Title: 1 etg del 2.pdf
Cable ID: D1116 Date / Time: 10/17/2013 12:33:40 PM Headroom 13.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]211 334 23 9.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.1 62.0 35.7 12 16.8 96.3 29.6SR 12-36 13.9 93.3 32.8 36 14.9 93.0 29.8MAIN 12-36 15.4 96.3 32.6 12 16.8 96.3 29.6SR 12-36 13.9 93.3 32.8 36 14.9 93.0 29.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.9 50.3 24.6 36 25.5 4.8 42.1