Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
To construct a type E output (output for the activation of a remote alarm-signalling device as required by EN54-2, [A]), you must use a remote communication device which is compliant with EN54-21 regulations [B] and which has a normally-open supervised activation input [C], a normally-closed fault signalling output [D] and a normally-open output to provide feedback indicating the successful communication [E].F3K9Ohm orange, white, red1IN2470Ohm yellow, purple, brownRELAY123NCCNOAThis is done by making the connection illustrated in the figure, using a relay output (of an IFM24160 module, IFM4R module or relay module) [A]configured as “communicator alarm condition output” and an input of an I/O module [F] configured as “communicator fault condition input”.BDEC44InstallationInstallation manual5.16FPMCPU front-plate module wiring - repeater connection