Title: 320.010-NU001 - Akkumuleringstank med coil - 500 L.pdf
TECHNICAL INFORMATIONSTORAGE Material Capacity (L) Operating Pressure (Pmax) Test Pressure (hydrautic) (PT) Allowable Temperature (TS) Size&WeightCalbon steel S235JR (1.0038) 500 L 6 Bar.8,7 Bar.Max+15/+95C 1930*915*915*&150KgHEAT EXCHANGER (CORRUGATED DHW STAINLESS STEEL PIPE)Stainless steel AISI316L CORRUGATED DHW PIPE 6,5 m2 10 Bar.Material Surface (S) Operating Pressure (Pmax) Test Pressure (PT) Allowable Temperature (TS) 1. Insulated 100 mm thickness soft polyurethane (PU) thermal insulation and covered with red leatherette with zip.14 Bar. Min.+5C/Max.+95CWeight (KG)ColorQtyISO 9001:2008/LST EN ISO 9001:2008~150RAL 90061Refra ® ©NameSignatureDateDrawing. QtyProduct:Drawed ByApproved ByS. Marcinkevičius A.Ribokas2016.10.20UAB "Refra" Darius and Girėnas st.107 Vilnius. www.Refra.euCombi buffer tank (CTVF500-65 F IFHS6.5/3xSN100/PN6/PU100/PVC )Surface Area m2Material:Carbon steel S235JR (EN 1.0038)Code007THT375S.001A3Language LT