Title: Ahlsell.pdf
8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 05 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/06/2022 01:41:15 PM Operator: Pam Headroom 3.3 dB (NEXT 1,2-3,6) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505095Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]7.7 38 1 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]37.6 487.0 43.1Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 3.3 268.0 34.8 1,2 5.5 268.0 32.2SR 1,2-3,6 4.8 268.0 34.8 3,6 7.0 268.0 32.2