Title: FDV-DOKUMENTASJON.pdf
Icu kA 85 400/415 V 50/60 Hz Icu kA 50 440 V 50/60 Hz Icu kA 35 525 V 50/60 Hz Icu kA 20 690 V 50/60 Hz Icu kA 10 Ics to IEC/EN 60947 test cycle O-t-CO-t-CO Ics kA 240 V 50/60 Hz Ics kA 85 400/415 V 50/60 Hz Ics kA 50 440 V 50/60 Hz Ics kA 35 525 V 50/60 Hz Ics kA 10 690 V 50/60 Hz Ics kA 7.5 Maximum back-up fuse, if the expected short-circuit currents at the installationlocation exceed the switching capacity of the circuit-breaker. Utilization category to IEC/EN 60947-2 A Lifespan, mechanical(of which max. 50 % trip by shunt/undervoltage release) Operations 20000 Lifespan, electrical AC-1 400 V 50/60 Hz Operations 10000 415 V 50/60 Hz Operations 10000 06/21/2019Eaton 265815 ED2019 V57.0 EN2 / 9