Title: 2 etg del2.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.1 42.8 36.0 36 9.2 218.5 5.2SR 12-36 13.4 18.8 45.8 36 13.5 22.8 41.3MAIN 36-45 9.9 250.0 4.7 36 9.5 250.0 2.0SR 12-36 14.7 241.0 5.6 36 15.0 241.0 2.9010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.2 13.8 20.3SR 45 2.1 12.4 20.5MAIN 45 6.2 156.5 12.1SR 36 4.5 206.5 10.9010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1