Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Connection for 0…20 mA or 4…20 mA (selectable with jumpers on type PCD3.W410)DAVOLTAGE CONTROLLED CURRENT SOURCE4 (A2)5I+ 24 VDCAn external 24 VDC sup- ply is required for current outputs.R = 0...500 Ω6-80PCD3.W4x0Block diagramDATA0DAs u BWRITEADDRs u BO/ I123DDDAAAVJUMPER J2D C PReference VoltageVOLTAGE CONTROLLED CURRENT SOURCECVC9876543210A3A2A1A024 VDCProgrammingProgramming examples for the PCD3.W4x0 can be found in a separate manual and on the TCS Support site www.sbc-support.com.xx7 and RIOs: the firmware reads in the values according to the configuration (I/O Builder or network configurator).Watchdog: This module can interact with the watchdog, if it is used on base address 240. In this case, the last input with address 255 cannot be used. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD3 components.6-81