Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 20,6 10,3 10,3 497,00Remote: 45-12 21,2 10,3 10,9 497,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,9 23,9 4,0 494,00Remote: 36 27,8 23,8 4,0 499,00Worst Value: Local: 36 27,9 23,8 4,1 500,00Remote: 36 27,8 23,8 4,0 500,00PS-ACRF: Pass Worst Margin: Local: 12 67,3 56,3 11,0 1,75Worst Value: Local: 45 20,3 7,3 13,0 497,00Remote: 12 71,7 60,0 11,7 1,15Remote: 12 20,4 7,3 13,1 497,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:05Signature:______________________ Page: 78Copper Certification ReportCable Label: 521.002-UD-71 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:04:56 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: