Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
[Pair 45] [Pair 45] [Pair 45]31.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.6 462.0 29.6 36 8.2 455.0 27.2SR 36-45 8.0 480.0 28.8 36 8.4 456.0 27.1MAIN 36-45 9.5 497.0 28.0 36 8.7 500.0 25.0SR 36-45 8.2 491.0 28.3 36 8.6 490.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.6 3.5 54.4 45 14.0 3.0 52.7SR 36-45 14.6 3.5 54.4 45 13.9 2.6 53.9MAIN 36-45 17.5 470.0 11.8 45 18.7 499.0 8.3SR 36-45 17.7 479.0 11.6 45 18.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 26.6 96.8 24.8 36 25.2 96.3 22.3SR 36-78 25.7 107.0 23.1 36 26.3 107.0 20.6MAIN 36-45 39.7 497.0 -12.2 36 39.0 500.0 -15.3SR 36-45 38.7 496.0 -12.1 36 39.3 495.0 -14.90804000250 MHz