Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
OBJEKT / Plan 10 / FUSE044 06.02.2020 08:36R LOW OhmR: 0.50ΩR+: 0.5Ω R-: 0.5Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE045 06.02.2020 14:36Z-LINEZ: 1.35ΩIsc: 171A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE045 06.02.2020 14:37Zs(rcd)Z: 1.15ΩIsc: 200A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE045 06.02.2020 14:39RCD II: 28.5mAUci: 0.2V t: 84.0ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE045 07.02.2020 12:57SPÆNDINGUln: 228V Ulpe: 231V Unpe: 3V f: 50.0HzOBJEKT / Plan 10 / FUSE045 07.02.2020 13:00TEST RAPPORTSide:17MISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESMISLYKKESNr.106106107107108108109109110110111111ResultatZs(rcd)Z: 1.57ΩIsc: 146A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE045 07.02.2020 13:01RCD II: 28.5mA