Title: +038=360.000-LC007T_06-Coadis line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
m An electrics box that is enclosed and of large dimensions, fitted with a DIN rail, will be able to accommodate and protect all the control components from dust. The safety of the electrical cables must be ensured using cable glands. The electrical and hydraulic feeds must both be on the same side to facilitate maintenance operations. In order to ensure reliability, the control will be factory-fitted (except for the room terminal) to eliminate any risks of leaks, for electrical safety and for the proper protection of components.Coanda effect cassettem The fresh air enters through a smooth metal sleeve (with no flow control) or via a self-adjusting collar and module assembly designed to supply the determined flow rate with a AP between 50 and 100 Pa.m Resilient mounts will be placed between the unit's mountings and the threaded rods to prevent any transmission of noise.m Guarantees