Title: 2wayEPIV_PICS_en.pdf
Communicative characterised control valve with sensor- operated flow control, 2-way (EPIV)Object NameObject Type [Instance]DescriptionCommentValuesFlagsBusTerminationBI[99]Bus Termination120 Ohm bus termination resistor can be set.0:Disabled 1:EnabledSummaryStatusBI[101] Summary StatusIf StatusActuator MI[106] is Actuator_cannot_move(2) or Mechanical_travel_increased(4) then Not_OK(1)0:OK 1:Not OKInternalActivityMI[100]Internal ActivityTest: Internal test running, activated by bus1:None 2:Test 3:AdaptionStatusActuator *MI[106] Status ActuatorMechanical overload e.g. blocked valve or Gear disengaged button is pressed.1:OK 2:Actuator cannot move 3:Gear disengaged 4:Mechanical travel increasedStatusDeviceMI[110] Status DeviceIndicates general status about the device1:OK 2:BusWatchdog triggeredOverrideMO[1] Override ControlOverriding the setpoint with defined values1:None 2:Open 3:Close 4:Min_Vmin 5:Mid_Vmid 6:Max_VmaxCommandMV[120]