Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 17,5 8,0 9,5 460,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,3 26,7 2,6 499,00Remote: 36-45 29,6 26,7 2,9 500,00Worst Value: Local: 36-45 29,3 26,7 2,6 499,00Remote: 36-45 29,6 26,7 2,9 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 68,2 57,3 10,9 2,20Remote: 45-12 68,2 57,3 10,9 2,20Worst Value: Local: 12-45 21,1 10,2 10,9 500,00Remote: 45-12 21,5 10,2 11,3 498,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,1 24,0 4,1 491,00Remote: 36 28,4 23,8 4,6 500,00Worst Value: Local: 36 28,1 24,0 4,1 491,00Remote: 36 28,4 23,8 4,6 500,00