Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]11.0 47 0 1.78Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]36.0 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.6 449.0 30.3 36 6.0 453.0 27.3SR 12-36 6.4 464.0 29.6 36 7.2 464.0 26.7MAIN 36-45 6.0 500.0 27.8 36 6.7 499.0 25.0SR 12-36 7.6 497.0 28.0 36 7.7 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.9 6.1 49.5 45 21.5 81.0 24.1SR 45-78 19.9 6.1 49.5 45 21.5 15.3 38.6MAIN 36-12 21.8 500.0 11.3 45 23.2 499.0 8.3