Title: V20-06-02 VVS-anlegg plan 6 - DM3-1.pdf
LD007T Q:120 m³/h Kjøling: 675 W 0.054 L/s Varme: 650 W 0.016 L/s370.101: 28 mm +c 2790LD007T Maks:200 m³/h Kjøling: 630 W 0.050 L/s Varme: 465 W 0.011 L/s2 LD007T Maks:200 m³/h Kjøling: 630 W 0.050 L/s Varme: 465 W 0.011 L/sLD007T Maks:200 m³/h Kjøling: 630 W 0.050 L/s Varme: 465 W 0.011 L/s370.101: 28 mm +c 2790Kontor 6-031WISE IAQSF002T-160SF002T-160 ø160 UK=2682WISE RTAø315 UK=25531 4 4 2 = K U 0 0 4 x 0 0 6 : 6 0 0.Møterom 6-032SF002T-160ø160 UK=2682SF002T-160LD009T Maks:200 m³/h Kjøling: 630 W 0.050 L/sLD009T Maks:200 m³/h Kjøling: 630 W 0.050 L/sLD009T Maks:200 m³/h Kjøling: 630 W 0.050 L/s0 6 3WISE RTA WISE IAQDN25 0,16 L/sø250 UK=2615ø250 UK=2615SF009T 1400x600 5940 m³/hø315 UK=2553ø315 UK=2553MA 110mm1400x600 UK=2235ø315 UK=25531400x400 UK=16971 4 4 2 = K U 0 0 4 x 0 0 8Fancoil 2kW tilknyttes kombibaffelkurs:6 0 0.0 6 3ø160 UK=2682LD009T Maks:200 m³/h Kjøling: 435 W 0.034 L/sÅpent kontorlandskap-2 6-136-2