Title: Sirkulasjonspumper.pdf
0.38 l/s 50 kPa 60 dm 110 CE,VDE,EAC,CN ROHS,WEEE DCast iron EN-GJL-200 ASTM A48-200B PES 30%GF0 .. 40 °C 10 bar G 1 1/2" PN 10 180 mmVann -10 .. 110 °C 20 °C 998.2 kg/m³ 1 mm²/s9 .. 84 W 50 / 60 Hz 1 x 230 V 0.09 .. 0.75 A X4D F0.18 5.11 kg 5.75 kg 0.015 m³ 380790060 5732572 4615541 9042326 DE 84137030Utskrift fra Grundfos Product Center [2021.21.005]Firmanavn: Grundfos Laget av: Telefon:Aleksander StortjønnliDato:23.08.2021H [kPa]MAGNA3 25-60, Modell D7065Q = 0.38 l/s H = 50 kPa n = 89 % / 3115 rpm Pumpemedie = Vann Væsketemperatur under drift = 20 °C Massetetthet = 998.2 kg/m³605550454035302520151050Eta pumpe+motor+frekvensomf. = 37 %00,2 0,4 0,6 0,8 1,0 1,2 1,4 1,6 1,8 2,0 2,2 2,4 2,6Q [l/s]P1 [W]80706050403020100P1 (motor+frekv.omf) = 51.36 W1111.554239185901135 20 9 10 8 18 5 18 56971Example of plug-connected motor with mains switch, backup fuse and additional protectionLLRCD/RCCB