Title: Operating instructions - K3G500PB3301.pdf
At the same time, the effective power in this operating state (operational readiness) is typically < 6 W.; Remove the cap from the cable gland.Only remove caps where cables are fed in.4.2.4 Residual current circuit breaker (RCCB); Equip the cable glands with the seals provided in the terminal box.; Route the wire(s) (not included in scope of delivery) into the terminalIf the use of a residual current device (RCD) is required in your installation, only AC/DC-sensitive residual current devices (type B or B+) are permissible. As with variable frequency drives, residual current devices cannot provide personal safety while operating the device. When the device power supply is switched on, pulsed charging currents from the capacitors in the integrated EMC filter can lead to the instant tripping of residual current devices. We recommend the use of residual current circuit breakers (RCCB) with a trip threshold of 300 mA and delayed tripping (super-resistant, characteristic K).box.