Title: Installasjonsmanualer.pdf
The batteries will degrade quickly if used frequently, or in high operating temperatures. Should the batter- ies have reached the end of their life cycle, contact SOCOMEC After Sales Service. Batteries must be replaced even if the "Replace battery" LED is not lit.Battery charge fault or other causes.Contact SOCOMEC After Sales Service"Replace battery" icon lit.Batteries flat.Charge the batteries for a minimum of 8 hours. If the problem persists, contact SOCOMEC After Sales Service to have for battery replacement.Faulty communication between PC and UPS.Wrong transmission speed.RS232 connection incorrect.Change the transmission speed and test again.See "Communication" section of this manual. Reconnect the UPS to the COM1/COM2 port of the PC.USB connection incorrect.Reconnect the UPS to the USB port of the PC.UPS functions in "Battery Mode" even though a.c. mains is connected and healthy.Mains voltage not registering at UPS input.Thermal switch on the rear panel has been tripped.