Title: bn305_cgb.pdf
116-P-BN305/CGB, Rev. C, 2016-02-02 Protecting life, environment and propertyDual Monitored Input/Output Unit – BN-305Technical specificationsPart numberDescriptionDimensions (mm)125 x 125 x 75116-BN-305Dual monitored input/output unitWeight (g)390Housing materialPolyamide 6.6.ColourLight greyConnectorsMountingWall mounting, 110 mm bolt spacePowerCurrent consumptionTemperature rangeHumidityDegree of protection Cable glands (PG- 13,5), includedCommunication loop protocolCable terminalsCable requirements Al_ComConnects to Al_Com loop only0,1 mA25 to +70 °C10 % - 95 % RH (non-condensing)IP67Autronica loop communication protocol (AL_Com)Max 2.5 mm² single core wires