Title: 32 Pumper modbuss teknisk data.pdf.pdf
0x000x0ASlaveMinimumReplyDelay = 0x000A00002 HI00002 LO0x000x00RegisterOffset = 0x000000003 HI00003 LO0x000x00Reserved value = 0x000000004 HI00004 LO0x000x04SoftwareDefinedBitRate = 0x0004If there is no response from the slave, see Fault finding, section 14.1.2 CIM/CIU 200 Modbus communication faults or 14.2.2 CIM/ CIU 260 3G/4G cellular communication faults.13.10 Setting the setpointThis section shows how to set a new setpoint (reference).In the example, slave address 0x01 is used, and a value of 55 % (5500: 0x157C) is set as new setpoint.Request from master to slaveFieldValueDescriptionSlave address0x01Function code0x06Write single registerStart address HIStart address LO0x000x67Setpoint address = 00104 (0x0068)Value HIValue LO0x150x7CNew setpoint value = 5500 (0x157C)Example of response from slave to masterFieldValueDescriptionSlave address0x01Function code0x06Write single registerStart address HI