Title: Data tester Smestad skole - Detaljert.pdf
601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-36 23,6 12,5 11,1 382,00Remote: 36-12 23,7 12,5 11,2 382,00Worst Value: Local: 12-45 21,9 10,4 11,5 490,00Remote: 12-45 22,1 10,4 11,7 487,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,3 25,4 3,9 448,00Remote: 36 29,2 23,8 5,4 500,00Worst Value: Local: 36 28,5 23,8 4,7 497,00Remote: 36 29,2 23,8 5,4 500,00PS-ACRF: Pass Worst Margin: Local: 12 72,1 61,2 10,9 1,00Worst Value: Local: 12 19,7 7,4 12,3 487,00Remote: 45 71,2 61,2 10,0 1,00Remote: 12 19,9 7,5 12,4 485,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:02Signature:______________________ Page: 59Copper Certification Report