Title: +038=433.002-FS058T_02-FDV Eaton Tavlebyggeren DM3.E3=433.02.07.pdf
Technical data ETIM 7.0 Devices for distribution board-/surface mounting (EG000062) / Main switch for distribution board (EC001545) Electric engineering, automation, process control engineering / Electrical installation, device / Modular serial built-in device for electrical circuit distributors / Main switch for distribution board (ecl@ss10.0.1-27-14-23-01 [AFZ813014]) Switching function Other Number of contacts as normally open contact 4 Number of contacts as normally closed contact 4 Number of contacts as change-over contact 0 Number of poles 4 Rated current 63 A Rated voltage 240 V Min. rated voltage 240 V Rated switching capacity 12.5 kA Short-circuit breaking capacity (Icw) 2 kA Voltage type AC Forced segregation (according to DIN VDE 0113) No With signal lamp No Colour calotte Lamp type Lamp socket Max. lamp power 0 W Width in number of modular spacings 4 Built-in depth 69.5 mm Degree of protection (IP)2 / 4IP40DimensionsDimensions single productMas_IS Line drawing Main load-break switch