Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
29.9 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.4 477.0 28.9 36 9.3 477.0 26.1SR 36-45 6.3 463.0 29.6 36 7.8 463.0 26.8MAIN 36-45 9.6 482.0 28.7 36 9.7 495.0 25.2SR 36-45 6.9 491.0 28.3 36 8.1 490.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.9 3.8 53.8 45 13.5 2.3 55.2SR 36-45 14.8 291.0 16.0 45 13.4 2.1 55.7MAIN 36-45 15.5 471.0 11.8 45 17.1 500.0 8.3SR 36-45 15.9 485.0 11.5 45 17.0 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 29.5 74.3 28.8 12 29.6 77.3 25.7SR 12-45 28.8 77.0 28.3 12 29.8 77.0 25.8MAIN 36-45 39.0 496.0 -12.1 36 38.4 495.0 -14.9SR 36-45 35.4 491.0 -11.8 45 36.8 491.0 -14.70804000250 MHzACR-N (dB)