Title: Ahlsell.pdf
Test Summary: PASSRemote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 250509416.1 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 20 Test Limit: EN50173 PL2 Class Ea Limits Version: V3.0 Date / Time: 05/20/2022 03:39:33 PM Operator: Pam Headroom 8.9 dB (NEXT 3,6-4,5) Cable Type: Cat 6 F/UTP NVP: 70.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]41.3 201 4 6.9Wire Map (T568B) PASS