Title: 36 Siemens GDB181-MO.pdf.pdf
For detailed descriptions of the function behind a certain item, e.g. “how does RemoteFactoryReset in register 256 work”, please cf. section 10.2.Reg.NameR/WUnitScalingRange / enumerationProcess Values1SetpointRW%0.010..1002Override controlRW----0 = Off / 1 = Open / 2 = Close3 = Stop / 4 = GoToMin 5 = GoToMax3Actual positionR%0.010..1004Actual Flow [rel.]R%0.010..1205Actual Flow [abs.]Rm3/h / l/s10..600006Actual PressureRPa0.10..500256CommandRW--0 = Ready 1 = CalibrateAdaption 2 = SelfTest 3 = ReInitDevice 4 = RemoteFactoryResetReg.NameR/WUnitScalingRange / enumerationParameters257Opening directionRW----0 = CW / 1 = CCW258Adaptive ModeRW----0 = Off / 1 = On259Operating ModeRW----0 = VAV / 1 = POS260MinPositionRW%0.010..100261MaxPositionRW%0.010..100262Actuator Running Time Rs1150385VnomRWm3/h0.00010…429496.7295386