Title: økernvn 94.pdf
Cable ID: D4135 Date / Time: 09/10/2013 02:42:02 Headroom 15.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]215 339 23 9.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.3 97.8 32.5 36 16.4 97.5 29.5SR 36-45 21.0 21.9 43.0 45 22.5 33.3 37.1MAIN 12-36 15.3 97.8 32.5 36 16.4 97.5 29.5SR 12-36 23.4 89.0 33.1 78 23.9 98.8 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 23.4 59.0 23.2 36 24.9 46.0 22.4