Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
2Define the position of the fire-barrier kit on the run component. The fire-barrier kit must be positioned more than 200 mm from any joint block (seepage66).3Install the fire-barrier kit around the run component. If the fire-barrier kit is installed around a run component with lateral reinforcement, then the components of the fire-barrier kit must be cut accordingly.4After installing the fire-barrier kit, use mortar or fire-resistant plaster to fill the gaps between its component parts. The material used to fill the gaps must meet the applicable requirements in force (for example, DIN 1045 and DIN 1053-1) to maintain the fire-resistance rating of the partition wall or floor slab.5Install the run component with the fire-barrier kit on supports, through the partition wall or floor slab. Do not place any support directly under the fire-barrier kit.6Install the KTA5000 and KTC6300 run components with two fire barrier kits, one for each run component (seepage66).7