Title: bn305_cgb.pdf
Short-circuit: 0-235 Ω Normal: 1200-4800 Ω Activate: 260-1000 Ω Open circuit: 5400-∞ ΩLED connector: A pin header enables the option to add LED indicators. The indication is a short blink at 0,5Hz period. LED activate: The input or output is in Activation condition. LED fault: There is a fault on the input or the unit itself.LED3 ms flash at 0,5 Hz Output: 10 mA current source 16-24 VDC Maximum length of connected wire: 3 mApprovalsSee website0470Autronica Fire and Security AS, N-7483 Trondheim 11 0470-CPD-0031EN 54-17:2005 Short circuit isolators EN 54-18:2005 Input/output devicesAutronica Fire and Security AS | Tel.: +47 90 90 55 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 2Dual Monitored Input/Output Unit – BN-305DimensionsConnectors and DIP switches on circuit boardAutronica Fire and Security AS | Tel.: +47 90 90 55 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 3Descriptions of connection optionsInput configuration A