Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
GODKJENT*GODKJENTNr. 136136137137138138139139140140141141142142TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 11.06.2020 15:18R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 11.06.2020 15:29SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 10:12Z-LINEZ: 0.48ΩIsc: 483A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 10:12Zs(rcd)Z: 0.41ΩIsc: 566A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 10:12RCD II: 28.5mAUci: 0.0V t: 17.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 10:13RCD tt: 64.1msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF035 C16/2 12.06.2020 09:28Tallberg Elektro A/S Tlf.22796640