Title: datablad domina engelsk.pdf
Technical speciﬁcations b b b b b b Dardo Plus control unit b b b b b b bCentralised control by Dardo Plus control unit Self-diagnosis version (Activa) Available for maintained or non-maintained operation Installation for ﬂush mounting and false ceiling Compliant with IEC EN 60598-2-22 standard Can be inhibited with rest mode via Teleur range of remote controls orProtection rating: IP 42 or IP 65, IK 07 or IK 10 Insulation class: II i Operating temperature: 0…40°C Fire behaviour (IEC 60695-2-10), incandescent wire: 850°C Light source: ﬂuorescent lamp Power supply: 230 V, 50 Hz Complete recharge in 12 h for models with 1 h autonomyDimensionsDimensions (mm)ABC6/11 W 100, 140 and 210 lm 149302688/24 W 85, 145, 150, 400 and16938282640 lmInstallation rules (examples for 85 and 640 lm) The photometric data is approximated (average values): for project calculations, scattering coefﬁcients must be taken into consideration.Domina 85 lm3 m10.50 m111110.50 m10.50 m