Title: +175=432.001_432 Hovedfordelinger.Beskrivelse.pdf
Class 1 (-10...15...30...55"C), to EN 61036 and IEC 1036Temperature1 0...55"C (nominal), -20...7 0" C (storage)HumidityUp to 95% (without condensing)EMCEmissionTo ËN 61036 and IEC 1036lmmunityTo EN 61036 and IEC 1036ConnectionsScrew terminals, 2.5 mm2ProtectionlP 20, to EN 60529 and IEC 529MaterialsAll plastic pañs are self-extinguishing to UL94 (V0).2Selection of current transformer ratio The measuring range is selected according to the ratio of the external current transformers by means of dip switches. These are easily accessible through a hole in the front plate of the meter. The selected current transformer ratio will not be activated until the TAE-2 has been reconnected (i.e. after disconnection and reconnection of the power supply).After selection of the current transformer ratio the hole is sealed using a plug, which is included on delivery.Jrne-r @o00000 kwhCurrent transformer ratioln30 ono off)34oln506080zln100150 200zlj.*