Title: UNITOUCH_SP.pdf
A mixed architecture with standard room devices and Bluetooth low energy enabled devices is not recommended.Wireless CommunicationsType Bluetooth 4.2 Frequency 2402 - 2480 MHzTemperature SensorRange 0°C to 50°C (32°F to 122°F) Accuracy Sensing component; ±0.20°C(±0.36°F) Overall accuracy; ±0.50°C (±0.90°F)Resolution 0.10°C (0.18°F)Humidity SensorAccuracy <±3%: RH 0% to 70%Resolution 1%CO₂ SensorMeasurement Range 0 to 2000 ppmOperating Elevation 0 to 4877m (16000 ft)Warm-up Time < 2 minutes (operational), 10 minutes (maximum accuracy)CO2 Accuracy1 400-1250 ppm ± 30 ppm or 3% ofreading, whichever is greater1250-2000 ppm ±5% of reading + 30ppm1.Tolerance based on span gas of ±2% and ABC Logic enabled.2 / 3Sensor Options[blank]: no optionsH : with Humidity sensorCH : with CO2 and Humidity sensorTemperature Dependence±0.2% FS per °C (±0.11% per °F)Stability <2% of FS over life of sensor (15years) Pressure Dependence 0.135% of reading per mm Hg;