Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]13.1 57 1 2.11Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]35.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.2 473.0 29.1 36 6.2 454.0 27.2SR 36-45 6.9 473.0 29.1 36 7.3 463.0 26.8MAIN 36-45 6.9 500.0 27.8 36 6.7 499.0 25.0SR 36-45 7.9 500.0 27.8 36 8.1 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.7 7.8 47.4 45 21.9 20.1 36.2SR 12-36 20.7 465.0 11.9 45 21.9 28.1 33.3MAIN 36-12 20.9 465.0 11.9 12 23.3 465.0 8.9SR 12-36 20.7 465.0 11.9 36 22.8 464.0 8.90100806040200250 MHzACR-F (dB)