Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD46 Date / Time: 28/01/2022 12:41:45 Headroom 8.6 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]38.6 198 14 7.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]24.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 8.6 237.0 33.5 4,5 9.5 242.5 30.4SR 4,5-7,8 9.7 38.8 46.9 3,6 11.2 205.0 31.7MAIN 4,5-7,8 8.6 237.0 33.5 4,5 9.5 242.5 30.4SR 1,2-3,6 11.0 233.5 33.6 3,6 11.7 246.0 30.3PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)