Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
kW 4,56 3,66 2,80 5,68 4,91 4,19 9,25 6,96 4,83 10,63 8,25 6,10 13,14 10,16 8,61 19,76 13,43 10,25 23,68 17,26 10,25Water flow l/h 488 391 298 599 513 441 972 730 505 1118 866 639 1383 1067 903 2071 1403 1068 2486 1807 1068kW 5,67 4,55 3,47 6,97 5,96 5,12 11,30 8,48 5,87 13,00 10,07 7,43 16,08 12,41 10,50 24,08 16,32 12,42 28,91 21,01 12,42Emission correction factors for different working conditions. Multiply the factors by the emission figures in the 7-12°C table above.Water (°C) 7/12 °C 10/15 °C 14/18 °CTotal emissionAir (°C) K K K25-18 26-18.5 28-20 Water (°C) 0,82 0,56 0,350,89 0,63 0,411,11 0,82 0,527/12 °C 10/15 °C 14/18 °CSensible emission Air (°C) K K K25-18 26-18.5 28-20 1,06 0,94 0,9 0,78 0,72 0,580,9 0,72 0,5Note:the correction factors are indicative, as they are average values.6Emission of 4 pipe units with standard cooling batterySkyStarCooling emission of 2 battery units (4 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.