Title: 564 6131_30-31-xxx-500 Tilstedeværelsesdetektor tak 360 hvit.pdf
IR receiver (only premium)C Sensor for brightness detection1 − 4Individual sectors with switch-off function (via parameter setting). For numbering see the rear of the deviceCAUTION The unit contains highly sensitive sensors and lens systems.  Do not cover or mask lens segments since this will interfere withthe function of the device. Do not clean the device and the lens system with abrasive oraggressive cleaning agents.Technical data Supply voltage Max. current consumption24 V < 12 mAKNX connectionBus connecting terminal Line type Wire stripping0.6 – 0.8 mmJ-Y(St)Y, 2 x 2 x 0.8 mm 5 – 6 mmSwitch-on time after switch-off (programmable) Adjustable brightness range Opening angle for brightness measurement Temperature range Protection type Remote operation (*)Storage temperatureapprox. 1 secondapprox. 1 – 1000 luxapprox. 20°5 °C – +45 °C IP 20 only premium -20 °C – +70 °CiDescripción del producto