Title: 1 etg del 2.pdf
MHz100NEXT @ Remote (dB)806040200050100150200250MHz100ACR-F @ Remote (dB)806040200050100150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz100RL @ Remote (dB)806040200050100150200250MHzLinkWare Version 8.1Cable ID: D1001 Date / Time: 10/17/2013 10:34:53 AM Headroom 7.8 dB (NEXT 12-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]98 151 6 4.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]21.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.4 224.0 36.1 12 9.2 224.0 33.5