Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 37,9 68,0 197,0 11,0 6,7Limit 100,0 - 555,0 50,0 25,0Margin 62,1 - 358,0 39,0 18,3Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,7 3,1 2,4 3,10Worst Value: Local: 36 16,4 43,6 27,2 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 19,1 15,1 4,0 78,50Remote: 78 17,0 15,1 1,9 78,50Worst Value: Local: 12 16,7 8,6 8,1 348,00Remote: 78 13,7 8,7 5,0 337,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,8 26,8 3,0 495,00Remote: 36-45 28,9 26,7 2,2 498,00Worst Value: Local: 36-45 29,8 26,8 3,0 495,00Remote: 36-45 28,9 26,7 2,2 498,00dB 050100