Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Critical applications include those with the need for high level of continuity of service, such as secured power distribution in hospitals, IT data centers, cooling power supplies or similar applications with a high load factor.Unfavorable conditions include: high ambient temperature, high level of humidity, dusty or polluted environments, and intensive vibrations.QGH3492101-01 11/201873Commissioning and MaintenanceCarry out the following maintenance procedures in critical environments:  Carry out the basic maintenance procedures every year as described previously.  Check that there is no abnormal increase in ambient temperature.  If the busbar trunking system is accessible, carry out infrared temperature measurements on all theelectrical connections (joint blocks, terminal connections, tap-off units). If the busbar trunking system is not accessible, install a thermal monitoring system which communicatestemperatures to a remote supervision point.