Title: etg u1.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]236 374 26 10.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]7.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.3 87.3 33.3 36 15.9 87.3 30.3SR 12-36 12.8 87.3 33.3 12 14.4 87.0 30.3MAIN 12-36 14.6 97.0 32.5 36 16.5 96.8 29.5SR 12-36 12.9 97.0 32.5 12 14.5 96.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 26.1 37.3 27.2 12 25.9 5.3 41.2SR 45-12 25.8 36.5 27.4 12 26.5 5.8 40.4MAIN 36-12 27.0 88.8 19.7 12 26.9 78.8 17.7SR 36-12 26.8 89.5 19.6 36 28.1 98.8 15.701008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 18.1 13.8 39.1 12 20.0 13.6 36.2