Title: +135.01=564.001-XS020T_01-Montasje 5202AB13_bma_d-e-blinds_Norsk.pdf
Product and Application Description The UP 520/13 shutter / blind actuator is a KNX device with one relay output. The device is installed in a flush-mount wall box (60 mm Ø, depth 60 mm). The bus is connected via a bus termi- nal block. The actuator electronics are supplied via the bus volt- age. The UP 520/13 may be used to control blinds, shutters, awnings, windows, or doors. The device is designed to drive (per channel) one AC 230V drive (motor) with electromechanical limit switches or with integrated electronics for disconnection at the limit positions. For drives with electromechanical limit switches the actuator can be configured to detect the status of the electromechanical limit switches such that the travel time between the end posi- tions can be measured via a synchronization run. The travel time of the blind / shutter is automatically measured from the upper end position to the lower end position and vice versa. The meas- urement is only reliable for drives with electromechanical limit switches.