Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
Fan abnormalCheck if the fan is running normally.Charger failureThe charge failsConsult dealer.Battery Over VoltageBattery voltage is higher than normal value Check if the battery quantity is right.Over ChargeBattery is over chargedThe UPS will turn off the charger until the battery voltage is normalModel Pin ErrorInternal UPS faultConsult dealer.Ambient Over TemperatureThe ambient temperature is too highCheck the environment ventilation.Heatsink Over TemperatureInside temperature of UPS is too highCheck the ventilation of UPS and the ambient temperature.Ambient NTC abnormalUPS internal faultConsult dealer.Para Bat DifferThe battery packs of some UPSs are dis- connectedCheck if all the battery pack is connected.Para Line DifferThe mains input of some UPSs is disconnected Check the building wiring and input cable.Check if the input breaker is closed.Ensure the UPSs are connected to same input source.IP Fuse OpenInput fuse break