Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
/ENTSKAuditorium))]])noa)[Clearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 46.5%, Floor 20.0%, Light loss factor: 0.80EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 22 Perpendicular illuminance (adaptive) [Ix] 510 (= 500) 379 609 0.74 0.62 Surrounding area: 0.500 m 2 Surrounding area 16 Perpendicular illuminance (adaplive) [IX] 534 (= 300) 426 628 0.80 0.68 3 Background area 13 Perpendicular illuminance (adaptive) [Ix] 366 (= 100) 317 426 0.87 0.74Wall zone: 0.300 m# Luminaire ®(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 24 iGuzzini illuminazione - Q518 Laser Blade XS - Downlight HC 33.8W 2116 33.8 62.6 Total via all luminaires 50784 811.2 62.6Lighting power density: 9.04 W/m? (Floor area of room 89.70 m?)Consumption: 980 - 1550 kWh/a of maximum 3150 kWh/aThe energy consumption quantities do not take into account light scenes and their dimming levels.