Title: Installasjonsmanualer.pdf
Relay contacts can be set individually for NO (default) or NC operation, and programmed selectively for customized monitoring of the UPS.If requested, the UPS can also be switched off utilizing a remote external shutdown contact. The command is acknowledged when the contact is made and held for 3 seconds (default), whereas the external contact must be made between the common and input pins.The external contact MUST be dedicated and voltage-free, so as not to cause permanent damage to the UPS.The shutdown input can be configured alternatively as a battery test input.22 NETYS RT 1.1-3.3 kVA - Ref.: IOMNETRTXX0B-EN 0110.6.1 Internal circuit10.6.1-1+5VCPU Pin10.6.1-310.6.2 Standard conﬁ gurationSW1SW2OFFOFFONOFFCommonR1R2R3R4R5R6GND-RInputrelay contactNONCX X - T R T E N W R D 8 5 010. COMMUNICATION10.6.1-2R1 General alarmR2 No mainsR3 Battery lowR4 On by-passR5 OverloadR6 OvertemperatureGND-R