Title: økernvn 94.pdf
MAIN 36-45 7.5 246.0 5.1 36 7.3 250.0 2.0SR 36-78 13.5 247.0 5.0 36 15.1 246.5 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.7 10.5 20.9SR 45 3.8 10.4 20.9MAIN 36 7.8 171.0 11.7SR 36 4.9 198.0 11.006050050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94