Title: +038=249.001-#####._01-10203518-01-RIA-NOT-007 Lydmålinger Collier_rev01.pdf
Object:Multirom(gipsvegg)Source room:5- 212Rec eiving room:5- 213Condition:Condition:Type:Type:Location:Location:Frequency range acc ording to theArea of c ommon partition:10,00m²c urve of shifted referenc e values (ISO 717- 1)Source room volume:Rec eiving room volume:13m³→ ⎯ B d70FrequencyR',f1/3 oc tave'R[Hz]50[dB]28,9, x e d ni60638010012516020025027,918,021,728,830,234,141,8n o i t c u d e r d n u o s t n e r a p p A5031545,64040046,350039,163043,980048,4100050,230125052,9160053,7200053,3250048,720315048,5400051,8500053,2106312525050010002000 Hz 4000Frequency, f, Hz ⎯→Rating according to ISO 717- 1 R'w Evaluatio n based o n field measurement results o btained in o ne-third-o ctave bands by an engineering metho d.(C;Ct r) =46(2;7) dBC50-3150 = Ctr,50-3150 =310dB C50-5000 = dB Ctr,50-5000 =210