Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
Temperatures T3 and T4 can be programmed into the calculator’s memory, whereby these temperatures can be used for energy calculation with fixed temperature reference, as used in the calculations of the energy types E4, E5, E6 and E7 (see application drawings in paragraph 6.2)The temperatures can be entered from the factory or by means of METERTOOL, in the range 0.01…180°C, after installation.Kamstrup A/S · Technical Description · 5512-571_R1_GB _11.201645MULTICAL® 8016.9 Display functions