Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
For Ni 100 (PCD2.W350) Validity: Computational error: ± 1.65 °CTemperature range - 50 … +250 °CT= - 28.7 +300 • DV 36287.294 • 10-6 • (DV - 1850)2For Pt 100 (PCD2.W350) Validity: Computational error: ± 1 °CTemperature range - 50 … +600 °CT= - 99.9 +650 • DV 3910+ 6.625 • 10-6 • (DV -2114)2For Pt 1000 (PCD2.W360) Validity: Computational error: ± 0.25 °CTemperature range - 50 … +150 °CT= - 178.1 +200 • DV 2509+ 3.873 • 10-6 • (DV -2786)2T = temperature DV = digital valueHardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-60Saia-Burgess Controls Ltd.Input/output (I/O) modulesAnalogue input modules, electrically isolated6.9Analogue input modules, electrically isolatedPCD2.W305 PCD2.W315 PCD2.W3257 analogue inputs 12 bit resolution, 0..10 V 7 analogue inputs 12 bit resolution, 0..10 V 7 analogue inputs 12 bit resolution, 0..10 VGalvanic separation of outputs to PCD, channels themselves are not separated