Title: 32 TA-Modulator_DN15-32.pdf.pdf
10.0∆p insert PPS: 0°C – +90°C (+32°F – +194°F)∆p insert AMETAL®: -20° – +120°C (-4°F – +248°F)PN 16 (230 psi)PN 16 (230 psi)∆pVmax: 400 kPa = 4 bar (58 psi)∆pVmax: 600 kPa = 6 bar (87 psi)∆pVmin DN 15-20 (1/2”-3/4”): 15 kPa = 0.15 bar (2.2 psi)∆pVmin DN 15-20 (1/2”-3/4”): 15 kPa = 0.15 bar (2.2 psi)∆pVmin DN 25-32 (1”-1 1/4”): 23 kPa = 0.23 bar (3.3 psi)∆pVmin DN 25-32 (1”-1 1/4”): 23 kPa = 0.23 bar (3.3 psi)TA-Modulator + EMO TM!H1H2~15 mm (~0.60")~15 mmTA-Modulator + TA-Slider 160!H1H2~15 mm (~0.60")~15 mmEMO TM/TA-Slider 160IP54IP54IP541“X”DNH115552064SizeH11/2"2.17"3/4"2.52"DNH11555206425643278SizeH11/2"2.17"3/4"2.52"1”2.52”1 1/4” 3.07”IP54H2107107H24.21"4.21"H2119119130133H24.68"4.68"5.12”5.24”1135q24“5”Example!