Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
RCD: UtlřsningsstrřmI: 27.0mAUci: 0.0V t: 202.8ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 524V Rnpe: >30.0MΩ Um: 518VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF029 C16/2/003 / Mal 2 10.03.2022 13:42 (TomekElektriker)KONTINUITET: R200mA LPER: 0.13ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF030 C16/2/003 10.03.2022 14:35 (TomekElektriker)SPENNING TRMS Uln: 234V Ulpe: 233V Unpe: 1V f: 49.98HzSYS.: TN/TTZ-LINEZ: 0.22ΩIsc: 1.07kA R: 0.21Ω Xl: 0.02Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.1V t: 75.7ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTTALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:19GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTNr.5555565657575858TEST RAPPORTResultatISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 525V Rnpe: >30.0MΩ Um: 521V