Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Zs(rcd)Z: 0.32ΩIsc: 710A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 05.11.2020 12:25Tallberg Elektro A/S Tlf.22796640Side:23GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.154154155155156156157157158158159159TEST RAPPORTResultatRCD II: 28.5mAUci: 0.2V t: 15.5ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 06.11.2020 13:22R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF042 16C2/003 05.11.2020 11:22KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 06.11.2020 09:58SPĆNDINGU12: 233V U1pe: 0V U2pe: 233V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF043 16C2/003 06.11.2020 09:59Z-LINEZ: 0.59Ω