Title: LUX34 Lysmåler.pdf
24Vac/dc (22…30Vac/dc) < 0,1VA 0-10V, < 1mA0...1000 lx* or 0...10000 lx 0…100 lx* or 0 …500 lx * factory setting -50 …+50 °Cphotodiode Pt1000 EN60751 B 90 x 94 x 44 mm IP 54, cable entry down PBT, PC and PAWiring: 1 2 3 424 Vac/dc 0V 0-10Vdc output (= light level) 0-10Vdc output (= -50…+50 °C)Ordering guide: Model LUX 34Product number 1133310LUX 34-1001133311Description light level transmitter 1000 lx / 10000 lx light level transmitter 100 lx / 500 lxProducts fulfil the requirements of directive 2004/108/EY and are in accordance with the standards EN61000-6-3: 2001 (Emission) and EN61000-6-2: 2001 (Immunity).Produal OyKeltakalliontie 18 48770 Kotka FINLAND www.produal.comTel: +358-5-230 9200 Fax: +358-5-230 9210 info@produal.fi