Title: +038=360.000-OU045T_05-PCD2.m4160 PLS SBC - User Manual.pdf
n.c.non connecté24GND23GND22++24 V21++24 V20++24 VThe PCD2.C1000/C2000 module holders provide the following internal supply  currents for the inserted or connected modules:TypeMaximal currentPower consumption+5VV+PCD2.C1000 PCD2.C20001400 mA800 mAIn der Regel 2WPCD-BusC D V 4 2DC+5Vy l p p u SDCCLR0VV+ (16,2V)When planning PCD2 systems, it is important to check that the internal power  supplies to the I/O module racks are not overloaded. This check is especially  important when using analog, counting and positioning modules, as some of these  modules have a high power consumption.It is recommended to use the calculation table a www.sbc-support.com.User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-214-44System overviewSaia-Burgess Controls AGExtension connection