Title: Igangkjøringsprotokoller på sirkulasjonspumper V.2017.07.17.pdf
Check expansion joints installed: ok Check vibration damper installed: ok Check air locks are avoided (suction side): ok Check for pipes adequate support: ok Check mechanical seal for leaks: okReal setp0|nt (head pmssure) 8.5m Flow at preseted setpoint (all valves opened): 35.08m3/h Power consumption W: 1521W Head pressure at regular working cond. : 2.55m Flow at regular working cond. : 8.03m3/h i Name Audnus Daniulis_Signature: %UAB ENSO PROJECTS REGISTRATION CODE 301340546, VAT LT10000363761 2 TILZES ST 41, IBAN LT35401 0042501594250, DNB BANKAS, SWIET AGBLLZ2XLT-471 B2 KAUNAS, LITHUANIA TECE 370837 322 258 WWW.ENSOBALTIC.COMIENSL]ENGINEERING SOLUTIONSPRE-STARTup check-list - CIRCULATION PUMPS Commissioning report No. DO 2 Date: [3/02/ ¥Service partner: