Title: økernvn 94.pdf
4020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: T3025 Date / Time: 09/12/2013 02:32:36 Headroom 10.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]98 155 10 4.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.8 76.8 34.2 36 14.0 76.8 31.2SR 12-36 10.1 76.8 34.2 36 12.9 76.8 31.2MAIN 12-36 12.2 100.0 32.3 36 14.4 100.0 29.3SR 12-36 10.7 100.0 32.3 36 13.3 100.0 29.310080604020NEXT (dB)