Title: Hardware Installation Guide.pdf
With elevator control on the LNL-1300 reader, door strike and contact are not available, and REX (Request to EXit) is disabled.Addresses assigned to input/output panels do not need to be consecutive. On the first panel, the inputs/ outputs represent the first sixteen floors (e.g.: Input 1 = first floor, Input 2 = second floor, etc.). The second panel represents the next sixteen floors (floor 17 through 32), etc.revision 6 — 333LNL-1300 Single Reader Interface ModuleOverview of Elevator ControlAccess Control SystemIntelligent System ControllerMaximum: 4000 feet (1219.2 meters) 5 conductorsOutput Control ModuleInput Control ModuleSingle Reader InterfaceSingle Reader Interface ModuleSingle Reader InterfaceUp to 128 Outputs - eight Output Control ModulesUp to 128 Inputs - eight Input Control ModulesElevator Control RoomElevator Reader (inside cab)334 — revision 6Hardware Installation Guide63Configuration