Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]26.0 113 2 3.90Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.3 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.4 453.0 30.1 36 8.4 457.0 27.1SR 12-36 6.1 452.0 30.1 36 6.7 457.0 27.1MAIN 36-78 9.9 499.0 27.9 36 8.8 498.0 25.1SR 12-36 6.6 493.0 28.2 36 7.1 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.1 500.0 11.3 45 20.4 497.0 8.3SR 45-78 19.4 500.0 11.3 45 20.5 500.0 8.3MAIN 78-45 19.1 500.0 11.3 45 20.4 497.0 8.3SR 45-78 19.4 500.0 11.3 45 20.5 500.0 8.30100806040200250 MHzACR-F (dB)