Title: Simployer - Data testrapport =514.204-FS001.pdf
LinkWare™ PC Version 10.4Cable ID: 521.204-UD60 Date / Time: 28/01/2022 13:24:39 Headroom 6.2 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]51.4 264 19 9.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]20.5 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 9.0 131.0 37.9 3,6 9.6 20.3 48.9SR 4,5-7,8 6.2 172.5 35.9 4,5 8.6 172.5 33.0MAIN 1,2-3,6 9.5 179.0 35.6 3,6 11.3 220.0 31.1SR 4,5-7,8 7.4 223.0 34.0 7,8 8.6 223.5 31.0