Title: 370.011 LC002_22 kW isvannsenhet OPU 30B.pdf
Available static pressure : Total air flow : Fan[Pa] [m3/h] [n]30 7.400 1Total power input R.P.M.[kW]1,38 83 %ACOUSTIC PERFORMANCESSWL fan discharge SPL front of the unit[dB(A)] [dB(A)]83 63at the air supply mouth without sound absorbers på 2 meter i fritt felt (ISO 3744)SOUND PRESS.AND POWER LEV.IN OCTAVE BANDFreq.of the cent.of the oct.band SWL fan discharge SPL front of the unitTot. 83 6363Hz 81 61125Hz 81 61250Hz 82 62500Hz 79 591kHz 73 532kHz 75 554kHz 74 548kHz 71 51OFFER N.: OF 000051 rev. 0 date : 26/08/2016 - A UNIT : UPFLOW AIR COND.WITH CHILLED WATER COILCUSTOMER : OPU 30bEXTERNAL CONNECTIONSChilled water coil connections Inlet Outlet1 x 1 1/4" F 1 x 1 1/4" FCondensing drain diameter19x25 mmELECTRICAL CHARACTERISTICSPower supply400/3/50+N+ PE