Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]22.9 99 1 3.58Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]30.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.3 447.0 30.3 36 9.6 468.0 26.5SR 36-45 10.9 478.0 28.9 36 10.0 473.0 26.3MAIN 12-36 9.5 499.0 27.9 36 10.0 499.0 25.0SR 12-36 11.7 500.0 27.8 36 11.0 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 20.3 499.0 11.3 45 20.8 499.0 8.3SR 36-45 20.1 500.0 11.3 45 20.4 500.0 8.3MAIN 45-36 20.3 499.0 11.3 45 20.8 499.0 8.3