Title: +175=263.001_DL001_DOP Fireswitch BVT No. 006CPR2015-04-08.Produktinformasjon.pdf
We herewith declare that the Actulux fire switch BVT IP40 item no. 111781 - 111797 and BVT IP65 item no. 111725- -complies with thw relevant requirements for components laid down in EN 12101-9 is in conformity with the provisions of Council Directive 2004/108/EC as amended and has been manufactured according to the following harmonized standards EN 50081-2, EN50082-2, EN 61000-4-2, -4-3, - 4-4, -4-5, and EN 50204.When the above-mentioned Actulux fire switch is installed with a smoke ventilation control unit and a window actuator fitted to a window, the total system is to be considered as a machine, which is not to be put into service until it has been installed according to instructions and requirements. The total system then complies with the requirements of the Council Directive 2006/42/EC as amended.Wir erklären hiermit, dass die Actulux RWA Bedienstelle BVT IP40. Art. nr. 111781 - 111797 und BVT IP65. Art. nr. 111725-