Title: DOCA0005EN-12.pdf
See “Device object” on page 109 for information on the proprietary properties in the Device object.See “Device object” on page 109 for information on the proprietary properties in the Device object.DOCA0005EN-12BACnet communications implementationConfiguring basic communication parametersBefore communicating with the meter via BACnet protocol, use the front panel to configure the following settings:SettingPossible values960019200Baud rate384005760076800Mac Address1 - 127Device ID0 - 4194303Make sure that the Mac Address is unique on the serial loop and the Device ID is unique in your BACnet network.Communications LED indicator for BACnet metersThe LED indicates the status of the meter’s communications with the network.LED stateDescriptionThe LED is offCommunication is not active.The LED is flashingCommunication is active.NOTE: The LED flashes even if there is a communications error.Change of Value (COV) subscriptions