Title: 360.002 - Tilluft.pdf.pdf
18 FLOWDAMPER LEO-0-315315DUCT315SILENCERLKR-315-1200315DUCT315BEND-90MAGIB-C4-*-*315DUCT31519 T-BRANCHTCPU_DK-*-*0,0 315/315DUCT315DUCT315L [m]1,00,30,20,60,80,3Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]12004,30,7 Sound in:Attenuation: Addition:12004,313,6 Sound in:Addition:12004,30,2 Sound in:Attenuation: Addition:12004,311,0 Sound in:Attenuation:12004,30,2 Sound in:Attenuation: Addition:12004,32,8 Sound in:Attenuation: Addition:12004,30,4 Sound in:Attenuation: Addition:12004,311,5 Sound in:Attenuation: Addition:Dividing:6002,10,2 Sound in:Attenuation: Addition:6002,1Sound in:Attenuation: Addition:Dividing:1063 [dB]47.00.1 +25.746.9+44.849.00.0 +25.749.04.045.00.0 +25.745.00.0 +35.345.50.1 +25.745.40.0 +25.63.042.50.1 +10.642.40.0 +11.94.1125 [dB]39.60.1 +24.639.6+43.845.20.0 +24.645.28.0