Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 12:36Zs(rcd)Z: 0.46ΩIsc: 495A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 12:37Tallberg Elektro A/S Tlf.22796640Side:2GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.1515161617171818191920202121TEST RAPPORTResultatRCD II: 28.5mAUci: 0.0V t: 104.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 12:37RCD UbUc: 0.1V Rl: 4Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 12:37RCD tt: 68.1msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 12.06.2020 12:31R LOW OhmR: 0.04ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 12.06.2020 12:34KONTINUITET R: 0.1ΩGrenseverdi: 1.0Ω