Title: +038=744.004-UN003T_02-Montering og vedlikehold av Teknoware armaturer Nortek FDV.pdf
Make sure that each luminaire in the same circuit has a different address.DIP 5 OFF: ADDRESSES 1-16 (1-16 LO) DIP 5 ON: ADDRESSES 17-32 (17-32 HI) DIP 6 OFF: MAINTAINED LUMINAIRE DIP 6 ON: NON-MAINTAINED LUMINAIRE / LOCAL CONTROLLER MODE (See image 1)Battery/Super Capacitor disconnected Duration test and light source fault 1Hz OFF Test in progressON2Hz1Hz1Hz1Hz = Slow blinking (about once / second) 2Hz = Fast blinking (about twice / second)PERIODICAL CHECKS AND MAINTENANCE The operation and condition of the luminaires must be verified according to local laws and regulations. For example, the European EN 50172 standard instructs, that:  the operation of the emergency lighting system in battery mode is to be tested briefly monthly, and, at the same time, the emergency mode of each luminaire is tested monthly, by switching the luminaire to battery feed, and the visibility, cleanliness and function of the luminaires is inspected