Title: DOCA0005EN-12.pdf
IP degree of protectionMeter bodyIP20iEM31•• / iEM32•• / iEM34•• / iEM35••Meter body except bottom wiring surfaceIP20iEM33••Impact ratingIK08iEM31•• / iEM32•• / iEM33•• / iEM34•• / iEM35••Active energy display rangeIn kWh or MWh up to 99999999 MWhIn kWh: 8 + 1 digits up to 99999999.9iEM32•• / iEM34•• / iEM35••iEM31•• / iEM33••500 flashes / kWhiEM31••Energy pulsing LED (yellow)15000 flashes / kWh without consideration of transformer ratios200 flashes / kWhiEM32••iEM33••24000/x flashes /kWhiEM34••5 flashes / kWhiEM35••1The pulses / kWh of the energy pulsing LED cannot be changed.Environmental characteristics CharacteristicValueMetersOperating temperature25 to 55 °C (-13 to 131 °F) (K55)25 to 70 °C (-13 to 158 °F) (K70)iEM31•• / iEM32•• / iEM33••iEM34•• / iEM35••Storage temperature40 to 85 °C (-40 to 185 °F)Pollution degree2Relative humidity5% – 95% RH non-condensingMaximum dewpoint 36 °C (97 °F)