Title: 360.001 - Tilluft.pdf
MAGID-C1-315145 FLOWDAMPER LEO-0-315DUCTMAGID-C1-315SILENCERLKR-315-1200315315315315315315315315315315SizeSound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]0,212004,33,912004,312004,30,912004,312004,30,312004,312004,361Sound in:Attenuation: Addition:6,3 Sound in:2,8 Sound in:Attenuation: Addition:Sound in:0,7 Sound in:Attenuation: Addition:34,9 Sound in:Addition:0,2 Sound in:Attenuation: Addition:11,0 Sound in:Attenuation:63 [dB]45.20.0 +0.028.928.90.4 +25.730.430.40.1 +25.731.6+53.453.50.0 +25.753.44.0125 [dB]40.10.0 +0.024.924.90.4 +24.627.627.60.1 +24.629.3+52.452.40.0 +24.652.48.0250 [dB]26.70.0 +0.021.721.70.4 +23.625.625.60.1 +23.627.7+43.443.50.0 +23.643.616.0500 [dB]21.90.0 +0.021.221.20.6 +22.624.724.70.2 +22.626.7+42.442.50.1 +22.642.525.01k [dB]19.70.0 +0.020.1