Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 36]40.5 175 2 6.01Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]23.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.5 499.0 29.3 36 9.5 500.0 26.4SR 36-45 9.2 493.0 29.4 36 7.8 476.0 26.9MAIN 12-36 7.5 499.0 29.3 36 9.5 500.0 26.4SR 36-45 9.2 493.0 29.4 36 8.0 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.9 500.0 11.3 45 19.7 500.0 8.3SR 78-45 18.9 500.0 11.3 45 18.9 500.0 8.3MAIN 45-78 18.9 500.0 11.3 45 19.7 500.0 8.3SR 78-45 18.9 500.0 11.3 45 18.9 500.0 8.30100806040200250 MHzACR-F (dB)