Title: +038=370.101-QH009._01-Siemens Fukt_tempføler QFA3160_AQF3100.pdf
The types QFA3160D and QFA3171D provide the measured values on its LCD display. The following measured values are displayed alternately in intervals of 5 s:Temperature: Humidity:in °C or °F in % r. h.Range 1 2 3Measuring range 1 2 3Test function activeU1 U2I1I2°F °C10 V5 V20 mA12 mAQFA31...DDisplay temperature unit°F °C5 V0 V5 V10 V5 V0 V12 mA4 mA12 mA20 mA12 mA4 mAn e 3 0 Z 8 5 8 1The setting elements are located inside the cover. A setting element consists of 6 pins and a jumper. It is used for selecting the required temperature measuring range and for activating the test function. Types with LCD display have a second setting element with 4 pins and a jumper.The different jumper positions have the following meaning: (cid:120) For the active temperature measuring range: