Title: +038=360.021-#####._06-360.021 Gold RXF-12 Ventilasjonsaggregat Swegon - Installasjonsanvisning.pdf
Digital inputs, terminals 4-17, are of extra-low voltage type. Analogue inputs, terminals 18-19 have an input impedance of 66 kΩ.Wiring terminalFunctionRemarks1,2,3Connections for EIA -4851= Communication connection A/RT+, 2= Communication connection B/RT–, 3= GND/COM.4,5External stopStops the air handling unit by opening the circuit. On delivery, this function is fitted with a jumper. If the connection is interrupted, the air handling unit will stop.6,7External fire/smoke function 1External fire and smoke function. On delivery, this function is fitted with a jumper. If the connection is interrupted, the function will trip and initiate an alarm.8,9External fire/smoke function 2External fire and smoke function. On delivery, this function is fitted with a jumper. If the connection is interrupted, the function will trip and initiate an alarm.10,11External alarm 1External contact function. Optional: Normally open/normally closed.12,13External alarm 2