Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]34.4 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.3 451.0 30.2 36 6.6 452.0 27.3SR 12-36 6.3 478.0 28.9 36 6.6 479.0 26.0MAIN 12-36 6.6 495.0 28.1 36 7.3 497.0 25.1SR 12-36 6.3 478.0 28.9 36 6.6 479.0 26.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.4 6.8 48.6 45 21.8 7.6 44.6SR 45-78 20.4 8.9 46.3 45 21.8 6.0 46.7MAIN 12-36 21.4 470.0 11.8 36 22.5 470.0 8.8SR 36-12 21.9 479.0 11.6 12 23.6 471.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 31.6 213.0 10.2 12 33.9 212.5 7.7SR 12-36 32.4 204.5 11.1 36 34.2 205.5 8.4MAIN 12-36 40.0 495.0 -12.1 36 40.7 497.0 -15.1