Title: Data tester Smestad skole - Detaljert.pdf
Limit 100,0 - 555,0 50,0 25,0Margin 49,0 - 291,0 36,0 16,3Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 1,90Worst Value: Local: 45 21,5 43,8 22,3 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 24,5 17,8 6,7 41,75Remote: 78 23,7 18,7 5,0 29,35Worst Value: Local: 78 15,4 8,0 7,4 474,00Remote: 12 15,0 8,0 7,0 453,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,4 26,7 2,7 500,00Remote: 36-45 30,3 26,7 3,6 499,00Worst Value: Local: 36-45 29,4 26,7 2,7 500,00Remote: 36-45 30,3 26,7 3,6 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):