Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Each connection to these terminals must be completed following the instructions in paragraph 5.5.1.Cables:2 wire shielded cable Proper section (minimum 0.5mm², maximum 2.5 mm²) Compliant with local laws and regulations in forceNote:In order to comply with EN12094-1 standard requirement, if more than one extinction channel is managed by a single Previdia Max panel (more than one IFMEXT module installed on a single panel) a backup FPMCPU unit have to be installed in the system, this backup unit will provide the disablement function for each extinction channel also in the unlikely event of main FPMCPU system fault.Connection of Input terminals