Title: Kapasitetsmåler Mecon.pdf
Design / materialOrifice plate2"/ DN 50 - 4"/ DN 100Housing tube in Stainless steel with turned groovedconnection6"/ DN 150 - 8"/ DN 200Housing tube in Coated steel/optional in Stainless steelwith rolled grooved connectionDifferential pressure sampling tubeBrassFloatStainless steelBypass orificeStainless steelFilterStainless steelSealPerbunancertificationsclassification by Pressure EquipmentFor liquids of fluid group 2, complies with requirements ofDirective (97/23/EC)article 3, paragraph 3 (sound engineering practice (SEP))FM Approval 0003044464VdS Approval G415006The version with rolled grooved ends may only be used in combination with FM/VdS-approved pipe couplings manufactured by Minimax, Modgal, Victaulic (except pipe couplings of the type "Style 77") and Jinan Meide casting couplings type 1G.Operating instructions FO Turbo-Lux 3 FM VdSwww.mecon.dePage 13 / 1605/2015 OI_FO_Turbo-Lux 3 FM VdSDimension and weights7 Dimension and weights