Title: Bytesteinen 1 - =514.202-FS001.pdf
Cable ID: 521.202-UD054 Date / Time: 30/03/2021 11:12:59 Headroom 7.7 dB (NEXT 3,6-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 1,2]18.3 93 6 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]30.4 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 7.7 219.0 34.1 4,5 9.3 193.0 32.1SR 1,2-3,6 9.0 211.5 34.4 1,2 9.5 212.0 31.4MAIN 3,6-7,8 7.7 219.0 34.1 7,8 9.5 237.5 30.5SR 1,2-3,6 10.0 248.5 33.2 1,2 9.5 212.0 31.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)