Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
PCD3.A200 PCD3.A210 PCD3.A220 PCD3.A251PCD3.A4104 make contacts 2 A 4 break contacts 2 A 6 make contacts 2 A 6 changeover contacts + 2 make contacts 2 A, 24-pole cage clamp terminal block 8 outputs 0.5 AInstallation instructionsFor reasons of safety it is not permissible to connect low voltages (up to 50 V) and higher voltages (50…250 V) to the same module.If a Saia PCD® module is connected to a higher voltage (50…250 V), approved com- ponents for this voltage must be used for all elements that are electrically connected to the system.Using higher voltage (50…250 V), all connections to the relay contacts must be connected on the same circuit, i.e. in such a way that they are all protected against one AC phase by one common fuse. Each load circuit may however be fused individually.