Title: 40 Bender Datablad.pdf.pdf
0…99 s (0 ms)* 0…999 s (200 ms)* 0…999 s (200 ms)* ≤ 180 ms ≤ 30 ms tan = tae + ton1/2 ≤ 3.5 s ≤ 180 ms 500…600 msDisplays, memoryMeasured value display range RCMS…-D / -L0…30 A (CT Type A) 0…20 A (CT type B) Display range, measured value RCMS…-D4/-L4 (channels 9…12) 0…125 A (CT type A) Error of indication ± 10 % ON/ALARM (RCMS…-D…) LEDs ON/ALARM / measuring channel 1…12 (RCMS…-L…) backlit graphical display (RCMS…-D…) 2 x 7.62 mm (RCMS4…-L) 300 data records (RCMS…-D…) 300 data records per measuring channel (RCMS…-D…) off / 0…999 (off)* D, GB, F (GB)* on/off (off)*LC display 7-segment display History memory Data logger Password Language Fault memory alarm relayInputs/outputsTest/reset button Cable length for external test/reset buttoninternal/external 0…10 mInterfaceInterface/protocol Baud rate Cable length Cable (shielded, shield connected to PE on one side) For UL application: : Copper lines Terminating resistor Device address, BMS bus