Title: 03 - Døli pleie- og omsorgssenter 18.03.2016.pdf
energibruk tilstand før [kWh]Graddager4492GD1 020 484408 226918 4271 326 653Luftmengder maksLuftmengderGj.vinner %SFPDriftstid/ukeDriftsuker/årOppvarmingVifteenergi% Til gode som varme Netto oppvarmingSamlet forbruk kWh/årIDAreal som ventileresStartStoppStartStoppStartStoppStartStoppStartStoppStartStoppStartStopp36.01Vestlig sengebygg23 00023 00084 %207:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:001055286 78569 76725 %69 344139 110Vestlig sengebygg23 00016 10084 %200:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:00635236 45029 30225 %29 12458 4260520025 %0036.02Østlig sengebygg23 00023 00084 %207:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:0007:0022:001055286 78569 76725 %69 344139 110Østlig sengebygg23 00016 10084 %200:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:0000:0009:00635236 45029 30225 %29 12458 4260520025 %0036.03Adm./kjøkken/kantine10 20010 20040 %307:0017:0007:0017:0007:0017:0007:0017:0007:0017:0007:0017:0007:0017:00705296 21930 94025