Title: 564 JRAS_X23021 Persiennemodul 2_4_8 kanal.pdf
Button/LEDButtonand LEDButtons Two buttons and LEDs per outputand LEDsIP 20II, in the installed statePage 1 of 4 JRAS_x23021_TD_EN_V1-0 2CDC 506 063 D0202The outputs can be directly controlled on the device using the manual push buttons. The LEDs on the front of the device signal the status of the outputs.Individual outputs can be copied or exchanged to reduce the programming effort.The Blind/Roller Shutter Actuator is a modular installation device for installation in the distribution board on 35 mm mounting rails. The connection to the ABB i-bus® is implemented via bus connection terminals.21…30 V DC, via KNX< 12 mAmaximum 250 mW2.230.2.1 2*4.230.2.1 48.230.2.1 8(mutually mechanically interlocked)independent outputs, each with up to 2 drives operating in parallel.independent outputs, each with up to 2 drives operating in parallel.maximum 230 V AC, 45 … 65 Hz6 A6 A (AC1/AC3) at 230 V AC or 6 A (AC1/AC3) at 400 V AC100 mA at 5 V or 10 mA at 10 V or 1 mA at 24 V