Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
MERCOR SA – The company reserves the right to make modifications and changes14/21mcr WIP multi-plane fire dampersTechnical dataSupply power requirement: -during movement -during sustaining sizing (apparent power) protection class protection degree rotation angle fire damper position movement time: -travel between limit positionsBE24, BE24-12-ST AC 24 V 50/60Hz / DC 24VBE230 , BE230-12 AC 230V 50/60 Hz12 W 0.5 W 18 VA III8 W 0.5 W 15 VA IIIP 54 100(cid:176) (-5(cid:176) ...+95(cid:176) ) Shaped connector 12 mm or 14mm< 60 s for 90°Operating temperature range sound intensity level: -30 ...+50(cid:176) C ~ 62 dB (A)SupplyTechnical dataBLE24 AC 24 V 50/60Hz / DC 24VBLE 230 AC 230V 50/60 Hzpower requirement: -during movement -during sustaining sizing (apparent power) protection class protection degree rotation angle fire damper position movement time: -travel between limit positionsIII4 W 0,5 W10 VA