Title: økernvn 94.pdf
250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3195 Date / Time: 09/11/2013 03:12:47 Headroom 1.7 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]185 280 8 8.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]13.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 2.0 42.3 47.9 36 4.3 42.5 45.4SR 36-45 1.7 42.8 47.8 36 2.2 246.5 32.8MAIN 36-78 5.6 250.0 35.3 36 6.5 250.0 32.7SR 12-36 2.5 243.0 35.5 36 2.2 246.5 32.810080