Title: 2 etg del2.pdf
Cable ID: T2061 Date / Time: 10/10/2013 03:05:18 PM Headroom 13.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]307 486 34 13.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 99.5 32.3 36 15.9 99.5 29.3SR 12-36 13.7 94.0 32.7 36 15.3 93.8 29.8MAIN 12-36 14.0 99.5 32.3 36 15.9 99.5 29.3SR 12-36 13.7 94.0 32.7 36 15.5 99.5 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 16.4 41.0 26.4 36 19.1 35.3 24.7