Title: 2 etg del2.pdf
Wire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 247.5 35.4 36 1.2 235.0 33.2SR 36-450.7 *245.5 35.5 36 0.5 *238.0 33.1MAIN 36-45 1.3 247.5 35.4 36 1.4 247.5 32.8SR 36-45 0.7 245.5 35.5 36 0.7 250.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 11.7 54.3 29.5 45 12.8 48.0 27.6SR 45-36 11.5 54.3 29.5 45 13.2 47.5 27.7MAIN 45-36 14.7 248.5 16.3 36 17.4 248.5 13.3SR 36-45 15.4 249.0 16.3 45 15.2 215.5 14.5010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz