Title: +038=370.103-SB005T_03-Energy Valve Reguleringsventil Belimo - Merknader for prosjektering.pdf
In this setting, the power output at the heat exchanger is used as a control variable (e.g. Y = 10 V' <–> Q' = 20 kW). The valve unit selects the opening angle automatically so that the requested power is provided to the heat exchanger. Influences of differential pressure and temperature fluctuations are automatically compensated for –> pressure and temperature-indepen- dent operation.6Notes for project planning / Project planningProject planningRelevant informationThe data, information and limit values on the data sheets of the electronic pres- sure-independent characterised control valves Belimo Energy Valve™ must be taken into account. – EV..R+BAC (DN 15...50 with standard actuator) – EV..R+KBAC (DN 15...50 with electrical fail-safe) – P6..W..EV-BAC (DN 65...150 with standard actuator) – P6..W..EV-KBAC (DN 65...150 with electrical fail-safe) – EV..F+BAC (DN 65...150 with standard actuator) – EV..F+KBAC (DN 65...150 with electrical fail-safe)Dimensions