Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 27.11.2020 11:56R LOW OhmR: 0.13ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 27.11.2020 11:56Tallberg Elektro A/S Tlf.22796640Side:22GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.153153154154155155156156157157158158159159TEST RAPPORTResultat KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 30.11.2020 09:18SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.1HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 30.11.2020 09:18Z-LINEZ: 0.46ΩIsc: 505A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF039 16C2/003 30.11.2020 09:19Zs(rcd)Z: 0.43ΩIsc: 532A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A