Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
SR 78-45 16.2 500.0 11.3 45 16.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.6 29.5 41.0 45 15.4 26.9 39.6SR 36-45 15.4 26.9 42.1 36 17.1 27.3 39.5MAIN 12-36 32.0 500.0 -12.4 36 31.5 500.0 -15.3SR 12-36 28.6 500.0 -12.4 36 29.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.5 495.0 8.0SR 45 8.1 481.0 8.0MAIN 45 7.5 495.0 8.0SR 45 8.1 481.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: MCKINSEY 4 ETGMcKinsey 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00442.8 m60Insertion Loss (dB)504030201000250 MHz500