Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,3 26,7 2,6 500,00Remote: 36-45 29,2 26,7 2,5 500,00Worst Value: Local: 36-45 29,3 26,7 2,6 500,00Remote: 36-45 29,2 26,7 2,5 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,8 10,4 10,4 487,00Remote: 45-12 68,3 57,3 11,0 2,20Worst Value: Local: 12-45 20,8 10,4 10,4 487,00Remote: 45-12 21,5 10,4 11,1 487,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,9 24,1 3,8 489,00Remote: 45 28,1 23,8 4,3 500,00Worst Value: Local: 36 27,8 23,8 4,0 500,00Remote: 45 28,1 23,8 4,3 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,4 61,2 11,2 1,00Worst Value: Local: 45 20,0 7,4 12,6 490,00Remote: 45 71,1 61,2 9,9 1,00