Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 36-45 39.6 423.0 -7.2 45 41.0 423.0 -10.0SR 36-45 37.5 423.0 -7.2 45 39.7 423.0 -10.0MAIN 36-45 41.3 480.0 -11.1 36 42.7 481.0 -14.0SR 36-45 38.2 481.0 -11.1 36 40.4 482.0 -14.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.4 437.0 8.0SR 45 4.6 437.0 8.0MAIN 45 5.4 437.0 8.0SR 45 4.6 437.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Uni ConsultUniconsult tester.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA0046.1 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz