Title: 10 Enea EM411R Modul 1 inn + 1 potri_eng DB.pdf.pdf
The module has a short-circuit isolator which, in the event of short-circuit between the two poles of the control panel loop cable, is capable of interrupting the negative pole and thus isolating the section involved in the short-circuit. For the isolator specification, please refer to the “ILP Specification” document.The module should be housed inside an electrical mounting box, as per the diagram, with the following characteristics: • Minimal internal dimensions: 100 x 60 x 40 mm • Protection grade IP44 or higher • Compliant with the established standards and codes relating to the Installation ofelectrical systemsThe two removable serial number stickers should be taken off the module; one should be attached to the box where the device is to be housed, the other to the installation layout.ATTENTION!Once all the loop devices have been properly connected, refer to the control panel installation and programming manual for instructions regarding the configuration and addressing procedures.