Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 43,0 68,0 223,0 12,0 7,6Limit 100,0 - 555,0 50,0 25,0Margin 57,0 - 332,0 38,0 17,4Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,8 3,0 2,2 2,80Worst Value: Local: 36 18,4 43,8 25,4 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 19,4 15,1 4,3 78,00Remote: 78 13,8 8,9 4,9 321,00Worst Value: Local: 78 13,8 9,0 4,8 318,00Remote: 78 13,8 8,9 4,9 321,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,9 26,7 3,2 499,00Remote: 36-45 30,6 26,7 3,9 499,00Worst Value: Local: 36-45 29,9 26,7 3,2 499,00Remote: 36-45 30,6 26,7 3,9 499,00dB 0601200Local250500 MHzdB 0