Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
AC120KN4DKH360 cassette type <L+> (947 x 947 x 365)AC140KN4DKH2610 × 215Step 4 Installing the indoor unitWhen deciding on the location of the air conditioner the following restrictions must be taken into account.1 Determine the positions of the pipe and the drainStep 3 Optional: Insulating the body of the indoor unithose hole as shown in the pattern sheet, and drill the hole with an inner diameter of 14 mm.If you install a cassette type indoor unit on the ceiling when temperature is over 27°C and humidity is over 80%, you must apply an extra 10 mm thick polyethylene insulation or a similar type of insulation to the body of the indoor unit.Cut away the part where pipes are pulled out for the insulating work.NOTESince the diagram is made of paper, it may shrink or stretch slightly due to temperature or humidity. For this reason, before drilling the holes, be sure to maintain the correct dimensions between the markings.A