Title: Ahlsell.pdf
MAIN 3,6-7,8 16.4 10.4 52.0 3,6 17.1 10.5 49.5SR 3,6-7,8 17.4 8.8 53.6 3,6 17.5 10.0 50.0MAIN 3,6-4,5 49.0 500.0 -17.1 3,6 50.8 500.0 -20.0SR 3,6-4,5 46.5 479.0 -15.4 3,6 46.7 489.0 -19.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 3,6 6.3 496.0 8.0SR 3,6 4.9 476.0 8.0MAIN 3,6 6.3 496.0 8.0SR 3,6 4.9 476.0 8.04060500250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-44030201000250 MHzProject: Ahlsell Site: Not Set Floor: Not Set Rack: Not Set Untitled1Building: Not Set Room: Not Set Patch: Not SetPage 13Test Summary: PASSRemote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 250509510.3 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz