Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 12-45 8.7 478.0 29.7 45 9.1 481.0 26.8SR 36-45 7.0 499.0 29.3 36 7.9 498.0 26.4MAIN 12-45 8.7 478.0 29.7 45 9.4 499.0 26.4SR 36-45 7.0 499.0 29.3 36 7.9 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 5.0 51.3 45 14.4 5.9 46.9SR 36-45 14.8 23.4 37.9 45 14.4 6.9 45.5MAIN 45-78 16.1 496.0 11.3 45 15.9 500.0 8.3SR 78-45 15.8 497.0 11.3 45 15.6 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 21.1 41.3 36.9 45 20.4 40.8 34.6SR 36-78 24.9 41.0 37.0 36 22.9 41.0 34.5MAIN 12-45 35.2 500.0 -12.4 45 35.3 499.0 -15.2SR 36-45 32.9 499.0 -12.3 36 34.0 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.6 492.0 8.0SR 12 6.8 467.0 8.0MAIN 12 7.6 492.0 8.0SR 12 6.8 467.0 8.040010080250 MHzRL (dB)