Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 51,6 68,0 268,0 15,0 9,1Limit 100,0 - 555,0 50,0 25,0Margin 48,4 - 287,0 35,0 15,9Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 1,0 3,0 2,0 2,80Worst Value: Local: 45 22,5 43,8 21,3 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 25,5 18,4 7,1 33,25Remote: 78 20,5 13,9 6,6 103,00Worst Value: Local: 12 17,4 9,3 8,1 298,00Remote: 12 16,3 8,3 8,0 369,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,6 26,7 1,9 499,00Remote: 36-45 31,0 26,7 4,3 500,00Worst Value: Local: 36-45 28,6 26,7 1,9 499,00Remote: 36-45 31,0 26,7 4,3 500,00dB 0601200Local250500 MHzdB 0