Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 18Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N | S ’ < Site 1/ Building 1/ Storey 10 / Kontor 3 / ViewsKontor 3Kontor 3DIALux Page 19Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Kontor 3 / Results summary, EN 12464/ENTSKKontor 3 i T L T - EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max1 Visual task area 12 Surrounding area 13 Background area 1Perpendicular illuminance (adaptive) [Ix] 566 (= 500)Surrounding area: 0.500 mPerpendicular illuminance (adaptive) [Ix] 513 (= 300)Perpendicular illuminance (adaptive) [Ix] 289 (= 100)Wall zone: 0.100 m434 635 0.77386 608 0.75193 343 0.670.680.630.56The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 20