Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
SR 36-45 15.8 478.0 11.6 45 16.3 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 23.1 67.8 30.2 45 24.5 66.0 28.1SR 12-45 27.1 72.0 29.3 12 28.3 72.0 26.8MAIN 12-45 37.7 487.0 -11.5 36 38.7 500.0 -15.3SR 36-45 36.0 497.0 -12.2 45 37.0 496.0 -15.00804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.6 209.0 10.8SR 12 5.2 499.0 8.0MAIN 12 7.7 481.0 8.0SR 12 5.2 499.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Uni ConsultUniconsult tester.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00426.2 m60Insertion Loss (dB)504030201000250 MHz