Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]28.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.1 499.0 29.3 36 7.6 500.0 26.4SR 36-45 9.2 491.0 29.4 36 8.8 491.0 26.6MAIN 12-36 8.1 499.0 29.3 36 7.6 500.0 26.4SR 36-45 9.3 500.0 29.2 36 9.0 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.8 7.1 48.2 45 20.5 5.0 48.3SR 45-78 19.8 7.1 48.2 45 20.7 6.1 46.5MAIN 78-45 21.6 500.0 11.3 45 21.5 498.0 8.3SR 78-45 21.6 500.0 11.3 45 21.2 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.6 58.5 32.3 45 23.9 54.5 30.8SR 36-45 24.1 54.5 33.2 36 24.8 58.3 29.8MAIN 12-36 36.5 499.0 -12.3 36 36.1 500.0 -15.3