Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 36]33.9 146 1 4.90Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.7 500.0 29.2 36 5.9 500.0 26.4SR 36-45 6.0 473.0 29.8 36 6.2 500.0 26.4MAIN 36-78 7.7 500.0 29.2 36 5.9 500.0 26.4SR 36-45 6.2 500.0 29.2 36 6.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.5 5.9 49.9 45 20.5 43.0 29.6SR 45-78 18.5 5.9 49.9 45 20.2 500.0 8.3MAIN 45-12 20.9 496.0 11.3 45 20.9 497.0 8.3SR 12-45 20.5 496.0 11.3 45 20.2 500.0 8.30100806040200250 MHzACR-F (dB)