Title: +038=462.001-NB001._03-Installasjons og Brukerveiledning Xstorage Eaton.pdf
The battery rack consists of a nineteen inches wide rack mount 42U cabinet with multiple mounting slots designed to house the battery packs, and a connection unit secured in place with screws. Table 12: Battery rackModelWidth (mm) Depth (mm) Height (mm) Weight (kg) Static load Rack42U60010402020117(kg) 80010 battery packs + 1 connection unit© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL21 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guideFigure 10. Battery rack with battery packs installedFigure 11. Battery rack dimensions© Eaton 2019. All rights reserved.Revision: 001 Document ID: PCS M MANUAL22 (50)Eaton xStorage PCS Medium 50-200 kWUser's and installation guideThe number of battery racks is determined by the energy capacity (kWh) requirements of the project. Table 13: Number of battery racks based on energy capacityNumber of racks12345678910Strings per rackNomi- nal ca- pacity (kWh)