Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
GODKJENTGODKJENTNr. 189189190190191191192192193193TEST RAPPORTResultatDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 10:26R LOW OhmR: 0.03ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 11:11KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 10:24KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 10:25R LOW OhmR: 0.17ΩR+: 0.1Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Himling 16.06.2020 10:26R LOW OhmR: 0.13ΩR+: 0.1Ω R-: 0.2Ω Grenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:27GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT