Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
Hydraulic specifications ■ Available static system pressure Units with hydraulic module (single variable and fixed-speed (*) high pressure pump)Data applicable for: - Pure water at 20°C - Refer to the section "Evaporator water flow rate"’ for the water flow rate values (*) Sizes 360 to 600 only■ EvaporatorDYNACIAT LG, sizes 080-150180170160150a P k140, d a e h130120e r u s s e r P11010090807060501 LG 080 2 LG 090-100 3 LG 120 4 LG 130 5 LG 15000,511,522,5Water flow rate, l/s33,5 1243 44,55DYNACIAT LG, sizes 180-300220210200190180a P k, d a e h170160150140e r u s s e r P13012011010090807060507 LG 180 8 LG 200 9 LG 240 10 LG 260 11 LG 300012345Water flow rate, l/s677898 1011DYNACIAT LG, sizes 360-600220210200190180a P k170160, d a e h150140e r u s s e r P13012011010090807060