Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 14060 123.0 114.3Lighting power density: 4.41 W/m? (Floor area of room 27.89 m?) Consumption: 150 - 240 kWh/a of maximum 1000 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 28Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N l S ’ < Site 1/ Building 1/ Storey 10/ Mate 12/ ViewsMote 12Motte 12DIALux Page 29Dronning Mauds gate 1310. og 11. etasjeSite 1/ Building 1/ Storey 10 / Mete 12 / Results summary, EN 124648/28/2019/ENTSKMote 12 g il ] B : AN g ! NN I TN N BN B L. EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max1 Visual task area4 Perpendicular illuminance (adaptive) [Ix] 502 (= 500)