Title: +039=335.001-NT001._01-2016_001.pdf
Marking The box is marked with a product label.InstallationBefore installation, the power must be off.Note, for a control panel with dual outputs (eg. SigmaXT+}, the two jumpers J1 and J2 below the terminals to the control panel must be cut.The shown ( + ) and { - } are when the control panel is activated (discharged).The specified colours for the low pressure are for connections to a manometer, where the ‘BL’ is only for ‘dummy’ cannection, so that there is no floating wire from the cable, with three wires.When the wires are connected to the ‘spring’ terminal, a special tool or a screwdriver at 3.5 mm must be used to “release’ the spring.The ACTUATOR (1 and 2) are for connections to an actuator with four wires, where the colours from the solenoids are specified. Eg. Ci IS8 series from Fire Eater.Fig. 1 Junction box boardACT1/ACT2 2x 6KBQ (Not for SigmaXT+)c Default resistors are for the SigmaXT control panel, 5o there is no fault at the panel.40V/4A