Title: +038=453.003-LZ001. Defrost Snow Nexans leggeanvisning.pdf
(m)(m²)(m)Min (-5%)Nominal valueMin (+10%)1100 1500 1800 2150 2600 33000.4 0.4 0.4 0.4 0.8 0.89.1 12.1 14.7 17.4 11.1 14.03.6 4.8 5.9 7.0 8.9 11.238.0 50.6 61.2 72.6 86.4 109.245.7 33.5 27.9 23.4 19.3 15.248.1 35.3 29.4 24.6 20.3 16.052.9 38.8 32.3 27.1 22.3 17.7DEFROST SNOW– heating cable elements for snow- and ice meltingPowerPower/mLength of cableResistance / element (Ohm)(Watt)(W/m)(m)Min (-5%)Nominal valueMin (+10%)640 890 1270 1900 2700 340028 28 28 28 28 2822.9 31.9 45.4 68.1 96.4 120.078.5 56.5 39.6 26.5 18.6 14.882.7 59.4 41.7 27.8 19.6 15.690.9 65.4 45.8 30.6 21.6 17.1The base The heating cable(s) shall be installed on a stable and levelled base. This can be compressed paver sand, quarry dust, concrete or asphalt.Asphalt The heating cable(s) can be covered in asphalt with a maxi- mumtemperatureof160°C.