Title: 370.011 LE001_LF001 (slave-backup maskin dersom master svikter).pdf
30 3.200 1Total power input R.P.M.[kW]0,51 82 %ACOUSTIC PERFORMANCESSWL fan discharge SPL front of the unit[dB(A)] [dB(A)]77 57at the air supply mouth without sound absorbers på 2 meter i fritt felt (ISO 3744)SOUND PRESS.AND POWER LEV.IN OCTAVE BANDFreq.of the cent.of the oct.band SWL fan discharge SPL front of the unitTot. 77 5763Hz 75 55125Hz 75 55250Hz 76 56500Hz 73 531kHz 67 472kHz 69 494kHz 68 488kHz 65 45OFFER N.: OF 000049 rev. 0 date : 26/08/2016 - B UNIT : Nedblåsende enhet uten kondensatorCUSTOMER : UPA 111bEXTERNAL CONNECTIONSFrigorific connectionsInlet Outlet1 x 12 mm ODS 1 x 12 mm ODSFrigorific lines between unit and condenserLiquid lines up to 100 m (equilvalent lenght) Discharge lines up to 100 m (equilvalent lenght)1 x 1/2" (12,70 mm) 1 x 5/8" (15,88 mm)Condensing drain diameter19x25 mmELECTRICAL CHARACTERISTICSPower supply400/3/50+N+ PE