Title: +038=744.004-UN003T_02-Montering og vedlikehold av Teknoware armaturer Nortek FDV.pdf
Self-testing Self-contained Lumi Test luminaires (A and M models) include an internal self-testing procedure. The Lumi Test luminaires test their LED light output in emergency mode briefly once a day. The luminaires also test their full-time emergency mode duration twice a year. The indicator LEDs show the status of the luminaire. The following figure shows the function of the indicator LEDs:Each output circuit must have a separate neutral line. Neutral lines are not allowed to be connected together.Set the address in the following way: 1. Find the address module with a DIP switch inside the luminaire. 2. Check on your central battery unit for the maximum number of addresses (16 or32). If the maximum number is 16, use the LO setting (=factory setting).Red LEDGreen LED OFF OFF No supply ON OFF OK 2Hz OFF Low charging state 1Hz ON Light source fault 1Hz Duration test fault ON3. Set the address from 1 to 16 (LO) or 17 to 32 (HI)