Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
60RL @ Remote (dB)504030201050000250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.10.03-UF068 Date / Time: 27-02-2020 22:28:07 Headroom 7.6 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]35.3 154 3 5.24Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.6 499.0 29.3 36 7.5 498.0 26.4SR 36-78 8.7 473.0 29.8 45 8.6 495.0 26.5MAIN 36-45 7.6 499.0 29.3 36 7.5 498.0 26.4SR 36-78 9.0 487.0 29.5 45 8.6 495.0 26.510080604020NEXT (dB)