Title: Hardware Installation Guide.pdf
The Input Control Module requires a 12 to 24 VDC ± 10% power source for its input power.revision 6 — 285LNL-1100-U Input Control ModuleWire the Power In input with 18 AWG (minimum) twisted pair cable.Power SourceRequirementsCurrentDC power sourceIsolated, non-switching, regulated DC power300mA for 12VDC 150mA for 24VDCNote:Be sure to observe polarity.Power source wiring49.7UL Listed InstallationsFor UL Installations, the following must be observed:All field wiring terminals are suitable for single wire only.Use 22 AWG minimum for wiring all inputs and RS-485.The use of AC Strikes is “Not Evaluated by UL” and therefore cannot be used in UL Installations.Environmental for UL installations: - -Temperature: -10 to +49°C (14 to 120°F) operating Humidity: 85+/-5% at 30+/-2°C (86°F)286 — revision 6Hardware Installation Guide50SpecificationsNote:For UL installation, refer to section UL Listed Installations on page 286.