Title: +135.01=370.004-OE401T_02-320 Datablad Energimåler UH50.._.pdf
The exterior diameter must be between 4 and 6 mm. All wiring must be able to be guided to the meter through the existing bushings. It may be convenient to connect the cables before the meter in a single multi-conductor cable on a split box. Do not connect shielded cables to the side of the meter (connect to one end only).CE2N5324en 2018-08-18Building TechnologiesPulse module WZU-P2Function description The pulse module WZU-P2 enables the meter to communicate with a pulse collector to transmit measured values. It outputs pulses that can be derived from the energy, volume, tariff register 1 or tariff register 2. Two channels are available; their function can be adapted using the service software. The outputs are in the form of standard pulses or "fast pulses". The pulse duration is identical for channel 1 and channel 2.NOTICEThe module can be plugged into both slots, but fast pulses can only be output via slot 2.Standard pulses Standard pulse valencieskWh *)1 kWh10 kWh100 kWhMJ *)1 MJ