Title: økernvn 94.pdf
SR 12-36 15.4 4.4 51.4 12 17.2 3.9 49.4MAIN 12-36 16.2 249.5 16.2 36 18.7 249.5 13.2SR 12-36 15.9 248.0 16.3 12 18.1 249.5 13.2010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 11.3 35.3 38.5 36 12.5 66.3 27.4SR 36-78 13.1 238.0 5.9 36 14.3 43.0 33.5MAIN 12-36 14.9 240.5 5.6 36 14.8 240.5 3.0SR 36-78 13.1 238.0 5.9 78 14.6 245.5 2.5010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 7.4 205.0 10.9SR 12 5.6 4.3 21.0MAIN 78 7.4 205.0 10.9SR 36 8.8 248.0 10.1010080050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040200050100150MHzProject: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASS