Title: Simployer - Data testrapport =514.204-FS001.pdf
60.4 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD66 Date / Time: 28/01/2022 13:29:00 Headroom 8.1 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]54.6 280 20 9.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.6 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 8.1 37.0 47.2 4,5 9.7 37.0 44.5SR 1,2-3,6 9.2 87.0 41.0 3,6 10.5 218.5 31.2MAIN 1,2-3,6 10.2 239.5 33.4 3,6 10.1 240.0 30.5SR 1,2-3,6 10.4 240.0 33.4 3,6 10.8 250.0 30.2