Title: DM1-3 plan 05 lysberegningsrapport.pdf
Consumption[87 - 140] kWh/aLighting power densityRoom5.40 W/m²Utilisation profile: Offices, Writing, typewriting, reading, data processingLuminaire listpcs.Manufacturer Article No.Article name1Fagerhult22226-402Notor Rec Delta 3K 2400 white HL Single CLOTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 350 kWh/aPΦ50.0 W4996 lmCheckLuminous efficacy99.9 lm/W75201104 DM1-3 McKinseyBuilding 1 · Storey 1 · FSP 1 FSP176201104 DM1-3 McKinseyBuilding 1 · Storey 1 · FSP 1 FSP1PropertiesĒ(Target)FSP1 Perpendicular illuminance (adaptive) Height: 0.800 m, Surrounding area: 0.500 m450 lx (≥ 500 lx)Surrounding area 41 Perpendicular illuminance (adaptive) Height: 0.800 m401 lx (≥ 300 lx)Background area 30 Perpendicular illuminance (adaptive) Height: 0.000 m, Wall zone: 0.500 m177 lx (≥ 100 lx)Utilisation profile: Offices, Writing, typewriting, reading, data processingEmin370 lx310 lx53.1 lxEmax509 lx490 lx248 lx