Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]34.6 150 2 5.22Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.9 478.0 29.7 36 7.6 481.0 26.8SR 12-36 7.9 496.0 29.3 36 7.8 498.0 26.4MAIN 12-36 8.2 498.0 29.3 36 7.7 498.0 26.4SR 12-36 7.9 496.0 29.3 36 7.8 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.7 6.0 49.7 45 19.5 500.0 8.3SR 45-78 18.7 6.0 49.7 45 20.2 498.0 8.3MAIN 45-78 19.4 497.0 11.3 45 19.5 500.0 8.3