Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 10.3 479.0 29.6 36 10.3 479.0 26.8SR 36-45 8.5 489.0 29.5 36 8.0 485.0 26.7MAIN 36-78 10.3 479.0 29.6 36 10.6 494.0 26.5SR 36-45 8.8 500.0 29.2 36 8.1 488.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-36 15.7 492.0 11.4 45 14.5 2.6 53.9SR 36-78 15.9 492.0 11.4 45 14.6 3.0 52.7MAIN 45-12 15.8 500.0 11.3 12 18.6 500.0 8.3SR 36-78 15.9 492.0 11.4 78 18.6 492.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.2 31.5 40.2 36 19.1 31.5 37.8SR 36-45 20.2 31.5 40.2 36 20.3 31.5 37.8MAIN 36-78 34.2 479.0 -11.0 36 34.9 497.0 -15.1SR 36-45 32.9 500.0 -12.4 36 32.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)