Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF020 C16/2 10.06.2020 11:10Tallberg Elektro A/S Tlf.22796640Side:1Rapport opprettet02.09.2020GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.889910101111121213131414TEST RAPPORTResultatSPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF020 C16/2 12.06.2020 12:33R LOW OhmR: 0.10ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF020 C16/2 12.06.2020 12:34KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 10:45R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 10:49SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF021 C16/2 10.06.2020 12:35Z-LINEZ: 0.50ΩIsc: 461A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A