Title: EDM_AQAR32_01-S-2GB.pdf
All units are equipped with two scroll compressors fitted in tandem for adapting to partial system loads.The general operation status of the machine is continuously under the control of an IHM controller.The SYSAQUA R32 L and SYSAQUA R32 H units can operate without water tank, thanks to the IHM controller that implements an auto-adaptative control logic ensuring a total protection of the compressors at different load or water volume conditions.Finned coil The finned coil can work as evaporator (for H version) and condenser (for L and H version) and it is made of seamless copper tubes mechanically expanded into aluminimum fins. The fins of SYSAQUA R32 H coils are made of aluminium with hydrophylic bluefincoatingtofacilitatewaterdropletsdrain.The minimum water volume requested in cooling mode is 3.5L/kW for application air conditioning and 10L/kW for application process.