Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]22.7 99 2 3.52Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.7 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.3 483.0 28.6 36 7.0 472.0 26.3SR 36-45 6.3 453.0 30.1 36 7.3 453.0 27.3MAIN 36-45 8.0 498.0 27.9 36 7.8 498.0 25.1SR 36-45 6.5 499.0 27.9 36 7.5 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.1 4.3 52.7 45 16.3 4.3 49.7SR 45-78 16.2 4.3 52.7 45 16.3 4.3 49.7MAIN 78-45 17.0 499.0 11.3 78 18.6 490.0 8.4SR 78-45 16.6 496.0 11.3 45 18.0 496.0 8.30100806040200250 MHzACR-F (dB)