Title: Sprinklerhode våt.pdf
The minimum spacing between sprin- klers is 8 feet (2,4 m). The maximum spacing between sprinklers cannot exceed the length of the coverage area (Table A or B) being hydraulically calculated (e.g., maximum 12 feet for a 12 ft. x 12 ft. coverage area, or 20 feet for a 20 ft. x 20 ft. coverage area).TFP400Page 3 of 6InstallationThe TYCO RAPID RESPONSE Series LFIl Residential Pendent and Recessed Pendent Sprinklers (TY2234) must be installed in accor- dance with this section:General InstructionsDo not install any bulb type sprin- kler if the bulb is cracked or there is a loss of liquid from the bulb. With the sprinkler held horizontally, a small air bubble should be present. The diam- eter of the air bubble is approximately 1/16 inch (1,6 mm).A leak-tight 1/2 inch NPT sprinkler joint should be obtained by applying a minimum-to-maximum torque of 7 to 14 ft.-Ibs. (9,5 to 19,0 Nm). Higher levels of torque can distort the sprin- kler Inlet with consequent leakage or impairment of the sprinkler.