Title: økernvn 94.pdf
20100002550 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 7.4Cable ID: D4031 Date / Time: 09/10/2013 12:32:38 Headroom 13.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]152 240 16 6.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.4 88.8 33.2 12 15.4 88.8 30.2SR 36-45 20.0 26.0 41.8 36 21.2 90.3 30.0MAIN 12-36 13.7 93.3 32.8 36 15.9 99.5 29.3SR 36-45 20.3 99.3 32.4 36 21.2 90.3 30.01008060