Title: 2 etg del2.pdf
MAIN 12-36 9.7 20.4 44.9 12 10.1 11.5 48.5SR 12-36 10.7 13.1 49.6 12 10.6 11.5 48.5MAIN 12-36 13.4 247.0 5.0 36 12.4 246.0 2.4SR 36-45 12.4 249.5 4.7 36 13.3 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.7 20.6 19.4SR 45 3.2 20.6 19.4MAIN 36 7.0 222.0 10.5SR 36 7.4 209.5 10.8010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94