Title: Fosnagata Spredenett 3.etg FLUKERAPPORT.pdf
ACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 45-78 21.6 44.0 36.1 45 20.0 44.0 33.6SR 36-45 20.5 44.0 36.1 45 20.7 44.0 33.6MAIN 36-45 37.1 498.0 -12.3 45 37.6 498.0 -15.1SR 36-45 38.2 484.0 -11.3 36 39.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.2 28.4 18.7SR 45 8.6 28.9 18.7MAIN 36 8.8 490.0 8.0SR 36 10.7 364.0 8.440010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-51 TR-4100BASE-TX 10GBASE-T ATM-155 TR-16 Active100BASE-T4 ATM-25 100VG-AnyLan TR-16 Passive60402000250 MHzProject: F13 3 ETGUntitled1Test Summary: PASSModel: DSX-5000 Main S/N: 2552117 Remote S/N: 2552311 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00430.4 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)80604020500