Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
3 / E.433.11.01 TNS / Sikring 06011.03.2020 09:57SPENDINGUln: 235VUlpe: 235VUnpe: 0OVf: 50.0HzR IS0R: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQGODKJENT*GODKJENT216 | Dronning M.g.13 / E.433.11.01 TNS / Sikring 061I LLI0852020/ "10:102SPENDINGUln: 234VUlpe: 235VUnpe: 0Vf: 50.0HzR ISOR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQGODKJENT *GODKJENTDronning M.g.13 / E.433.11.01 TNS / Sikring 062110820200 10i: 12SPENDINGUln: 235VUlpe: 235VUnpe: 0OVf: 49.9HzR ISOR: >200MQ Um: 262VUiso: 250VGrenseverdi: 1MQGODKJENT*GODKJENTDronning M.g.13 / E.433.11.01 TNS / Sikring 06312.03.2020 14:50GODKJENT*Nr.TEST RAPPORTResultatSPENDINGUln: 233VUlpe: 234VUnpe: 0Vf: 50.0HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 063 GODKJENT* 12810 8r32/0 201" WHat:=5'0Z~LINE GODKJENTZ: 0.51QIsc: 450ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0A