Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]38.3 167 3 5.66Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.9 482.0 29.6 36 7.4 499.0 26.4SR 36-45 6.1 490.0 29.4 36 6.5 490.0 26.6MAIN 12-45 8.1 499.0 29.3 36 7.4 499.0 26.4SR 36-45 6.1 490.0 29.4 36 6.5 490.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.1 7.1 48.2 45 13.8 4.9 48.5SR 36-45 14.1 30.8 35.5 45 13.7 3.0 52.7MAIN 78-36 15.6 499.0 11.3 78 16.9 481.0 8.6SR 78-36 15.4 487.0 11.5 45 16.0 418.0 9.80100806040200250 MHzACR-F (dB)