Title: økernvn 94.pdf
MAIN 36-78 19.3 248.5 4.8 36 20.3 247.0 2.3SR 36-45 15.2 249.0 4.8 36 15.1 247.0 2.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.6 25.4 19.0SR 45 2.6 10.5 20.9MAIN 45 8.2 248.5 10.0SR 36 7.7 237.0 10.3010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94