Title: Operating instructions - K3G560PC0401.pdf
Any further mounting data required can be taken from the product drawing or Section Chapter 4.1 Mechanical connection.NOTE Damage to the device from vibration Bearing damage, shorter service life→ The fan must not be subjected to force or excessive vibrationStrength class of screws8.8; Secure the screws against unintentional loosening (e.g. use self-locking screws).from sections of the installation.→ If the fan is connected to air ducts, the connection shouldbe isolated from vibration, e.g. using compensators or similar elements.→ Ensure stress-free attachment of the fan to the3.6 Transport and storage conditionssubstructure.; The fan may not be handled in the area around the inlet nozzle duringMax. permitted ambient temp. for motor (transport/ storage) Min. permitted ambient temp. for motor (transport/ storage)+80 °C40 °Ctransport and installation. There is a risk of damage to the impeller.; Check the device for transport damage. Damaged devices are not tobe installed.