Title: Hardware Installation Guide.pdf
2. Wire the upstream host communication.3. Wire the downstream device communication.4. Wire the power input.5. Remove the plastic safety strip from the memory backup battery.19.1Wiring19.1.1Unsupervised Alarm Inputs: Power Fault and Cabinet Tamper MonitorsThe LNL-2000 features two alarm inputs that can be used for power fault and cabinet tamper monitoring. These inputs are connected using the Input 2 (IN2) and Input 1 (IN1) contact terminals on the ISC board.Input 2 and Input 1 are both simple N/C (normally closed) contact closure monitors.Note:If either of these inputs is not used, a shorting wire should be installed.Unsupervised Alarm Input WiringCABINET TAMPERGNDIN 2POWER FAULTGNDIN 119.1.2Upstream Host Communication