Title: V20-08-02 VVS-anlegg plan 8 - DM3.pdf
310.302 VVC: Cu 22mm 310.202 VV: Cu 28mm 310.102 KV: Cu 35mm 320.101, tur: 54mm 320.101, retur: 54mmSZ001T Ø400SK001T Ø315 Q:1050 m³/hFordelerstokkTeknisk rom ventileres med +/- 50m³/h. Kanalstuss, irispjeld og rist tilpasses.ø200 UK=3370SZ001T Ø125ø125 UK=3465SF002T-125SZ001T Ø125SK001T Ø200 Q:480 m³/hSF002T-200SF002T-200SF002T-200SF002T-200SF002T-160ø160 UK=3290ø200 UK=3250ø200 UK=3250WISE RTA WISE IAQWISE RTA WISE IAQKontor 8-123Møterom 8-122LD018T Maks:230 m³/h Kjøling: 310 W 0.025 L/s Varme: 555 W 0.013 L/sSTAD Dim:10/09 StengtLD021T Maks:200 m³/h Kjøling: 470 W 0.037 L/sLD018T Maks:200 m³/h Kjøling: 470 W 0.037 L/s Varme: 555 W 0.013 L/s6SZ002T 400 x1100Opp 310.001: 75Snitt 31000x500 UK=303Opp/Ned310.002: 75 UK = 3431Ned 370.101: DN 100 Opp, DN65Ned 370.101: DN 1007STAP/STAD DN 20Opp, DN65Opp+08 = 370.101 - OE 082 0.188 L/sLD018T Maks:220 m³/h Kjøling: 420 W 0.033 L/s Varme: 480 W 0.012 L/s