Title: 26 Manual for takslukvakt.pdf.pdf
6 BLÜCHER® CONNECTED ROOF - REV. 02 - MARCH 20215V DC 1A 0,5 W Class 3868 MHz SMA Up to 1500m in free line of sight10.96” OLED 128*64 dotMicroSDHC Class 4 or higher >4 GB1RT NO/NC 230VAC 5A 3 pin screw terminals (Max 1.5mm²)RS485 Up to 115200 Bauds 3 pin screw terminals (Max 1.5mm²) Yes, ON/OFF jumper configurationPG7 (diameter 2.5-6.5mm)IP 30 ABS 120 x 65 x 40mm (without antenna and cable glands) Ø4 mm10°C - 55°C -30°C - 80°C Below 80% non-condensing4.3 Monitor specificationsPower supply Battery Battery life Level Sensor Sensor electrodes Enclosure IP protection Material Size Environmental Working temperature Storage temperatureLithium battery LS 14500 3.6V (internal) AA Up to 10 yearsStainless A2IP68 Anti-UV PC 120 x 65 x 60mm35°C - 85°C -35°C - 85°C5 Mechanical installation5.1 Gateway