Title: ECY-303_SP.pdf
BACnet Listing BTL, WSP B-BCBACnet Interconnectivity BBMD forwarding capabilities BACnet Transport Layer IPWeb Server Protocol HTML5Web Server Application InterfaceREST API1.2.3.For more details about supported quantities, see the ECLYPSE Selection Tool.xlsm spreadsheet file available for download on the Documentation and Resources Portal. A controller can support a maximum of 2 Allure sensor models equipped with a CO2 sensor. Any remaining connected sensors must be without a CO2 sensor. A mixed architecture with standard room devices and Bluetooth low energy enabled devices is not recommended.HardwareProcessor Sitara ARM processorCPU Speed 600MHzModbus RTU 1 × RS-485 serialcommunications portMemory 4GB Non-volatile Flash (applications & storage) 512MB RAMRS-485 Wiring 1-pair + Common/shieldModbus TCP Devices must be on the samesubnetWireless Adapter Optional, USB Port ConnectionWi-Fi Communication ProtocolIEEE 802.11b/g/n