Title: +038=360.000-OU045T_05-PCD2.m4160 PLS SBC - User Manual.pdf
The following table displays the Parameters:ParameterDeclaration Type RangeDescriptionCOUNT_NUMInputR K Wert00:  Counter 0 1:  Counter 1START/STOPInputFTRUE / FALSEStart or Stop the CounterCONTInputFTRUE / FALSETrue:   Continuous counting False:   Counting until the ref value is reachedROTATEInputFTRUE / FALSETrue:     Overflow handling,see description Rotate False:   No Overflow handlingDIRInputFTRUE / FALSE Only in Mode X0 and X1 True:   False:   Input IX0 is not invertedInput IX0 is invertedREF_OUTInputFTRUE / FALSEThis Functionality is not supported  (set Always to FALSE)PULSE_OUTInputFTRUE / FALSEThis Functionality is not supported  (set Always to FALSE)REFInputR K Wertxxx 1)Maximum Value or Reference ValueXOB_NBRInputR K Wert0 32…630:32…63:No XOB call if Counter Value is  equal Ref Value  XOB is called if the Counter  reaches the Ref ValueXOB_INFOInputR K WertYYYY2)