Title: Simployer - Data testrapport =514.204-FS001.pdf
Test Summary: PASSModel: DTX-ELT Main S/N: 9862060 Remote S/N: 9862059 Main Adapter: DTX-CHA001 Remote Adapter: DTX-CHA00135.0 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD87 Date / Time: 28/01/2022 14:03:11 Headroom 7.2 dB (NEXT 1,2-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]49.1 253 19 8.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]21.0 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 8.5 216.0 34.2 3,6 9.2 215.5 31.3SR 1,2-7,8 7.2 117.5 38.7 1,2 8.0 215.5 31.3