Title: +038=30.001-NI004._04-V67--02 Oppleggskjema kjøling.pdf
MM 42x,X kW, xXxX l/hIkke utleidDN25+03=370.101-OE035 0.214 L/sMM 352.7 kW, 770 l/hUniconsultDN 100Syd / akse DDN 100Kjøling purewater+U1=370.104-OE90188HiFiHiFi370.101 DN 150370.104 DN 100+U1=370.001-OE902Kjølesentral Se systemskjema V67-0199370.101 DN 200+U2=370.101-OE902+U1=370.001-OE901Frikjøleveksler370.102 MM 421010370.103 DN 54370.101 Kombibaffel og reserver (nord / akse A)11Beregnet behov bafler plan 3-10 v/ 100% samtidighet 48 kW (15 / 18°C) 12Beregnet behov bafler plan 3-10 v/ 100% samtidighet 48 kW (15 / 18°C) 12DN40+10=370.101-OE103 0.595 L/sMM 54Pareto/Pecunia7.5 kW, 2142 l/hDN40+09=370.101-OE093 0.692 L/sMM 54Pareto8.7 kW, 2491 l/hDN25+08=370.101-OE083 0.292 L/sMM 42Pareto3.7 kW, 1051 l/hDN 40+07=370.101-OE073 0.586 L/sMM 42Pareto7.4 kW, 2110 l/hDN32+06=370.101-OE063 0.446 L/sMM 42SB15.6 kW, 1606 l/hDN 32+05=370.101-OE053 0.407 L/sMM 35McKinsey