Title: Hardware Installation Guide.pdf
TB2-4IN4TB3-1VOReader 1 Power Output – 12 VDCTB3-2LEDReader 1 LED Outputrevision 6 — 345LNL-1300e Single Door IP Interface ModuleConnectionsTB3-3BZRReader 1 Buzzer OutputTB3-4CLKReader 1 CLK/Data 1/TR+TB3-5DATReader 1 DAT/Data 0/TR-TB3-6GNDReader 1 GroundTB4-1LEDReader 2 LED OutputTB4-2BZRReader 2 Buzzer OutputTB4-3CLKReader 2 CLK/Data 1TB4-4DATReader 2 DAT/Data 0TB5-1VOAuxiliary Power Output - 12 VDCTB5-2GNDAuxiliary Power Output GroundTB5-3VINInput Power - 12 VDC (from local power supply)TB5-4GNDInput Power GroundTB6-1NORelay K1 - Normally Open ContactTB6-21-CRelay K1 - Common ContactTB6-3NCRelay K1 - Normally Closed ContactTB6-4NORelay K2 - Normally Open ContactTB6-52-CRelay K2 - Common ContactTB6-6NCRelay K2 - Normally Closed Contact66.1.1Input PowerThe LNL-1300e can be powered using either of the following (jumper-selected) methods: