Title: +038=249.001-#####._01-10203518-01-RIA-NOT-007 Lydmålinger Collier_rev01.pdf
09.02.2022Signature:HGA10203518-RIA-NOT-00722. februar 2022 / Revisjon 00Side 22 av 30Dronning Mauds gate 1-3multiconsult.noKontrollmålinger av lydisolasjon plan 5, akse 0-8Vedlegg 2.14Apparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation betw een roomsClient: Desc ription:Dronning Maugs gt. 1- 3 Lydisolasjon fra møterom 5- 123 til telefonrom 5- 211Date of test:09.02.2022Object:Telefonrom (gipsvegg)Source room: 5- 123Receiving room: 5- 211Condition:Condition:Type:Type:Location:Location:Frequency range ac cording to theArea of common partition:10,00m²curve of shifted reference values (ISO 717- 1)Source room volume:Receiving room volume:7m³→ ⎯ B d65FrequencyR'f1/3 octave'R[Hz]50[dB]29,1, x e d ni55638010012516020025025,824,128,537,641,042,843,3n o i t c u d e r d n u o s t n e r a p p A4531546,73540046,450050,3630