Title: 370.02-SC001 - Siemens SAL31.03T10 (Ventilmotor).pdf
8001)SAL..T10 rotary actuators only fit on VBF21.., DN65…150. For VBF21.., DN40/50 use SQK34.., SQK84.. (data sheet N4508) or SQK33.00 (data sheet N4506) rotary actuators.Product documentationDetailed information about the New Generation actuators can be found in the basic documentation "Electromotoric actuators SAX.., SAL.." (CE1P4040en).NotesEngineering SAL 31.. / SAL81..3-position actuators must have their own specific controller, refer to "Connection Diagrams" (page 8).SAL61..Up to 10 actuators can drive in parallel on a controller output with a rating of 1 mA. Modulating actuators have an input impedance of 100 kΩ.3 / 10Siemens Building TechnologiesElectromotoric rotary actuators for butterfly or slipper valvesCE1N4502en 2013-11-11MountingMaintenanceWarrantyNoteTechnical DataPower supplyFunction dataSignal inputs4 / 10Siemens Building TechnologiesIndoor useOutdoor use 1)1) Only in connection with weather shield ASK39.1