Title: DOCA0005EN-12.pdf
00—1AI00 - BACnet MAC Address01—1AI01 - BACnet Baud RateDigital input and output setting informationThe following AI objects display information about the meter’s I/O settings.NOTE: You can access the meter’s I/O configuration information over BACnet communications. However, you must use the front panel to configure the meter’s settings.Object ID UnitsDefault COVObject name / descriptionAI02 - Pulse Duration02ms1The energy pulse duration (or pulse width), in milliseconds, of the digital output.NOTE: This information only applies if the digital output mode is set to energy pulsing.AI03 - Pulse Weight03—1The pulses/unit setting of the digital input when it is configured for input metering.NOTE: This information only applies if the digital input mode is set to Input Metering.DOCA0005EN-12Analog Value objectDOCA0005EN-12Object ID UnitsDefault COVObject name / descriptionAI04 - Pulse Constant04—1The pulses/kWh setting of the digital output.