Title: Manual Elkjeler EL 160 - 500 Eco_No_Systemair_NY PANEL_jan -22_LOW.pdf
6. Sikkerhetsventil 6 bar DN 25/32 Minsteavstand mellom kjeletoppen og innvendig tak er 900 mm. Separat strømforsyning 230 V 1~ kreves for driftsspenning175.2.4 Effekt trinn EL 500 Eco7700151-01, -31El 500 Eco 204 kW400 V 3-faskW1521426363Relé 1Relé 2Relé 3Relé 4Relé 5Steg%kWK1K2K3K4K517%1510000210%2101000318%3611000421%4200100528%5710100631%6301100738%7811100851%10500110959%120101101062%126011101169%141111101282%168001111390%183101111493%1890111115100%204111117700151-02, -32El 500 Eco 252 kW400 V 3-faskW2142636363Relé 1Relé 2Relé 3Relé 4Relé 5Steg%kWK1K2K3K4K518%2110000217%4201000325%6300100433%8410100542%1050