Title: Kabelspesifikasjoner AutroSafe.pdf
Cable length (m) for AWG 20 (0,5mm²) 1600 1114 786 571 429 329 257Cable length (m) for AWG 18 (0,75mm²) 2400 1671 1179 857 643 493 386Cable length (m) for AWG 17 (1,0mm²) 3200 2229 1571 1143 857 657 514Cable length (m) for AWG 15 (1,5mm²) 4800 3343 2357 1714 1286 986 771Cable length (m) for AWG 13 (2,5mm²) 8000 5571 3929 2857 2143 1643 1286CablingAl_Com Fire Detection Loops AutroSafeLoop Driver ModuleStandard loop driver module BSD-310 High-power version BSD-311 (High- current)Max cable resistance (Ω)5020Maximum capacitance (µF)0,50,5Cable length (m) for AWG 20 (0,5mm²)650250Cable length (m) for AWG 18 (0,75mm²)1000400Cable length (m) for AWG 17 (1.0mm²)1300500Cable length (m) for AWG 15 (1,5mm²)2000800Cable length (m) for AWG 13 (2,5mm²)33001300In Integrated Fire & Gas Detection Systems, shielded cable is recommended. Cable dimension CSA 1.0mm2