Title: +038=365.009-SS002._04-mcr WIPT Stengespjeld Mercor - Montering.pdf
BF 385 125BFL 335 125BFN 385 125EXBF 460 175BE 385 125BLE 335 125817.5.2.sample installation in concrete block or full brick wallsGGXBk=B+310B12H5 5 1 + H = k H341. mounting pin 2. duct cover 3. fire damper mcr WIP 4. e.g. cement mortar* 5. e.g. masonry wall *it is possible to use a different sealing which ensures the required fire resistance5The thickness of the duct cover “G” is 50 mm for wall thickness up to 110 mm. For walls thicker than 110 mm manufacturer allows thickness of cover below 50 mm. For walls wider than dampers thickness, 30 mm duct covers can be used. The duct cover can be made of galvanized steel or stainless steel and painted any RAL color (standard RAL 9010).Distance between systems and partitions5 77575min. 2005 782