Title: ledmaster-lm5_cn.pdf
Autronica Fire and Security AS | Tlf.: +47 90 90 55 00 | E-post: info@autronicafire.no | www.autronicafire.no | Side 2LED-MASTER LM5) Avstand vegg til ledelys1 lxBelysning av rømningsveier iht. EN 1838 4.2.1Høyde h [m]a1 [m] EVG / 1h & 3h / 8ht* = 1ma2 [m] EVG / 1h & 3h / 8ht* = 1,5ma1 [m] EVG / 1h & 3h / 8ha2 [m] EVG / 1h & 3h / 8ha1 [m] EVG / 1h & 3h / 8ht* = 2ma2 [m] EVG / 1h & 3h / 8h1.001.75 / 1.50 / 1.254.75 / 4.25 / 3.501.50 / 1.25 / 1.004.50 / 3.75 / 3.001.25 / 1.00 / 1.004.00 / 3.25 / 3.751.502.80 / 2.50 / 2.007.00 / 6.25 / 5.252.50 / 2.25 / 1.756.75 / 6.25 / 5.002.50 / 2.00 / 1.506.50 / 5.75 / 4.752.003.00 / 2.75 / 2.257.75 / 7.00 / 5.753.00 / 2.50 / 2.007.75 / 6.75 / 5.752.80 / 2.50 / 1.807.50 / 6.75 / 5.502.503.25 / 2.75 / 2.258.50 / 7.50 / 6.253.25 / 2.75 / 2.008.50 / 7.50 / 6.003.00 / 2.50 / 1.758.25 / 7.25 / 5.753.003.50 / 3.00 / 2.259.00 / 8.00 / 6.503.50 / 3.00 / 2.259.00 / 7.75 / 6.25