Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.6 414.0 31.0 45 9.4 413.0 28.3SR 36-45 7.3 451.0 30.2 36 7.9 463.0 26.8MAIN 12-45 10.0 497.0 28.0 36 10.1 488.0 25.5SR 36-45 8.6 497.0 28.0 36 9.1 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.5 3.8 53.8 45 13.8 2.6 53.9SR 78-45 14.5 3.8 53.8 45 13.8 3.8 50.8MAIN 45-36 15.4 469.0 11.8 36 18.0 496.0 8.3SR 36-45 15.4 472.0 11.8 45 18.2 497.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 28.6 136.5 18.9 36 28.9 139.0 16.0SR 12-36 29.7 133.0 19.4 36 28.6 132.5 16.9MAIN 12-45 41.6 497.0 -12.2 36 42.3 495.0 -14.9