Title: R&H dronning_mauds_gate_1-3_2020-02-25_10-29-Måleprotokoll 360.011 og 360.020.xlsx
IDRIFTSETTING WISE LUFTMENGDE FUNKSJON Rom Merking Type Nodeadresse Tilluft/Avtrekksluft Min. luftmengde (m3/h) Maks. luftmengde (m3/h) SMB SMA Kjøleutgang Varmeutgang CU-trykk-/luftmengdegiver CU ekstern temp.giver Modbus trykk-/luftmengdegiver Luftmengderegulering Målte verdier Merknad Sign. Navn Testet 10-001 Møterom +10=360.020-LD416 WISE Parasol a 1192-B-PF-160 3161 T 41.196241 219.999957 225 10-001 Møterom +10=360.020-LD417 WISE Parasol a 1192-B-PF-160 3175 T 41.196241 219.999957 225 10-002 Møterom +10=360.020-LD418 WISE Parasol a 1192-B-PF-160 3193 T 26.284356 164.999886 169 10-002 Møterom +10=360.020-LD419 WISE Parasol a 1192-B-PF-160 3194 T 26.284356 164.999886 169 10-003 Møterom +10=360.020-LD421 WISE Parasol a 1192-B-PF-160 3197 T 26.284356 164.999886 171 10-003 Møterom +10=360.020-LD420 WISE Parasol a 1192-B-PF-160 3198 T 26.284356 164.999886 171 10-004 Pareto TV +10=360.020-LD431 WISE Parasol a 1192-B-PF-160 3201 T 26.284356 150.000114 155 10-004 Pareto TV +10=360.020-LD422 WISE Parasol a