Title: Hardware Installation Guide.pdf
476 — revision 6Note:In order to use this feature, the reader must be rev. LB. Previous revisions (C8, D, L, LA) of the LenelProx readers do not have this feature and cannot be upgraded.10. When installation is complete, insert screw-hole plugs into the screw clearance holes to conceal the screw heads. Screw-hole plugs are for one-time use. After they are seated, they cannot be removed without damaging the plugs.10. When installation is complete, insert screw-hole plugs into the screw clearance holes to conceal the screw heads. Screw-hole plugs are for one-time use. After they are seated, they cannot be removed without damaging the plugs.101.3.2SpecificationsCable to Controller - -6 conductor (not twisted pair), stranded, 22 AWG, color-coded insulation, overall shielded Length: up to 500 feetRead Range (metal compensated) - -5 VDC: typically 6 inches (15 cm) 12 VDC: typically 8 inches (20 cm)