Title: +038=310.101-SC020T_01-FDV-dokumentasjon - Danfoss AS - VA_VVS 5640741 med flere - EV220B 15-50_1.pdf
100001)The times are indicative and apply to water. The exact times will depend on the pressure conditions. Closing times can be changed by replacement of the equalizing orifice.InstallationOptional, but vertical solenoid system is recommended.Max. test pressure25 barViscosityMax. 50 cStValve body:BrassW.no. 2.0402Armature:Stainless steelW.no. 1.4105 / AISI 430 FRArmature tube:Stainless steelW.no. 1.4306 / AISI 304 LArmature stop:Stainless steelW.no. 1.4105 / AISI 430 FRMaterialsSpringsStainless steelW.no. 1.4310 / AISI 301O-rings:EPDM, FKM or NBRValve plate:EPDM, FKM or NBRDiaphragm:EPDM, FKM or NBR3Dezincification resistant brass (DZR) valve body, NCConnection ISO228/1Seal mate rialOrifice sizeKv-value [m³/h]Differential pressure Min. – max. [bar]Media temperature min. to max.[°C]Code numberG ½154032U5815G ¾208032U5820G 12511032U5825G 1 ¼EPDM1)32180.3 – 1630 – 1202)032U5832G 1 ½4024