Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
SPĆNDINGU12: 234V U1pe: 0V U2pe: 234V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF026 16C2/003 28.10.2020 14:04Z-LINEZ: 0.45ΩIsc: 516A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 196A Isc(0.76%): 392A Isc(1.15%): 593ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF026 16C2/003 28.10.2020 14:05Zs(rcd)Z: 0.36ΩIsc: 633A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF026 16C2/003 28.10.2020 14:07RCD II: 28.5mAUci: 0.2V t: 32.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF026 16C2/003 05.11.2020 11:15Tallberg Elektro A/S Tlf.22796640Side:7GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.5050515152525353545455555656TEST RAPPORTResultat KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF026 16C2/003 05.11.2020 11:26R LOW OhmR: 0.20Ω