Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
1 0 … 65,535 (16 bit) (can be extended with CPU counters) max. 20 kHz (at pulse/pause ratio 50 %) All data in this module are volatile (non-volatile Saia PCD® registers are available).Digital inputs “IN-A” and “IN-B” signal voltages: nominal voltage:24 VDC -30 … +5 V +15 … 30 V for source operation“low” range: “high” range: typically 7.5 mA 25 kHzInput current: Input filer: Process output Counter controlled output CCO: Current range:counter output (switches when count is 0 or 65,535) 5 … 500 mA(max. current leakage 1 mA) (min. load resistance 48 Ω in voltage range 5 … 24 V).Voltage range: Circuit type:Voltage drop: Output delay:5 … 32 V smoothed, residual ripple max. 10 % Electrically coupled, not short circuit protected, positive switching typically 2V at 500 mA < 10 µs,(longer for inductive load due to protective diode).