Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 36-45 23.7 42.0 36.7 45 24.8 42.3 34.1SR 36-45 22.0 41.8 36.7 36 22.8 41.8 34.3MAIN 36-45 34.6 500.0 -12.4 36 34.6 500.0 -15.3SR 36-45 36.4 500.0 -12.4 36 36.3 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.9 495.0 8.0SR 12 6.3 447.0 8.0MAIN 12 6.9 495.0 8.0SR 12 6.3 447.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Uni ConsultUniconsult tester.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00433.0 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500