Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
[Pair 45] [Pair 45] [Pair 45]33.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.0 409.0 31.1 36 6.7 463.0 26.8SR 12-36 9.8 409.0 31.1 36 9.8 469.0 26.5MAIN 12-36 8.2 498.0 27.9 36 7.6 498.0 25.1SR 12-36 10.4 498.0 27.9 36 10.3 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.9 9.6 45.6 45 20.9 7.3 45.0SR 45-78 18.9 9.8 45.5 45 20.9 6.1 46.5MAIN 36-45 21.6 500.0 11.3 36 23.3 500.0 8.3SR 45-36 21.6 496.0 11.3 36 22.1 469.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 31.9 208.5 10.7 36 31.8 148.5 14.8SR 36-45 26.9 137.0 18.8 36 28.7 143.0 15.5MAIN 12-36 40.1 498.0 -12.3 36 39.5 498.0 -15.1SR 12-36 42.3 498.0 -12.3 36 42.3 500.0 -15.30804000