Title: DOCA0005EN-12.pdf
Firmware_RevisionR—variesBACnet firmware version, stored in an x.x.x format (for example, 1.7.2).Application_Software _VersionR—variesMeter firmware version, stored in an x.x.xxx format (for example, 1.0.305).DescriptionR/W √configurableOptional description of the meter, limited to 64 characters.LocationR/W √configurableOptional description of the meter’s location, limited to 64 characters.Protocol_VersionR—variesBACnet protocol version (for example, version 1)Protocol_RevisionR—variesBACnet protocol revision (for example, revision 6)Protocol_Services_S upportedR—0000 0100 0000 1011 0100 0000 0000 0000 0110 0000The BACnet services supported by the meter: subscribeCOV, readProperty, readPropertyMultiple, writeProperty, deviceCommunicationControl, who- HAS, who-IsProtocol_Object_Typ es_SupportedR—1011 0000 1000 0000 0000 0000 0000 0000The BACnet object types supported by the meter: analog input, analog value, binary input, device