Title: +175=737.001_IK001_Brukermanual for Refra varmepumpe.Produktinformasjon.pdf
CB-HR22046I0C, 3208/RF, REF10082_E3 PE,N, ~3 / 400 V, 50Hz 150,0 - IP54 3p.+N, 200A IPC115D-10100 Dixell controller * VGIPC-0P000 Dixell EVD0000E21 Carel + EVD0000UC0 bat. EVDIS00RU0 Carel Provided 230 Vac 1 A max 230 Vac 1 A max - VACON01000-3L-0087-4- HVAC Out Max. 2A Provided ProvidedA mod. mod. mod. mod. - A A - mod. - -CONNECTIONSRecommended protection device Recommended cable electrical leads Evaporator contour IN / OUT Condenser contour IN / OUT UNIT EXTENT OF DELIVERY Protective charge Refrigerant quantitytype data mm mmfilling kgC160 5 x 70,0 mm2 copper, no longer than 30 m 100 / 100 – Flanged connection 58 / 58Not charged 13,7 kg R134a (total filling 27,4 kg)Chiller total oil quantitydm310,7 dm3, POE - BSE32 (2 contours x 5,35 dm3)OTHER INFORMATIONIMPORTANT WARNINGMachine contains fluorinated greenhouse gases covered by the Kyoto Protocol: (cid:1) R134a (CF3CH2F) (cid:2) R404А (CF3CHF2+CF3CH3+CF3CH2F) (cid:2) R407C (CH2F2+CF3CHF2+CF3CHF2F) (cid:2) R410A (CH2F2-CF3CHF2)