Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
TEST RAPPORTBruker:Teststed:Tallberg Elektro A/S Stanseveien 4+DM3.E3=433.08.03 Dronning Mauds gate 1-3Instrument dataType:EUROTEST COMBOSer.Nr.:13250825Modell:MI 3125BTProdusent:Metrel d.d.Nr. 11ResultatDM1-3. Plan 8 / DM3.E3=433.08.03 / XF000 OV32/4 06.11.2020 14:18SPĆNDINGU12: 405V U13: 406V U23: 406V f: 50.0Hz : 3.2.122DM1-3. Plan 8 / DM3.E3=433.08.03 / XF000 OV32/4 06.11.2020 14:14R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩ33DM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 05.11.2020 11:21KONTINUITET R: 0.1ΩGrenseverdi: 1.0Ω44DM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 05.11.2020 11:32R LOW OhmR: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0Ω55DM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 05.11.2020 12:26Z-LINEZ: 0.09ΩIsc: 2.45kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 931A Isc(0.76%): 1.86kA Isc(1.15%): 2.82kA66DM1-3. Plan 8 / DM3.E3=433.08.03 / XF001 16C2/003 05.11.2020 12:26