Title: 2 etg del2.pdf
100NEXT @ Remote (dB)806040202500050100150200250MHz100ACR-F @ Remote (dB)806040202500050100150200250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 8.1Cable ID: T2215 Date / Time: 10/10/2013 03:25:26 PM Headroom 1.3 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]189 298 20 8.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)