Title: 2 etg del2.pdf
250MHzLinkWare Version 8.1Cable ID: D2107 Date / Time: 10/10/2013 02:11:26 PM Headroom 11.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]57 90 6 2.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.2 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.2 92.3 32.9 36 12.7 92.3 29.9SR 12-36 12.0 46.0 37.8 36 13.2 92.3 29.9MAIN 12-36 11.2 92.3 32.9 36 13.1 98.0 29.4SR 12-36 12.4 98.0 32.4 36 13.5 98.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)