Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
AC120KN4DKHAC140KN4DKHC2613453453453457360_AirCon_Indoor_IM_ENG_EN.indb 72016-05-16 오후 5:32:11I n s t a l l a t i o n P r o c e d u r eEnglishInstallation ProcedureCAUTIONNOTEThe indoor unit must be installed according to the specified distances in order to permit accessibility from each side, to guarantee correct operation, maintenance, and repair of the unit. The components of the indoor unit must be reachable and removable under safe conditions for people and the unit.Do not hold the discharge while carrying the indoorA: Reference for the outer circumference of the unit(When insulating the body of the indoor unit, use A as the reference for its outer circumference.)Indoor unit type and modelsDimensions360 cassette type <S> (947 x 947 x 281)AC071KN4DKH2610 × 130unit to avoid the possibility of breakage.You must hold the hanger plate on the corner andAC090KN4DKHcarry the indoor unit.360 cassette type <L> (947 x 947 x 365)AC100KN4DKH2610 × 215