Title: Ahlsell.pdf
Remote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 25050959.5 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 28 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/04/2022 07:04:28 AM Operator: Pam Headroom 8.8 dB (NEXT 3,6-7,8) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]9.5 47 1 2.3Wire Map (T568B) PASS