Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Technical data Number of outputs: Output current:16, electrically connected 5In the voltage range 10 … 24 VDC, the load resistance should not be less than 48 Ω yes 8 A on 100% duty cycle Source operation (positive switching) 10 … 32 VDC smoothed, max. 10 % ripple max. 0.3 V at 0.5 A typically 50 μs, max. 100 μs for resistive load 4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) max 74 mA (all outputs = "1") typically 40 mA 0 mAShort circuit protection Total current per module: Operating mode: Voltage range: Voltage drop: Output delay: Resistance to interference: acc. to IEC 801-4 Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Load current Terminals:Spring terminal connection (not pluggable), for wires up to max. 0.5 mm2 (1 x AWG 20)6LEDs and connection terminalsBus connectorBus interfaceQuad output driverRecovery diodesLEDs (3 colour)Screwless terminalsA15 A14A13 A12A11 A10A9 A8