Title: 2 etg del2.pdf
4020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 8.1Cable ID: D2104 Date / Time: 10/10/2013 01:37:24 PM Headroom 13.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]78 123 8 3.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.5 97.0 32.5 36 15.4 88.5 30.2SR 12-36 19.0 96.5 32.6 36 20.5 97.0 29.5MAIN 12-36 13.5 97.0 32.5 36 15.4 97.0 29.5SR 12-36 19.0 96.8 32.5 36 20.5 97.0 29.510080604020NEXT (dB)