Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
26.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.2 480.0 29.6 45 8.1 480.0 26.8SR 36-45 6.7 487.0 29.5 36 7.1 486.0 26.7MAIN 12-45 8.2 480.0 29.6 45 8.2 500.0 26.4SR 36-45 6.8 500.0 29.2 45 7.3 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.1 3.8 53.8 45 13.9 2.9 53.1SR 36-45 14.1 3.9 53.5 45 13.8 2.5 54.3MAIN 45-36 15.4 479.0 11.6 45 15.2 476.0 8.7SR 36-45 15.3 479.0 11.6 45 15.1 471.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.3 40.3 37.2 36 19.4 39.3 35.1SR 12-36 21.5 46.0 35.5 36 20.8 39.3 35.1MAIN 36-45 34.8 500.0 -12.4 45 34.4 500.0 -15.3SR 36-45 32.9 500.0 -12.4 45 33.5 500.0 -15.30804000250 MHzACR-N (dB)