Title: økernvn 94.pdf
MAIN 12-36 8.9 28.0 41.3 12 10.7 28.0 38.9SR 12-36 8.8 28.0 41.3 12 10.4 19.9 42.8MAIN 36-45 17.0 249.5 4.7 36 16.9 249.5 2.1SR 36-45 17.0 249.5 4.7 36 17.8 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.0 21.6 19.3SR 36 2.7 21.6 19.3MAIN 45 6.9 203.0 10.9SR 45 7.1 226.0 10.5010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4