Title: 2 etg del2.pdf
Cable ID: D2013 Date / Time: 10/10/2013 10:58:28 AM Headroom 6.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]139 212 7 6.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 238.0 35.7 36 8.0 238.0 33.1SR 12-36 6.2 216.0 36.4 12 8.0 216.0 33.8MAIN 12-36 7.4 238.0 35.7 36 8.0 238.0 33.1SR 12-36 6.2 216.0 36.4 12 8.0 216.0 33.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.5 4.1 51.9 12 17.1 3.0 51.6