Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
1.0 x 106 operations 0.3 x 106 operations 3) 0.1 x 106 operations 1)3)Relay coil supply: 2)nominal 24 VDC smoothed or pulsed, 8 mA per relay coilVoltage tolerance, dependent on ambi- ent temperature:20°C: 17.0…35 VDC 30°C: 19.5…35 VDC 40°C: 20.5…32 VDC 50°C: 21.5…30 VDCOutput delay:typically 5 ms at 24 VDCResistance to interference: acc. to IEC 801-44 kV under direct coupling 2 kV under capacitive coupling (whole trunk group)Internal current consumption: (from +5 V bus)1…15 mA typically 10 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption:max. 32 mATerminals:Plug-in 10-pole spring terminal block (4 405 4954 0) or pluggable 10-pole screw terminal block (4 405 4955 0), both for wires up to 2.5 mm²1) With external protective diode 3) These ratings are not UL-listed2) With reverse voltage protection