Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Any shielding of analogue signals or communication cables should also be brought to the same earth potential, either via a Minus terminal or via the earthing bar. All Minus connections are linked internally. For problem-free operation, these connections should be reinforced externally with short wires of 1.5 mm2.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-25Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsPower supply, earthing scheme, cable layout3.7.4 Cable layoutWiring to the I/O modules can be laid in the cable channels on both sides.ExxxExxxAxxxAxxx3CPU24 VDC Batt WDRun Halt Error_PGU__ _ + + +SupplyWxxxWxxxAxxxAxxxThe cables to the terminals on the motherboard are run through the two side channels from the bottom or from the top.The terminals are accessible on the motherboard without removing the cover.