Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,3 26,7 2,6 498,00Remote: 12-36 30,6 29,9 0,7 400,00Worst Value: Local: 36-45 29,3 26,7 2,6 498,00Remote: 36-45 29,0 26,7 2,3 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 68,1 57,3 10,8 2,20Remote: 12-45 68,1 57,3 10,8 2,20Worst Value: Local: 12-45 23,8 11,6 12,2 425,00Remote: 45-12 24,0 11,6 12,4 426,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 28,1 23,8 4,3 498,00Remote: 36 29,3 27,1 2,2 400,00Worst Value: Local: 45 28,1 23,8 4,3 498,00Remote: 45 27,6 23,8 3,8 500,00PS-ACRF: Pass Worst Margin: Local: 12 67,4 56,3 11,1 1,75Worst Value: Local: 45 22,3 9,0 13,3 407,00