Title: 32 Pumper modbuss teknisk data.pdf.pdf
Fixed value.Fixed value.Set via DIP switch SW3. See section 5.2 Setting the stop bits and the parity bit.Set via DIP switch SW3. See section 5.2 Setting the stop bits and the parity bit.Off, flashing green, flashing red, permanently red. See section 5.5 Status LEDs.Using repeaters, you can increase this number. Legal address range is 1-247.Total length. Node address and CRC included. See section 13. Modbus RTU telegram examples.4.3 CIM 260 3G/4G cellularThe table below provides an overview of the specifications for Grundfos CIM/CIU 260. For further details, refer to the specific sections of this functional profile.Modbus cellular specificationsDescriptionCommentsData protocolModbus TCPData connection uses Modbus TCP.Slave addressFactory 231 (0xE7)You can change the address via Modbus register 00003, SoftwareDefinedModbusAddress.Cellular connection visual diagnostics LED1See section 6.2 Status LEDs.Maximum Modbus telegram size260 bytes