Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
(cid:19)(cid:24)(cid:18)(cid:20)(cid:21)(cid:18)(cid:20)(cid:20)(cid:3)(cid:3)(cid:3)(cid:20)(cid:28)(cid:29)(cid:20)(cid:21)In rooms with high humidity, brackets should be insulated by self adhesive insulation supplied.Installation Mark the position of the hangers, connection lines and condensate drain pipe, power supply cables and remote control cable (see dimensions); the cardboard template (supplied with the kit) may be of assistance for this operation. Depending on the type of ceiling the hangers can be fixed as shown in the drawing 17.Once the threaded hangers have been positioned, do not tighten the nuts, and insert the washers as shown in the drawing 18.First position the connection lines , as described in the chapter "Water connections". Remove the "T" bar in order to facilitate installation operations (See fig. 19).