Title: 2 etg del2.pdf
SR 12-36 5.4 230.0 6.7 36 4.9 229.5 4.1MAIN 36-45 5.0 250.0 4.7 36 4.8 250.0 2.0SR 36-45 5.4 247.5 4.9 36 5.1 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.8 4.8 21.0SR 45 3.8 4.8 21.0MAIN 45 8.2 226.0 10.5SR 36 8.2 249.0 10.0010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94