Title: Data tester Smestad skole - Detaljert.pdf
Margin 64,4 - 371,0 40,0 18,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 2,05Worst Value: Local: 45 15,3 43,6 28,3 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 23,2 14,2 9,0 96,25Remote: 78 19,6 11,6 8,0 172,00Worst Value: Local: 12 17,5 8,0 9,5 476,00Remote: 12 16,8 8,0 8,8 500,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,6 26,7 1,9 500,00Remote: 36-45 29,3 26,7 2,6 500,00Worst Value: Local: 36-45 28,6 26,7 1,9 500,00Remote: 36-45 29,3 26,7 2,6 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 22,9 12,2 10,7 399,00