Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
SR 78-45 14.6 500.0 11.3 45 15.2 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.6 42.0 36.7 45 25.0 42.3 34.1SR 12-45 25.9 50.0 34.4 36 25.6 41.8 34.3MAIN 36-45 35.3 500.0 -12.4 36 34.9 500.0 -15.3SR 36-45 33.5 495.0 -12.1 45 34.0 495.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.0 447.0 8.0SR 12 6.3 484.0 8.0MAIN 12 7.0 447.0 8.0SR 12 6.3 484.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Uni ConsultUniconsult tester.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00433.0 m60Insertion Loss (dB)504030201000250 MHz500