Title: økernvn 94.pdf
20100002550 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 7.4Cable ID: D4008 Date / Time: 09/10/2013 01:11:34 Headroom 16.7 dB (NEXT 36-78) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 45]142 218 9 9.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-78 18.6 80.8 33.8 12 19.6 74.0 31.5SR 36-78 16.7 29.0 41.1 78 17.0 92.5 29.9MAIN 12-78 19.2 94.8 32.7 78 19.8 97.3 29.5SR 36-78 16.9 92.8 32.8 78 17.0 92.5 29.91008060