Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z — N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / KJK / Room summaryKJKReflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Background area (KJK) Perpendicular illuminance (adaptive) [Ix] 221 (= 300) 130 265 0.59 0.49 Height: 0.000 m, Wall zone: 0.300 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 2 iGuzzini illuminazione - Q497 Laser Blade XS - Downlight HC 12.4W 739 12.4 59.6 9 iGuzzini illuminazione S.p.A - MI59 (1.0 M)+MXK3+MXMO0_LX43 610 144 42.4Underscore15: flexible strip - 5m - LED blanco - 14.4W 1220Im (1.0 m) - 3000K - Ledstrip Top surface low linear profile - L 1000 - Opal diffuser screen L 1000Total via all luminaires 6968 154.4 45.1Lighting power density: 8.32 W/m? (Floor area of room 18.55 m? ), Lighting power density: 11.30 W/m? = 5.13 W/m?/100 Ix (Area of working plane 13.66 m?)