Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Connection of polarized devices (sounders, etc.) to the OUT outputsOUTOUT12121KOhm - 1W brown, black, red1KOhm - 1W brown, black, redThe polarities refer to the active status of the output, the polarities invert for stand-by status.EN54:If the control panel default settings are left unchanged, the OUT 1 output will result as being configured as a type C output for the connection of audible/visual signalling devices. The output will activate in the event of any type of fire-alarm condition.Connection of non-polarized devices (relays, etc.) to the OUT outputsOUTOUT12121KOhm - 1W brown, black, red1KOhm - 1W brown, black, red1N4007 diodes1N4007 diodesThe polarities refer to the active status of the output, the polarities invert for stand-by status.Connection of a generic device to the RELAY output27.6VOUTRELAY12123NCCNOThe OUT output illustrated in the diagram is used as a power source and is programmed as continuously active.