Title: 03 - Døli pleie- og omsorgssenter 18.03.2016.pdf
Luftmengder maksLuftmengder driftGj.vinner %SFPMandagTirsdagOnsdagTorsdagFredagLørdagSøndagDriftstid/ukeDriftsuker/årOppvarmingVifteenergi% Til gode som varme Netto oppvarmingSamlet forbruk kWh/årIDAreal som ventileresStartStoppStartStoppStartStoppStartStoppStartStoppStartStoppStartStopp36.01Vestlig sengebygg23 00023 00040 %407:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:0010552325 445139 53325 %290 562430 09536.01Vestlig sengebygg23 00016 10040 %300:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:006352136 68743 95325 %125 699169 65236.03Østlig sengebygg23 00023 00040 %407:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:0010552325 445139 53325 %290 562430 09536.04Østlig sengebygg23 00016 10040 %300:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:006352136 68743 95325 %125 699169 65236.05Adm./kjøkken/kantine10 20010 20040 %407:0017:0007:0017:0007:0017:0007:0017:0007:0017:0007:0017:0007:0017:00705296 21941 25325 %85 905127 159Sum