Title: Data tester Smestad skole - Detaljert.pdf
1000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,9 25,4 3,5 448,00Remote: 36 28,2 23,8 4,4 500,00Worst Value: Local: 36 28,1 23,8 4,3 497,00Remote: 36 28,2 23,8 4,4 500,00PS-ACRF: Pass Worst Margin: Local: 12 73,1 61,2 11,9 1,00Worst Value: Local: 45 21,2 8,0 13,2 456,00Remote: 45 72,8 61,2 11,6 1,00Remote: 36 20,9 7,4 13,5 488,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 45Copper Certification ReportCable Label: 521.002-UD-144 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:54:48 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-Panel