Title: +038=433.002-FS031._02-Eaton Tavlebyggeren Produktblad.pdf
10.12 Electromagnetic compatibilityIs the panel builder's responsibility. The speciﬁcations for the switchgear must be observed.10.13 Mechanical functionThe device meets the requirements, provided the information in the instruction leaﬂet (IL) is observed.Technical data ETIM 7.0 Circuit breakers and fuses (EG000020) / Miniature circuit breaker (MCB) (EC000042)Electric engineering, automation, process control engineering / Electrical installation, device / Miniature circuit breaker system (MCB) / Miniature circuit breaker (MCB) (ecl@ss10.0.1-27-14-19-01 [AAB905014])Release characteristicCNumber of poles (total)4Number of protected poles4Rated currentA25Rated voltageV400Rated insulation voltage UiV440Rated impulse withstand voltage UimpkV4Rated short-circuit breaking capacity Icn EN 60898 at 230 VkA10Rated short-circuit breaking capacity Icn EN 60898 at 400 VkA10Rated short-circuit breaking capacity Icu IEC 60947-2 at 230 VkA15