Title: DM1-3 plan 09 lysberegningsrapport.pdf
Total luminous flux of all lamps Total power Total power per area (8.10 m²)5250.00 lm 69.3 W 8.56 W/m² (1.28 W/m²/100lx)Evaluation area 1 User profileEm Emin Emin/Em (Uo) Emin/Emax (Ud) UGR (2.3H 2.2H) PositionReference plane 1.1 Offices 5.26.5 (EN 12464-1, 8.2011) Conference and meeting rooms (Ra >80.00) Horizontal 670 lx 422 lx 0.63 0.47 <=18.2 0.75 m(>= 500 lx)(>= 0.60)(< 19.00)Major surfaces M 1.5 (Ceiling) M 1.1 (Wall) M 1.2 (Wall) M 1.3 (Wall) M 1.4 (Wall)Em 42 lx 46 lx 122 lx 45 lx 126 lx(>= 30 lx) (>= 50 lx) (>= 50 lx) (>= 50 lx) (>= 50 lx)Uo 0.90 0.73 0.25 0.74 0.25(>= 0.10) (>= 0.10) (>= 0.10) (>= 0.10) (>= 0.10)191015 test plan 9.rdfObject Installation Project number Date: : : :DM 1-3 plan 9 283 15.10.2019Summary, Room 2Result overview, Evaluation area 1Type No.\Make43iGuzzini illuminazione S.p.A/Lab/Ver. 03/17 Order No. Luminaire name