Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Uln: 232V Ulpe: 232V Unpe: 1V f: 50.0HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF028 C16/2 15.06.2020 09:06Z-LINEZ: 0.36ΩIsc: 640A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF028 C16/2 15.06.2020 09:06Zs(rcd)Z: 0.27ΩIsc: 847A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF028 C16/2 16.06.2020 09:44R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF029 C16/2 15.06.2020 09:54SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF029 C16/2 15.06.2020 08:27Z-LINEZ: 0.25ΩIsc: 917A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF029 C16/2 15.06.2020 08:28Tallberg Elektro A/S Tlf.22796640Side:8GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.5858595960606161626263636464