Title: FDV-DOKUMENTASJON.pdf
L-PEL-PEMI 3101TEST REPORT02.09.2020 11:23 (459)Unpe: 0VEurotestAT11210309Metrel d.d18.09.2020Model:31.08.2020 12:53 (459)31.08.2020 12:53 (459)NPE41119 / U1Ser.No.:SYS.: TN/TT22INSULATIONINSULATIONINSULATIONO:41119 Vaxa propertyPhillip Pedersens vei 20Operator:Page:1VOLTAGEΩΩΩΩΩΩ::::R+: 0.1CONTINUITY31.08.2020 12:52 (459)Instrument's dataNoResultsUm: 514VRlpe: 536MUln: 238VProducer:R: 0.10IscMinLN: 449AZ: 0.35Isc: 513APASSPASSPASSPASSRlpe: >30.0M6R: 0.32R+: 0.1f: 50.04HzUlpe: 238Vtype:Elektro Nettverk Service asIscMinLN: 420AR-: 0.1Tripout time41119 / U1 / PLASS 241119 / U1 / PLASS 202.09.2020 09:27 (459)TRMSUiso: 500VPASS*PASS*Fuse Type: BFuse Type: BSYS.: ITUm: 536VIscStd: 703AIscStd: 661AR200mAFuse T: 0.4sFuse T: 0.4sIsc_lim: 160.0AIsc_lim: 160.0A77MUL.: x1IscMaxLN: 738ATEST REPORTZ-LINEZ-LINERCDUnpe: 0VNPE02.09.2020 11:24 (459)