Title: +038=462.001-NB001._04-Produktbeskrivelse 200kW200kWh Xstorage Eaton.pdf
c. 3 pcs xStorage C&I Battery Rack - 42U, no doorsRack houses up to 10 battery packsStandard 19", 42U form factor, no front or rear doors, leveling feetRack includes:Mounting rails for battery packsIsolation contactors for up to two battery stringsDimensions: W600 x D1040 x H2022 mmd. 1 pc xStorage C&I System ControllerController communicates with BMSs of battery packs, inverterController provides customer controls over Modbus/TCPe. 1 pc xStorage C&I Application ControllerApplication controller enables independent operation byscheduling charging/discharging of storageProposed standard configuration includes 1 x Eaton PLC and power meter,suitable for e.g. solar self-consumption or peak shaving applicationControl parameters are adapted for the projectf. 1 pc 200kW DC cabinet, 6 stringsDC tie cabinet with fuses for battery strings and battery breaker to converterString fuse rating (DC+, DC-): 100 ABreaker rating: 500ADimensions approx: W800 x D300 x H2100 mm