Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Resistance to interference: acc. to IEC 801-4Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Terminals:8, electrically connected 5…500 mA (leakage current max. 0,1 mA) Within the voltage range 5…24 VDC, the load resistance should be at least 48 Ω. 4 A on 100% duty cycle Source operation (positive switching) 5…32 VDC, smoothed 10…25 VDC, pulsed ≤ 0.4V at 0.5 A Switch-on delay typ. 10 µs Switch-off delay typically 50 µs (ohmic load 5…500 mA), longer with inductive load, because of the protective diode. 4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 1…25 mA typically 15 mA 0 mALoad current Plug-in 10-pole spring terminal block (4 405 4954 0) or pluggable 10-pole screw terminal block (4 405 4955 0), both for wires up to 2.5 mm²LEDs and connection terminalsLED 0...7Terminal 0Terminal01234567Description LabelAddress LabelA4 0 00 1 2 3 4 5 6 7 8 9A0 A1 A2 A3 A4 A5 A6 A7 + –