Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
R+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF026 16C2/003 06.11.2020 13:17R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 06.11.2020 13:17R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 05.11.2020 11:40RCD II: 28.5mAUci: 0.1V t: 16.1ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 05.11.2020 11:37Z-LINEZ: 0.76ΩIsc: 304A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A Isc(0.38%): 116A Isc(0.76%): 231A Isc(1.15%): 350ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 05.11.2020 11:38Zs(rcd)Z: 0.69ΩIsc: 332A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM3.E3=433.08.03 / XF027 16C2/003 05.11.2020 11:40Tallberg Elektro A/S Tlf.22796640Side:8GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT