Title: Datasheet_LDALI-MS2-BT_LDALI-MS4-BT.pdf
G a t e w a y sDetection diameter: 10.8 m @ 3 m mounting height (92 m2),136 zones, opening angle: 122° (up to 5 m mounting height)Detection diameter: 7.2 m @ 3 m mounting height (44 m2),156 zones, opening angle: 100° (up to 5 m mounting height)Passive infrared motion detectorHighbay‑application: 5 m – 12 m mounting height, detection area: 256 m2 (opening angle: 73.6° @ 12 m, 122° @ 5 m)L ‑ V SImax. 12 mmax. 5 mMounting height,L ‑ S T A TLux level measurement0 – 4000 lux, resolution: 0.125 lux‑5 °C to 60 °C, resolution: 0.1 °C, accuracy: ±0.2 °C (0 °C to 70 °C)Temperature measurementRel. Humidity measurement0 % – 100 %, resolution 0.5 %, accuracy: typ. ±2.2 % R.H. @ 25 °C, 20 % – 80 % R.H. typ. ±4 % R.H. @ 25 °C, 0 % – 20 % R.H. and 80 % – 100 % R.H.L L ‑ ‑ D D A A L L I IConnection wires profile0.2 – 1.5 mm² [AWG 28 – 14]Wire stripping length6 mm [0.24 in]Wire length for digital inputs < 10 mR o u t e r s ,N CIIn t e r f a c e sA c c e s s o r i e s