Title: økernvn 94.pdf
Cable ID: D3038 Date / Time: 09/12/2013 09:49:48 Headroom 12.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]211 335 24 9.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.1 91.3 33.0 36 15.4 95.8 29.6SR 12-36 12.4 91.3 33.0 36 14.4 91.0 30.0MAIN 12-36 13.1 91.3 33.0 36 15.4 95.8 29.6SR 12-36 12.4 91.3 33.0 36 14.4 91.0 30.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.4 61.3 22.9 36 19.8 51.0 21.5