Title: Tørrsprinkler.pdf
FACE OF SPRINKLER FITTINGMINIMUM 1-3/4" (44,5 mm) DEFLECTOR TO CEILINGSPRINKLER FITTING (REFER TO DESIGN CRITERIA SECTION)FIGURE 6 PENDENT (TY3255) WITHOUT ESCUTCHEONFIGURE 7 UPRIGHT (TY3155) WITHOUT ESCUTCHEON2-3/8" ± 1/8" (60,3 ± 3,2 mm)FACE OF SPRINKLER FITTINGFACE OF MOUNTING SURFACE3" DIA. (76,2 mm)3.5°SPRINKLER FITTING (REFER TO DESIGN CRITERIA SECTION)1-3/4" DIA. (44,5 mm)CENTERLINE OF WATERWAY5/16" (7,9 mm)FIGURE 8 HORIZONTAL SIDEWALL (TY3355) WITH STANDARD ESCUTCHEONORDER LENGTHS: 1/2" to 45-3/4" (12,7 to 1162,1 mm) IN 1/4" (6,4 mm) INCREMENTSFACE OF SPRINKLER FITTING2-1/2" DIA. (63,5 mm)FACE OF MOUNTING SURFACE4-1/4" ± 1/8" (108,0 ± 3,2 mm)3-1/2" DIA. (88,9 mm)3.5°SPRINKLER FITTING (REFER TO DESIGN CRITERIA SECTION)CENTERLINE OF WATERWAY5/16" (7,9 mm)FIGURE 9 HORIZONTAL SIDEWALL (TY3355) WITH DEEP ESCUTCHEONFACE OF SPRINKLER FITTINGORDER LENGTHS: 5-1/2" to 48" (139,7 to 1219,2 mm) IN 1/4" (6,4 mm) INCREMENTS