Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 3 05-05-2020 23:13:38 Tester 11 etg.flw2442.1 m 94 94 0 0 0Cable ID: 521.11.02-UF001 Date / Time: 27-02-2020 19:37:37 Headroom 8.2 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]15.4 66 0 2.52Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.6 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.2 289.0 34.3 36 9.4 455.0 27.2SR 36-78 9.3 478.0 28.9 36 8.9 456.0 27.1