Title: Autronica lab kjoling Autronica 20.04.16.docx
Building Building Building Unit Unit Liquid Gas H.P.Gas Airflow Nominal Capacity Nominal Capacity Nominal Capacity Simulated Capacity Simulated Capacity Simulated Capacity Combi. Ratio Combi. Ratio Dept Fl Room Name Model name Liquid Gas H.P.Gas Airflow Cooling Cooling Heating Cooling Cooling Heating Cooling Heating Dept Fl Room Name Model name Liquid Gas H.P.Gas Airflow TC SHC TC TC SHC TC - - - - - mm mm mm CMM kW kW kW kW kW kW % % Building1 Roof New Outdoor AM080JXVHGH/EU 9.52 19.05 170.00 22.40 25.20 0.00 0.00 119.64 118.65 Building1 1F 320 Prosj. AM015HNNDEH/EU 6.35 12.70 8.20 1.50 1.00 1.70 0.00 0.00 0.00 Building1 1F 317 EMC / Røyk AM015HNNDEH/EU 6.35 12.70 8.20 1.50 1.00 1.70 0.00 0.00 0.00 Building1 1F 373 Testrom AM022FNNDEH/EU 6.35 12.70 9.00 2.20 1.58 2.50 0.00 0.00 0.00 Building1 1F 318 Testlab AM036FNNDEH/EU 6.35 12.70 10.50 3.60 2.50 4.00 0.00 0.00 0.00 Building1 1F 253 Testrom AM045FNNDEH/EU 6.35 12.70 11.50 4.50 3.46 5.00 0.00 0.00 0.00 Building1 1F 318 Testlab AM045FNNDEH/EU 6.35 12.70