Title: +135.01=564.007-XO001T_01-Montasje 5WG1_220_2DB31_bma_de_en_pille_norsk.pdf
Mounting General description The push button interface is built into in-wall boxes, ∅ 60 mm, depth 40 mm. In addition to the push button interface, a stand- ard device insert can be attached to the in-wall box. For mount- ing several conventional device inserts, several in-wall boxes must be combined via cable glands (only the in-wall box that holds the push button interface requires a depth of 40 mm). The cores of the eight-core cable set supplied with the device can be inserted in the series-connected in-wall boxes via the cable glands. Cable set The cable set consists of cores marked in specific colors with a plug fixed to one end. To allow for easy connection to the screw or plug-in terminals of switches and push buttons, ferrules are fixed to the free ends. Removing the bus terminal (Figure 3) - The bus terminal (B2) consists of two components (B2.1,B2.2) with four terminal contacts each.