Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
27.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.5 447.0 30.3 36 6.6 499.0 26.4SR 12-36 9.1 492.0 29.4 36 9.8 499.0 26.4MAIN 12-36 6.9 500.0 29.2 36 6.6 499.0 26.4SR 12-36 9.1 492.0 29.4 36 9.8 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.9 453.0 12.1 45 19.9 500.0 8.3SR 45-78 20.0 411.0 13.0 45 20.5 500.0 8.3MAIN 36-45 20.2 500.0 11.3 45 19.9 500.0 8.3SR 45-36 20.2 500.0 11.3 45 20.5 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.2 48.0 34.9 45 20.4 48.0 32.5SR 36-45 17.1 47.8 35.0 45 19.3 48.0 32.5MAIN 12-36 34.2 500.0 -12.4 36 33.9 499.0 -15.2SR 12-36 36.7 499.0 -12.3 36 37.1 499.0 -15.20804000250 MHzACR-N (dB)