Title: +038=360.000-NI001._59-DM1-3. 360.005 (5 etg) R&H - Målerapport.pdf
MÅLEPROTOKOLLVersjon nr 3Dato 17.02.01Blankett nr.: 68-091ANLEGG : SYSTEM :TILLUFT ROM NR.5-013 5-014 5-015 5-213 5-212 5-211 5-123 5-210 5-122 5-121 5-120 5-119 5-118 5-117 5-418 5-419 5-420 5-421 5-422 5-423 5-415 5-309Dronning Maud gt 1-3 360.005 5 etgTILLUFT Prosjektert Målt m3/h 198 1 436 119 90 86 81 389 81 1 199 159 162 189 189 288m3/h 200 1 435 115 90 80 80 400 80 1 200 160 160 190 190 300AVTREKK Avvik Prosjek Målt m3/h m3/h%1 0 3 0 8 1 -3 1 0 -1 1 -1 -1 -440039850 100 100 100 100 10050 101 100 101 99 100550 80558 861 8Dato : Ref. :Avvik %10 1 0 1 -1 012.01.2022 Harald Jensrud ANMERKNINGSentral avt4 3604 3650Total5 3105 31005 3105 3140KVALITETSHÅNDBOK Randem Hübert A/S - Stansevn. 11, 0975 OSLO - Telefon: 22 90 07 00 - Telefax: 22 90 07 10 E-mail: service@hybra.no