Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Isc: 539A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 15.06.2020 11:39Zs(rcd)Z: 0.37ΩIsc: 623A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF033 C16/2 16.06.2020 09:45R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF034 C16/2 16.06.2020 09:45R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF035 C16/2 16.06.2020 09:52R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 11:31Tallberg Elektro A/S Tlf.22796640Side:11GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*Nr.808081818282838384848585TEST RAPPORTResultatSPĆNDINGUln: 231V Ulpe: 231V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF039 C16/2 15.06.2020 11:31