Title: 2 etg del2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]234 372 27 10.0234 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 247.0 35.4 36 1.1 247.0 32.8SR 36-450.7 *245.5 35.5 36 0.7 *247.0 32.8MAIN 36-45 1.3 247.0 35.4 36 1.1 247.0 32.8SR 36-45 0.7 245.5 35.5 36 0.7 247.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.4 240.0 16.6 36 15.6 250.0 13.2SR 36-45 13.8 240.0 16.6 45 16.0 227.0 14.1MAIN 45-36 13.6 250.0 16.2 36 15.6 250.0 13.2