Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Flatwise with side incomer:Edgewise with centre incomer:Flatwise with centre incomerFlatwise with side incomer for Canalis KTA5000/KTC6300NOTE: Dry-type transformers can be connected to Canalis KTA5000 and KTC6300 only flatwise with side incomer arrangement or edgewise with center incomer arrangement.ProcedureThe procedure for connecting dry-type transformers is described in instruction sheets available on the Schneider Electric website:  For connecting Canalis KTA1000-4000/KTC1350-5000 to dry-type transformers: AAV32054.  For connecting Canalis KTA5000/KTC6300 to dry-type transformers flatwise: PHA44575.  For connecting Canalis KTA5000/KTC6300 to dry-type transformers edgewise: PHA44576.StepAction1Install the end feed unit with its supports (seepage41).2Check that the weight of the components does not rest on the transformer (seepage22).3Check the phase order of the run components in the installation, the end feed unit, and the transformer (seepage15).4