Title: TFP340_03_2007.pdf
The 11.2 K-factor, ELO-231 Sprinklers were subjected to full scale, high-piled storage, fire tests to qualify their use in lieu of 5.6 or 8.0 K-factor standard spray sprinklers for the protection of high-piled storage.Higher flow rates can be achieved at much lower pressures with the 11.2 K-factor, ELO-231 Sprinklers — mak- ing their use highly advantageous in high density applications, such as the protection of high-piled storage.An upright intermediate level version of the Series ELO-231 Sprinklers for in-rack applications can be obtained by utilizing the Series ELO-231 Up- right Sprinkler with the WSG-2 Guard & Shield, and a pendent intermediate level version of the Series ELO-231 Sprinklers can be obtained by utiliz- the Series ELO-231 Pendent ing Sprinkler with the WS-2 Shield. If there is a possibility of the pendent interme- diate level version being exposed to mechanical damage, a G-2 Guard can be added.