Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]29.2 127 2 4.41Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.2 410.0 31.1 45 9.8 499.0 26.4SR 36-45 8.2 494.0 29.4 45 8.8 493.0 26.5MAIN 36-78 10.8 497.0 28.0 36 10.5 498.0 25.1SR 36-45 8.2 494.0 29.4 36 9.7 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.1 4.0 53.2 45 13.9 2.3 55.2SR 78-45 15.0 500.0 11.3 45 13.9 2.3 55.2MAIN 45-78 15.5 500.0 11.3 45 16.7 500.0 8.3SR 78-45 15.0 500.0 11.3 45 15.6 500.0 8.30100806040200250 MHzACR-F (dB)