Title: V67--02 Oppleggskjema kjøling.pdf
Beregnet behov bafler plan 3-10 v/ 100% samtidighet 48 kW (15 / 18°C) 12Beregnet behov bafler plan 3-10 v/ 100% samtidighet 48 kW (15 / 18°C) 12DN40+10=370.101-OE103 0.595 L/sMM 547,5 kW, 2140 l/hPareto/PecuniaDN40+09=370.101-OE093 0.692 L/sMM 548,7 kW, 2490 l/hParetoDN25+08=370.101-OE083 0.292 L/sMM 423,7 kW, 1055 l/hPareto+07=370.101-OE073MM 425,8 kW, 1663,6 l/hParetoDN32+06=370.101-OE063 0.446 L/sMM 42SB15,6 kW, 1606 l/h+05=370.101-OE053MM 35Pareto4,5 kW, 1290,7 l/h+04=370.101-OE043MM 42Vika Invest4,8 kW, 1376,8 l/h+03=370.101-OE033EQTMM 354,3 kW, 1233,4 l/hNord / akse ADN 100370.101DN 100GladstadL'Escalier370.101 Kombibaffel og reserver (syd / akse D)Beregnet behov bafler plan 3-10 v/ 100% samtidighet 58 kW (15 / 18°C)DN40+10=370.101-OE106 0.527 L/sMM 426,6 kW, 1900 l/hPareto/PecuniaDN40+09=370.101-OE096 0.867 L/sMM 5410,9 kW, 3120 l/hParetoDN32+08=370.101-OE086 0.406 L/sMM 42