Title: +135.01=370.004-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Order numberS55561-F112S55561-F113S55561-F180S55561-F114S55561-F181S55561-F115S55561-F116S55561-F117TypeUH50-A05-00UH50-A21-00UH50-A23-00UH50-A36-00UH50-A38-00UH50-A45-00UH50-A50-00UH50-A61-0025 CE2N5324en 2018-08-1826 Building Technologies15 m3/h nominal flow rate, mounting length 270 mm, flanged DN 50, PN 25, control cable length 3 m, Pt500, Ø 6 mm, sensor length 100 mm, cable length 5 m, return sensor not integrated in the flow measuring section, energy unit display in MWh25 m3/h nominal flow rate, mounting length 300 mm, flanged DN 65, PN 25, control cable length 3 m, Pt500, Ø 6 mm, sensor length 100 mm, cable length 5 m, return sensor not integrated in the flow measuring section, energy unit display in MWh40 m3/h nominal flow rate, mounting length 300 mm, flanged DN 80, PN 25, control cable length 3 m, Pt500, Ø 6 mm, sensor length 150 mm, cable length 5 m, return sensor not integrated in the flow measuring section, energy unit display in MWh