Title: +038=310.101-SC020T_02-FDV-dokumentasjon - Danfoss AS - VA_VVS 5640952 med flere - Danfoss spoler.pdf
40T50 / -40T122110 – 120±10%605.011042N4192AP024B40T50 / -40T12224±10%605.011042N4193Technical dataDesignIn accordance with VDE 0580Insulation of coil windingsClass H according to IEC 85ConnectionSpade connector in accordance with DIN 43650 form AEnclosure, IEC 529IP00 with spade connector, IP65 / NEMA 2 with cable plugDuty ratingContinuousPlug typeCable plug (042N0156)Dimensions and weightTypeL without cable plug [in]L with cable plug [in]L with protective cap [in]Weight [kg / lbs]AP1.892.832.520.10 / 0.220.631.302 2 . 1IC.PD.600.1A.02 | 17Cable plugy Enclosure: Up to IP65y For use with Danfoss coils type AL, AM, AS, AZ,BA, BB, BD, BN (Center boss), BQ, and BYy AC / DC all voltages up to 250 V y Approved in accordance with:- CSA - VDECable plug sizeDescriptionSuitable for coil typesCode no.DIN 18Cable plug according to DIN 43650-A PG 11