Title: 1 etg del 2.pdf
SR 12-36 6.1 23.0 43.6 36 7.3 231.5 3.9MAIN 36-45 7.3 246.0 5.1 36 7.7 246.5 2.4SR 12-36 7.5 242.5 5.4 36 7.3 247.5 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.2 11.3 20.7SR 45 4.6 18.5 19.7MAIN 45 8.9 204.0 10.9SR 36 7.0 237.5 10.260500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94