Title: 1 etg del 2.pdf
173 274 19 7.3173 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.3 * 248.5 35.4 36 0.0 * 246.5 32.8SR 36-45 1.3 244.5 35.5 36 0.6 *246.5 32.8MAIN 36-45 0.3 248.5 35.4 36 0.0 246.5 32.8SR 36-45 1.3 250.0 35.3 36 0.6 246.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 19.3 243.5 16.5 12 20.2 113.0 20.1SR 36-45 19.6 243.5 16.5 45 20.8 223.5 14.2MAIN 45-36 19.3 244.0 16.4 36 20.2 245.5 13.4SR 36-45 19.6 244.0 16.4 36 21.0 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz