Title: 32 Pumper modbuss teknisk data.pdf.pdf
RESERVED00219RESERVED00220RESERVED00221FlowEstimationState00222Kp00223Ti00224DirectControlDescriptionMaximum pump frequency in % of nominal frequency. The scale is 0.01 %. Only available on MAGNA3 and MGE model H and later.Minimum value of setpoint range in % of sensor maximum value. The scale is 0.01 %. Only available on MAGNA3 and MGE model H and later.Maximum value of setpoint range in % of sensor maximum value. The scale is 0.01 %. Only available on MAGNA3 and MGE model H and later.State of the flow estimation algoritm 0: Flow estimation within range 1: Flow estimation below range 2: Flow estimation above rangeActual proportional gain. The scale is 0.1. Only available on MAGNA3 and MGE model H and later.Actual integral action time. The scale is 0.1 s. Only available on MAGNA3 and MGE model H and later.Actual selection between Direct/Inverse control. 0: Inverse control 1: Direct control Only available on MAGNA3 and MGE model H and later.23)B G(h s