Title: Data tester Smestad skole - Detaljert.pdf
1200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,9 10,2 10,7 500,00Remote: 12-45 23,7 12,3 11,4 394,00Worst Value: Local: 12-45 20,8 10,2 10,6 500,00Remote: 45-12 21,9 10,2 11,7 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,9 3,7 494,00Remote: 45 29,6 23,8 5,8 500,00Worst Value: Local: 36 27,5 23,9 3,6 496,00Remote: 45 29,6 23,8 5,8 500,00PS-ACRF: Pass Worst Margin: Local: 12 61,6 48,8 12,8 4,15Worst Value: Local: 45 20,1 7,2 12,9 500,00Remote: 12 72,6 61,2 11,4 1,00Remote: 12 20,6 7,2 13,4 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:14Signature:______________________ Page: 134Copper Certification Report