Title: Spjeldventil.pdf
AccessoriesDescriptionTypeElectrical accessories Stem heating flange ISO 5211, F05 (30W)ZR24-F05DescriptionTypeMechanical accessories Worm gear for D6.. butterfly valves, DN600Manual control for D6.. butterfly valves, for DN25...DN100 Worm gear for butterfly valves DN125...300 Manual control for D6.. butterfly valves, for DN125...DN150 Worm gear for D6.. butterfly valves, DN300...350 Worm gear for D6.. butterfly valves, DN400 Worm gear for D6.. butterfly valves, DN450 Worm gear for D6.. butterfly valves, DN500 Worm gear for D6.. butterfly valves, DN600 Worm gear for D6.. butterfly valves, DN700ZD6N-S100 ZD6N-H100 ZD6N-S150 ZD6N-H150 ZD6N-S350 ZD6N-S400 ZD6N-S450 ZD6N-S500 ZD6N-S600 ZD6N-S700Installation notesRecommended installation positionsThe butterfly valves may be mounted upright to horizontal. The butterfly valves may not be installed in a hanging position i.e. with the spindle pointing downwards.90°90°Water quality requirements