Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]22.9 99 1 3.61Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.2 449.0 30.3 36 9.3 457.0 27.1SR 12-36 8.3 399.0 31.4 36 7.7 471.0 26.4MAIN 12-36 10.0 500.0 27.8 36 9.6 496.0 25.2SR 12-36 10.1 500.0 27.8 36 7.8 481.0 25.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.7 4.0 53.2 45 18.1 3.8 50.8SR 45-78 15.7 4.0 53.2 45 18.1 3.8 50.8MAIN 12-36 21.8 486.0 11.5 36 22.7 487.0 8.5SR 36-12 21.9 486.0 11.5 45 22.1 498.0 8.30100806040200250 MHzACR-F (dB)