Title: +135.01=370.004-OE401T_02-320 Datablad Energimåler UH50.._.pdf
RTU communication over RS485, transmission rate up to 19200 baud, setting the transmission rate and parity of the software (USB, cable connection), refresh rate up to 10 sec. For UC50.. and for UH50.. as of firmware 5.15 and higherWZU-485E-BACMS/TP communication over RS485, transmission rate up to 76800 baud, setting the transmission rate and parity of the software (USB, cable connection), refresh rate up to 10 sec. For UC50.. and for UH50.. as of firmware 5.15 and higherBoth modules are externally powered with AC/DC 24 V and galvanically isolated from the processor unit. Switch off the module power supply before connecting it to the PC using the USB cable. The micro USB interface is used exclusively to configure the communication protocol and speed.Analog module WZU-AM17 CE2N5324en 2018-08-1818 Building Technologies