Title: økernvn 94.pdf
Cable ID: D4152 Date / Time: 09/10/2013 04:59:31 Headroom 11.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 45] [Pair 45] [Pair 45]151 225 2 7.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]10.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.8 92.3 32.9 36 15.1 99.0 29.4SR 12-36 11.1 90.0 33.1 36 13.7 90.0 30.1MAIN 12-36 12.8 99.0 32.4 36 15.1 99.0 29.4SR 12-36 11.1 99.0 32.4 36 13.7 99.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.8 5.6 43.6 36 24.1 4.0 43.6