Title: DOCA0005EN-12.pdf
Possible valuesDescriptionObject_IdentifierR—configurableThe unique device ID number for the meter, in the format of <device, #>.NOTE: You must use the front panel to configure the device ID number.A configurable name for the meter.Object_NameR/W √configurableThe meter ships from the factory with a name of <model name>_<serial number> (for example, iEM3265_0000000000).Object_TypeR—DeviceThe object type for the meterSystem_StatusR—OperationalThis value of this property is always Operational.Vendor_NameR—Schneider Ele ctricMeter manufacturerVendor_IdentifierR—10The BACnet vendor identifier for Schneider ElectricModel_NameR—iEM3165, iEM3265, iEM3365, iEM3465, iEM3565Device model (for example, iEM3265) and serial number in the format <model name>_<serial number> (for example, iEM3265_0000000000).Firmware_RevisionR—variesBACnet firmware version, stored in an x.x.x format (for example, 1.7.2).Application_Software _VersionR—