Title: Hardware Installation Guide.pdf
Single Reader Interface ModuleDual Reader Interface ModuleInput/Output Control Module(s)0 1 2 3 4 5 6 7 8 9 * #Up to 32 Single Reader Interface Modules (32 readers)0 1 2 3 4 5 6 7 8 9 * #0 1 2 3 4 5 6 7 8 9 * #Up to 32 Dual Reader Interface Modules (64 readers)Up to 16 Output Control Modules Up to 16 Alarm Input Control Modulesrevision 6 — 255LNL-1100 Input Control Module41.2The Input Control Module (Series 2)The series 2 Input Control Module board contains the following components: sixteen (16) software configurable alarm inputs, two (2) non-supervised alarm inputs, two (2) alarm output relays, one (1) RS-485 interface, one (1) power input, eight (8) DIP switches, jumpers, and status LEDs.Input Control ModuleTB1 I119TB5 I9I1210I9I2311I10I2 TB2 I3451213I10TB6 I11I3614I11I4715I12I4816I12TB3 I5TB7 I13I5I13I6I14I6 TB4 I7CTI14TB8 I15I7BAI15I8I16I8I16TB9 CTGNDBAJ4GNDJ912