Title: Hardware Installation Guide.pdf
The use of AC Strikes is “Not Evaluated by UL” and therefore cannot be used in UL installations.Reader power for UL installations: 300 mA maximum for an operating temperature range of -10 to +49°C (14 to 120°F).Environmental for UL installations: - -Temperature:-10 to +49°C (14 to 120°F) operating Humidity: 85+/-5% at 30+/-2°C (86°F)426 — revision 6Hardware Installation Guide88SpecificationsNote:For UL installations, refer to section UL Listed Installations on page 425.The LNL-1320 is for connection to low voltage, class 2 power-limited circuits only. These specifications are subject to change without notice.Primary power: 12 to 24 VDC + 10% - - -12 VDC @ 1200 mA (includes reader current) nominal 24 VDC @ 600 mA (includes reader current) nominal 49.1 BTU/hourOutputs: Form-C contacts, Relays 1-6 (K1-K6), 5 A @ 30 VDCInputs: - - -