Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
Drain pipeUnder gradientCAUTIONCeilingCheck that the indoor unit is level with the ceiling by using the leveller.Do not apply force to the piping on the unit sideInstall air ventilation to drain condensation smoothly.Air ventilationwhen connecting the drain hose. The hose should not be allowed to hang loose from its connection to the unit. Fasten the hose to a wall, frame or other support as close to the unit as possible.Support pieces1 to 1.5 mCeiling1/100 or moreCeiling14360_AirCon_Indoor_IM_ENG_EN.indb 142016-05-16 오후 5:32:15Install horizontally.Be horizontalIndoor unitFlexible hoseMax. allowable axis gap.Indoor unitMax. 20 mmMax. allowable bending angle.Indoor unitMax. 30˚NOTEIf a concentrated drain pipe is installed, refer to the figure below.Full thread bolt hanger1000 to 1500 mmIndividual air ventMain air vent (must be installed)200 mm or more300 to 550 mmMain drain pipe