Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The procedure for installing Canalis KTA5000/KTC6300 run component is described in the instruction sheet PHA33884, available on the Schneider Electric website.QGH3492101-01 11/201829Supports and Run ComponentsInstallation of Joint BlocksIntroductionOnce the two run components have been installed on the horizontal and vertical supports and aligned, you can install the joint block.The joint block provides the following:  Electrical junction between live conductors and between PE protective earth conductors.  Mechanical link between two run components or sections. It provides simultaneous continuity betweenall the conductors.ProcedureThe procedure for installing the joint block is described in the instruction sheet AAV32038, available on the Schneider Electric website.StepAction1Install the bottom cover under the aligned conductors of the two run components. Hand tighten the fixing screws.2Insert the joint block carefully between the two run components.3