Title: Bytesteinen 1 - =514.202-FS001.pdf
Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 2 07/05/2021 15:25:03 Untitled11748.1 m 54 50 4 0 0Cable ID: 521.202-UD001 Date / Time: 30/03/2021 09:59:34 Headroom 8.9 dB (NEXT 3,6-4,5) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 7,8]42.8 217 13 7.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]23.3 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 10.0 141.5 37.4 7,8 11.7 213.5 31.4SR 3,6-4,5 8.9 60.3 43.6 4,5 8.8 89.8 37.9