Title: +038=360.000-LC008T_04-Major line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
The technical design of the unit should allow it to be installed horizontally or vertically without modification.The control will be factory-fitted to the units to ensure correct operation. With vertically cased units, the control unit will be flush-mounted to the top of the casing. The flush-mounted control terminals will integrate perfectly with the exterior design of the casing by using the same RAL colours.The air filter, minimum G3 type according to EN779, with M1 fire resistance and fitted on removable runners must be easily accessible and removable.Air supply will be via a COANDA effect grille in order to ensure compliance with comfort standard ISO 7730. The fins must not under any circumstances be directed or able to be directed towards the occupied space.