Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
In case of abnormal temperature measurement results, check all the connections using a torque wrench. The torque for the joint block bolts should be 60 N•m (+/- 10%). If these values decrease significantly over time, consult Schneider Electric. If needed, the concerned material must be replaced with new factory-mounted products. Consult yourlocal Schneider Electric office for all replacements. Before re-energizing the busbar trunking system, carry out an insulation test as described in thecommissioning section (seepage68). After having performed all the necessary inspections and repairs mentioned above, it may be desirableto carry out infrared temperature measurements on all the electrical connections.74QGH3492101-01 11/2018QGH3492101-01 11/2018Canalis KTQGH3492101-01 11/2018Appendices7576QGH3492101-01 11/2018Canalis KTRelated documentsQGH3492101-01 11/2018Related DocumentsAppendix A Related DocumentsList of Instruction Sheets