Title: BRV59_434.001_Tavleskjema.pdf
Pumpe Magna3 40-150 320.004-JP401 608 W – 2,69 ABRV59 U016 434.001 US_021415161718XF54-6,3AI > I > I >135XK05246IO 1/B11 side 18Service- Bryter XS5Alarm KontaktUVWM 3 ~Turpumpe TP100 JP402 370.001 2,2 kW- 4,45 AByggautomasjonSide3av32ABCDEFGHIJKABCDEFGHJK12345L1L2L3NXF6XF710A10AIO 2 B1 side 22X114 1516 17Service- Bryter XS m/signal- kontaktService- Bryter XS m/signal- kontaktM 1 ~M 1 ~Impulsvifte U017 362.001 JV001 0,350KW 2,6AImpulsvifte U017 362.001 JV002 0,350KW 2,6ADokumentkode: Revisjon: Revisjonsdato: Utarbeidet av:<dok_kode> 04 28.09.2016 Fredrik Andresen6IO 2 B2 side 22Service- Bryter XS m/signal- kontakt7XF810A18 19M 1 ~Impulsvifte U017 362.001 JV003 0,350KW 2,6A8IO 2 B3 side 22Service- Bryter XS m/signal- kontakt9101112XF9XF1010A10AIO 2 B4 side 2220 2122 23