Title: Climate Controls Ltd - MG Series 2000.pdf
almost closed and set the 'close' setting wheel so it is just operating the switch - as in number 6above. Using the manual switch on your controller, open the vent a small distance and then close itagain, observing where the limit switch stops the vents. By adjusting the setting wheel in small stages(one tooth on the setting wheel represents approximately 0.2mm of rack travel) you will be able to setthe limit switch to stop the motor in the desired positions.Climate Controls Limited, Les Reines, Forest, Guernsey, Great Britain, GY8 0JD Tel: + 44 (0)1481 263860 Fax: + 44 (0)1481 265294 E-mail: mail@climate-controls.com Climate Controls Limited is registered in Guernsey under number 1569.Standard Limit switch assemblyA schematic of the travel limit switches as used in the MG2000, MG4000 and MG7000 is shown below:AnticlockwiseClockwisePrimary switchSecondary switchAnticlockwiseClockwiseSecondary switchPrimary switch