Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]24.1 104 1 3.81Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.6 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.9 462.0 29.6 45 9.3 461.0 26.9SR 36-78 8.7 427.0 30.7 36 8.4 452.0 27.3MAIN 36-45 10.0 495.0 28.1 36 9.9 496.0 25.2SR 36-78 9.2 482.0 28.7 36 9.4 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.6 3.5 54.4 45 13.7 2.4 54.7SR 45-78 14.6 3.5 54.4 45 13.8 2.6 53.9MAIN 78-45 15.1 499.0 11.3 45 16.7 500.0 8.3SR 45-78 15.2 499.0 11.3 78 17.1 499.0 8.30100806040200250 MHzACR-F (dB)