Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]43.5 188 2 6.44Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]22.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.1 499.0 29.3 36 8.1 500.0 26.4SR 12-36 6.9 398.0 31.4 36 7.6 466.0 27.1MAIN 12-36 8.1 499.0 29.3 36 8.1 500.0 26.4SR 12-36 7.5 487.0 29.5 36 8.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 19.6 500.0 11.3 45 19.7 500.0 8.3SR 12-45 19.3 500.0 11.3 45 19.4 500.0 8.3MAIN 45-12 19.6 500.0 11.3 45 19.7 500.0 8.3SR 12-45 19.3 500.0 11.3 45 19.4 500.0 8.30100806040200250 MHzACR-F (dB)