Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 23,1 11,5 11,6 429,00Remote: 12-36 22,6 11,4 11,2 436,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,8 23,8 4,0 500,00Remote: 36 28,2 23,8 4,4 500,00Worst Value: Local: 36 27,8 23,8 4,0 500,00Remote: 36 28,2 23,8 4,4 500,00PS-ACRF: Pass Worst Margin: Local: 12 72,4 61,2 11,2 1,00Worst Value: Local: 12 20,3 8,4 11,9 436,00Remote: 12 65,5 54,3 11,2 2,20Remote: 12 21,0 8,5 12,5 432,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:03Signature:______________________ Page: 63Copper Certification ReportCable Label: 521.002-UD-160 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 13:40:34 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein