Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 21,4 10,2 11,2 500,00Remote: 45-12 21,8 10,3 11,5 493,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,9 25,4 4,5 447,00Remote: 36 27,9 23,8 4,1 498,00Worst Value: Local: 36 28,4 23,8 4,6 498,00Remote: 36 27,8 23,8 4,0 500,00PS-ACRF: Pass Worst Margin: Local: 45 66,3 54,3 12,0 2,20Worst Value: Local: 45 19,6 7,2 12,4 500,00Remote: 12 19,6 7,4 12,2 490,00Remote: 12 19,5 7,4 12,1 491,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:12Signature:______________________ Page: 123Copper Certification ReportCable Label: 521.002-UD-95 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:49:44 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein