Title: 1 etg del 2.pdf
191 302 20 7.9191 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.1 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 249.5 35.4 36 1.1 248.0 32.8SR 36-45 1.1 249.5 35.4 36 1.0 *241.0 33.0MAIN 36-45 1.3 249.5 35.4 36 1.1 248.0 32.8SR 36-45 1.1 250.0 35.3 36 1.1 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.8 57.3 29.0 45 16.2 51.5 27.0SR 36-45 13.9 57.0 29.1 45 15.9 50.3 27.2MAIN 12-45 19.3 250.0 16.2 45 20.5 250.0 13.2SR 45-12 18.9 250.0 16.2 45 19.0 209.5 14.8010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz