Title: økernvn 94.pdf
Cable ID: D3196 Date / Time: 09/11/2013 03:13:19 Headroom 5.2 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]186 283 9 8.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]13.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.2 43.3 47.7 36 7.2 43.3 45.3SR 36-45 5.7 43.0 47.8 36 7.1 215.5 33.8MAIN 36-78 7.8 247.0 35.4 36 8.5 246.0 32.8SR 12-36 6.3 245.5 35.5 12 7.6 245.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.6 230.0 17.0 45 16.8 237.0 13.7