Title: 91879 FDV F13 Kafe.pdf
Electric engineering, automation, process control engineering / Electrical installation, device / Residual current protection system / MCB/RCCB combination (ecl@ss8.1-27-14-22-07 [AFZ810012])Number of poles (total)3Number of protected poles3Nominal rated voltageV400Nominal rated currentA20Rated fault currentA0.03Leakage current typeACurrent limiting class3Rated short-circuit breaking capacity EN 60898kA10Rated short-circuit breaking capacity IEC 60947-2kA0Frequency50 HzRelease characteristicCConcurrently switching N-neutralYesOver voltage category3Pollution degree2Width in number of modular spacings4Built-in depthmm70Suitable for flush-mounted installationNoDegree of protection (IP)IP20Surge current capacitykA0.25Voltage typeACAntinuisance tripping versionNo11/05/2016Eaton Industries GmbH http://www.eaton.eu © 10/2016 by Eaton Industries GmbH 108329 - HPL-ED2016 V26.0 EN2 / 2