Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]20.6 89 1 3.34Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.8 478.0 28.9 45 9.3 477.0 26.1SR 36-45 7.3 461.0 29.7 45 8.0 451.0 27.4MAIN 36-45 8.8 478.0 28.9 36 10.1 497.0 25.1SR 36-45 8.8 500.0 27.8 45 9.3 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.2 4.1 52.9 45 14.9 3.8 50.8SR 45-78 16.2 4.3 52.7 45 15.0 9.8 42.5MAIN 36-45 17.1 476.0 11.7 45 18.3 497.0 8.3SR 45-36 17.2 476.0 11.7 45 18.4 500.0 8.30100806040200250 MHzACR-F (dB)