Title: Jordfeilautomat 3+N.pdf
featuresRated short-circuit capacity lcnA6,000Break time under I△ns≤0.1Rated frequencyHz50/60Rated impulsewithstand voltage (1.2/50)UimpV4,000Dielectric TEST voltage at ind. Freq. for 1minkV2Insulation voltage Ui500Pollution degree2Electrical life2,000Mechanical life10,000Contact position indicatorYesMechanicalfeaturesProtection degreeIP20Ambient temperature(with daily average≤35℃)℃25...+40Storage temperature℃25...+70Terminal connection typeCable/U-type busbar/Pin-type busbarTerminal size top/bottom for cable2mmAWG2518-3InstallationTerminal size top/bottom for busbar2mmAWG1018-8Tightening torqueN·mIn-Ibs.218MountingOn DIN rail EN 60715 (35mm) by means of fast clip deviceConnectionFrom top and bottom2.3 Temperature deratingThe maximum permissible current in a circuit breaker depends on the ambient temperature where the circuit breaker is