Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
118 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 032 GODKJENT *12.03.2020 13:41SPENDINGUln: 236VUlpe: 236VUnpe: 0Vf: 50.1HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 032 GODKJENT * 12.03.2020 13:41ZLINE GODKJENTZ: 0.58QIsc: 395ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AL120Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 032 GODKJENT * 122508120200V I i8j11'2, Zs (rcd) GODKJENT Z: 0.52Q Isc: 442ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 032 GODKJENT * 12.03.2020 13:18R LOW Ohm GODKJENTR: 0.06QR+: 0.1QR: 0.1QGrenseverdi:1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 032 GODKJENT * 12 408%2020 13345RCD I a GODKJENTI: 28.5mAUci: 0.1Vt: 107.4msIdn: 30mAtype: ACH,Ulim: 25VDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 032 GODKJENT * 12.03.2020 14:37KONTINUITET GODKJENTR: 0.1QGrenseverdi:1.0QTEST RAPPORTR ISC GODKJENTR: >200MQ Um: 263V