Title: økernvn 94.pdf
40202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3195 Date / Time: 09/11/2013 06:13:10 Headroom 2.7 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]184 280 9 8.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]13.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 2.7 60.5 45.4 36 4.2 60.8 42.9SR 36-45 4.2 247.0 35.4 36 3.4 247.5 32.8MAIN 12-36 8.4 246.0 35.5 12 8.7 246.0 32.8SR 36-45 4.2 247.0 35.4 36 3.4 247.5 32.810080604020NEXT (dB)