Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
DANGERHAZARD OF ELECTRIC SHOCK, BURN, OR EXPLOSIONCarry out the tests to detect any short circuit or earth fault caused by incorrect installation before energizing the busbar trunking system.Failure to follow these instructions will result in death or serious injury.Follow these rules to energize the busbar trunking system:  The busbar trunking system should have no electrical load on it when it is energized. As the busbartrunking system may typically extend through several rooms and floors, verify that all devices fed from the busbar trunking system are in the OFF position. Energize the busbar trunking system in sequence, by starting at the source end and working towards the load end. Start by energizing the main devices, then the feeder devices, and then the branch-circuit devices. Turn the devices to the “ON” position with a firm positive motion. After the busbar trunking system has been energized, equipment such as lights, contactors, heaters,and motors can be switched on.