Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
The purpose of the SCOP is to characterise the seasonal efficiency of the heat pump by taking into account the full-load and part-load performances established for several outdoor temperature values. The SCOP is the ratio between the building's annual heating demand and the annual electricity consumption of the heating system. It is measured in accordance with the EN14825 standard based on an average reference climate that takes into account several reference temperatures between -10 °C and +16 °Cηs = 125%, which is a minimum SCOP of 3.33 valid from September 2017.The DYNACIAT complies with the European Ecodesign 2017 directive, offering SCOP values greater than 3.33 across the entire range.89The entire DYNACIAT LG range can be equipped with a hydraulic module on both the evaporator and condenser side, with all the components required to ensure the smooth running of the installation: - Expansion vessel (option): • 8 litres, 12 litres, 25 litres or 35 litres, depending on themodel