Title: Eurotester målerestultat.pdf
Isc: 266A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 101A Isc(0.76%): 202A Isc(1.15%): 306ABytesteinen 1 / =433.202 / SIKRING25 30.03.2021 13:47:09RCD II: 22.5mAUc: 9.1V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING25 30.03.2021 13:47:24R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING25 30.03.2021 13:47:39R LOW OhmR: 0.11ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING26 30.03.2021 14:17:38Z-LINEZ: 0.65ΩIsc: 355A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 135A Isc(0.76%): 270A Isc(1.15%): 408ABytesteinen 1 / =433.202 / SIKRING26 30.03.2021 14:18:52RCD II: 25.5mAUc: 9.5V Idn: 30mA type: AC Ulim: 50VTestet av: Andreas PedersenSide:12GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr. 7777787879798080818182828383TEST RAPPORTResultat