Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
30.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.0 470.0 29.3 45 10.2 470.0 26.4SR 36-45 8.2 465.0 29.5 36 8.4 465.0 26.7MAIN 36-45 10.3 500.0 27.8 36 11.1 497.0 25.1SR 36-45 8.7 500.0 27.8 36 8.8 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.8 3.5 54.4 45 14.2 3.5 51.4SR 78-45 14.7 3.5 54.4 45 14.2 3.5 51.4MAIN 78-45 16.6 500.0 11.3 45 18.0 498.0 8.3SR 45-78 17.0 500.0 11.3 45 18.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.8 93.0 25.4 36 26.5 92.3 23.0SR 12-36 24.6 85.0 26.8 36 25.9 84.5 24.4MAIN 36-45 39.6 500.0 -12.4 36 40.6 497.0 -15.1SR 36-45 38.0 500.0 -12.4 36 38.3 496.0 -15.00804000250 MHzACR-N (dB)