Title: Økernveien 94 Sprinklerberegning U2.pdf
Occupancy ClassificationDensity (l/min/m²)5.7Area of Application (m²)149.6Coverage per Sprinkler (m²)10Number of Calculated Sprinklers15In-Rack Demand (l/min)0Special HeadsHose Streams (l/min)0Total Water Required (incl. Hose Streams) (l/min)862.9Required Pressure at Source (bar)1.62Type of SystemWetVolume - Entire System (l)1335 lWater Supply InformationDateLocationSourceOVA PSID231035NotesFile: D:\Dokumentert\Kunder\Møller eiendom\Dokumentasjon\Økernvn 94 U2.tyc3Date 29.05.2018Copyright © 2002-2012 Tyco Fire Protection ProductsPage 2Job : Økernveien 94Date 29.05.2018Diagram for Design Area : DesignArea_1File: D:\Dokumentert\Kunder\Møller eiendom\Dokumentasjon\Økernvn 94 U2.tyc3Copyright © 2002-2012 Tyco Fire Protection ProductsNode Labels: Pipe Labels:Off OffPage 3Job : Økernveien 94Hydraulic Analysis for : DesignArea_1Calculation Info