Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Connection terminal for port A[D]Port-BConnection terminal for port B[F]Holes for the grounding bar screws[E]12VTerminals for the power supply to the RS485/fiber converter[G]CAN drive connector (opposite)IFMNET LEDColourOn solidFlashingCANBlueActivity on the CAN communication BUSRXAGreenData reception activity on port ATXARedTransmission activity on port ARXBGreenData reception activity on port BTXBRedTransmission activity on port BIFMNET module - technical specificationsPower supply voltage19-30 Vsupplied by IFM24160 moduleOperating temperaturefrom -5°C to +40°CConsumption @ 27.6V60mAMaximum voltage on OUT 12V0.8A for use inside the cabinet3.12IFM4R, internal module with 4 relaysThe IFM4R module provides 4 relay outputs with voltage-free contacts (Common, Normally Open and Normally Closed). The activation mode of each relay can be defined during the system configuration phase using the configuration software.