Title: 563-Carlo Gavazzi-24VDC Strømforsyning.pdf
10203040506 0°CAmbient temperatureAmbient temperature2504/03/2020Wiring diagramLine - LElectrical lineNeutral - NGroundVACVDC+LOADConnection specificationSPDM 30WSPDM 50WSPDM 75WSPDM 120WSPDM 240WTerminal typeScrew or spring terminal typeInput 6.35mm, 3pin screw terminalsScrew driver bladePhilips 1 ( PH 1 )3.5mm slotted or cross screwdriverTightening torque (recommended)5Nm5NmFlexible conductor cross section max2.5mm2 (screw) 2.0mm2 (spring)4mm2Flexible conductor cross section min0.2mm20.5mm2Conductor cross section AWG maxAWG26 (screw) AWG 24 (spring)AWG20 (PG wire >18AWG)Conductor cross section AWG minAWG12 (screw) AWG 14 (spring)AWG10 (PG wire >18AWG)Rigid conductor cross-section min2.5mm2 (screw) 2.0mm2 (spring)6mm2Rigid conductor cross-section max0.2mm20.5mm2Max wire diameter