Title: Installasjonsmanualer.pdf
Battery low shutdown: mains is absent and UPS switch off for minimum batterySd5Cold start Shutdown for low battery26 NETYS RT 1.1-3.3 kVA - Ref.: IOMNETRTXX0B-EN 0111. MAINTENANCESolutionContact SOCOMEC After Sales Service.Disconnect non-essential loads.Remove the short circuit on the load and restart the UPSUPS is off because of Emergency Power OFF button.Check that all emergency condition has been solved, and restart the UPS.Nothing to do, UPS is off due to software scheduled power off, UPS restart automatically at the programmed timeRestart the UPS if the load is lower than 8% of nominal power, set GF OFF on settings menuCheck mains supply and upstream switchConnect UPS to mains to recharge the battery12. TECHNICAL SPECIFICATIONSModelsNRT2-U1100NRT2-U1700NRT2-U2200NRT2-U3300Nominal PowerVA W1100 VA 900 W1700 VA 1350 W2200 VA 1800 W3300 VA 2700 WInput/Output phases1/1Electrical Specifications - InputInputVin