Title: 1 etg del 2.pdf
Cable ID: D1072 Date / Time: 10/17/2013 12:20:37 PM Headroom 13.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]297 469 31 12.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]4.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.7 98.3 32.4 36 15.5 95.0 29.7SR 12-36 15.3 98.3 32.4 36 15.9 98.5 29.4MAIN 12-36 13.7 98.3 32.4 36 15.6 98.3 29.4SR 12-36 15.3 98.3 32.4 36 15.9 98.5 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.6 40.0 26.6 36 21.1 49.3 21.8