Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
The module contains 6 relays with normally-open contacts for direct or alternating current up to 2 A, 250 VAC. The module is especially suited wherever AC switching circuits with infrequent switching have to be controlled. For space reasons, there is no integrated contact protection. Each group of 3 relays has a common connection.Technical dataNumber of outputs:3+3 make contacts with common terminalType of relay (typical):RE 03 0024, SCHRACKSwitching capacity: (contact lifetime)2A, 250 VAC AC1 0.7 x 106 operations 1 A, 250 VAC AC11 2 A, 50 VDC DC11 1 A, 24 VDC DC111.0 x 106 operations 0.3 x 106 operations 3) 0.1 x 106 operations 1)3)Relay coil supply: 2)nominal 24 VDC smoothed or pulsed, 8 mA per relay coilVoltage tolerance, dependent on ambi- ent temperature:20°C: 17.0…35 VDC 30°C: 19.5…35 VDC 40°C: 20.5…32 VDC 50°C: 21.5…30 VDCOutput delay:typically 5 ms at 24 VDCResistance to interference: acc. to IEC 801-4