Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
CAUTIONAlways remember to connect the air conditioner tothe grounding system before performing the electric connections. Use a crimp ring terminal at the end of each wire.The indoor unit is powered through the outdoor unit by means of a H07 RN-F connection cable (or a more power model), with insulation in synthetic rubber and a jacket in polychloroprene (neoprene), in accordance with the requirements specified in the standard EN 60335-2-40.1 Remove the screw on the electrical component boxand remove the cover plate.2 Route the connection cord through the side of the indoor unit and connect the cable to the terminals refer to the figure below.3 Route the other end of the cable to the outdoor unitthrough the ceiling & the hole on the wall.4 Reassemble the electrical component box cover,carefully tightening the screw.2016-05-16 오후 5:32:16Example) 1phase modelFor connecting the power and communication cablesLIndoor unitN2 F1 FOutdoor unit1(L)2(N)LNIndoor power