Title: Data tester Smestad skole - Detaljert.pdf
PS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,9 3,7 496,00Remote: 36 28,5 23,8 4,7 500,00Worst Value: Local: 36 27,6 23,8 3,8 498,00Remote: 36 28,5 23,8 4,7 500,00PS-ACRF: Pass Worst Margin: Local: 45 18,9 7,2 11,7 499,00Worst Value: Local: 45 18,9 7,2 11,7 500,00Remote: 12 71,5 60,0 11,5 1,15Remote: 12 19,1 7,3 11,8 493,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:07Signature:______________________ Page: 94Copper Certification ReportCable Label: 521.002-UD-189 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:27:27 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: