Title: Operating instructions - K3G560PC0401.pdf
box.; First connect the "PE" (protective earth).; Connect the wires to the corresponding terminals.Use a screwdriver to do so. When connecting, ensure that no wire ends fan out.4.2.5 Leakage currentFor asymmetrical power systems or if a phase fails, the leakage current can increase to a multiple of the nominal value.4.2.6 Locked-rotor protectionDue to the locked-rotor protection, the starting current (LRA) is equal to or less than the nominal current (FLA).4.3 Connection in terminal box4.3.1 Preparing cables for connectionOnly strip the cable as far as necessary, ensuring that the cable gland is sealed and there is no strain on the connections. For tightening torques, see Chapter 3.1 Product drawing.NOTE Tightness and strain relief are dependent on the cable used.→ This must be checked by the user.Fig. 3: Connecting wires to terminals; Seal the terminal box.Fig. 2: Recommended stripped lengths in mm (inside terminal box) Legend: CL = control lines