Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Temperature error: Burst protection: (IEC 801-4) Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Terminals:8 bit (0 … 255) < 5 µs for 0 … 10 V: for 0 … 20 mA: 0 … 500 Ω for 4 … 20 mA: 0 … 500 Ω for 0 … 10 V: 1 % ± 50 mV for 0 … 20 mA: 1 % ± 0.2 mA for 4 … 20 mA: 1 % ± 0.2 mA for 0 … 10 V: < 15 mVpp for 0 … 20 mA: < 50 µApp for 4 … 20 mA: < 50 µApp typically 0.2 %, (over temperature range 0 … +55 °C) ± 1 kV, with unshielded cables ± 2 kV, with shielded cables 1 mA≥ 3 kΩ30 mAmax. 0.1 A (type PCD2.W410 only, for current outputs) Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-66Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W4x0ConnectionsBus connectorReference voltageBus interface40