Title: isover_fireprotect_produktdokumentasjon_spfr_010-0202_2016_no_-_gyldig_til_07_2021.pdf
Tabell A.7: Design Steel Temperature (TKritisk) 600oC: Design table for ISOVER Fire Protect 150 mineral wool boards for fire protection on steel to Standard Fire Exposure. Design values from ENV 13381-4:2007 numerical regression. Regression constants multiplied with factor kMOD = 0,996 to satisfy prEN 13381- 4:2009 Section 13.5.1 Criteria for acceptability.Multiple R0,998985600oCR20,99797230609012015018021024050202020202030355060202020202535506070202020203040607080202020253550607090202020304060708010020202030506070110202020355070801202020254050708013020202540607014020203050608015020203050608016020203050708017020203050708018020203550701902020356070200202035607021020204060802202020406080230202040608024020204060802502025406080F/AOpen and closed steel sectionsCritical steel temperature: ao = 0kMOD = 0,996Fire Resistance time in minutesSP Fire Research AS Postadresse Postboks 4767 Sluppen 7465 TrondheimBesøksadresse Tillerbruveien 202 7092 TillerTelefon 464 18 000E-post / web post@spfr.no www.spfr.no