Title: VPL16.pdf
M 16Thread G 1/2 "M 16Connection:Technical data:1 23 424 Vac/dc supply 0 V0...10 Vdc output 4...20 mA outputATTENTION ! Device may be damaged by overpressure if installation is made against fluid and closed valve.Supply Ranges (to choose at commissioning)OutputsAccuracy Temperature drift Long term stability < +/- 0,2 bar / year Operating conditions - humidity24 Vac / dc, 1VA 0...2,5 bar 0...6,0 bar 0...10 bar 0…16 bar 0...10 Vdc, < 2 mA 4...20 mA, < 800 Ω < +/- 0,1 bar < +/- 0,06 bar / 10Knon-condensingOrder instruction:VPL 16 VPL 16-Npressure transmitter pressure transmitter with displaytemperature 0…+60 °C 0…+85 °C 50 bar IP 54Permissible medium temperature Max overpressure Protection class - sensor or cable entry down Tool Material27 mm AISI 303 stainless heat resisting plasticwetting parts housingProducts meet the requirements of directive 89/336/EEC and standards EN50081-1: 1992 (Emission) and EN50082-2: 1995 (Immunity).