Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
Bruker:Tallberg Elektro A/S Stanseveien 4Instrument dataType:EUROTEST COMBOModell:MI 3125BTNr. 11ResultatOBJEKT / Plan 10 / FUSE022 10.02.2020 13:09Z-LINEZ: 0.52ΩIsc: 439A Sikringstype: C SIKRING I: 25A SIKRING T: 35ms Isc_lim: 250.0A22OBJEKT / Plan 10 / FUSE022 10.02.2020 13:10RCD II: 28.5mAUci: 0.2V t: 103.1ms Idn: 30mA type: AC Ulim: 50V33OBJEKT / Plan 10 / FUSE022 10.02.2020 13:10SPÆNDINGUln: 230V Ulpe: 230V Unpe: 2V f: 49.9Hz44OBJEKT / Plan 10 / FUSE022 10.02.2020 13:11Zs(rcd)Z: 0.32ΩIsc: 715A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A55OBJEKT / Plan 10 / FUSE022 06.02.2020 11:52R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.3Ω Grenseverdi: 1.0Ω66OBJEKT / Plan 10 / FUSE025 07.02.2020 13:07TEST RAPPORTTeststed:Pecunia Dronning Maudsgate 1-3Ser.Nr.:13250825Produsent:Metrel d.d.Side:1Rapport opprettet08.03.2022GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*