Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
RCD: UtlřsningsstrřmI: 27.0mAUci: 0.2V t: 62.3ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 521V Rnpe: >30.0MΩ Um: 516VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF025 C16/2/003 / Mal 1 10.03.2022 13:52 (TomekElektriker)KONTINUITET: R200mA LPER: 0.04ΩR+: 0.1Ω R-: 0.0Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF025 C16/2/003 / Mal 2 10.03.2022 11:54 (TomekElektriker)SPENNING TRMS Uln: 233V Ulpe: 1V Unpe: 234V f: 49.97HzSYS.: TN/TTZ-LINEZ: 0.50ΩIsc: 456A R: 0.50Ω Xl: 0.04Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ATALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:11GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr.333334343535TEST RAPPORTResultatRCD: UtlřsningsstrřmI: 27.0mAUci: 0.4V t: 26.2ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 522V Rnpe: >30.0MΩ Um: 515VUiso: 500V Grenseverdi: 1MΩ