Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
TALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:24GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTTEST RAPPORTNr. 7878ResultatColliers Plan 5 / JORDING / GULV KANAL 10.03.2022 13:45 (TomekElektriker)KONTINUITET: R200mA LPER: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5Ω7979Colliers Plan 5 / JORDING / KABEL BRU 09.03.2022 14:07KONTINUITET R: 0.0ΩGrenseverdi: 0.7Ω8080Colliers Plan 5 / JORDING / KABEL BRU 10.03.2022 14:25 (TomekElektriker)KONTINUITET: R200mA LPER: 0.03ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5Ω8181Colliers Plan 5 / JORDING / HIMLING 10.03.2022 13:43 (TomekElektriker)KONTINUITET: R200mA LPER: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5Ω8282Colliers Plan 5 / JORDING / HIMLING 10.03.2022 13:44 (TomekElektriker)KONTINUITET: R200mA LPER: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5Ω8383Colliers Plan 5 / JORDING / HIMLING 10.03.2022 13:45 (TomekElektriker)