Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 45-78 17.0 500.0 11.3 45 17.5 497.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.4 55.3 33.1 45 23.7 55.5 30.5SR 12-45 25.6 56.3 32.8 45 24.3 56.0 30.4MAIN 12-45 37.7 474.0 -10.7 36 38.9 499.0 -15.2SR 36-45 36.5 500.0 -12.4 45 36.2 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.8 474.0 8.0SR 12 5.6 491.0 8.0MAIN 45 6.8 474.0 8.0SR 12 5.6 491.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00429.2 m60Insertion Loss (dB)504030201000250 MHz500