Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
29.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 396.0 31.4 36 6.9 459.0 27.0SR 36-45 8.7 464.0 29.6 36 8.4 455.0 27.2MAIN 12-36 8.9 500.0 27.8 36 7.5 500.0 25.0SR 36-45 9.6 500.0 27.8 36 8.7 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.7 500.0 11.3 45 20.4 499.0 8.3SR 45-78 18.8 500.0 11.3 45 20.3 500.0 8.3MAIN 78-45 18.7 500.0 11.3 45 20.4 499.0 8.3SR 45-78 18.8 500.0 11.3 45 20.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 26.7 66.0 30.6 36 27.8 65.5 28.2SR 36-45 29.5 66.0 30.6 36 29.2 66.0 28.1MAIN 12-36 37.1 500.0 -12.4 36 35.8 500.0 -15.3SR 36-45 37.8 500.0 -12.4 36 37.0 500.0 -15.30804000250 MHzACR-N (dB)