Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
NOTE: This check is to be performed only if the busbar trunking system is commissioned at the same time as the transformer. The upstream circuit breaker protection setting checks are related to transformer commissioning.NOTE: If this check is successful, the busbar trunking system can be commissioned and the energized operating tests performed with the appropriate protective equipment.7Tap-off units check Check that all the tap-off units are disconnected or isolated in off-load position.  Check that the protective devices are correctly rated (current, breaking capacity) withrespect to the loads supplied, or in accordance with the specification drawings.(1) No neutral insulation check is required if the earthing system is such that the neutral is connected to or used as the earth.Energizing the EquipmentDANGERHAZARD OF ELECTRIC SHOCK, BURN, OR EXPLOSION