Title: +038=433.000-NI003._09-Testrapport elektriske anlegg - DM3.E3=433.08.03, Pareto plan 08.pdf
U12: 234V U1pe: 235V U2pe: 0V f: 50.1HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF200 16C2/003 06.11.2020 13:33R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM3.E3=433.08.03 / XF201 16C2/003 06.11.2020 09:41SPĆNDINGU12: 233V U1pe: 233V U2pe: 0V f: 50.0HzDM1-3. Plan 8 / DM3.E3=433.08.03 / XF201 16C2/003 06.11.2020 14:11R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩTallberg Elektro A/S Tlf.22796640Side:32GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTNr.TEST RAPPORTResultatKommentar:Rapporten ble utarbeidet av Tomasz LenartowiczTallberg Elektro A/S Tlf.22796640Side:33