Title: +038=442.002-UP033T_02-TALEXXdriver LCU 60W 12 24V IP20 Tridonic Produktblad.pdf
Storage temperature ts Dimensions L x W x H Hole spacing D100 – 277 V 90 – 305 V 176 – 288 V 0.59 A 0.32 A 0.26 A 0.58 A 0.32 A 0.26 A 0 / 50 / 60 Hz > 87 % > 85 % > 87 % > 89 % > 85 % > 89 % 0.99C 0.95C 0.96C 0.99C 0.95C 0.96C 0.5 W -0 / +10 % -0 / +5 % 60 W 42 W 4.8 – 60 W ≤ 0.5 s ≤ 1 s 10 ms 1 kV 1 kV < 500 V -25 ... +60 °C -25 ... +45 °C -40 ... +85 °C 250 x 40 x 21 mm 223 mmApproval marksStandardsEN 55015, EN 60598-1, EN 60598-2-22, EN 61000-3-2, EN 61000-3-3, EN 61347-1, EN 61347-2-13, EN 61547, EN 62384, EN 62493Specific technical datae p y Tg n i s a cx a Mr u t a r e p m e tc t et u p t u Oe g a t l o vt u p nx a Mr e w o pLCU 60W 24V TOP SR 1 For input voltage from 120 to 277 V AC (50 / 60 Hz) with 100 % load. For input voltage from 100 to 120 V AC (50 / 60 Hz) with 80 % load.85 °C24 V74 WArticle information 05/18 Subject to change without notice.www.tridonic.comt u p t u Ot n e r r u ce g n a r0.2 – 2.5 A3