Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]25.5 110 1 3.84Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]30.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.0 462.0 29.6 36 10.3 463.0 26.8SR 12-45 9.5 427.0 30.7 36 9.4 481.0 25.9MAIN 36-45 10.8 494.0 28.1 36 10.9 494.0 25.3SR 36-78 10.6 495.0 28.1 36 9.5 495.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.5 4.5 52.2 45 14.3 3.3 52.0SR 45-78 15.5 4.5 52.2 45 14.3 3.4 51.7MAIN 78-45 16.0 498.0 11.3 45 17.9 497.0 8.3