Title: crouse-hinds-powerplus-panelboards-brochure-brochure.pdf
3030Up to 22513NoTable C. To Size Panels with GFI or EPD Branch BreakersMaximum Number of GFi or EPd BreakersPanel sizeWith Main Lug or Main Breakersingle PoleTwo PoleB2112(10 with 3 pole MCB, 11 with 2 pole MCB)Each factory sealed panel is equipped with 42 load wires for GFI/EPD breakers and any combination with standard branch breakers. Determine the total number of load wires required to complete your panel. You may not exceed 42 load wires.Load Wires RequiredSingle pole breaker=1Single pole GFI (or EPD) breaker=2Two pole breaker=2Two pole GFI (or EPD) breaker=3C2114Three pole breaker=3Maximum Total: 42 load wires (factory sealed)EPLDN PanelsMaximum Total: 82 load wires (non-factory sealed)DEPLDN only - can go up to 42 GFI or EPD circuits. EPLDN will accommodate up to 225 amp main breaker.11 ampshaveadedicatedlocationformainbreaker.SizeCorderedwithsuffix2M00or3M00areprovidedwith36branchcircuitsformaximumbreakerampacity. 12