Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 45-78 16.6 495.0 11.3 78 17.9 497.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 23.4 81.5 27.4 45 23.9 71.3 26.9SR 36-45 24.6 75.5 28.6 45 25.4 71.5 26.9MAIN 12-45 38.3 497.0 -12.2 45 38.3 499.0 -15.2SR 36-45 37.1 499.0 -12.3 45 38.3 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.9 500.0 8.0SR 12 4.7 486.0 8.0MAIN 45 6.9 500.0 8.0SR 12 4.7 486.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00426.2 m60Insertion Loss (dB)504030201000250 MHz500100