Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
00250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.03.04-UF014 Date / Time: 14-08-2020 07:49:51 Headroom 8.0 dB (NEXT 12-36) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]18.2 79 1 2.82Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 454.0 30.0 36 7.5 465.0 26.7SR 36-45 9.0 472.0 29.2 36 8.6 478.0 26.0MAIN 12-36 8.9 500.0 27.8 36 7.9 496.0 25.2SR 36-45 9.4 497.0 28.0 36 9.0 496.0 25.210080604020NEXT (dB)