Title: 32 Pumper oversik.pdf.pdf
Utskrift fra Grundfos Product Center [2022.07.007]VerdiTPE3 40-240 S-A-F-A-BQQE-HAC99272254 57138263609935500 omdr/min6.222 l/s 182.1 kPa 240 dm 74 mm BQQE ISO9906:2012 3B2 AStøpejern EN-GJL-250 ASTM class 35 Composite PES+30% GF A20 .. 50 °C 10 bar 10 bar / 120 °C DIN DN 40 PN 6/10 250 mm 56C F Vann -25 .. 120 °C 20 °C 998.2 kg/m³20 .. 50 °C 10 bar 10 bar / 120 °C DIN DN 40 PN 6/10 250 mm 56C F Vann -25 .. 120 °C 20 °C 998.2 kg/m³90SB IE5 1.5 kW 50 Hz 1 x 200-240 V 9.20-7.60 A 0.99 480-5900 omdr/min 87.5% 87.5 % IP55 F ELEC 99138026HMI300 - grafisk FM300 - Avanceret Built-in0.70 24.4 kg 31.6 kg 0.1 m³ 98481395 381601240 5745878 4616191 9043461Firmanavn: Laget av: Telefon:Kristian Torgrim OpstadDato:07.02.2022H [kPa]TPE3 40-240, 1*230 V260Pumpemedie = Vann Væsketemperatur under drift = 20 °C Massetetthet = 998.2 kg/m³240100 %22020090 %18016080 %14012070 %10060 %806050 %4040 %2025 % 19 %00123456789Q [l/s]