Title: økernvn 94.pdf
MAIN 45-78 15.7 27.1 41.7 12 16.7 26.9 39.3SR 12-36 11.7 29.1 40.8 36 13.5 29.1 38.4MAIN 36-45 23.4 249.0 4.8 36 22.9 249.0 2.1SR 36-45 18.7 249.0 4.8 36 18.9 244.5 2.6010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.6 22.1 19.3SR 36 3.1 22.0 19.3MAIN 36 8.9 249.0 10.0SR 36 9.8 243.0 10.1010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flw