Title: SysAQ R32 100HP.pdf
Refrigerant charge for the unit 10,90 kgCompressor ValueNumber of compressors 2Compressor type ScrollCompressor startup type DirectPlant side heat exchanger Cooling HeatingNumber of exchangers 1Exchanger type PlatesTotal fluid flow rate* 17871 18346 I/h Minimum fluid flow rate 12800 I/h Minimum fluid volume (Comfort) 1316 L Pressure drop 335 353 kPaThe plant side exchanger waterflow rate is equal to the standard rating water flow rateWater connections ValueWater connection type Male Gas ThreadWater connection inlet diameter 2"1/2Water connection outlet diameter 2"1/2Fan ValueNumber of fans 2Fan type Axial FansFan speed 15 Hz External static pressure 0,0 Pa Maximum absorbed power per fan 2,10 kw Total air flow 41300 m’/hThe certified performances, conditions and the certification of the software have to be verified in www.eurovent-certification.com Systemair AC SELECT v1.0] 2022-08-15SYSAQUAR32HSYSAQUA R32 100.H.AC‘systemairCondenser Value2