Title: økernvn 94.pdf
Cable ID: T4186 Date / Time: 09/11/2013 12:16:48 Headroom 8.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]196 301 12 9.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.6 238.0 35.7 12 9.5 238.0 33.1SR 36-78 8.9 229.5 35.9 78 9.1 224.0 33.5MAIN 12-36 8.6 238.0 35.7 12 9.5 238.0 33.1SR 36-78 8.9 229.5 35.9 78 9.2 248.0 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.5 4.6 50.9 12 16.6 3.1 51.3