Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Isc: 1.28kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF050 C16/2 15.06.2020 13:46Zs(rcd)Z: 0.09ΩIsc: 2.50kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF050 C16/2 16.06.2020 09:53R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF051 C16/2 15.06.2020 13:16R LOW OhmR: 0.31ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF051 C16/2 15.06.2020 13:17KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF051 C16/2 15.06.2020 13:14Tallberg Elektro A/S Tlf.22796640Side:15GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr.108108109109110110111111112112113113114114115115TEST RAPPORTResultat R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0Ω