Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
SR 45-36 18.5 500.0 11.3 45 20.0 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 20.4 57.5 32.5 45 20.6 58.5 29.8SR 36-45 18.8 58.3 32.3 45 20.4 58.0 29.9MAIN 36-45 36.5 498.0 -12.3 36 35.5 498.0 -15.1SR 12-36 36.3 499.0 -12.3 36 37.3 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.3 477.0 8.0SR 45 6.8 469.0 8.0MAIN 45 7.3 477.0 8.0SR 45 6.8 469.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: SP1 BANK 4 ETGSMN 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00428.1 m60Insertion Loss (dB)504030201000250 MHz500100