Title: +038=433.000-NI003._27-Testrapport Elektriske Anlegg Pactum Plan 10 UF 433.10.01.pdf
Zs(rcd)Z: 1.30ΩIsc: 177A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADronningMaudsgat / 433.10.01 Plan10 / SIKRING45 13.02.2020 10:40Z-LINEZ: 0.84ΩIsc: 273A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADronningMaudsgat / 433.10.01 Plan10 / SIKRING45 13.02.2020 10:40Z-LINE dUdU: 5.9%Sikringstype: C SIKRING I: 16A SIKRING T: 35ms dU_lim: 4.0% Isc: 272A Z: 0.85Ω Zref: ___ΩDronningMaudsgat / 433.10.01 Plan10 / SIKRING45 13.02.2020 10:48Side:15GODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESMISLYKKESNr.9393949495959696979798989999TEST RAPPORTResultatRCD II: 28.5mAUci: 0.1V t: 15.1ms Idn: 30mA type: AC Ulim: 50VDronningMaudsgat / 433.10.01 Plan10 / SIKRING45 13.02.2020 10:52KONTINUITET R: 0.8ΩGrenseverdi: 1.0ΩDronningMaudsgat / 433.10.01 Plan10 / SIKRING45 13.02.2020 10:52R LOW OhmR: 0.73ΩR+: 0.7Ω R-: 0.7Ω Grenseverdi: 1.0Ω