Title: +038=67.005-##003._04-Ø6 Trykktransmitter.pdf
Contact your local Johnson Controls®/PENN® representative for more information on options available for high-volume orders with specific application requirements, including 316L stainless steel construction and pressure ranges up to 1,764 psi (120 bar).1/8 in. 27 NPT External Thread (Style 49)Note: Transducer shown with Packard connectors.Figure 2: Dimensions for P499 transducers and wire harness with Packard connectors, in. (mm)P499 Series Electronic Pressure Transducers Product/Technical Bulletin2IMPORTANT: Locate pressure tap points on the top side of the refrigerant lines to reduce risk of equipment damage or malfunction caused by accumulation of oil, liquids, or sediment in the pressure chamber.IMPORTANT: Avoid severe pressure pulsations on high-side pressure connections by positioning the transducer away from compressor discharge.Table 2: Wire harnesses with Packard connectorsProduct code number1 WHA-PKD3-200CLength6 1/2 ft (2.0 m)To mount the P499 transducer: