Title: +038=360.019-#####._05-360.019 Gold SD-30 Ventilasjonsaggregat Swegon - Installasjonsanvisning.pdf
6,7External fire/smoke function 1External fire and smoke function. On delivery, this function is fitted with a jumper. If the connection is interrupted, the function will trip and initiate an alarm.8,9External fire/smoke function 2External fire and smoke function. On delivery, this function is fitted with a jumper. If the connection is interrupted, the function will trip and initiate an alarm.10,11External alarm 1External contact function. Optional: Normally open/normally closed.12,13External alarm 2External contact function. Optional: Normally open/normally closed.14,15External low speedExternal contact function. Overrides the time switch from stop to low speed operation.16,17External high speedExternal contact function. Overrides the time switch from stop or low speed to high speed operation.18,1920,21Demand controlCirculation pump, heating circuit