Title: 1 etg del 2.pdf
Cable ID: T1001 Date / Time: 10/17/2013 02:07:38 PM Headroom 2.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]96 145 4 4.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]21.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.0 235.0 35.8 36 6.9 237.0 33.1SR 12-36 2.9 237.5 35.7 36 3.7 233.5 33.2MAIN 36-78 6.0 235.0 35.8 36 6.9 237.0 33.1SR 12-36 2.9 237.5 35.7 36 3.7 233.5 33.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.4 6.3 48.3 12 16.8 3.3 51.0