Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Colliers Plan 5 / DM3.E2=433.05.02 / XF027 C16/2/003 / Mal 1 10.03.2022 13:48 (TomekElektriker)KONTINUITET: R200mA LPER: 0.08ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF027 C16/2/003 / Mal 2 10.03.2022 12:22 (TomekElektriker)TALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:15GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.45454646TEST RAPPORTResultat SPENNING TRMS Uln: 233V Ulpe: 233V Unpe: 1V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.25ΩIsc: 916A R: 0.25Ω Xl: 0.01Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 28.5mAUci: 0.0V t: 12.8ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 524V Rnpe: >30.0MΩ Um: 522VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF027 C16/2/003 / Mal 2 10.03.2022 13:50 (TomekElektriker)KONTINUITET: R200mA LPER: 0.05ΩR+: 0.1Ω R-: 0.0Ω Grenseverdi: 0.5Ω