Title: Bytesteinen 1 - =514.202-FS001.pdf
20.6 mLinkWare™ PC Version 10.4Cable ID: 521.202-UD046 Date / Time: 21/04/2021 19:09:11 Headroom 7.6 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]20.8 106 7 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]28.7 238.0 35.0Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 7.6 231.5 33.7 4,5 8.7 233.0 30.7SR 1,2-4,5 9.5 191.0 35.1 4,5 11.3 108.0 36.5MAIN 4,5-7,8 7.6 231.5 33.7 4,5 8.7 233.0 30.7SR 4,5-7,8 9.9 243.5 33.3 4,5 11.5 231.5 30.7