Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 64,7 68,0 336,0 18,0 11,4Limit 100,0 - 555,0 50,0 25,0Margin 35,3 - 219,0 32,0 13,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,3 3,0 1,7 2,80Worst Value: Local: 36 27,4 43,8 16,4 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 22,0 14,7 7,3 85,75Remote: 78 22,6 18,5 4,1 31,25Worst Value: Local: 78 16,1 8,8 7,3 331,00Remote: 78 15,0 8,0 7,0 416,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):