Title: etg u1.pdf
Cable ID: T0004 Date / Time: 10/22/2013 01:21:04 PM Headroom 12.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]80 128 10 3.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.3 85.5 33.4 36 14.0 85.5 30.4SR 12-36 14.8 85.5 33.4 36 16.1 85.5 30.4MAIN 12-36 12.3 85.5 33.4 36 14.8 98.0 29.4SR 12-36 14.8 85.5 33.4 36 16.9 97.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 23.9 92.5 19.3 45 24.5 3.5 44.7