Title: DOCA0005EN-12.pdf
5 = All partial energy reset (configure to reset all partial energy logs)nciDIPulseConstSNVT_count_32Pulse constant (pulses/unit)Digital input status (only Bit 1 is used)0 = relay opennvoDIStatusSNVT_count1 = relay closedNOTE: The information provided by this variable only applies if the digital input control mode is set to Input Status.Alarm statusAlarm status (only Bit 1 is used)nvoAlmStatusSNVT_count0 = Alarm is inactive1 = Alarm is activeAcknowledgement status (only Bit 1 is used):nvoAlmUnAckStateSNVT_count0 = historic alarm is acknowledged by the user1 = historic alarm is unacknowledged by the usernvoAlmLastTimeSNVT_time_stampTimestamp of last alarm (DD/MM/YYYY hh:mm:ss)nvoAlmLastValueSNVT_power_fValue at last alarmOverload alarm configuration:nciAlmEnableSNVT_count0 = disabled1 = enablednciAlmPkUpSetPtSNVT_power_fActive power alarm pickup setpoint in kWRelated topics