Title: Tørrsprinkler.pdf
FIGURE 15 MODEL DSB-2 DRY SPRINKLER BOOT WITH SIDEWALL SERIES DS-1 DRY-TYPE SPRINKLERTFP500 Page 8 of 10Installation TYCO Series DS-1 5.6K Pendent, Upright, and Horizontal Sidewall, Stan- dard Response, Standard Coverage Dry-type Sprinklers must be installed in accordance with this section.General Instructions Series DS-1 Dry-type Sprinklers must only be installed in fittings that meet the requirements of the Design Cri- teria section. See the Design Criteria section for other important require- ments regarding piping design and sealing of the clearance space around the Sprinkler Casing.Do not install any bulb-type sprinkler if the bulb is cracked or there is a loss of liquid from the bulb. With the sprin- kler held horizontally, a small air bubble should be present. The diameter of the air bubble is approximately 1/16 in. (1,6 mm) for the 135°F (57°C) rating to 1/8 in. (3,2 mm) for the 360°F (182°C) rating.