Title: økernvn 94.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.6 28.1 41.2 36 10.4 28.3 38.8SR 12-36 8.4 28.3 41.2 36 10.4 28.3 38.8MAIN 36-45 16.0 248.0 4.9 36 16.3 248.0 2.2SR 36-45 17.2 248.0 4.9 36 17.2 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.1 32.0 18.5SR 36 4.6 18.5 19.7MAIN 36 7.9 186.0 11.3SR 36 5.0 174.0 11.6010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4