Title: økernvn 94.pdf
RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: T4026 Date / Time: 09/11/2013 09:56:35 Headroom 11.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]65 103 7 2.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.8 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.4 50.3 37.2 36 13.6 85.8 30.4SR 12-36 11.2 85.5 33.4 36 13.1 85.8 30.4MAIN 12-36 12.0 95.8 32.6 36 13.8 96.0 29.6SR 12-36 11.8 95.8 32.6 36 13.6 95.8 29.610080604020NEXT (dB)