Title: 1 etg del 2.pdf
Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T1143 Date / Time: 10/21/2013 08:03:05 AM Headroom 10.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]197 312 22 8.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 18.1 44.4 36 16.2 81.5 30.8SR 12-36 10.6 96.3 32.6 36 12.9 96.3 29.6MAIN 12-36 14.6 96.3 32.6 36 16.7 96.3 29.6SR 12-36 10.6 96.3 32.6 36 12.9 96.3 29.610080604020NEXT (dB)