Title: økernvn 94.pdf
Cable ID: T4049 Date / Time: 09/11/2013 10:15:25 Headroom 14.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]226 358 25 9.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.2 95.8 32.6 36 15.8 95.8 29.6SR 12-36 14.0 79.8 33.9 36 15.5 60.8 32.9MAIN 12-36 14.2 95.8 32.6 36 15.8 95.8 29.6SR 12-36 14.0 79.8 33.9 36 15.7 97.0 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.4 49.8 24.7 36 19.1 56.0 20.7