Title: 1 etg del 2.pdf
100ACR-N @ Remote (dB)806040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 8.1Cable ID: T1011 Date / Time: 10/21/2013 12:45:07 PM Headroom 5.9 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]144 219 7 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]17.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-78 7.7 182.5 37.6 12 7.2 244.5 32.9SR 36-78 5.9 247.5 35.4 12 7.6 197.5 34.4MAIN 12-78 7.7 244.5 35.5 12 7.2 244.5 32.9SR 36-78 5.9 247.5 35.4 78 7.8 247.0 32.81008060