nominal voltage:Input current: Input filer: Circuit type: Digital outputs Number: Terminal 4 Terminal 5 Terminal 6 Terminal 7 Switching capacity: Short circuit protection: Electrical isolation: Voltage drop:O0: O1: O2: O3:4 configurable as emergency stop or for general use configurable as limit switch LS1 or for general use configurable as reference switch or for general use configurable as limit switch LS2 or for general use 24 VDC “low” range: “high” range: for safety reasons, normally-closed contacts (negative logic) should be used typically 6.5 mA < 1 ms electrically connected30…+5 V +15…30 V for source operation only,