Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 11:36Zs(rcd)Z: 0.58ΩIsc: 396A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 12:38Tallberg Elektro A/S Tlf.22796640Side:17GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.116116117117118118119119120120121121122122TEST RAPPORTResultat R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 12:38KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 10.06.2020 12:44RCD UbUc: 0.5VRl: 17Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF033 C16/2 10.06.2020 11:04R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF033 C16/2 10.06.2020 11:11SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 49.9Hz