Title: 1 etg del 2.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.9 18.6 45.9 36 10.9 18.8 43.4SR 12-36 8.4 22.0 44.1 36 10.4 18.8 43.4MAIN 36-45 15.8 249.5 4.7 36 15.4 248.0 2.2SR 36-45 15.5 250.0 4.7 36 15.4 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 5.0 21.4 19.4SR 78 4.4 33.3 18.4MAIN 36 8.4 223.0 10.5SR 36 8.8 237.0 10.360500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1