Title: økernvn 94.pdf
Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: D4005 Date / Time: 09/10/2013 11:52:18 Headroom 2.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]240 372 18 11.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 2.3 62.3 45.2 36 4.6 62.3 42.7SR 36-78 4.1 61.8 45.2 36 6.1 61.8 42.7MAIN 36-78 7.3 235.5 35.8 36 7.5 235.5 33.1SR 36-78 5.8 216.5 36.4 36 7.7 250.0 32.710080604020NEXT (dB)