Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]31.6 137 2 4.83Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.7 500.0 29.2 36 9.4 500.0 26.4SR 12-36 9.1 459.0 30.0 36 10.2 489.0 26.6MAIN 12-36 9.7 500.0 29.2 36 9.4 500.0 26.4SR 12-36 9.2 489.0 29.5 36 10.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.2 5.9 49.9 45 19.6 500.0 8.3SR 45-78 18.2 5.9 49.9 45 19.5 495.0 8.3MAIN 78-45 19.0 500.0 11.3 45 19.6 500.0 8.3