Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
31.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.0 473.0 29.1 36 7.5 466.0 26.6SR 36-45 7.6 461.0 29.7 36 7.5 466.0 26.6MAIN 36-45 8.5 496.0 28.0 36 8.7 500.0 25.0SR 36-45 8.5 496.0 28.0 36 8.6 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.8 5.9 49.9 45 18.2 82.0 24.0SR 78-45 17.8 5.9 49.9 45 18.1 18.1 37.1MAIN 78-45 18.1 500.0 11.3 78 19.8 500.0 8.3SR 45-78 18.8 500.0 11.3 36 19.9 481.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 29.8 140.5 18.4 36 31.0 110.5 20.0SR 12-36 27.2 107.5 23.0 36 26.6 108.0 20.4MAIN 36-45 38.8 496.0 -12.1 36 39.6 500.0 -15.3SR 36-45 38.8 496.0 -12.1 36 39.4 496.0 -15.00804000250 MHzACR-N (dB)