Title: Tappevann - VV.pdf
NodeTypeSeriesBEND-90PEXPIPEPEXBEND-90PEXPIPEPEXBEND-90PEXPIPEPEX26 DOMESTICPIPEKR001TBEND-90KR001TPIPEKR001TBEND-90KR001TPIPEKR001T43 RETURN WAREDUCER KR001TPIPEKR001TBEND-90KR001TPIPEKR001TBEND-90KR001TPIPEKR001TBEND-90KR001TPIPEKR001TSTOPVALVE KR001TPIPEKR001T59 CONN.NODEProductSizeMAGI-PEX-B 15MAGI-PEX-1 15MAGI-PEX-B 15MAGI-PEX-1 15MAGI-PEX-B 15MAGI-PEX-1 15Kitchen tap 1 12MAGI-CU-15 15 (L)MAGI-CU-B1-15 (L)MAGI-CU-15 15 (L)MAGI-CU-B1-15 (L)MAGI-CU-15 15 (L)MAGI-CU-R1 28/12MAGI-CU-12 12MAGI-CU-B1-12MAGI-CU-12 12MAGI-CU-B1-12MAGI-CU-12 12MAGI-CU-B1-12MAGI-CU-12 12AT3601-1010MAGI-CU-12 1212Domestic Water Pressure Calculation ReportL [m]Insulationqv sum [l/s]qv dim [l/s]v (dim) [m/s]dp/L [Pa/m]dp (flow) [kPa]0,200000,200002,551,10,90,200000,200002,557113,66,30,200000,200002,551,00,10,200000,200002,557113,60,4