Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
26.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.8 471.0 29.8 36 7.3 500.0 26.4SR 36-45 6.6 469.0 29.8 36 6.3 500.0 26.4MAIN 36-78 8.0 499.0 29.3 36 7.3 500.0 26.4SR 36-45 6.7 500.0 29.2 36 6.3 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.1 7.6 47.6 45 19.8 500.0 8.3SR 78-45 19.1 7.6 47.6 45 19.6 500.0 8.3MAIN 78-45 19.9 500.0 11.3 45 19.8 500.0 8.3SR 45-78 20.3 500.0 11.3 45 19.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.6 41.0 37.0 45 20.3 41.0 34.5SR 45-78 20.3 44.8 35.9 45 20.8 44.8 33.4MAIN 12-36 34.6 500.0 -12.4 36 33.8 500.0 -15.3SR 36-45 33.0 500.0 -12.4 36 32.8 500.0 -15.30804000250 MHzACR-N (dB)