Title: 40 Bender brukermanual.pdf.pdf
3.3 Device variantsRCMS residual current monitoring systems differ depending on the residual cur- rent monitor version used, RCMS460… or RCMS490….RCMS460-D Device version RCMS460-D utilises a backlit graphical display. This version is used for local display of detailed information about all devices connected to the bus in the control cabinet. This device can be used to parameterise all RCMS de- vices connected to the BMS bus and to display all measurement details. Several RCMS-D devices can be used within one system.RCMS460-L Device version RCMS460-L utilises a two-digit 7-segment display where the address of this device is displayed within the BMS bus. The alarm LEDs indicate in which measuring channel the response value has been exceeded. Parameters can be set via an RCMS…D, an Ethernet gateway (z. B. COM460IP) or a Condi- tion Monitor (z. B. COMTRAXX CP700).