Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
25.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.4 499.0 29.3 36 8.1 500.0 26.4SR 36-45 7.1 500.0 29.2 36 7.3 500.0 26.4MAIN 36-45 8.4 499.0 29.3 36 8.1 500.0 26.4SR 36-45 7.1 500.0 29.2 36 7.3 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.7 92.0 26.0 45 13.9 2.4 54.7SR 36-45 14.7 92.0 26.0 45 13.9 2.6 53.9MAIN 36-78 15.6 471.0 11.8 45 15.4 472.0 8.8SR 78-36 15.8 486.0 11.5 45 15.8 479.0 8.60100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.4 34.8 39.0 36 21.1 47.3 32.7SR 36-45 23.2 37.5 38.1 36 22.5 37.5 35.6MAIN 36-45 33.6 499.0 -12.3 36 33.4 500.0 -15.3SR 36-45 32.3 500.0 -12.4 36 32.6 500.0 -15.30804000250 MHzACR-N (dB)