Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
26.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 4.8 457.0 30.1 36 5.3 467.0 27.0SR 12-36 6.5 500.0 29.2 36 7.2 500.0 26.4MAIN 12-36 4.9 464.0 29.9 36 5.6 500.0 26.4SR 12-36 6.5 500.0 29.2 36 7.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.7 488.0 11.5 45 19.3 500.0 8.3SR 78-45 18.6 488.0 11.5 45 19.6 499.0 8.3MAIN 45-78 18.7 488.0 11.5 45 19.3 500.0 8.3SR 78-45 18.6 488.0 11.5 45 19.6 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.8 43.3 36.3 36 20.6 43.5 33.8SR 36-45 18.6 43.0 36.4 45 19.4 43.0 33.9MAIN 12-36 32.5 500.0 -12.4 36 32.4 500.0 -15.3SR 12-36 33.2 500.0 -12.4 36 34.0 500.0 -15.30804000250 MHzACR-N (dB)