Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
The following connection diagram shows a typical wiring layout for: ● voltage outputs with the PCD3.W605 and .W625 modules or ●current outputs for the PCD3.W615 moduleConnection for 0…10 V (W605) or -10 V…+10 V (W625):DA4 (A2)5UR ≥ 3 kΩConnection for 0…20 mA (W615)DAVOLTAGE CONTROLLED CURRENT SOURCE4 (A2)+ 24 VDC5IR = 0...500 ΩAn external 24 VDC supply is required for current outputs.6-90PCD3.W6x5Block diagramA0 COM A1 COM A2 COM A3 COM A4 COM A5 COMp m A P Oe g a t st u p t u OC A DVCCGalvanic separated s erial interfaceDC / DC ConverterμControllerI/O - Bus+Uin -UinFilterRef erence - Voltage 2.5VCOMn o i t a r a p e s+5 V GNDc n a v a GilPCD - BusProgrammingFor programming the modules PCD3.W6x5, an FBox is available.xx7 and RIOs: the firmware reads in the values according to the configuration (I/O Builder or network configurator).