Title: Romtermostat møterom.pdf
EGT 336, 338: Room temperature sensorHow energy efficiency is improved Exact room temperature measurement for energy-efficient control of HYAC systems and energy con- sumption monitoring.Areas of application For room temperature measurement and setpoint adjustment for heating and air-conditioning systems in dry rooms.FeaturesMeasurement of room temperature+ Room control panel with many functional, design and colour variants« Device insert with transparent front, fits into frame with 55 x 55 mm aperture » Frames must be ordered as accessoriesTechnical description « Nickel thin-film sensor in accordance with DIN IEC 43760 « Cable entry at rear, plug-in connection terminais for 0.12...0.5 mm?wire (0.4...0.8 mm o)