Title: bn305_cgb.pdf
S1.6 ONThe output can be set to Normal Open or Normal Closed operation by DIP switch 1.7:Figure 1DIP 1.7 OFF = Normally open • DIP 1.7 ON = Normally closedDIP switch 1.8 determines the state of output if the unit loses its power.DIP 1.8 OFF = Relay remains in current state • DIP 1.8 ON = Relay switches to initial state as chosen by DIP 1.7DIP 1.8 OFF = Relay remains in current state • DIP 1.8 ON = Relay switches to initial state as chosen by DIP 1.7Autronica Fire and Security AS | Tel.: +47 90 90 55 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 4Dual Monitored Input/Output Unit – BN-305Descriptions of Function OptionsFunction CON OFFS1.1 OFFS1.2 ONS1.3 OFFS1.4 OFF1 2 3 4 5 6 7 8Function: Fault condition signalling input unit with feedback function.(See location of DIP switch S1 on the circuit board drawing)The relay contact will follow the state of the input.Function ANumber of addresses: 2S1.1 OFFS1.2 OFFS1.3 OFFS1.4 OFF