Title: økernvn 94.pdf
Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: D4123 Date / Time: 09/09/2013 12:27:03 Headroom 1.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]180 284 18 7.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.4 250.0 35.3 36 4.6 250.0 32.7SR 12-36 1.6 237.0 35.7 36 1.1 241.0 33.0MAIN 36-45 5.4 250.0 35.3 36 4.6 250.0 32.7SR 36-45 1.6 248.5 35.4 36 1.1 241.0 33.010080604020NEXT (dB)