Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Workplane (Wardrobe) Perpendicular illuminance (adaptive) [Ix] 213 (= 200) 115 313 0.54 0.37 Height: 0.000 m, Wall zone: 0.500 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 5 iGuzzini illuminazione - Q497 Laser Blade XS - Downlight HC 12.4W 739 12.4 59.6 Total via all luminaires 3695 62.0 59.6Lighting power density: 4.10 W/m? (Floor area of room 15.10 m? ), Lighting power density: 7.81 W/m? = 3.66 W/m2/100 Ix (Area of working plane 7.94 m?)Consumption: 51 kWh/a of maximum 550 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 106Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ’ S ’ <Site 1/ Building 1/ Storey 11/ Wardrobe / ViewsWardrobeWardrobeDIALux Page 107