Title: Instructions manual - THGT fan.pdf
10.5 10.6 Area may then be secured and inspected to ascertain if hazard exists prior to removal of system or replacement of fan equipment.ATEX fan equipment should not be reused in a different ATEX application.3411 Annexes:Annex 1: Extended storage checklist Applicable to: Large fans with metal impellers, not supplied in cartons, should be stored so that:- Impellers must be rotated minimum 10 turns once a month. Motor insulation tested every 3 months. Motor anti-condensation heater energized, if fitted. Storage must not exceed 1 year, without review by supplier / manufacturer for possible damage to motor, bearings, grease. Regular inspection and check list to be completed.Project ID:Client:Fan ID: Fan Code: Fan ATEX Code: Fan Serial No: ItemActionFrequencyMotor ATEX Code: Motor Serial No: 52 Storage maintenance schedule13467891011DateS1Visual inspection: environment safe, no damage, no corrosion1 month√SignRotate motor / impeller shaftDateS2