Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
1 1 630 4,3 3,08 740 9,4 6,14 528 10,5 33 24 101 1 710 4,98 3,52 856 8,8 5,22 449 6,5 34 25 1010 3 1165 6,51 4,83 1120 19,8 9,36 805 22,5 48 39 335 2 380 2,18 1,6 375 6,2 2,85 245 7,6 39 30 8 1,4 0,75 2 870 5,28 3,84 908 13,6 7,54 649 15,5 39 30 17 3,0 1,45 2 1130 7,17 5,2 1233 17 7,16 616 11 47 38 32 3,6 1,1820 x 820 x 303Condensate pump absorption: 10 W(E) = Eurovent certified performance.= The sound pressure levels are 9 dB(A) lower than the sound power levels and apply to the reverberant field of a 100 m3 room and a reverberation time of 0.5 sec.= The sound pressure levels are 9 dB(A) lower than the sound power levels and apply to the reverberant field of a 100 m3 room and a reverberation time of 0.5 sec.30SkyStar ECM SkyStar ECMSkyStarEmissionCooling emission of 1 battery units (2 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.ECM Mod.SK 12SK 22SK 32SK 42SK 52Speed Vdc