Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
All I/O-Channels are galvanically isolated to the Saia PCD® and external power supply. (But all channels are galvanically connected to each other.)All I/O-Channels are galvanically isolated to the Saia PCD® and external power supply. (But all channels are galvanically connected to each other.)Every channel has two connection terminals.5-98PCD2.W525 Combined analogue input/output module with galvanic isolationConfigurationModule connections/LEDThe connections of the module terminal are the following:Description of the LED: ● Off: ● On: ● Blinking slow: Channel error (Over range/under range/short circuit/open load) ● Blinking fast: Uext is lower than specified (< 19 V)Module is not powered. Uext (24 V) is missing. Module is running without errorsHow to configure the inputsEach input channel is configured by a DIP-Switch with four switches. The function of each switch is the following:Switch nr. 1 2 3 4OffDifferential ModeGain=1On