Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.3 446.0 30.3 36 9.3 451.0 27.4SR 36-45 8.4 465.0 29.5 36 9.3 466.0 26.6MAIN 36-45 9.9 500.0 27.8 36 9.7 496.0 25.2SR 36-45 9.4 500.0 27.8 36 10.0 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.1 468.0 11.8 45 14.4 3.0 52.7SR 36-45 15.2 416.0 12.9 45 14.4 2.6 53.9MAIN 36-45 15.1 468.0 11.8 45 17.3 468.0 8.8SR 45-36 15.4 473.0 11.7 36 17.5 473.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 26.4 83.0 27.2 12 26.4 73.3 26.5SR 12-36 27.0 88.0 26.3 12 27.5 83.3 24.6MAIN 36-45 38.4 500.0 -12.4 36 38.9 500.0 -15.3