Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 10:07Z-LINEZ: 0.42ΩIsc: 543A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 10:07Zs(rcd)Z: 0.36ΩIsc: 635A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 10:08RCD UbUc: 0.1V Rl: 2Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 10:08Tallberg Elektro A/S Tlf.22796640Side:9GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.6262636364646565666667676868TEST RAPPORTResultatRCD tt: 57.9msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 12:26R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF026 C16/2 12.06.2020 12:26KONTINUITET R: 0.2Ω