Title: Igangkjøringsprotokoller på sirkulasjonspumper V.2017.07.17.pdf
~ Check expansion jOlnts |nstalled ok Check vibration damper installed: ok Check air locks are avoided (suction side): ok Check for pipes adequate support: ok Check mechanical seal for leaks: ok ( 'ump starting iz 5 = Real setpoint (head pmssure) 6.20m Flow at preseted setpoint (all valves opened): 50.5m3/h Power consumption W: 1598W Head pressure at regular working cond. : 4.5m Flow at regular working cond. : 35m3/h Work performed Name: Audrius Daniulis - Signature: ﬁUAB ENSO PROJECTS REGISTRATION CODE 301340546, VAT LT1 00003637612 TILZES ST 41, IBAN LT35401 0042501594250, DNBBANKAS, SWIFT AGBLL2XLT