Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Isc: 591A R: 0.39Ω Xl: 0.02Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.0V t: 274.7ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 518V Rnpe: >30.0MΩ Um: 520VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF026 C16/2/003 / Mal 3 10.03.2022 13:52 (TomekElektriker)KONTINUITET: R200mA LPER: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF026 C16/2/003 / Mal 4 10.03.2022 11:50 (TomekElektriker)SPENNING TRMS Uln: 236V Ulpe: 235V Unpe: 1V f: 49.99HzSYS.: TN/TTZ-LINEZ: 0.41ΩIsc: 558A R: 0.41Ω Xl: 0.02Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.3V t: 64.3ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTTALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:14GODKJENTGODKJENTGODKJENTGODKJENT*