Title: økernvn 94.pdf
SR 36-45 15.6 98.8 18.7 45 18.1 98.8 15.701008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 28.3 47.3 24.0 36 30.2 47.3 21.0SR 12-36 25.2 47.3 24.0 12 26.5 44.3 21.9MAIN 12-36 32.9 100.0 11.9 36 34.1 100.0 8.9SR 12-36 27.9 94.5 12.9 36 30.7 100.0 8.901008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.1 26.0 17.9SR 36 5.4 26.0 17.9MAIN 36 4.1 26.0 17.9SR 36 9.3 88.3 12.501008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002111 ft60Insertion Loss (dB)