Title: etg u1.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]181 287 20 7.8181 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.4 * 246.0 35.5 36 0.8 * 250.0 32.7SR 36-450.7 *242.0 35.6 36 1.2 236.5 33.1MAIN 36-45 0.4 248.0 35.4 36 0.8 250.0 32.7SR 36-45 0.7 242.0 35.6 36 1.2 238.5 33.010080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 19.3 250.0 16.2 12 20.9 5.4 46.6SR 45-12 19.1 250.0 16.2 45 19.7 250.0 13.2MAIN 45-12 19.3 250.0 16.2 12 21.1 249.5 13.2