Title: økernvn 94.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.7 * 249.5 35.4 36 0.9 * 246.5 32.8SR 36-451.0 *249.5 35.4 36 0.3 *248.0 32.8MAIN 36-45 0.7 249.5 35.4 36 0.9 249.5 32.7SR 36-45 1.0 249.5 35.4 36 0.3 248.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 9.2 57.5 29.0 36 11.9 57.5 26.0SR 45-36 9.4 70.0 27.3 45 12.1 49.0 27.4MAIN 36-45 11.3 179.5 19.1 45 13.4 172.5 16.5SR 45-36 10.7 182.5 19.0 36 13.9 182.0 16.0010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250