Title: +038=433.002-FS030._05-Eaton Tavlebyggeren Produktblad.pdf
Degree of ProtectionIP20, IP40 (when ﬁtted)Terminals top and bottomTwin-purpose terminalsTerminal protectionFinger and back-of-hand proof to BGV A2Terminal capacities2 mm2 mm1 x 252 mm2 x 10Thickness of busbar materialmm0.8 … 2Mounting positionAs requiredDesign veriﬁcation as per IEC/EN 61439 Technical data for design veriﬁcationRated operational current for speciﬁed heat dissipationInA20Heat dissipation per pole, current-dependentPvidW0Equipment heat dissipation, current-dependentPvidW12.8Static heat dissipation, non-current-dependentPvsW003/07/2019Eaton 279062 ED2019 V53.0 EN1 / 8Heat dissipation capacityPdissW0Operating ambient temperature min.°C40Operating ambient temperature max.°C75linear, per +1 °C, results in a 0.5% reduction of current carrying capacityIEC/EN 61439 design veriﬁcation10.2 Strength of materials and parts10.2.2 Corrosion resistanceMeets the product standard's requirements.