Title: 1 etg del 2.pdf
Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 5 10/25/2013 07:31:39 AM økernveien 2410.flw48321 ft 278 278 0 0 0Cable ID: T1062 Date / Time: 10/17/2013 03:23:20 PM Headroom 1.0 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]222 353 26 9.5222 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.0 250.0 30.750403020Worst Case Margin Worst Case Value10