Title: økernvn 94.pdf
150200250MHzLinkWare Version 7.4Cable ID: D3419 Date / Time: 09/11/2013 03:34:20 Headroom 6.4 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]75 118 8 3.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.6 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.4 241.0 35.6 78 6.3 228.5 33.4SR 36-78 7.1 241.5 35.6 78 7.9 241.5 33.0MAIN 36-78 6.4 241.0 35.6 36 6.6 238.0 33.1SR 36-78 7.1 241.5 35.6 78 7.9 241.5 33.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)