Title: +038=360.000-LC007T_04-Coadis line 600 Fan-coil CIAT - Manual.pdf
(cid:121)(cid:3)(cid:39)(cid:72)(cid:86)(cid:76)(cid:74)(cid:81)(cid:3)The positioning of the hydraulic networks is crucial to the correct operation of the system. Drain valves should therefore be placed at the appropriate points and in sufficient number. In addition, strainers should be fitted, as well as drains at circuit high points, balancing tees and shut-off valves on each coil and, if necessary, discharge valves.(cid:121)(cid:3)(cid:41)(cid:76)(cid:79)(cid:87)(cid:85)(cid:68)(cid:87)(cid:76)(cid:82)(cid:81)(cid:29)An efficient filtration system (recommended efficiency of 0.5 mm) should be fitted on the supply water and return water lines.(cid:121)(cid:3)(cid:41)(cid:79)(cid:88)(cid:86)(cid:75)(cid:76)(cid:81)(cid:74)(cid:29)(cid:3)