Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
(See fig. 8). ... connecting condensate piping to sewage system drain without appropriate trap. Trap height must be calculated according to the unit discharge head in order to allow sufficient and continuous water evacuation (See fig. 9-10). ... only partial insulation of the piping. Non-level installation which will cause condensate dripping (See fig. 11). ... flattening pipes or condensate pipes (See fig. 12-13). ...slack on electrical connections (See fig. 14).panels or, if the ceiling is constructed of masonry, that access to the unit is guaranteed.ATTENTION: Only restrict the air outlets as indicated in the drawing fig.15 For units equipped with electric heaters the use of the “AIR SUPPLY OBSTRUCTION” kit is NOT allowed.Prior to installation It is advisable to place the unit as close as possible to the installation site before removing it from the packaging. The grille panel and the control are separately packed for maximum protection (See fig. 16).