Title: 40 Produktark nettanalysator 4x-serie.pdf.pdf
It provides access to menu screens when pressed for 3 seconds. When the PIN is active, a password is asked before entering the menu. After the correct password is entered, access to menu is allowed. It is used to reach the desired adjustment screen and to save the changed settings. Pressing the button is enough for this operation.While on measuring screen: It is used to browse between Min, Max, Demand and Max Demand screens.While on measuring screen: It is used to browse between Min, Max, Demand and Max Demand screens.Terminal Structure1) 45-300 VAC Supply Input 3 terminal connections (2 pins)2) Current measuring input terminal block (8 pins): L1 L2 L3 ve N3) Voltage measuring input terminal block (5 pins): L1 L2 L3 L4 (Earth) and N4) RS-485 terminal block (4 pins)Module Input:Digital Input/Output4 digital outputs4 digital inputsRelay Output2 relay outputs4 digital inputsAnalog Output2x 0/4 – 20mA circuit or2x 0/2 – 10V circuit9INSTALLATION