Title: 1 etg del 2.pdf
SR 36-45 13.7 41.5 31.8 45 16.0 41.8 28.8MAIN 36-45 17.6 239.5 16.6 36 18.9 234.5 13.8SR 45-36 17.2 239.0 16.6 36 18.5 238.0 13.7010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.9 15.0 48.2 12 8.7 14.9 45.9SR 12-36 6.7 15.0 48.2 36 8.7 15.0 45.8MAIN 36-45 9.7 250.0 4.7 36 9.1 249.5 2.1SR 36-45 9.8 248.5 4.8 36 9.4 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.8 20.4 19.5SR 45 3.9 12.5 20.5MAIN 45 8.1 241.0 10.2SR 45 5.0 187.5 11.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active