Title: 360.002 - Avtrekk.pdf
0.0 +24.336.529.07.50.0 +24.324.424.40.2 +16.224.8+0.024.80.1 +16.225.425.48k [dB]21.60.1 +17.322.9+32.633.10.0 +17.333.218.015.20.0 +17.319.419.40.2 +9.219.6+0.019.60.1 +9.220.020.0Lp [dB]34,7LocationLevel3. etasje3. etasje3. etasje3. etasjeTeknisk etasjeTeknisk etasje1. Etasje1. Etasje3. etasje3. etasjeNodeTypeDUCTBEND-90DUCTBEND-90DUCTBEND-90DUCTDUCT4 TAPDUCTProductSize900x800LBR_SE-*-*-*-*-* 900x800800x800LBR_SE-*-*-*-*-* 800x800700x800LBR_SE-*-*-*-*-* 800x700800x700800x700MAGIO-RC-*500500L [m]1,76,80,30,70,70,2Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]108804,20,3 Sound in:Attenuation: Addition:108804,211,2 Sound in:Attenuation: Addition:108804,71,9 Sound in:Attenuation: Addition:108804,713,9 Sound in:Attenuation: Addition:108805,40,1 Sound in:Attenuation: Addition:108805,415,3 Sound in: