Title: økernvn 94.pdf
MAIN 36-78 12.9 239.0 5.8 12 14.8 250.0 2.0SR 12-36 12.5 230.5 6.6 12 11.7 230.5 4.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 1.8 6.4 21.0SR 36 1.4 * 6.1 21.0MAIN 36 5.4 211.5 10.7SR 36 3.9 214.5 10.7010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94