Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.9 147 2 5.16Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.1 469.0 29.8 36 8.2 499.0 26.4SR 36-45 8.7 496.0 29.3 36 9.1 496.0 26.5MAIN 36-45 9.7 500.0 29.2 36 8.2 499.0 26.4SR 36-45 8.7 496.0 29.3 36 9.1 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.4 402.0 13.2 45 13.8 8.0 44.2SR 36-45 14.5 18.4 40.0 45 13.8 8.0 44.2MAIN 45-78 15.5 499.0 11.3 45 15.1 500.0 8.3SR 78-45 15.2 499.0 11.3 45 15.0 500.0 8.30100806040200250 MHzACR-F (dB)