Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]15.2 66 1 2.47Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 4.4 259.0 35.1 36 6.2 300.0 31.4SR 36-78 3.8 297.0 34.1 36 5.5 240.5 33.0MAIN 12-36 8.3 497.0 28.0 36 7.6 473.0 26.3SR 12-36 6.0 497.0 28.0 36 7.8 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.3 496.0 11.3 45 20.4 259.0 14.0SR 12-45 19.3 271.0 16.6 45 20.1 241.0 14.6MAIN 36-45 19.3 496.0 11.3 45 21.4 500.0 8.3