Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Side:21GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.146146147147148148149149150150151151152152TEST RAPPORTResultat KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 30.11.2020 09:24SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.1HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 30.11.2020 09:25Z-LINEZ: 0.80ΩIsc: 287A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 30.11.2020 09:25Zs(rcd)Z: 0.51ΩIsc: 447A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 30.11.2020 09:26RCD II: 28.5mAUci: 0.0V t: 15.4ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF038 16C2/003 30.11.2020 11:55 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254V