Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
Display of all machine parameters (3 access levels, User/ Maintenance/Factory, password-protected): temperature, setpoints, pressures, water flow rate (hydraulic version), runtime.Display of trend curves for the main values - Storage of maintenance manual, wiring diagram and spare parts list.Display of trend curves for the main values - Storage of maintenance manual, wiring diagram and spare parts list.23Using the integrated Webserver, a simple internet connection uses the unit's IP address to access the Connect Touch interface on the PC, facilitating everyday management tasks and maintenance operations.A range of communication protocols are available: MODBUS/ JBUS RTU (RS485) or TC/IP as standard, LONWORKS – BACNET IP (Certified BTL) as an option, enabling most CMS/ BMS to be integrated.Web serverIP addressSeveral contacts are available as standard, enabling the machine to be controlled remotely by wired link: - Automatic operation control: when this contact is open,the machine stops