Title: Motorventiler fyrrom - VQE DN65-150.pdf
/ Warranty: The technical data and pressure differences indicated here are applicable only in com- bination with SAUTER valve actuators. The warranty does not apply if used with valve actuators from other manufacturers./ Definition of ∆p s: Maximum admissible pressure drop in the event of a malfunction (pipe breakafter the valve) at which the actuator reliably closes the valve by means of a return spring. / Definition of ∆p max: Maximum admissible pressure drop in control mode at which the actuatorreliably opens and closes the valve.Combination of VQE with electric actuators, actuating power 1000 NActuatorAVM322F120 AVM322F122AVM322SF132Actuating power1000 N1000 NControl signal2-/3-point2-/3-pt., 0...10 V, 4...20 mARunning time120/240 s120/80 s∆p [bar]Closes against the pressure∆pmax∆pmaxVQE065F3002.52.5VQE080F3001.51.5Cannot be used to close with the pressureA Maximum media temperature: 100 °C