Title: Aggregatkjøring.pdf.pdf
installation according to 60204-1The supply unit consist ofDamperPressure drop2PaDamper bladesStandardActuator force21NmNumber of shafts1Empty sectionPressure drop2PaLength100mmSystemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.002-3/Unit no. 20Date 18.06.2021Page 30/40FilterDimensioning pressure drop101PaInitial pressure drop/Final pressure drop51/151PaVelocity, face area1.98m/sVelocity, filter area0.12m/sFilter classF7 - ePM1 60%Filter size6x[592x490x25] + 2x[287x490x25]Filter length520mmFilter descriptionCamfil Hi-Flo II XLTRotary heat exchangerSupplyExtractAir flow1440014400m³/hPressure drop156156PaAir temperature before/after25.0/13.722.0/-16.7°CAir relative humidity before/after