Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
28.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.7 478.0 28.9 36 8.1 464.0 26.7SR 36-45 3.5 465.0 29.5 36 4.8 467.0 26.6MAIN 36-45 10.8 500.0 27.8 36 9.2 500.0 25.0SR 36-45 4.4 483.0 28.6 36 6.2 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.4 500.0 11.3 45 17.1 3.9 50.5SR 78-45 17.3 481.0 11.6 45 17.0 3.9 50.5MAIN 78-45 17.4 500.0 11.3 45 18.4 500.0 8.3SR 78-45 17.4 500.0 11.3 45 17.7 481.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.5 60.3 31.9 36 25.8 64.5 28.4SR 36-45 22.0 59.8 32.0 36 23.8 64.0 28.5MAIN 36-45 38.2 500.0 -12.4 36 37.0 500.0 -15.3SR 36-45 32.9 500.0 -12.4 36 33.9 499.0 -15.20804000250 MHzACR-N (dB)