Title: 1 etg del 2.pdf
RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 8.1Cable ID: D1061 Date / Time: 10/17/2013 12:32:02 PM Headroom 1.1 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]234 371 27 10.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.1 243.5 35.5 36 1.7 249.0 32.7SR 45-78 8.2 211.0 36.5 78 9.0 250.0 32.7MAIN 36-45 1.1 243.5 35.5 36 1.7 249.0 32.7SR 45-78 8.9 250.0 35.3 78 9.0 250.0 32.710080604020NEXT (dB)