Title: økernvn 94.pdf
80604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: D4104 Date / Time: 09/11/2013 09:40:11 Headroom 5.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]133 203 7 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.1 243.0 35.5 78 8.2 243.0 32.9SR 36-78 5.2 235.0 35.8 36 6.7 235.0 33.2MAIN 36-78 7.1 243.0 35.5 78 8.2 243.0 32.9SR 36-78 5.2 235.0 35.8 36 6.7 235.5 33.1