Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID 521.204-UD78 521.204-UD79 521.204-UD80 521.204-UD81 521.204-UD82 521.204-UD83 521.204-UD84 521.204-UD85 521.204-UD86 521.204-UD87 521.204-UD88 521.204-UD89 521.204-UD90Summary PASS PASS PASS PASS PASS PASS PASS PASS PASS PASS FAIL PASS PASSTest Limit EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class E EN50173 Channel Class EPage 2 28/02/2022 11:07:49 Simployer - Data testrapport =514.204-FS001.flwLength 55.0 m 55.2 m 48.7 m 48.9 m 48.9 m 48.9 m 40.7 m 34.8 m 35.0 m 49.1 m 10.7 m 4.6 m 38.6 mHeadroom 8.2 dB (NEXT) 9.0 dB (NEXT) 9.7 dB (NEXT) 6.7 dB (NEXT) 8.5 dB (NEXT) 7.4 dB (NEXT) 8.2 dB (NEXT) 7.6 dB (NEXT) 8.8 dB (NEXT) 7.2 dB (NEXT) -5.4 dB (NEXT) 7.1 dB (NEXT) 9.3 dB (NEXT)