Title: 563-Belimo-Motor til kuleventil DN40-50 SR24A-SR.pdf
Connection via safety isolating transformer. • Parallel connection of other actuators possible. Observe the performance data. • Direction of rotation switch is covered. Factory setting: Direction of rotation Y2.WiringdiagramsAC/DC24V,modulatingT ~ + –Y UDC (0)2...10 V DC 2...10 VY1Y21235Cable colours: 1 = black 2 = red 3 = white 5 = orange2SR24A-SR • en-gb • 2014-08-13 • subject to changeswww.belimo.euSR24A-SRElectrical installationOverridecontrol(frostprotectioncircuit)T ~ – +YDC (0)2...10 Vcd1235Y1Y2cdY1 / Y2Y1A – AB = 100%A – AB = 0%Y2 DC (0)2...10 VDimensions[mm]Furtherdocumentationwww.belimo.euRotaryactuator,Modulating,AC/DC24V,20NmCable colours: 1 = black 2 = red 3 = white 5 = orangeDimensionaldrawings118R 6533108Overview Valve-actuator combinations • Data sheets for ball valves • Installation instructions for actuators and/or ball valves • General notes for project planning