Title: 1 etg del 2.pdf
100150200250MHz100ACR-N @ Remote (dB)806040200050100150200250MHz100RL @ Remote (dB)806040200050100150200250MHzLinkWare Version 8.1Cable ID: D1232 Date / Time: 10/17/2013 10:41:28 AM Headroom 6.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]61 93 3 2.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]24.2 246.5 30.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 7.1 188.5 37.4 78 7.2 194.0 34.5SR 12-36 6.1 211.0 36.5 36 6.5 211.0 33.9MAIN 36-78 7.8 243.0 35.5 78 7.9 249.5 32.7SR 36-78 6.1 227.0 36.0 36 6.5 211.0 33.9