Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
31.1 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 419.0 30.9 36 8.0 420.0 28.1SR 36-45 6.5 476.0 29.0 36 7.5 476.0 26.1MAIN 36-45 9.3 498.0 27.9 36 9.4 497.0 25.1SR 36-45 7.5 499.0 27.9 36 8.2 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.0 5.0 51.3 45 17.4 19.9 36.3SR 78-45 17.0 5.0 51.3 45 17.4 37.8 30.7MAIN 36-78 18.5 494.0 11.4 78 18.7 500.0 8.3SR 78-45 18.3 500.0 11.3 45 19.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 30.4 93.8 25.3 45 31.9 93.5 22.8SR 12-36 29.7 96.8 24.8 36 30.2 97.3 22.1MAIN 36-45 39.1 498.0 -12.3 36 39.6 497.0 -15.1SR 36-45 37.3 498.0 -12.3 36 38.4 498.0 -15.10804000250 MHzACR-N (dB)