Title: 1 etg del 2.pdf
MAIN 12-36 10.5 26.0 42.2 12 11.5 21.8 41.8SR 12-36 10.1 26.0 42.2 36 11.6 25.9 39.8MAIN 36-45 17.8 243.0 5.4 36 18.3 249.0 2.1SR 36-45 17.2 249.5 4.7 36 17.4 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.9 21.8 19.3SR 36 3.6 21.6 19.3MAIN 45 8.2 241.5 10.2SR 36 8.1 225.5 10.560500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94