Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Yes No 5 V 300 mA 400 mA TVS diode 39 V +/- 10 % NoPower supply to all modules Internal current consumption: from +5 V bus (without encoder) Internal current consumption: from V+ bus (without encoder) External current consumption:typically 210 mA, max. 230 mA (250 mA in SSI operation) 15 … 20 mA0 … 2 mA (without load current) 1 A for outputs Total current consumption for all I/O modules including encoders must not exceed 1.6 A. PCD2.H32x modules should be plugged onto the base unit wherever pos- sible (not the expansion housing). Operational conditions Ambient temperatureoperation: 0 … +55 °C without forced ventilation, storage: EC mark according to EN 61 000-6-3 and EN 61 000-6-2 Based on Saia PCD® user program and pre- programmed function blocks (FB). Pluggable 10-pole spring terminal block (4 405 4847 0), for wires up to 1.5 mm²20 … +85 °CNoise immunity:Programming:Terminals:5-131PCD2.H32xLEDs and connection terminalsBus connectorBus connectorAddressing circuit (FPGA)