Title: +038=360.000-LC007T_06-Coadis line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
tube system)Onepiece couplings (40 mm centre distance) with rotating lemale couplings wilh inlegraled flal lace and seals, [or easy fitting of control valves.One, two or three row circular coil with low pressure drop.Copper tube, continuous aluminium fins (1.6 mm spacing)Bleeding and drainingo Nominal pressure of 16 bar (at 20°C)Test pressure of 24 barMax. hot water inlet temperature:4tube application: 80°C,2tube application: 70°C,2tube/2wire application: 55°C (min. air flow rate: 2%m3lh).Min. cold water inlet temperature: 6°CElectric heater (2tube + electricsystem)230/1/50 singletube electrical elements inserted into the aluminium housing.2 temperature limiters with manual and automatic reset, inserted into the aluminium housing and easily accessible via the return/supply interface without the need to open the suspended ceiling.Heating element supply connected to the terminal block inside the electrics box.