Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3062 Date / Time: 09/12/2013 03:08:23 Headroom 14.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]161 256 19 6.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.3 87.3 33.3 36 14.0 91.3 30.0SR 36-45 16.8 91.0 33.0 36 17.3 91.3 30.0MAIN 12-36 14.7 97.3 32.5 36 14.5 99.5 29.3SR 36-45 17.0 97.5 32.5 36 17.6 99.5 29.310080604020NEXT (dB)