Title: EP..R_MOD_ BACdatasheet_en-gb.pdf
5 Nm (DN 15...25) 10 Nm (DN 32...40) 20 Nm (DN 50) BACnet MS/TP Modbus RTU (ex works) MP-Bus DC 2...10 V DC 0.5...10 V DC 2...10 V Start point DC 0.5...8 V End point DC 2...10 V 45 dB(A) 30...100% of Vnom ±10% (of 25...100% Vnom) ±6% (of 25...100% Vnom) @ 20 °C / Glycol 0% vol. Cold and warm water, water with glycol up to max. 50% vol. -10...120°C 1600 kPa 1400 kPa 350 kPa 200 kPa for low-noise operationwww.belimo.comEP..R+MOD • en-gb • 2018-04-27 • subject to changes12Safety notesProduct featuresFunctional data Flow characteristicLeakage rateInstallation positionMaintenance Manual overrideequal percentage (VDI/VDE 2178), optimised in the opening range (switchable to linear) Leakage rate A, air-bubble-tight (EN 12266-1) Upright to horizontal (in relation to the stem) Maintenance-free with push-button, can be lockedFlow measurement Measuring principle Measuring accuracy Measuring accuracy noteMin. flow measurement