Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
(cid:20)(cid:21)(cid:28)(cid:43)(cid:28)(cid:23)(cid:66)(cid:42)(cid:37)(cid:16)(cid:22)(cid:17)(cid:76)(cid:81)(cid:71)(cid:71)(cid:3)(cid:3)(cid:3)(cid:21)(cid:26)h s i lg n EAlign and level the unit by adjusting the nuts and locknuts on the threaded hangers, maintaining a distance of 25 -30 mm between the sheet metal body and the underside of the false ceiling.Reposition the "T" bar and align the unit in relation to the bar by tightening the nuts and locknuts. After the condensate drain pipe and the water ducts have been connected check, check to make sure that the unit is level (See fig. 21).Condensate drain pipeSee fig. 22 - 23.To ensure correct condensate water flow, the drain pipe should have a gradient of 2% without obstructions. Furthermore an odour trap of at least 50 mm depth should be made to prevent unpleasant odours from reaching the room.