Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Isc: 321A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 122A Isc(0.76%): 244A Isc(1.15%): 369ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF033 16C2/003 05.11.2020 12:36Zs(rcd)Z: 0.66ΩIsc: 349A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATallberg Elektro A/S Tlf.22796640Side:14GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTNr. 9696979798989999100100101101102102TEST RAPPORTResultatDM1-3. Plan 8 / DM3.E3=433.08.03 / XF033 16C2/003 05.11.2020 12:36RCD II: 28.5mAUci: 0.3V t: 82.4ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF033 16C2/003 06.11.2020 13:18R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF033 16C2/003 05.11.2020 11:18KONTINUITET R: 0.4ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF033 16C2/003 05.11.2020 11:32R LOW OhmR: 0.24Ω