Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Time saved in electrical wiring: Due to plug-in screw terminals, spring terminals or ready-made cables and ribbon cable adapters.I/O modules and I/O terminal blocks may only be plugged in and removed when the PCD and the external +24 V are disconnected from the power supply.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-2566-44Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.G4006.7.1 PCD2.G400, multi-functional input/output moduleApplicationCombined module with digital and analogue inputs and outputs. This module is designed to extend the range of uses for the PCD. The functions and the technical specification are based on the existing PCD2 modules.The technical details should be taken from the descriptions of these modules.Number and type of inputs/outputs10 digital inputs, E0…E9 (addresses 0…9)Technical data as for PCD2.E110, but without the option of sink operation option, i.e. no “L” connection.