Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
SPENNING TRMS Uln: 235V Ulpe: 235V Unpe: 1V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.47ΩIsc: 485A R: 0.47Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.1V t: 54.3ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 526V Rnpe: >30.0MΩ Um: 517VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF029 C16/2/003 / Mal 1 10.03.2022 13:41 (TomekElektriker)KONTINUITET: R200mA LPER: 0.18ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF029 C16/2/003 / Mal 2 10.03.2022 11:38 (TomekElektriker)SPENNING TRMS Uln: 233V Ulpe: 232V Unpe: 1V f: 49.99HzSYS.: TN/TTTALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:18GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.53535454TEST RAPPORTResultatZ-LINEZ: 0.39ΩIsc: 583A R: 0.39Ω Xl: 0.01Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A