Title: V20-06-01 VVS-anlegg plan 6 - DM1.pdf
Møterom 6-1063 4 7 2 = K U 5 2 1 ø5 2 1 Ø T 1 0 0 K Sh / ³m 0 8 : QLD021T Maks:220 m³/h Kjøling: 200 W 0.016 L/sLD021T Maks:220 m³/h Kjøling: 200 W 0.016 L/sKontor 6-129WISE RTAKontor 6-128WISE RTAø160 UK=2685SF002T-160SF002T-160WISE RTA WISE IAQMøterom 6-1215 8 6 2 = K U 0 6 1 ø0 5 2 Ø T 1 0 0 Q Sh / ³m 0 6 6 Q:5 8 6 2 = K U 0 6 1 ø8 6 6 2c + m m 8 2 : 1 0 1 . 0 7 33 0 7 2c + m m 8 2 : 1 0 1 . 0 7 3ø200 UK=2665SF002T-200ø200 UK=2643370.101: 35 mm +c 2790 370.101: 35 mm +c 2810WISE IAQSF002T-160SF002T-200ø160 UK=2685320.102: 18 mm +c 2790 320.102: 18 mm +c 2790370.101: 28 mm +c 2790370.101: 28 mm +c 279035mm35mm22 mm+06 = 370.101 - OE 066 0.270 L/s+06 = 320.102 - OE 065 0.086 L/sOpp/ned 320.102: 54mm 320.102: 54mmLD018T Maks:150 m³/h Kjøling: 300 W 0.025 L/s Varme: 300 W 0.010 L/sLD018T Maks:150 m³/h Kjøling: 300 W 0.025 L/s Varme: 300 W 0.010 L/sLD018T Maks:220 m³/h Kjøling: 470 W 0.037 L/s Varme: 700 W 0.018 L/s9