Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
1KOhm - 1W brown, black, red1N4007 diodes1N4007 diodesThe polarities refer to the active status of the output, the polarities invert for stand-by status.40InstallationInstallation manualConnection of devices with an alarm output to channels configured as inputThe wiring diagram illustrates a connection made to one of the channels of the IFM4IO module [A], configured as input. The connected device [B] is equipped with a normally open output for alarm signalling [C].A1IN23K9Ohm orange, white, red470Ohm yellow, purple, brownBCConnection of devices with alarm and fault outputs to channels configured as inputThe wiring diagram illustrates a connection made to one of the channels of the IFM4IO module [A], configured as input. The connected device [B] is equipped with a normally closed fault signalling output [C] and a normally open alarm signalling output [D].A1IN2470Ohm yellow, purple, brown3K9Ohm orange, white, redBCD