Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
SR 45-78 17.4 350.0 14.4 45 19.4 402.0 10.2MAIN 78-45 17.9 395.0 13.3 45 19.4 408.0 10.0SR 45-78 17.9 395.0 13.3 45 19.5 403.0 10.10100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.6 27.8 41.7 45 19.6 27.8 39.3SR 36-45 19.1 28.0 41.6 36 20.8 28.0 39.2MAIN 12-36 31.2 500.0 -12.4 36 30.0 500.0 -15.3SR 36-45 30.3 500.0 -12.4 36 30.5 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.3 476.0 8.0SR 45 9.1 496.0 8.0MAIN 45 7.3 476.0 8.0SR 45 9.1 496.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasjeTest Summary: PASS