Title: 1 etg del 2.pdf
Cable ID: T1009 Date / Time: 10/21/2013 12:44:17 PM Headroom 5.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]137 209 7 6.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.6 246.5 35.4 36 7.7 246.5 32.8SR 12-36 5.4 62.5 45.1 36 5.5 62.5 42.7MAIN 36-78 6.6 246.5 35.4 36 7.7 246.5 32.8SR 36-78 5.4 237.0 35.7 36 7.1 237.0 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.6 3.3 54.0 12 16.0 2.6 52.8