Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
I/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24?V are disconnected from the power supply.6-103PCD3.W8006.14.1PCD3.W800, Analogue manual control module with 4 output channels, 0…+10 V, 10 bit resolutionApplicationThe PCD3.W800 module is a rapid analogue output module with a manual control option. In Automatic mode, there are 4 analogue 0…+10 V output channels available, each with 10 bit resolution.Three of the analogue output channels have manual control functionality. In this mode, the output voltage is preset via the potentiometer on the front panel. (for emergency and manual operation, see also section 3.20).Technical data