Title: Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.pdf
after the valve) at which the actuator reliably closes the valve by means of a return spring. / Definition of ∆p max: Maximum admissible pressure drop in control mode at which the actuatorreliably opens and closes the valve.Combination of VUE with electric actuator, actuating power 250 N, 500 NActuatorAVM105F100AVM105F120 AVM105F122AVM105SF132AVM115F120 AVM115F122AVM115SF132Actuating power250 N250 N250 N500 N500 NControl signal2-/3-point2-/3-point2-/3-point, 0...10 V2-/3-point2-/3-point, 0...10 VRunning time30 s120 s35/60/120 s120 s60/120 s∆p [bar]Closes against the pressure∆pmax∆pmax∆pmax∆pmax∆pmaxVUE015F350 VUE015F340 VUE015F330 VUE015F320 VUE015F310 VUE015F300 VUE020F3004.04.04.06.06.0VUE025F3002.82.82.86.06.0VUE032F3002.12.12.15.25.2VUE040F3001.41.41.43.33.3VUE050F300 VUE050F2000.90.90.92.02.0Cannot be used to close with the pressure10.1