Title: økernvn 94.pdf
190 301 21 8.1190 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.3 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 3.5 236.5 35.7 36 3.8 231.5 33.3SR 36-450.1 *248.5 35.4 36 1.1 245.0 32.9MAIN 12-36 3.7 247.0 35.4 36 3.9 249.0 32.7SR 36-45 0.1 248.5 35.4 36 1.1 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 11.1 64.5 28.0 36 13.7 53.3 26.7SR 36-45 11.3 64.5 28.0 45 14.0 64.5 25.0MAIN 36-45 17.7 245.5 16.4 36 17.7 209.5 14.8SR 45-36 17.3 245.5 16.4 36 16.8 216.0 14.5010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz