Title: 360.002 - Tilluft.pdf.pdf
3.0 +2.914.10.1 +2.914.3+17.519.20.0 +2.919.316.0Lp [dB]LocationLevel2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje1. EtasjeNodeTypeDUCTBEND-90DUCT113 T-BRANCHDUCTDUCT114 TAPDUCTDUCT115 TAPProductSize400MAGIB-C4-*-*400400TCPU_DK-*-*0,0 400/400400400MAGIO-RC-*400/315315315MAGIO-RC-*315/250L [m]0,71,01,80,41,90,3Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]13002,90,2 Sound in:Attenuation: Addition:13002,91,3 Sound in:Attenuation: Addition:13002,90,3 Sound in:Attenuation: Addition:13002,95,6 Sound in:Attenuation: Addition:Dividing:6501,40,1 Sound in:Attenuation: Addition:6501,4Sound in:Attenuation: Addition:Dividing:6502,31,9 Sound in:6502,30,4 Sound in:Attenuation: Addition:6502,3Sound in:Attenuation: Addition:Dividing:3251,83,6 Sound in:4263 [dB]50.00.0 +19.149.9