Title: Våtventil Brukermanual.pdf
11713To System65410 Alarm Pressure Switch 11 Alarm Line Ball ValveTo Drain(Lockable - Normally Open)112 Series 760 European Water Motor AlarmAssembly (Optional/Sold Separately)813 System Test Valve 14 15 Series 752V Retard Vent Kit * (Optional/Sold Separately)System Pressure Gauge (0-25 Bar)To Drain2The Series 752V Retard Vent Kit is required any time an air break is needed above the Series 752 VdS Retarding Chamber Assembly. In addition, the Series 752V Retard Vent Kit is required if multiple valves are tied into one water motor alarm and a check valve isolates each line.3From Water SupplyI-751.VDS_4EXPLODED VIEW DRAWING – INTERNAL VALVE COMPONENTSClapperAlarm OutletSeatExaggerated for clarityBill of Materials 1 Valve Body 2 Clapper Shaft Retaining Bushing (Qty. 2) 3 Clapper Shaft 4 Clapper 5 Clapper Spring 6 Clapper Seal 7 Seal Retaining Ring