Title: +038=433.002-FS006._01-Eaton Tavlebyggeren Produktblad.pdf
25 Operating ambient temperature max. °C 75 linear, per +1 °C, results in a 0.5% reduction of current carrying capacity Technical data ETIM 7.0 Circuit breakers and fuses (EG000020) / Miniature circuit breaker (MCB) (EC000042) Electric engineering, automation, process control engineering / Electrical installation, device / Miniature circuit breaker system (MCB) / Miniature circuit breaker (MCB)(ecl@ss10.0.1-27-14-19-01 [AAB905014]) Release characteristic Other Number of poles (total) 4 Number of protected poles 4 Rated current A 40 Rated voltage V 400 Rated insulation voltage Ui V 440 Rated impulse withstand voltage Uimp kV 4 Rated short-circuit breaking capacity Icn EN 60898 at 230 V kA 10 Rated short-circuit breaking capacity Icn EN 60898 at 400 V kA 10 Rated short-circuit breaking capacity Icu IEC 60947-2 at 230 V kA 0 Rated short-circuit breaking capacity Icu IEC 60947-2 at 400 V kA 0 Voltage type AC Frequency Hz 50 - 60 Current limiting class 3 Suitable for ﬂush-mounted installation No Concurrently