Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
COIL Made of copper tubes with bonded aluminium fins for maximum transfer contact. The coil has 1, 2 or 3 rows for 2 pipe models and 2+1 rows for 4 pipe models (the heating row is on the inside part of the coil). For 4 pipe systems two versions are available: SK 04, SK 14, SK 24, SK 34, SK 44, SK 54, SK 64 supply an higher heating emission; SK 26, SK 36, SK 56, SK 66 supply an higher cooling emission. The heat exchanger is not suitable for use in corrosive atmosphere or in environments where aluminium may be subject to corrosion.CONDENSATE COLLECTION TRAY High density ABS polystyrene foam condensate tray, shaped in order to optimize the air diffusion, fire retardant rating B1 to DIN 4102.AIR FILTER Synthetic washable filter, easily removable.CONDENSATE PUMP Float switch centrifugal pump with 650 mm of maximum head, integral to the unit and wired to the control panel on the outside of the casing.VALVE SET Two or three way valves for ON/OFF operation, with pipe mounting kit and thermostatic actuator.