Title: V20-05-01 VVS-anlegg plan 5 - DM1.pdf
SF002T-160Resepsjon 5-110SK001T Ø160 Q:280 m³/hLD022T Maks:80 m³/h Kjøling: 80 W 0.006 L/s Varme: 200 W 0.005 L/sWISE RTAø200 UK=2602WISE IAQ WISE RTABack office 5-206SF002T-125Library 5-108ST020T-125 50 m³/hWardrobe 5-205SF002T-2005 2 1 - T 2 0 0 F S0 2 7 2c + m m 8 2 : 1 0 1 . 0 7 3Storage 5-2040 2 7 2c + m m 8 2 : 1 0 1 . 0 7 3ST020T-125 50 m³/hWISE RTA WISE IAQLD007T Maks:230 m³/h Kjøling: 280 W 0.022 L/s370.101: 42 mm +c 2790 370.101: 42 mm +c 2790LD007T Maks:230 m³/h Kjøling: 280 W 0.022 L/sSpiserom 5-106370.101: 42 mm +c 2790 370.101: 42 mm +c 2790LD007T Maks:230 m³/h Kjøling: 280 W 0.022 L/s320.102: 28 mm +c 2790 320.102: 28 mm +c 2790WISE IAQWISE RTALD007T Maks:230 m³/h Kjøling: 625 W 0.050 L/sVrimleareal 5-104ø250 UK=2620ø250 UK=2620ø250 UK=2620h / 3m 0 7 8 20 5 3 x 0 0 0 1 T 5 1 0 F S1000x350 UK=2500SF002T-125WISE RTAWISE IAQMøterom 5-103WISE RTA800x250 UK=2600CR 2 5-201SF002T-125SF002T-125ø250 UK=2620