Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 45-36 18.0 466.0 11.9 45 20.0 490.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 26.8 133.5 19.3 45 28.0 133.0 16.8SR 12-45 28.0 134.0 19.2 45 28.2 133.0 16.8MAIN 12-45 40.3 496.0 -12.1 45 41.0 496.0 -15.0SR 12-45 41.4 496.0 -12.1 36 41.9 495.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.1 430.0 8.0SR 12 5.8 493.0 8.0MAIN 45 6.1 430.0 8.0SR 12 5.8 493.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00417.8 m60Insertion Loss (dB)504030201000250 MHz500100