Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
50/60 ± 0.05 %Overload – Normal Mode (@ 25°C)10 m 1 m 10 s 100 mskW105 to 125 125 to 150 > 150 > 170Overload – Battery Mode (@25°C)2 m 30 s 100 mskW105 to 125 125 to 150 > 150Crest Factor3:1Voltage distortion< 5 % Non Linear Load; < 2 % Linear LoadElectrical Specificationsn - BatteryTypeSealed lead acid maintenance free-expected life 3/5 yearsVoltage240 VBUT> 5 min> 4 minCharger4 A4 AEnviromentOperating temperature°C0 to 40 °C 1Relative humidity%0 to 95 % No CondensingMax. altitudem< 1000 m without deratingAcoustic noisedBA50 dB at front 1 m55 dB at front 1 mStandardsSafetyEN 62040-1, EN 60950-1EMCEN 62040-2 C3Product CertificationCEProtection LevelIP20Mechanical Characteristics with standard batteriesDimensions (W x D x H)mm428 x 970 x 720Weightkg7325,58429,51. 15-25 °C for a longer battery life.ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0037H S I L G N EIN WESTERN EUROPE