Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
The minimum size of an installation opening necessary for correct installation of the mcr WIP type fire damper is:Bo = (A + Bz + 80) [mm]Ho = (H + 180) [mm]MixtureC1 [mm] A [mm]BF 385 125BFL, BEN 335 125BFN, BEE 385 125BE 385 125BLE 335 125KW1 335 165EXBF 460 1756.3. BUILDING IN (EMBEDDING)The mcr WIP type fire damper works correctly if the rotation axis of the partition is horizontal. The release and control mechanism may be located on the right or left of a fire damper irrespectively of the air flow direction. Installing a fire damper on its side, i.e. with rotation axes of the partition being vertical, is only permitted when this has been previously made known to the manufacturer at the time of placing the order.