Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
This is used to introduce fresh air into the environment directly through the diffuser. The kit includes a flow separator to be fitted inside the cassette, and a circular fitting for connection to the flexible system ducting. The flow of air is sent directly to just one of the outlet louvers, without passing through the coil. The air flow of fresh air introduced into the environment depend on the inlet static pressure.ModelSK 0-1-2-3SK 4-5-6IdenTIfIcaTIonPRT 600PRT 800code90792309079231Correlation between flow-rate / static pressureSK 0-1-2-3SK 4-5-6m3/hPam3/hPa80 120 160 200 2403 8 15 25 36160 200 300 400 5003 8 15 25 36The diameter of the fitting is 150 mm for SK 0 - 1 - 2 - 3 and 180 mm for SK 4 - 5 - 6.Units with remote electric board