Title: +038=433.002-FS030._05-Eaton Tavlebyggeren Produktblad.pdf
1-phase frequency converter due to thedetection of mixed frequencies (type F)(cid:129) Reduction of nuisance tripping (type F or G/A)thanks totime delayed trippingincreased current withstand capability3 kA(cid:129) Higher load rating with DC residual currentsup to 10 mA (Type F)(cid:129) Contact position indicator red - green(cid:129) The -OL types are speciﬁ cally designed tofulﬁ ll the tripping characteristic requirementsof I2  Iz in the Norwegian electrotechnicalstandard NEK 400-8-823.(cid:129) Fault current tripping indicator white - blue(cid:129) Guide for secure terminal connection(cid:129) 3-position DIN rail clip, permits removal fromexisting busbar system(cid:129) Comprehensive range of accessories can bemounted subsequentlyProtective Devices Combined RCD/MCB Devices NdRBM, 2-pole digital1.1(cid:129) Wide variety of rated tripping currents(cid:129) Rated currents up to 25 A(cid:129) Tripping characteristics B, C, D