Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
on plant installation.All cables for connection to the unit, as well as its accessories, must be H05 VV-F with PCV insulation in compliance with EN 6033-2-40.All cables for connection to the unit, as well as its accessories, must be H05 VV-F with PCV insulation in compliance with EN 6033-2-40.Disconnect all circuits from power supply before acting on energized components.Disconnect all circuits from power supply before acting on energized components.Make earthing before any other electric connections.In compliance with the installation instructions, the contact opening of all disconnecting devices (4 mm) must allow full disconnection under the conditions of overvoltage class III (earthing) according Connect power supply L (line), N (neutral) and to the wiring diagram and respect the polarities shown on the bottom of the electrical boxes, see fig. 36-38-39-40.