Title: VV-PL-03-002.pdf.pdf
EDCBAø160Avtrekk heis55DSO-125 100 m³/hUK= 14.26ø16055NETTING-160 100 m³/h360.001-SK4316 LEO-0-160360.001-SZ402 FKRS-EU/160/ZXXø200UK= 14.02319 TRAPPNETTING-630 3600 m³/h360.002-SZ501 FKR-EU/DE/630/ZXXTellus-LOV VAV-H-200 300 m³/h6666UK= 13.902000x10002100x24002200x3200ø630Inntak og avkast kondensisoleres med ArmaflexLKK-1209D H=1000LKK-1209D H=1000360.002-SQ5319 LEO-0-500LKR-500-1200ø500UK= 13.97320 TEKTellus-Lov-H-200 300 m³/h2100x24002200x32002000x10002000x1000360.002-SQ4329 LEO-0-2007777ø20088FKV-250 Cooling 230 m³/hø250UK= 14.22ø250UK= 14.22ø200LKR-200-300ø200UK= 14.31DSO-125 100 m³/hø200DSO-125 100 m³/hø200LKR-200-900332-1 KORRIDOR-1360.002-SK5331 LEO-0-200ø200UK= 14.31360.002-SZ503 FKRS-EU/200/ZXX360.002-SZ502 FKR-EU/DE/500/ZXX360.002-IV001ø16088UK= 14.31800x700ø400910910FKV-250 Cooling 230 m³/hFKV-250 Cooling 230 m³/h