Title: økernvn 94.pdf
100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3407 Date / Time: 09/11/2013 06:20:19 Headroom 7.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]159 244 9 7.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]15.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.1 232.5 35.9 36 8.0 197.0 34.4SR 36-78 7.1 231.5 35.9 36 8.0 249.5 32.7MAIN 36-78 7.1 232.5 35.9 36 8.2 232.5 33.2SR 36-78 7.4 250.0 35.3 36 8.0 249.5 32.710080604020NEXT (dB)