Title: 2 etg del2.pdf
Cable ID: T2051 Date / Time: 10/11/2013 10:04:27 AM Headroom 1.1 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]255 403 27 10.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.1 247.5 35.4 36 1.2 250.0 32.7SR 36-78 7.2 238.5 35.7 36 8.8 238.0 33.1MAIN 36-45 1.1 247.5 35.4 36 1.2 250.0 32.7SR 36-78 7.2 238.5 35.7 36 8.8 238.0 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 17.3 162.5 20.0 12 18.0 159.0 17.2