Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
AInsulate the end of the pipe and some curved area by using separate insulator.8360_AirCon_Indoor_IM_ENG_EN.indb 82016-05-16 오후 5:32:122 Perform the following steps to install inspection holesin accordance with the panel type.aFor the recessed installation of the square panel.Install an inspection hole to the direction of connection parts of the refrigerant pipe and the drain hose. (1 point)Refrigerant pipeIndoor unit displayInspection holeb For recessed installation of the circular panelInstall inspection holes to both directions of the connection part of the refrigerant pipe and the drain hose and of the indoor unit display. (2 points)Inspection holeRefrigerant pipeIndoor unit displayInspection hole3 Insert bolt anchors, use existing ceiling supports or construct a suitable support as shown in figure.ConcreteHole in anchor Hole in plugInsertSuspension bolt (M10) - field supply360_AirCon_Indoor_IM_ENG_EN.indb 9