Title: økernvn 94.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.3 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 5.8 240.5 35.6 45 4.9 245.0 32.9SR 36-450.4 *230.5 35.9 36 0.8 *241.0 33.0MAIN 12-36 5.9 246.5 35.4 36 5.0 248.5 32.7SR 36-45 0.5 248.5 35.4 36 1.0 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.1 60.0 28.6 36 15.1 58.3 25.9SR 36-45 13.2 60.3 28.6 45 15.1 58.3 25.9MAIN 45-12 15.4 250.0 16.2 45 17.0 250.0 13.2SR 45-12 14.7 249.0 16.3 45 16.0 248.0 13.3010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250