Title: Sprinklerhode stående_hengende.pdf
NOTICE The TYCO Series TY-FRB Sprinklers described herein must be installed and maintained in compliance with this document, as well as with the applicable standards of the National Fire Protection Association, in addition to the standards of any other authori- ties having jurisdiction. Failure to do so may impair the performance of these devices.Maximum Working Pressure 175 psi (12.1 bar) 250 psi (17.2 bar)*The maximum working pressure of 250 psi (17.2 bar) only applies to the listing by Underwriters Laborato- ries, Inc. (UL).General Description The TYCO Series TY-FRB, 5.6 K-factor, Upright (TY313) and Pendent (TY323) Sprinklers described in this data sheet are quick response, standard coverage, decorative 3 mm glass bulb-type spray sprinklers designed for use in light or ordinary hazard, commercial occupan- cies such as banks, hotels, and shop- ping malls.