Title: +038=370.101-QH009._01-Siemens Fukt_tempføler QFA3160_AQF3100.pdf
I23 0 G 8 5 8 1G, G0Operating voltage AC 24 V (SELV) or DC 13.5...35 VG1, G2Operating voltage DC 13.5...35 VU1 U2I1Signal output DC 0...10 V for relative humidity 0...100 % Signal output DC 0...10 V for temperature range 0...50 °C (R2 = factory setting) (cid:16) 35...+ 35 °C (R1) or (cid:16) 40…+70 °C (R3) Signal output 4…20 mA for relative humidity 0...100 %I2Signal output 4…20 mA for temperature range 0...50 °C (R2 = factory setting) (cid:16) 35...+ 35 °C (R1) or (cid:16) 40…+70 °C (R3)Note on connection terminals of the QFA3171(D): Terminals G1((cid:14)) and I1 ((cid:16)) for the humidity output must always be connected to power, even if only the tem- perature output G2 ((cid:14)) and I2 ((cid:16)) is used!Room sensors QFA31..CE1N1858en 2016-07-21Dimensions (all dimensions in mm)QFA31..(D) Dimensioning without (with) LCD-display800 68 24 8M 16 x 1,510,5ø 15QFA31.. with AQF3100404910,75 3 13,5446 30 38 2