Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF040 C16/2 10.06.2020 11:23R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF040 C16/2 10.06.2020 11:28SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzTallberg Elektro A/S Tlf.22796640Side:27GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr. 184184185185186186187187188188189189190190TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF040 C16/2 10.06.2020 12:44Z-LINEZ: 0.44ΩIsc: 521A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF040 C16/2 10.06.2020 12:44Zs(rcd)Z: 0.38ΩIsc: 608A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF040 C16/2 10.06.2020 12:44RCD tt: 67.5msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF040 C16/2 10.06.2020 12:44RCD Ub