Title: +038=360.000-LC007T_06-Coadis line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
Option of deactivating a heater on site by removing a shunt from the terminal block, to reduce the electrical power.COADIS LINE 600Condensate drain panSingle unit main pan in highdensity sealed PSE for use in all climates, naturally sloped and removable from below without the need to open the suspended ceiling.Fire rating: M1.ABS PC auxiliary pan with no water retention provided as an accessory for the recovery of condensates from the valves and coming from the main pan.Gravity drain: height 70 mm.Drainage bushing: external @ 15 to 20 mm.Fan motor assembly= HEE motorHigh energy efficiency motor enabling a reduction of upto 85% in electricity consumption.BLAC (Brushless Alternating Current) brushless technology offering more linear torque progression and a lower operating sound level than BLDC (Brushless Direct Current) technology.Sealed, tropicalised, with protected shaft.3speed gradual operation by 010V or on/off control signal, without expansion board.Ball bearings