Title: +038=360.000-LC007T_06-Coadis line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
Input power (W) 12 21 5 1 - 0.18 0.40 0.09 028 Input current (A) 0.07 017 0.04 0.13 0.02 0.10Motor operating range: min. return T°: 0°C Max. return T°: 40°CDevice data plateThe name plate contains all the information required to identify the unit and its configuration. This plate is positioned on the technical face containing all the connections, above the fresh air inlet.1Code2Serial number3Description of the unit4Rated motor output5Motor rotation speed6Coil type7Wiring diagram reference8Motor speed wiring9Maximum service pressure10Electric heater specifications (if fitted)12HEAT PUMPSAIR CONDITIONINGREFRIGERATIONAIR HANDLINGHEAT EXCHANGENA 14.696 App— =>» Comfort unitsCIATCoanda effect cassetteCondensate drain pumpMaximum flow rate 20 I/hDischarge height 10 m (flow rate = 41/h) Maximum pressure 14 m (flow rate = Ol/h) Sound level at 1 m as per EN I1SO 3744(measurements taken at LNE, water pump, 23dBA