Title: 32 Pumper modbuss teknisk data.pdf.pdf
Select GENIpro port number: GENIPROPORT <port no.> Default value is 49152. This is only relevant when using Grundfos PC Tools. It is possible to configure the APN connection with a single multi- parameter command:SETAPN <parameter 1, parameter 2, parameter 3, …>Select Password: PASSWORD <ASCII string>– <parameters>:<APN>,<Modbus port>,<GENIproport>,The need for a password depends on your operator and the type of subscription.<username>,<password>,<authentication>,<connection>, <data roaming>, <data silence timeout>Setting a SCADA PIN code:ExampleSETSCADACODE <access code> will enable write access protection. Default is an empty SCADA PIN code, meaning no protection.SETAPN Grundfos.dk2.tdc,502,49888,Grundfos,4321,normal,server,off, 60.Activating the SCADA PIN code: SCADACODE <ON | OFF>. Default is "Off".Activating the SCADA PIN code: SCADACODE <ON | OFF>. Default is "Off".Selecting the Modbus address: MODBUSADDR <1-247> Default value is 231.