Title: +038=360.000-FA041._05-UV-Turbo Kjøkkenhette Jeven - Brosjyre.pdf
Reported dB(A) values apply at 10 m2 Sabine, which corresponds to an attenuation of 4 dB.The sound power level Lw in each octave band is obtained by adding the correction factor Kok to the actual sound level. LpALw= LpA+Kok.We reserve the right to make changesRecommended air flowSpigot sizeExtract air flowPressure lossmml/sm3/hPaØ 3150-2000-7200-60TurboSwing®1100 rpmTurboSwing 1100 rpm) a P120 100Damper ½ closedDamper open(s Ps s o80 70 60 50dB(A) =44dB(A) =40le r u s s e r P4030dB(A) =3580 100120 160 200240 320 400l/s300 500 700 1000 1400m3/hReported dB(A) values apply at 10 m2 Sabine, which corresponds to an attenuation of 4 dB.Correction factor KokHz125250500100020004000Kok715576tol.±3±3±2±2±3±4Turbo Hood9ADJUSTABLE SUPPLY AIR DEVICESSUPPLY AIR HOOD JSI-R TURBO