Title: Data tester Smestad skole - Detaljert.pdf
Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 21,3 11,0 10,3 459,00Remote: 45-36 21,5 11,0 10,5 459,00Worst Value: Local: 36-45 21,3 10,9 10,4 462,00Remote: 45-36 21,5 11,0 10,5 459,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 30,4 27,0 3,4 402,00Remote: 36 29,0 23,8 5,2 500,00Worst Value: Local: 36 27,5 23,8 3,7 497,00Remote: 36 29,0 23,8 5,2 500,00PS-ACRF: Pass Worst Margin: Local: 45 19,4 8,0 11,4 459,00Worst Value: Local: 45 19,4 8,0 11,4 459,00Remote: 12 72,3 61,2 11,1 1,00Remote: 36 19,9 7,9 12,0 461,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:57Signature:______________________ Page: 22Copper Certification Report