Title: økernvn 94.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.4 38.8 37.3 36 15.1 38.8 34.8SR 12-36 10.1 36.0 38.2 12 12.0 33.3 36.8MAIN 12-36 23.8 239.0 5.8 36 23.7 249.5 2.1SR 12-36 19.4 238.5 5.8 36 20.0 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.2 25.4 19.0SR 45 3.6 25.5 19.0MAIN 45 9.5 231.0 10.4SR 36 6.7 232.0 10.306050050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4