Title: +135.01=370.003-OE401T_02-320 Datablad Energimåler UH50.._.pdf
8.82.640110309.5440130288.8760954915.45601104514.381001057724.41116016010031.61324011517756.022600120433136,950 *)2 AA lithium batteries (Li-SOCI2) 3.6 V At least 6 years1 D-cell lithium battery (Li-SOCI2) 3.6 V 6…16 years (depending on configuration)CE2N5324en 2018-08-18Building TechnologiesPower pack AC 110/230 V WZU-AC110/230-15 *) WZU-AC110/230-50 *)Power pack AC 110/230 V ● Protection class ● Voltage range ● Frequency ● Maximum power consumption ● Overvoltage category IIII AC 100 to 240 V 50/60 Hz 2.5 VA CAT 2per EN 61010-1Length of connecting cable ● External fusing of supply line ● Backup time in the event of power failure1.5 m/5 m Automatic cutout 6 A ≥4 h) The power pack has two outputs. One supplies the meters; the other an optional plug-in GPRS module.Power pack AC/DC 24 V WZU- ACDC24-00