Title: Eurotester målerestultat.pdf
Bytesteinen 1 / =433.202 / SIKRING23 30.03.2021 14:08:50R LOW OhmR: 0.17ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING24 30.03.2021 14:06:48Z-LINEZ: 0.87ΩIsc: 264A Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A Isc(0.38%): 100A Isc(0.76%): 200A Isc(1.15%): 303ABytesteinen 1 / =433.202 / SIKRING24 30.03.2021 14:07:06RCD II: 27.0mAUci: 9.0V t: 20.5ms Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING24 30.03.2021 14:07:15R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING24 30.03.2021 14:07:29R LOW OhmR: 0.12ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.5ΩTestet av: Andreas PedersenSide:11GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr. 717172727373747475757676TEST RAPPORTResultatBytesteinen 1 / =433.202 / SIKRING25 30.03.2021 13:46:48Z-LINEZ: 0.87Ω