Title: Bytesteinen 1 - =514.202-FS001.pdf
Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]51.2 261 17 8.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]21.0 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 7.5 202.0 34.7 4,5 8.6 202.5 31.8SR 1,2-4,5 9.7 246.5 33.2 4,5 10.8 22.3 48.2MAIN 4,5-7,8 7.5 202.0 34.7 4,5 8.6 202.5 31.8SR 1,2-4,5 9.7 246.5 33.2 1,2 11.1 246.5 30.3PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 15.1 3.3 53.0 4,5 16.0 3.6 49.1SR 7,8-4,5 15.0 3.4 52.7 4,5 16.0 3.6 49.1MAIN 7,8-4,5 15.7 199.5 17.3 4,5 16.3 196.5 14.4