Title: 050083 30 E 542 20 002 Plan 3 - Brann og nødlys - Fløy B.pdf
STYRESKAP FOR RØYKLUKER MÅ SAMMENKOBLES SLIK AT DE STYRER LUKENE SAMTIDIG VED DETEKTERT RØYK I GLASSTAK SIGNAL KAN HENTES FRA ASPIRASJONSDETEKTOR KLEMME "BRANDRELÉ" (NO)+71177=542.151-UN001T.06.055I/O-ENHETER FOR VENTILASJONSAGGREGATER PLASSERING PÅ TEGNING ER IKKE RIKTIG IHT. PLASSERING AV AGGREGATER360.001SLØYFE TILBAKE TIL PLAN 1,5TRAPP 3 3.050SLØYFE FRA PLAN 1,5+71177=542.151-XZ001T.06.060360.004+71177=542.151-XZ001T.06.067TIDLIGERE 66RØYKLUKE I TAK RØYKLUKESKAP ER PLASSERT NEDERST I TRAPPESJAKTC-1D-1D-1RØYKLUKER - STYRESKAP FOR GLASSTAK5G1,5 TILFØRSEL FRA 433.203 - XF203 3G1,5 TIL MOTOR - STRØM 3G0,75 TIL MOTOR - SIGNALSTYRESKAP FOR LUKER FASADE PLAN 1 OG 1,5 3G1,5 TILFØRSEL FRA 433.203 - XF202STYRESKAP FOR LUKER FASADE PLAN 1 OG 1,5 3G1,5 TILFØRSEL FRA 433.203 - XF2022 STK. MOTORER/LUKER PLAN 1 ØST - 3G2,5 2 STK. MOTORER/LUKER PLAN 1 ØST - 3G2,52 STK. MOTORER/LUKER PLAN 1,5 VEST - 3G2,5SE OGSÅ TOPOLOGISKJEMA FRA BRAMO TEGNINGNUMMER: 69582E-1E-14567