Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
A.4.2Installation direction for switching higher voltagesFor reasons of safety it is not allowed that low voltages (up to 50 V) and higher voltages (50 … 250 V) are connected to the same module.If a Saia PCD® system module is connected to a higher voltage (50 … 250 V) ap- proved components for this voltage have to be used for all elements which are galvanically connected to the system.Using higher voltage (50 … 250 V), all connections to the relay contacts are to be connected on the same circuit. That means at one point in such a way that they are all protected against one AC-phase by only one fuse. Each load circuit may be protected individually by a fuse of max. 2A.LNPCD2.A200max. 10 ABurdenmax. 2 AA-2Installation direction and relays contact protectionLNPCD2.A210max. 10 ABurdenmax. 2 APCD2.A220LNBurdenmax. 6 Amax. 6 ABurdenPCD2.A250LNBurdenmax. 8 Amax. 8 ABurdenA-3Installation direction and relays contact protection