Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
SR 78-45 16.8 500.0 11.3 45 18.2 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.4 61.0 31.7 36 21.9 61.0 29.2SR 36-45 23.9 61.3 31.6 36 23.6 61.3 29.1MAIN 12-36 37.2 500.0 -12.4 36 38.2 497.0 -15.1SR 36-45 37.9 489.0 -11.7 36 38.5 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.7 447.0 8.0SR 45 9.1 483.0 8.0MAIN 45 8.7 447.0 8.0SR 45 9.1 483.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: SP1 BANK 4 ETGSMN 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00426.4 m60Insertion Loss (dB)504030201000250 MHz500