Title: +038=433.002-FS052._06-Eaton Tavlebyggeren Produktblad.pdf
Electric engineering, automation, process control engineering / Electrical installation, device / Residual current protection system / Residual current circuit breaker (RCCB) (ecl@ss10.0.1-27-14-22-01 [AAB906014])Number of poles4Rated voltageV415Rated currentA40Rated fault currentmA30Rated insulation voltage UiV440Rated impulse withstand voltage UimpkV4Mounting methodDIN railLeakage current typeASelective protectionNoShort-time delayed trippingYesShort-circuit breaking capacity (Icw)kA10Surge current capacitykA3Frequency50 HzAdditional equipment possibleYesWith interlocking deviceYesDegree of protection (IP)IP20Width in number of modular spacings4Built-in depthmm70.5Ambient temperature during operating°C25 - 40Pollution degree2Connectable conductor cross section multi-wiredmm²1.5 - 16Connectable conductor cross section solid-coremm²1.5 - 35Dimensions09/04/2019