Title: Data tester Smestad skole - Detaljert.pdf
Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,2 23,8 3,4 498,00Remote: 36 28,7 23,8 4,9 500,00Worst Value: Local: 36 27,2 23,8 3,4 498,00Remote: 36 28,7 23,8 4,9 500,00PS-ACRF: Pass Worst Margin: Local: 12 66,0 54,3 11,7 2,20Worst Value: Local: 45 20,5 8,1 12,4 451,00Remote: 12 65,8 54,3 11,5 2,20Remote: 45 21,4 8,0 13,4 456,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:58Signature:______________________ Page: 27Copper Certification ReportCable Label: 521.002-UD-055 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 14:52:46 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: