Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
clean or replace the unit air filters. - check and clean the drain pan and the condensate discharge of the unit.clean or replace the unit air filters. - check and clean the drain pan and the condensate discharge of the unit.check tightness of electric connections.Additional maintenance • The electric panel is easily accessibleThe inspection or replacement of internal components such as: fan motor, coil, condensate discharge pump, float switch, electric heater (if fitted), involve the removal of the condensate drain pan.Condensate drain pan removal • During the removal operation of the condensate drain pan protect thefloor with a plastic sheet under the uniRemove the frame-grille assembly by loosening the screws. • Remove the four fixing brackets on the side of the drain pan and carefully remove the condensate drain pan.Remove the frame-grille assembly by loosening the screws. • Remove the four fixing brackets on the side of the drain pan and carefully remove the condensate drain pan.