Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Model: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00414.3 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: OLAV V 5 ETG-DM1 4ETG 01 Date / Time: 01-12-2022 12:17:45 Cable Type: OM4 Multimode 50 Backscatter Coefficient: -68.0dB (850 nm) Backscatter Coefficient: -75.8dB (1300 nm)n = 1.482000 (850 nm) n = 1.479000 (1300 nm)Loss (R->M) PASS Date / Time: 01-12-2022 12:17:45 Test Limit: EN50173 Fiber Optic Link Limits Version: 7.1 CertiFiber Pro (2388501 V6.1 Build 3) Module: CFP-QUAD(2440413) Calibration Date: 19-07-2017 certifiber pro remote (2412037 v6.1 build 3) Module: CFP-QUAD(2440405) Calibration Date: 19-07-2017