Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
5 V supply of encoder yes no 5 V 300 mA 400 mA (this current also loads the +5 V Bus on the module)max. 140 mA typically 125 mA 0 mA6Noise immunity: Programming:Terminals:0 … +55 °C without forced ventilation, -20 … +85 °COperation: Storage: CE mark acc. to EN 61 000-6-3 and EN 61 000-6-2 Based on PCD user program and pre-programmed function blocks (FB). Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-105Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.H31xLEDs and connection terminalsPCD2.H310Bus connector Adressing circuit Connector for address programming. (not for user)ProcessorPotentiometer for balancing output voltage (not for user)DAC (D/A converter)Supply6PowerRefINBALEDs987 Ref6 Out5 nc4 IN3 nc2 B1 nc0 AScrew terminalsPCD2.H311PowerPw 5V INBALEDs987 5V6 Out5 /IN4 IN3 /B2 B1 /A0 A