Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
Isc: 601A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ATallberg Elektro A/S Tlf.22796640Side:27GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTNr. 181181182182183183184184185185186186187187TEST RAPPORTResultatDM1-3. Plan 8 / DM3.E3=433.08.03 / XF049 16C2/003 19.11.2020 12:24Zs(rcd)Z: 0.32ΩIsc: 708A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF049 16C2/003 19.11.2020 12:25RCD II: 28.5mAUci: 0.2V t: 108.3ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF049 16C2/003 19.11.2020 10:51KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF050 16C2/003 06.11.2020 14:11R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF050 16C2/003 06.11.2020 10:56Z-LINEZ: 0.36Ω