Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 36-45 14.4 477.0 11.7 45 17.0 495.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 31.6 222.0 9.3 36 30.8 222.0 6.7SR 12-36 31.6 222.0 9.3 36 31.9 232.0 5.8MAIN 12-36 44.0 491.0 -11.8 36 43.8 499.0 -15.2SR 36-45 41.8 500.0 -12.4 36 41.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 6.0 497.0 8.0SR 12 4.6 488.0 8.0MAIN 12 6.0 497.0 8.0SR 12 4.6 488.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00412.6 m60Insertion Loss (dB)504030201000250 MHz500