Title: 1 etg del 2.pdf
Cable ID: D1402 Date / Time: 10/17/2013 01:24:27 PM Headroom 0.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]48 75 5 2.048 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]25.8 246.5 30.450403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 0.5 * 221.5 36.2 36 0.1 * 250.0 32.7SR 12-36 5.4 221.5 36.2 36 6.1 222.0 33.6MAIN 36-45 0.5 250.0 35.3 36 0.1 250.0 32.7SR 12-36 5.5 228.5 36.0 36 6.5 250.0 32.71008060