Title: 563.X0X-RY001 SLASXCX - temperatur og CO2 sensor.pdf
0 to 100% AQI for VOCOverride buttonDisplay models feature momentary-to-ground override buttonAccuracy±15% of measured valueWiring TerminalsOutput scale0 to 1,000 ppb of total VOC (TVOC)LevelVentilation RecommendationTVOC (ppb)Terminal blocks Screw terminal torqueScrew terminals, 18-24 AWG0.2 N-m (2.0 in-lbF) max.>61% Greatly increased>610Regulatory InformationAQI table*RH Sensor20 to 61% Significantly increased 200 to 61010 to 20% Slightly increased100 to 2005 to 10% Average50 to 1000 to 5% Target value0 to 50Agency approvalsUL 916, European conformance CE: EN61000-6-2 EN61000-6-3 EN61000 Series - industrial immunity EN 61326-1 FCC Part 15 Class B, REACH, RoHS, Green Premium, RCM (Australia), ICES-003 (Canada), EAC (Russia)HS sensorThin-film capacitive, replaceableAccuracyHysteresis±2% from 10 to 80% RH @ 25°C (77 °F)1.5% typical