Title: økernvn 94.pdf
MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: T3414 Date / Time: 09/13/2013 08:38:15 Headroom 11.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]245 373 12 11.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]6.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 20.0 19.0 44.0 36 21.0 99.3 29.4SR 12-36 11.8 67.5 35.1 36 14.1 90.5 30.0MAIN 36-78 21.3 99.5 32.3 36 21.0 99.3 29.4SR 12-36 12.0 96.8 32.5 36 14.2 96.8 29.510080604020NEXT (dB)