Title: 1 etg del 2.pdf
Cable ID: D1039 Date / Time: 10/17/2013 11:59:05 AM Headroom 12.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 45]159 253 18 7.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.2 90.0 33.1 36 15.2 90.0 30.1SR 12-36 12.9 90.0 33.1 36 14.7 90.3 30.0MAIN 12-36 13.5 98.3 32.4 36 15.5 98.5 29.4SR 12-36 13.2 96.3 32.6 36 14.8 96.3 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.1 2.8 49.8 45 20.3 2.4 48.1