Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
6-74Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W6x56.11.1 PCD2.W6x5, analogue outputs,electrically isolated, 6 (4) channels, 10 bit resolutionApplicationHigh-speed output module for general use, electrically isolated, 6 (4) channels, each with 10 bit resolution. Different variants for voltage 0..10 V, -10 V...+10 V and current 0..20 mA are available.Module overview PCD2.W605: PCD2.W615: PCD2.W625:Voltage 0..10 V Current 0...20 mA Voltage -10..10 VChannels 6 (O0 … O5) 4 (O0 … O3) 6 (O0 … O5)Resolution 10 mV 20 μA 20 mVTechnical dataOutput ranges: Galvanic separation:see module overview 500 V, electrical isolation of outputs to PCD, channels themselves not separated6Resolution (digital representation): 10 bit (0 … 1023) Load resistance:>3 kΩ <500 Ω* >3 kΩ ± 0.4 % ± 0.7 % ± 0.4 %