Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 30,9 68,0 160,0 9,0 5,8Limit 100,0 - 555,0 50,0 25,0Margin 69,1 - 395,0 41,0 19,2Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,5 3,0 2,5 2,35Worst Value: Local: 36 13,3 43,6 30,3 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 14,0 8,9 5,1 323,00Remote: 78 14,3 8,8 5,5 328,00Worst Value: Local: 12 14,0 8,9 5,1 323,00Remote: 78 14,3 8,8 5,5 328,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass