Title: 4. Leieavtaler.pdf
20. Submit detailed sprinkler and fixed extinguishing system plans to FM Global for review. Complete the plan review stage as far in advance as possible prior to the installation of the automatic sprinkler systems. The submittal includes some preliminary sprinkler drawings with the expectation that more detailed drawings will be completed by the main/sprinkler contractor. A comprehensive list ofrequired information is available in FM Global Property Loss Prevention Data Sheet 2-0, Installation Guidelines for Automatic Sprinklers, section 2.7.21. The automatic sprinkler systems should be fed from an adequate and reliable dedicated water supply based on the final hydraulic calculations of the automatic sprinkler systems. Most likely this will need to be comprised of a fire pump and suction tank for the sprinkler system.