Title: økernvn 94.pdf
Cable ID: T4162 Date / Time: 09/11/2013 12:08:33 Headroom 8.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]113 171 5 6.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]12.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.2 98.8 32.4 36 10.1 98.8 29.4SR 12-45 9.2 45.5 37.9 12 10.6 45.0 35.0MAIN 12-36 8.2 98.8 32.4 36 10.1 98.8 29.4SR 12-36 10.6 87.3 33.3 36 11.1 87.0 30.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-36 20.1 13.1 36.3 36 20.6 77.3 17.9