Title: 2 etg del2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]303 477 31 13.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.1 73.8 34.5 36 15.9 96.5 29.6SR 12-36 13.5 98.8 32.4 36 15.1 98.8 29.4MAIN 12-36 14.1 96.5 32.6 36 15.9 96.5 29.6SR 12-36 13.5 98.8 32.4 36 15.1 98.8 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 24.3 93.0 19.2 12 24.8 96.0 16.0SR 45-12 24.1 94.3 19.1 36 24.7 99.3 15.7MAIN 45-12 24.3 93.0 19.2 12 24.9 100.0 15.6SR 45-12 24.1 94.3 19.1 36 24.7 99.8 15.601008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.6 8.5 44.0 12 18.9 8.5 41.0