Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
As the Canalis KTA5000/KTC6300 are made of two run components, the fire barrier kits for Canalis KTA5000/KTC6300 are made of two fire barriers, one for each run component. The distance between both run components must be 130 mm. Both fire barriers must be installed side by side and sealed together with fire barrier sealant KTB0000SC1 supplied with the KTB0622CF• fire barrier kit.66QGH3492101-01 11/2018Canalis KTCommissioning and MaintenanceQGH3492101-01 11/2018Commissioning and MaintenanceChapter 7 Commissioning and MaintenanceWhat Is in This Chapter?This chapter contains the following topics:TopicCommissioningCommissioning Check-list Before EnergizingMaintenanceQGH3492101-01 11/2018Page68717367Commissioning and MaintenanceCommissioningSafety InstructionsDANGERHAZARD OF ELECTRIC SHOCK, BURN, OR EXPLOSION Only qualified electrical maintenance personnel should install, operate, service or maintain thisequipment.