Title: +175=737.001_IK001_Brukermanual for Refra varmepumpe.Produktinformasjon.pdf
Ethylene Glycol Correction Factors 0.9950 0.9920 0.9870 0.9830 0.9790 0.9910 0.9820 0.9770 0.9690 0.9610 1.0700 1.1300 1.1800 1.2600 1.280010% 20% 30% 40% 50% 10% 20% 30% 40% 50% 10% 20% 30% 40% 50%Propylene Glycol Correction Factors10% 20% 30% 40% 50% 10% 20% 30% 40% 50% 10% 20% 30% 40% 50%0.9900 0.9800 0.9700 0.9600 0.9500 0.9870 0.9750 0.9620 0.9420 0.9300 1.0700 1.1500 1.2500 1.3700 1.4200Check the installation. Perform all necessary tests of strength, leakage. Check functional of safety devices, check of the complete installation before filling of the water, Ethilene-glycol and putting into operation.Protect from freezing Manufacturer of machine ensures its normal work only under the condition that appropriate measures are taken: - ensure sufficient flow of fluid through the condenser and evaporator. - taken measures to protect the condenser and the evaporator from freezing.