Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Uc: 0.1V Rl: 3Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF050 C16/2 15.06.2020 08:53RCD II: 28.5mAUci: 0.1V t: 83.1ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF050 C16/2 16.06.2020 09:49R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF051 C16/2 16.06.2020 09:49R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF051 C16/2 16.06.2020 09:55R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF052 C16/2 15.06.2020 14:00Tallberg Elektro A/S Tlf.22796640Side:18GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*Nr.128128129129130130131131132132133133TEST RAPPORTResultatSPĆNDINGUln: 231V Ulpe: 231V Unpe: 1V f: 49.9HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF052 C16/2 15.06.2020 14:00Z-LINEZ: 0.28Ω