Title: +038=433.002-FS043._05-Eaton Tavlebyggeren Produktblad.pdf
Is the panel builder's responsibility. The speciﬁcations for the switchgear must be observed.10.13 Mechanical functionThe device meets the requirements, provided the information in the instruction leaﬂet (IL) is observed.Technical data ETIM 7.0 Low-voltage industrial components (EG000017) / Power circuit-breaker for trafo/generator/installation protection (EC000228)01/04/2019Eaton 147398 ED2018 V51.0 EN3 / 9Electric engineering, automation, process control engineering / Low-voltage switch technology / Circuit breaker (LV < 1 kV) / Circuit breaker for power transformer, generator and system protection (ecl@ss10.0.1-27-37-04-09 [AJZ716013])Rated permanent current IuA250Rated voltageV690 - 690Rated short-circuit breaking capacity lcu at 400 V, 50 HzkA50Overload release current settingA125 - 250Adjustment range short-term delayed short-circuit releaseA250 - 2500Adjustment range undelayed short-circuit releaseA3000 - 3000Integrated earth fault protectionNo