Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 17.7 500.0 11.3 45 17.5 3.8 50.8MAIN 78-45 17.7 500.0 11.3 45 18.9 500.0 8.3SR 78-45 17.7 500.0 11.3 45 19.0 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 29.8 91.8 25.6 36 30.5 102.0 21.4SR 36-45 25.6 96.0 24.9 36 26.1 96.3 22.3MAIN 36-45 39.1 497.0 -12.2 36 38.6 496.0 -15.0SR 36-45 35.0 492.0 -11.9 45 36.6 492.0 -14.70804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.3 446.0 8.0SR 45 6.2 445.0 8.0MAIN 45 8.3 446.0 8.0SR 45 6.2 445.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS