Title: Data tester Smestad skole - Detaljert.pdf
Remote: 45-12 23,2 12,3 10,9 395,00Worst Value: Local: 12-45 21,7 10,2 11,5 500,00Remote: 12-45 21,5 10,2 11,3 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,8 3,3 500,00Remote: 36 27,9 23,8 4,1 498,00Worst Value: Local: 36 27,1 23,8 3,3 500,00Remote: 36 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 12 68,3 56,3 12,0 1,75Worst Value: Local: 45 20,0 7,2 12,8 500,00Remote: 12 72,6 61,2 11,4 1,00Remote: 45 19,3 7,2 12,1 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:09Signature:______________________ Page: 104Copper Certification ReportCable Label: 521.002-UD-97 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:36:00 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein