Title: +135.01=315.001-UB003T_01-Montering og service 1039.pdf
Technical data .............................................................. 9 Installation .................................................................. 14 Operation .................................................................... 17 Maintenance ..........................................................17-21 Spare parts ............................................................25-263 (28)1030EN 817 I (ISO 3822) 50 -1000 kPa 0.27 l/s (300 kPa) 160 kPa (0.2 l/s) max. +80°C0 40 5 3. x a m1030F (1030F-105)EN 817 I (ISO 3822) Oras lab. 50 -1000 kPa 0.21 l/s (300 kPa) 0.07 l/s (300 kPa)(with flow controller) 1030F-105 270 kPa (0.2 l/s) max. +80°C0 40 5 4. x a m1035EN 817 I (ISO 3822) 50 -1000 kPa 0.27 l/s (300 kPa) 160 kPa (0.2 l/s) max. +80°C1 6 30 5 30 4. x a m4 (28)ø33.5ø10ø33.5G3/8ø33.5G1/2ø1025187211ø5425187211ø5425187211ø5415°15°15°5 2 13 6 13 6 5 1 2 15 2 13 6 11035F (1035F-104, 1035F-105)