Title: +038=433.002-FS020._12-Tavlebyggeren Eaton FDV.pdf
1 / 4Solid2 mm1 - 25Thickness of busbar materialmm0.8 … 2Admissible ambient temperature range°C25 … +40Climatic proofingaccording to IEC 68-2 (25 - 55 °C, 90 - 95 % Humidity)DesignverificationasperIEC/EN61439 Technical data for design verificationRated operational current for specified heat dissipationInA16Heat dissipation per pole, current-dependentPvidW0Equipment heat dissipation, current-dependentPvidW10.9Static heat dissipation, non-current-dependentPvsW0Heat dissipation capacityPdissW0Operating ambient temperature min.°C25Operating ambient temperature max.°C400IEC/EN 61439 design verification10.2 Strength of materials and parts10.2.2 Corrosion resistanceMeets the product standard's requirements.10.2.3.1 Verification of thermal stability of enclosuresMeets the product standard's requirements.10.2.3.2 Verification of resistance of insulating materials to normal heatMeets the product standard's requirements.