Title: 2 etg del2.pdf
Cable ID: T2070 Date / Time: 10/10/2013 03:18:31 PM Headroom 13.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]212 334 22 9.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.8 99.3 32.4 36 15.0 99.3 29.4SR 12-36 13.9 90.0 33.1 36 14.9 90.0 30.1MAIN 12-36 13.8 99.3 32.4 36 15.0 99.3 29.4SR 12-36 13.9 93.0 32.8 36 14.9 93.3 29.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.0 59.8 23.1 36 18.7 59.8 20.1