Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
(3) Values shown are a guideline only. Please refer to the unit nameplate (4) On delivery, the vessels are preinflated to a standard value, which may not be the optimum one for the installation. To enable the water volume to be varied as desired, adapt the inflation pressure to a value close to that which corresponds to the static height of the installation. Fill the installation with water (bleeding out any air) at a pressure more than 10 to 20 kPa higher than the vessel pressure.14Water chillersHeat pumpDYNACIAT LGTechnical characteristicsDYNACIAT LG360390450480520600HeatingNominal capacitykW137156172183206230Standard unit Full load performances*HW1COPkW/kW5,605,575,495,645,595,56Nominal capacitykW131148163174197218HW2COPkW/kW4,424,434,374,404,484,36Nominal capacitykW125140155166189209HW3COPkW/kW3,583,623,563,603,763,59kWh/kWh6,246,286,186,246,246,08SCOP 30/35°C