Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 49,7 68,0 258,0 14,0 8,6Limit 100,0 - 555,0 50,0 25,0Margin 50,3 - 297,0 36,0 16,4Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 1,90Worst Value: Local: 36 21,1 43,8 22,7 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 15,9 9,2 6,7 299,00Remote: 78 22,7 16,8 5,9 52,50Worst Value: Local: 78 15,2 8,0 7,2 430,00Remote: 78 14,2 8,0 6,2 399,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass