Title: 1 etg del 2.pdf
SR 12-36 17.1 34.8 38.7 36 17.2 39.8 34.5MAIN 12-36 20.5 249.5 4.7 36 19.6 249.5 2.1SR 12-36 25.1 224.5 7.2 36 26.2 227.0 4.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.8 41.8 17.8SR 36 4.1 209.5 10.8MAIN 36 6.1 232.5 10.3SR 36 4.1 209.5 10.8010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94