Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 12:40R LOW OhmR: 0.16ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 12:40KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 10.06.2020 10:47R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 10.06.2020 10:50Tallberg Elektro A/S Tlf.22796640Side:8GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.565657575858595960606161TEST RAPPORTResultatSPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 11.06.2020 15:18R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 10:06RCD II: 28.5mAUci: 0.1V t: 103.9ms Idn: 30mA type: AC Ulim: 25V