Title: 40 Bender brukermanual.pdf.pdf
External devices connected to the BMS bus or switched on for the first time are displayed by the RCMS…-D not until a few minutes later in the external devices list. You don't need to wait for the list to appear. You can select and set the external device immediately via the address.The search for the device starts:3: --If "no access to the menu" appears, press the "ESC“ button to exit the display. Possible causes are:76RCMS460-490_D00067_03_M_XXEN/12.2017Operation  No device with this address available.   Connected device does not support this programming function.   Access not possible at the moment. The "External devices" menu is not suitable for programming this RCMS… If you otherwise try to program it, the error message "Own address" will appear. Press the "ESC" button to exit this menu.When the device has been recognised, the RCMS…-D reads the current set- tings of the connected device. The address and the device type will be dis- played in the first line.