Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Grenseverdi: 1.0QTEST RAPPORTResultatR ISO GODKJENTR: >200MQ Um: 262VUiso: 250VGrenseverdi: IMQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 044 GODKJENT * 12.03.2020 15:16KONTINUITET GODKJENTR: 0.2QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 044 GODKJENT * 12.03.2020 15:16R LOW Ohm GODKJENTR: 0.17QRt: 0.2QR: 0.2QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 044 GODKJENT* 12.03.2020 15:17SPENDINGUln: 233VUlpe: 233VUnpe: 0OV£: 49.9HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 044 GODKJENT * 1725 0)s) 2(0))(0) B AZLINE GODKJENTZ: 0.50QIsc: 464ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1~3 / E.433.11.01 TN-S / Sikring 044 GODKJENT * (2N0SIN2020 S RNSTz 0i]Zs (rcd) GODKJENTZ: 0.43QIsc: 538ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 044 GODKJENT * 12./03,2020 15:25RCD I A GODKJENTI: 28.5mA