Title: +038=433.000-NI003._27-Testrapport Elektriske Anlegg Pactum Plan 10 UF 433.10.01.pdf
GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 121213131414151516161717TEST RAPPORTResultatDronningMaudsgat / 433.10.01 Plan10 / SIKRING26 13.02.2020 11:47Z-LINEZ: 0.35ΩIsc: 654A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADronningMaudsgat / 433.10.01 Plan10 / SIKRING26 13.02.2020 11:48Zs(rcd)Z: 0.31ΩIsc: 737A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADronningMaudsgat / 433.10.01 Plan10 / SIKRING26 13.02.2020 11:48RCD II: 28.5mAUci: 0.2V t: 32.7ms Idn: 30mA type: AC Ulim: 50VDronningMaudsgat / 433.10.01 Plan10 / SIKRING26 13.02.2020 11:49Z-LINE dUdU: 2.1%Sikringstype: C SIKRING I: 16A SIKRING T: 35ms dU_lim: 4.0% Isc: 749A Z: 0.31Ω Zref: ___ΩDronningMaudsgat / 433.10.01 Plan10 / SIKRING26 13.02.2020 11:49RCD UbUc: 0.0V Rl: 1Ω Idn: 30mA type: AC Ulim: 50VDronningMaudsgat / 433.10.01 Plan10 / SIKRING26 13.02.2020 11:47SPÆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzSide:3GODKJENT*GODKJENT