Title: Manual - Varmemåler M3 - Løs fra rør.pdf
Tighten all the terminals carefully, making sure that the connections are completely secure.Warning: Be careful when entering cables into the terminal in order to avoid potential malfunctioning caused by the contact between the sheath and clamp.Hydrosplit M3 Manuale utente – User manual - v1.6.5_ITA_ENG34TERMINAL BOARD DESCRIPTIONNumbersIndicationDescription1/5/6/2Forward flowInlet temperature sensor3/7/8/4Return flowreturn temperature sensor10/11/50Flow INFlow meter input51/52/53C1 INVolume meter input 154/55/56C2 INVolume meter input 157/58Cold OUTCooling pulse output16/17Hot OUTHeating pulse output24/25MBUSM-Bus network connection59/60Aux PowerPower supply connectionTEMPERATURE SENSORS CONNECTIONConnect the inlet temperature sensor in the terminals 5 and 6;Connect the return temperature sensor in the terminals 7 and 8;Warning: To avoid errors in the energy calculation, respect the correspondence between the inlet and