Title: 40 Bender brukermanual.pdf.pdf
Example: Alarm "residual current“ on measuring channel 1.Residual currentExit 1.Chan.: 13. Press the "ESC" button to exit the function.RCMS460-490_D00067_03_M_XXEN/12.201775Operation6.6.8 Menu 8: External devices This menu can be used for setting and operating external devices connected via the BMS bus to this RCMS…-D. In this way, settings at RCMS…-L or other RCMS…-D, for example, can be carried out. The menu options of the external devices available via this function are indicated on the RCMS…-D display. Mo- difications of the external device settings are stored automatically in the exter- nal device. After calling up this menu, the address and type of devices already stored will be displayed. The display will be updated every five minutes.Exit 1.RCMS460-D 2.RCMS460-L 3. --Use the Up/Down buttons to select the address of the external device and confirm with the "↵" button.