Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
17.5-117.5-217.5-317.5-417.5-517.5-617.5-7Wait for the complete shutdown.ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0031H S I L G N E3217. OPERATING MODES17.6. OPERATION FROM MANUAL BY-PASS TO NORMAL OPERATION17.6-117.6-217.6-317.6-417.6-517.6-617.6-717.6-85 secITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0018. VISUAL AND AUDIBLE WARNING SIGNALSABCDIEHFGKey DescriptionConditionALoad on bypass, in Eco-mode or Maintenance bypass closedAutomatic bypass alarmSteadyFlashingBBattery OKBattery alarmSteadyFlashingCOutput voltage presentSteadyDLoad presentOverloadSteadyFlashingEOutput load indicatorSteps of 10%FActivation code alarmGeneral alarmSteadyFlashingGInverter onInverter general alarmSteadyFlashingHInput rectiﬁ er active, input mains OKInput rectiﬁ er general alarm/Input mains alarmSteadyFlashingIRemaining battery capacityBattery rechargingSteps of 25%Sequence