Title: +038=433.000-NI003._15-Testrapport elektrike anlegg - DM3.E1=433.06.01, Ryggsekk plan 06 (Working Copy).pdf
DM1-3. Plan 6 / DM3.E1=433.06.01 / XF012 16C2/003 30.11.2020 09:27SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.1Hz66DM1-3. Plan 6 / DM3.E1=433.06.01 / XF013 16C2/003 30.11.2020 12:25 (ELEKTRIKER)Tallberg Elektro A/S Tlf.22796640Side:1Rapport opprettet27.12.2020GODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.77889910101111TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM3.E1=433.06.01 / XF013 16C2/003 30.11.2020 11:35SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM3.E1=433.06.01 / XF014 16C2/003 30.11.2020 12:28 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM3.E1=433.06.01 / XF014 16C2/003 30.11.2020 10:48SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0Hz