Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 16.06.2020 09:49R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 16.06.2020 09:55R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF050 C16/2 15.06.2020 08:33SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF050 C16/2 15.06.2020 08:34Tallberg Elektro A/S Tlf.22796640Side:17GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.121121122122123123124124125125126126127127TEST RAPPORTResultatZ-LINEZ: 0.47ΩIsc: 488A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF050 C16/2 15.06.2020 08:34Zs(rcd)Z: 0.42ΩIsc: 544A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF050 C16/2 15.06.2020 08:34RCD Ub