Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF033 C16/2 12.06.2020 12:08KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF033 C16/2 12.06.2020 12:08R LOW OhmR: 0.31ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF034 C16/2 10.06.2020 11:04R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF034 C16/2 10.06.2020 11:11SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF034 C16/2 12.06.2020 10:06Tallberg Elektro A/S Tlf.22796640Side:19GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.130130131131132132133133134134135135TEST RAPPORTResultatRCD II: 28.5mAUci: 0.1V t: 103.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF034 C16/2 12.06.2020 10:07Z-LINEZ: 0.42ΩIsc: 543A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A