Title: 4. Leieavtaler.pdf
11. Design Cleanrooms in accordance with FM Global Property Loss Prevention Data Sheet 1-56, Cleanrooms. Please send specifications for the Cleanrooms to FM Global for review prior to any installation.2015-01-07: Not applicable at this stage as there is no plan to install clean rooms.1'! report is provided to you for infonnalional purposes only to reduce the possibility ofl= lo insured property by bringing lo your attention certain potential 117.nrdsor conditions. Life, safety, or health issues are not addressed. You must make the dec1~1un wh~lher tu lltkc a111• aetion FM Glol>af undanake 1111 July 10~ - ,-rtyby ""''""' • • - ~ Oe "''"""''""""'hi,'""' Th, O,b,h~••FM G-"''"""' "''"'~'~ft__f/!rL2015-01-07: Only minor quantities to be used. Ventilation to be provided in the ignitable liquids cabinets.13 . Avoid locating sensitive or critical equipment in the any basement areas (i.e. , electric equipment).