Title: økernvn 94.pdf
100150200250MHzLinkWare Version 7.4Cable ID: D3417 Date / Time: 09/12/2013 12:31:16 Headroom 6.5 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]103 157 5 4.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]20.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.7 200.0 36.9 36 9.3 203.5 34.2SR 36-78 6.5 199.5 36.9 36 6.7 222.5 33.5MAIN 12-36 9.4 232.5 35.9 36 9.4 232.5 33.2SR 36-78 6.7 250.0 35.3 36 6.7 222.5 33.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)