Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
4 inputs for Ni 100 probes 2 mA -50 °C … +150 °Cbetter than 0.4 °CPCD2.W112 Current sources Measuring range Accuracy of measurement4 inputs for Pt 1000 probes 0.2 mA -50 °C … +150 °Cbetter than 0.2 °CPCD2.W113 Current sources Measuring range - Accuracy of measurement4 inputs for Ni 1000 probes 0.2 mA -50 °C … +150 °Cbetter than 0.4 °CPCD2.W114 Current sources Measuring range Accuracy of measurement4 inputs for Pt 100 probes 0.2 mA 0 °C … +350 °Cbetter than 0.4 °CAccuracy of measurementsThe curves below show the maximum measurement error (measurement and repeating accuracy).Total error = linearization error + repeating errorEach channel is calibrated to the minimum and maximum values:50 °C +150 °C→ →0 4095+ 2 LSB - 2 LSBFor these two values, the measurement error = 0.5-57Deviation (LSB)+6 +5 +4 +3 +2 +1 0 +1 +2 +3 +4 +5 +6Measurement50 00 1024+50 2047.5+100 3071+150 4095°C LSB