Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]33.7 146 2 5.05Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.1 494.0 29.4 36 6.8 498.0 26.4SR 36-78 9.0 476.0 29.7 36 7.8 473.0 26.9MAIN 12-36 6.1 494.0 29.4 36 6.8 498.0 26.4SR 36-78 9.1 479.0 29.6 36 8.1 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.9 499.0 11.3 45 21.9 499.0 8.3SR 78-45 20.2 499.0 11.3 45 21.1 500.0 8.3MAIN 45-78 20.9 499.0 11.3 45 21.9 499.0 8.3SR 78-45 20.2 499.0 11.3 45 21.1 500.0 8.30100806040200250 MHzACR-F (dB)