Title: Tappevann - KV.pdf.pdf
KR001TMAGI-CU-35 35 (L)1. EtasjeBEND-45KR001TMAGI-CU-B1- 351. EtasjePIPEKR001TMAGI-CU-35 35 (L)1. Etasje29 BRANCHKR001TMAGI-CU-T1- 35/351. EtasjePIPEKR001TMAGI-CU-35 35 (L)1. EtasjeBEND-90KR001TMAGI-CU-B1- 351. EtasjePIPEKR001TMAGI-CU-35 35 (L)Domestic Water Pressure Calculation ReportCalculation date:09.05.2022 13:28Project number:633146-01Client name:Drammen KommuneOrganization name:Asplan Viak AsAuthor:Tom SvanbergFluid type:WaterTotal pressure:400.0 kPaFluid density:1000 kg/m3Network volume:82.5 lThermal conductivity:20.00000 W/m*K:20.00000 W/m*K:L [m]Insulationqv sum [l/s]qv dim [l/s]v (dim) [m/s]dp/L [Pa/m]dp (flow) [kPa]K factor0,1 BI002T/139,600000,862211,07599,60,1BI002T/139,600000,862211,070,61.0000,1 BI002T/139,300000,849331,06582,70,0BI002T/139,300000,849331,060,30.4911,3 BI002T/139,300000,849331,06582,70,7BI002T/139,30000