Title: +038=744.004-UN003T_02-Montering og vedlikehold av Teknoware armaturer Nortek FDV.pdf
LUMINAIRE CLASSIFICATION LABEL According to the requirements of the standard EN 60598-2-22, the emergency luminaires shall be classified and marked according to their function and construction. Therefore, a sticker with four squares must be attached on the luminaire, in a visible place. The first square is already filled in the factory, the rest of the squares are to be filled after the installation.a) First segment containing one position: TYPE (Marked already in the factory)once per year, the full duration test of 1 h, or a separately determined longer time, is to be made, by switching to battery feedonce per year, the full duration test of 1 h, or a separately determined longer time, is to be made, by switching to battery feedX Zself-contained luminaire centrally supplied luminaireall the tests and results are recorded in the logbook of the emergency lighting system, and when asked, presented to the authorities