Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
SR 45-78 19.3 461.0 12.0 45 19.7 500.0 8.3MAIN 78-45 19.5 496.0 11.3 45 19.2 496.0 8.3SR 45-78 19.7 496.0 11.3 45 19.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.6 47.8 35.0 36 25.7 47.5 32.6SR 36-45 24.5 47.8 35.0 36 26.1 47.5 32.6MAIN 36-78 35.0 499.0 -12.3 36 33.7 499.0 -15.2SR 12-36 34.9 499.0 -12.3 36 35.0 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.8 448.0 8.0SR 45 8.5 430.0 8.0MAIN 45 7.8 448.0 8.0SR 45 8.5 430.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasjeTest Summary: PASS