Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
12 LG 360 13 LG 390 14 LG 450 15 LG 480 16 LG 520 17 LG 60050012345678Water flow rate, l/s91011 12 12 13 14 1513 16 1728Water chillersHeat pumpDYNACIAT LGHydraulic specifications ■ Available static system pressure Units with hydraulic module (single variable and fixed-speed (*) high pressure pump)Data applicable for: - Pure water at 20°C - Refer to the section "Evaporator water flow rate"’ for the water flow rate values (*) Sizes 360 to 600 only■ CondenserDYNACIAT LG, sizes 080-150180170160150a P k140, d a e h130120e r u s s e r P110100901 LG 080 2 LG 090-100 3 LG 120 4 LG 130 5 LG 150807060500,00,51,01,52,02,53,03,54,0 34,5 4 512Water flow rate, l/sDYNACIAT LG, sizes 180-300220210200190180a P k170160, d a e h150140e r u s s e r P1301201101007 LG 180 8 LG 200 9 LG 240 10 LG 260 11 LG 3009080706050012345678 9 10 117Water flow rate, l/s