Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
When the module or CPU powers up, both analogue outputs of the PCD3.W500 module are set at the maximum value of +10 V (or a random value between 0 and +10 V). If this should cause problems, XOB 16 (the cold-start routine) should be used to initialize both these outputs to zero or any desired cold-start value.If the debugger is connected or the P100 handheld service device is plugged in, there is no cold-start when the CPU supply switches on. Both analogue outputs of the PCD3.W500 are then set to the maximum value of +10 V, despite the reset routine.Programming examples for the PCD3.W500 can be found on the TCS Support site. www.sbc-support.com.xx7 and RIOs: the firmware reads and writes the values according to the configuration (I/O Builder or network configurator)