Title: FDV-DOKUMENTASJON.pdf
41119 / U1 / PLASS 441119 / U1 / PLASS 4NPENPELimit: 0.90ML-PE,N-PEXl: 0.04R+: 0.0R+: 0.0SYS.: TN/TTSYS.: TN/TTSYS.: TN/TTSYS.: TN/TTINSULATIONR: 0.03Fuse I: 32A02.09.2020 09:28 (459)02.09.2020 09:28 (459)41119 / U1 / PLASS 541119 / U1 / PLASS 5VOLTAGEΩΩΩΩΩΩΩ:CONTINUITY02.09.2020 11:28 (459)R-: 0.0R-: 0.0NoResultsUc: 0.0VIdn: 30mAtype:IscMaxLN: 653AElektro Nettverk Service asRlpe: >30.0MRnpe: >30.0MCONTINUITYΩPASSPASSPASSUlpe: 239VR-: 0.141119 / U2 / PLASS 141119 / U2 / PLASS 1Tripout timetype:::Uc: 0.2V02.09.2020 09:58 (459)R+: 0.1f: 50.04HzUlpe: 238VR: 0.34Um: 534VIscStd: 677Af: 50.01HzTRMSTRMSUiso: 500VUiso: 500VPASS*PASS*PASS*Fuse Type: BSYS.: ITSYS.: ITR200mAL-PEFuse T: 0.4sIsc_lim: 160.0AMUL.: x1Page:51414TEST REPORTZ-LINEIscMinLN: 430A02.09.2020 11:31 (459)41119 / U2RCDUnpe: 0VUnpe: 0VIsc: 495AIscMaxLN: 711A1616NPE