Title: Simployer - Data testrapport =514.204-FS001.pdf
Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]27.9 143 10 5.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]27.2 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 10.1 232.0 33.7 1,2 11.1 231.5 30.7SR 3,6-7,8 10.4 69.3 42.6 3,6 10.8 69.0 39.9MAIN 1,2-3,6 10.4 250.0 33.1 3,6 11.4 247.5 30.2SR 1,2-3,6 11.3 231.5 33.7 3,6 12.6 232.0 30.7PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 16.1 3.5 52.4 4,5 17.3 3.9 48.5SR 7,8-4,5 16.0 5.8 48.1 4,5 17.4 4.0 48.2MAIN 7,8-4,5 16.5 241.5 15.6 4,5 18.7 241.5 12.6