Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]113 179 13 4.8113 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]20.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 3.4 245.5 35.5 36 4.2 239.5 33.0SR 36-450.0 *248.5 35.4 36 0.8 *245.0 32.9MAIN 36-45 3.4 245.5 35.5 36 4.3 245.5 32.8SR 36-45 0.0 248.5 35.4 36 0.8 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 18.6 5.4 49.6 12 19.2 4.1 48.9SR 45-12 18.7 5.3 49.8 12 19.3 4.8 47.7MAIN 36-12 19.8 247.0 16.3 12 20.1 247.0 13.3SR 45-12 19.9 247.0 16.3 12 20.5 248.0 13.3010080604020050100150MHzACR-F (dB)2002500100806040