Title: 40 Produktark nettanalysator 4x-serie.pdf.pdf
Measuring Voltage Input (Vin)Measuring Current Input (Iin) Measuring Power Range Measuring Energy Range Class Voltage Current Frequency cosφ Active Power Reactive Power Active Power Energy Reactive Power Energy Current Transformer Ratio (Ctr) Voltage Transformer Ratio (Vtr) Demand Time Communication (Isolated) Baud Rate Address Parity Stop Bit45 ~ 300 V AC/DC (MPR4X) 24 ~ 60 V AC/DC (MPR4X-D) 45-65 Hz <5 VA <1 VA 10 – 300 VAC (L-N) 10 – 690 VAC (L-L) 0.05 – 5.5A ~ 0...9999 MW 9999999.9 k/M (Wh, VArh)0.5% 0.5% 0.1% ±0.2% 1% 1% 1% 2% 1...5000 1MV / measurement Adjustable between 1-60 minutes MODBUS RTU (RS-485) 2400 – 115200 bps 1 – 247 None, Even, Odd 1Max Communication Distance1200 m (MODBUS/RS-485 side, with signal amplifier)Internal Memory Relay Outputs (2 pcs, with module) Pulse Outputs (4 pcs, with module) Pulse Width Time between two pulse peaks Transition Time Digital Inputs (4 pcs, with module) Analog Voltage Output (2 pcs, with module) Analog Current Output (2 pcs, with module)