Title: 564 KNX Værstasjon GPS  5 fasader 70155.pdf
WARNING! Risk of injury caused by components moved automatically! The automatic control can start system components and place people in danger (e.g. moving windows/awnings if a rain/wind alarm has been triggered while cleaning). • Always isolate the device from the mains for servicing andPole installation The device is installed on the pole with the enclosed clamp.PoleFig. 8 Bottom viewcleaning.The device must regularly be checked for dirt twice a year and cleaned if necessary. In case of severe dirt, the sensor may not work properly anymore.Insert the clamp in the mount through the recess. Tighten the clamp on the pole.Fig. 15Sensor offset downwards.ATTENTION The device can be damaged if water penetrates the housing. • Do not clean with high pressure cleaners or steam jets.Make sure that the arrows are pointing upward.2.3.2. Assembly with Mounting Arm FixWith the Mounting Arm Fix, the weather station can be flexibly mounted on the wall.