Title: DOCA0005EN-12.pdf
NOTE: You can access the meter’s configuration information over BACnet communications. However, you must use the front panel to configure the meter’s settings.Object ID Units Default COVObject name / description44Secon ds10AI44 - Meter operation timeThe time in seconds since the meter was last powered up45—1AI45 - Number of phases1, 346—1AI46 - Number of wires2, 3, 4AI47 - Power system type0 = 1PH2W L-N1 = 1PH2W L-L47—12 = 1PH3W L-L with N3 = 3PH3W11 = 3PH4W13 = 1PH4 wire multi L-N48Hz1AI48 - Nominal frequency50, 60AI49 - Number of VTs49—10 - 10NOTE: only applies to the iEM3265 / iEM3465 / iEM356550V1AI50 - VT PrimaryNOTE: only applies to the iEM3265 / iEM3465 / iEM356551V1AI51 - VT SecondaryNOTE: only applies to the iEM3265 / iEM3465 / iEM3565AI52 - Number of CTs52—11, 2, 3NOTE: only applies to the iEM3265 / iEM3465 / iEM356553A1AI53 - CT Primary