Title: Hardware Installation Guide.pdf
0 1 2 3 4 5 6 7 8 9 * #0 1 2 3 4 5 6 7 8 9 * #Up to 32 Dual Reader Interface Modules (64 readers)Up to 16 Output Control Modules Up to 16 Alarm Input Control Modulesrevision 6 — 291LNL-1200 Output Control Module51.2The Output Control Module (Series 2)The LNL-1200 series 2 board contains the following components: sixteen (16) alarm output relays with sixteen (16) corresponding status LEDs, two (2) unsupervised alarm inputs, one (1) RS-485 interface, one (1) power input, eight (8) DIP switches, and jumpers.Output Control Module1234568910 111213 141516NONCCK1K9COUT 1NC1 B T5 B TNOOUT 9NONCCCOUT 2NCK2K3K11K10NOOUT 10NOK4K12NCCCOUT 3NC2 B T6 B TNOOUT 11OUT 4NONCOUT 12CCNCK5K13NONOK6K14NCCCOUT 5NC3 B T7 B TNOOUT 13NONCC7 KCOUT 6NC5 1 KNOOUT 14NONCC8 KCOUT 7NCNO4 B T