Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
Model rating (1.0 p.f.) Number of output phases Crest factor Rated output voltage Output voltage variation, steady state Total voltage harmonic distortion, 100% linear load Total voltage harmonic distortion, 100% non-line- ar load Voltage unbalance at reference unbalanced load Voltage transient (r.m.s) at 100% step load Recovery time to steady state at 100% step load Rated output frequency Output frequency variation Maximum synchronized phase error Maximum slew-rate when synchronizing Rated output power110 ms50 kW / 50 kVA3 phases + neutral 3 220/380 V; 230/400 V; 240/415 V, configurable < 1%< 1.2%< 3%< 0.1%4%140 ms 238 A 50 or 60 Hz, configurable ± 0.1 Hz317 A< 1° with static balanced load0,4 Hz/s100 kW / 100 kVA150 kW / 150 kVA200 kW / 200 kVAOverload capability On inverterOverload capability On inverter, stored energy mode Output current limitation, short-circuit capability