Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 45-78 18.0 493.0 11.4 45 19.1 496.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 29.3 122.5 20.8 45 30.1 117.5 19.0SR 36-45 31.7 112.5 22.3 12 33.0 127.0 17.6MAIN 36-45 40.4 493.0 -11.9 36 41.1 500.0 -15.3SR 36-45 38.3 493.0 -11.9 36 39.0 493.0 -14.80804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.2 493.0 8.0SR 12 4.9 493.0 8.0MAIN 12 6.2 493.0 8.0SR 12 4.9 493.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00420.6 m60Insertion Loss (dB)504030201000250 MHz