Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]29.9 129 1 4.54Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]27.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.0 498.0 29.3 36 8.4 498.0 26.4SR 12-36 8.2 473.0 29.8 36 8.4 474.0 26.9MAIN 36-45 9.0 498.0 29.3 36 8.4 498.0 26.4SR 12-36 8.7 500.0 29.2 36 8.6 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.7 6.6 48.8 45 21.0 498.0 8.3SR 78-45 19.7 7.0 48.3 45 20.4 500.0 8.3MAIN 45-78 21.0 500.0 11.3 45 21.0 498.0 8.3SR 78-45 20.2 496.0 11.3 45 20.4 500.0 8.30100806040200250 MHzACR-F (dB)