Title: 36 Siemens GDB181-MO.pdf.pdf
Configuration and retrieval of device parameters can be accomplished with the following tools:Using the PC software ACS941or ACS931 together with the interface converter AST22 via the configuration and maintenance interface of the VAV Compact Controller orUsing the handheld tool AST20.6.2.1 PC software ACS941 and ACS931The PC software ACS941 is designed for service and maintenance staff and is used for setting and displaying the parameter values on a PC. Instructions for use of this software can be found in datasheet N5854 ([7]).The PC software ACS941 allows to set or to display the parameters as listed in section 6.1. The software supports trend functions and allows comparing the values set by the OEM with the values currently stored in the device. Thus, changes by parties other than the OEM can be detected.Figure 1: ACS941 with VAV (left) and network (right) configuration pane