Title: 2wayEPIV_PICS_en.pdf
0…100Overridden = true, if the gear is disengagedAbsPosAI[2]Absolute Position in degree0...max angleThe unit depends on the device: [°] for actuators with rotary movementOverridden = true, if the gear is disengagedSpAnalogAI[6]Analog Setpoint in %0...100Shows the setoint in % if actuator is control by analog signal (SpSource MV[122] is Analog(1)).If SpSource MV[122] is Bus(2), then Out_Of_Service is TRUERelFlowAI[10] Relative Flow in %0...100AbsFlow_UnitSelAI[19]Absolute Flow in selected unit0...VnomFlow in unit selected in MV[121]Sens1AnalogAI[20]Sensor 1 as analog valueCurrent value of sensor 1 in case Sensor1Type MV[220] is passive.If Sens1Type MV[220] is Switch(5) or Sens1Type MV[220] is None(1) or SpSource MV[122] is Analog(1) then Out_Of_Service is TRUESpRelAO[1] Relative Setpoint in %0...100Setpoint for actuator between Min AV[97] and Max AV[98] if controlled via bus.If SpSource MV[122] is Analog(1) then Out_Of_Service is TRUEMax