Title: V20-06-01 VVS-anlegg plan 6 - DM1-1.pdf
ø160 UK=2685LD021T Maks:220 m³/h Kjøling: 595 W 0.047 L/sø250 UK=2615LD021T Maks:220 m³/h Kjøling: 595 W 0.047 L/sÅpent kontorlandskap-1 6-105-1LD021T Maks:220 m³/h Kjøling: 200 W 0.016 L/sLD021T Maks:220 m³/h Kjøling: 200 W 0.016 L/s320.102: 18 mm +c 2790320.102: 18 mm +c 2790370.101: 28 mm +c 2790370.101: 28 mm +c 279028mmLD018T Maks:220 m³/h Kjøling: 200 W 0.016 L/s Varme: 490 W 0.012 L/sSTAP/STAD DN2013131415+06 = 320.102 - OE 063 0.082 L/sLD018T Maks:185 m³/h Kjøling: 450 W 0.036 L/s Varme: 410 W 0.010 L/sLD018T Maks:110 m³/h Kjøling: 200 W 0.016 L/s Varme: 230 W 0.006 L/sLD018T Maks:220 m³/h Kjøling: 570 W 0.045 L/s Varme: 470 W 0.011 L/sLD018T Maks:220 m³/h Kjøling: 570 W 0.045 L/s Varme: 470 W 0.011 L/sST001T-160-250 130 m³/hWISE director (trådløs router)50 m3/h tilluft og avtrekk i teknisk rom.22mmSnitt P6-D370.101: 42 mm +c 2790 370.101: 42 mm +c 2796