Title: økernvn 94.pdf
SR 12-36 13.3 43.5 35.8 36 15.2 49.0 31.7MAIN 36-45 23.3 248.0 4.9 36 22.5 248.5 2.2SR 36-45 20.4 248.0 4.9 36 21.2 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 1.9 26.9 18.9SR 45 2.7 26.9 18.9MAIN 45 8.4 151.0 12.2SR 36 7.1 192.5 11.2010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94