Title: datablad gb fx net alc.pdf
See further information in the FX NET Installation and Commissioning Guide.Dimensions (h*w*d) [mm] Weight (fully equipped, excl. batteries) Ingress protection class Operating ambient temperature Storage ambient temperature Maximum ambient humidity Back frame material Cover material Cover color Number of ALC, CLC and IOC boards - FX-ALCA, FX-ALCB and/or FX-CLC together - FX-IOC - FX-ALCA, FX-ALCB, FX-CLC and FX-IOC together Number of addresses per detection circuit Total number of addressable detectors and manual call points connected to the panel Mains supply voltage Mains supply power Operating voltage range Maximum current consumption in standby condition Maximum current consumption in alarm conditionFX NETFXL NET578 x 425 x 13011 kg12 kgFXM NET 328 x 425 x 130 6 kgFXS NET 328 x 417x79 4,4 kgIP40 +5…+40°C 0…+50°C 95 % RH sheet steel plastic bluish grey442144215821126512504252230 VAC ±10% / 50 ... 60Hz 160 VA80 VANA21 ... 30 Vdc1,0 A @ 24Vdc