Title: BRV Ahlsell No 150 kW BRV 59.pdf
SINGLE PHASE - QUOTATION Heat Exchanger : B8THx30/1P-SC-M (4x3/4"&16)Art No : 14361-030Connection DataF1 - F2 - F3 - F4 -ISO-G 3/4" & SOLDER 16(20) ISO-G 3/4" & SOLDER 16(20) ISO-G 3/4" & SOLDER 16(20) ISO-G 3/4" & SOLDER 16(20)Connection LocationsSide 1: Side 2:F2/F4 (In / Out) F3/F1 (In / Out)Fluid Side 1 : Water Fluid Side 2 : WaterFlow Type : Counter-Current SSP Alias : B8TDUTY REQUIREMENTS Heat load Inlet temperature Outlet temperature Flow rate Max. pressure drop Thermal lengthkW °C °C l/s kPaSide 1115,00 60,00 0,6707 25,0 1,104PLATE HEAT EXCHANGER Total heat transfer area Heat flux Mean temperature difference O.H.T.C. (available/required) Pressure drop -total* - in ports Port diameterNumber of channels Number of plates Oversurfacing Fouling factor Reynolds number Port velocitym² kW/m² K W/m²,°C kPa kPa mm% m²,°C/kWm/sSide 122,7 3,60 17,5/17,5 (up/down) 153657 2,79www.swep.net