Title: 30. Technoporten_Brannalarmutstyr datablad.pdf
The Solista LX Ceiling has a unique lens design that distributes the light in a cylindrical shape to achieve the required illumination specified by EN 54-23. Designed for installation at a height of up to 3m and with a discrete appearance, the device is ideal for a variety of applications, including bedrooms, bathrooms and toilets.FeaturesTechnical SpecificationUltra low current consumption of 10mAUp to 7.5m coverage volumeMounting Type Ceiling0.5Hz or 1Hz Flash rateVoltage 9 - 60VDCCoverage switch to 3mCurrent 10 - 25mA dependent on settingCoverage (y) 7.5m (Switchable to 3m)*Mounting Height (x) 3m (max)BenefitsCoverage Volume Code C-3-7.5Use where current consumption is a key considerationCoverage Volume 132m3 (21m3)Ideal for bedrooms, bathrooms and toiletsFlash Rate 1Hz (Switchable to 0.5Hz)Switch flash rate to 0.5Hz to reduce current consumptionReduces power consumption by up to 50%Operating Temperature -25ºC to +70ºCMonitoring Reverse Polarity