Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]22.0 95 1 3.34Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]31.6 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.0 462.0 29.6 36 9.3 455.0 27.2SR 36-45 7.3 485.0 28.5 36 7.5 489.0 25.5MAIN 12-45 9.0 462.0 29.6 36 10.5 499.0 25.0SR 36-78 7.5 494.0 28.1 36 7.6 494.0 25.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.8 3.8 53.8 45 13.7 2.9 53.1SR 45-78 14.8 3.5 54.4 45 13.7 2.9 53.1MAIN 36-45 16.8 473.0 11.7 45 17.8 500.0 8.3SR 45-36 16.9 473.0 11.7 45 17.9 495.0 8.30100806040200250 MHzACR-F (dB)