Title: 36 Siemens GDB181-MO.pdf.pdf
VminRW%0.0120..100387VmaxRW%0.010..120388Altitude LevelRWm10..5000389Unit SwitchRW----0 = m3/h1 = l/s513Backup ModeRW----0 = Go to BackupPosition1 = Keep last position2 = Disabled514Backup PositionRW%0.010..100515Backup TimeoutRWs10..65535764Modbus AddressRW----1..247 / 255 = “unassigned”765BaudrateRW----0 = auto / 1 = 9600 / 2 = 19200 3 = 38400 / 4 = 57600 / 5 = 76800 6 = 115200766Transmission FormatRW----0 = 1-8-E-1 / 1 = 1-8-O-12 = 1-8-N-1 / 3 = 1-8-N-2767Bus TerminationRW----0 = Off / 1 = On768Bus Conf. Command----0 = Ready / 1 = Load / 2 = Discard769StatusR----See below33 / 40VAV Compact Controller Modbus RTUA6V10631862_en--_d 2019-09-13Register “Status”Supported function codes34 / 40Siemens Smart InfrastructureReg.NameR/WValueExampleDevice information1281Factory Index