Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 33,7 68,0 175,0 9,0 6,2Limit 100,0 - 555,0 50,0 25,0Margin 66,3 - 380,0 41,0 18,8Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,5 3,0 2,5 1,60Worst Value: Local: 36 14,5 43,5 29,0 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 18,8 12,8 6,0 133,00Remote: 78 17,2 12,6 4,6 138,00Worst Value: Local: 78 15,2 8,0 7,2 465,00Remote: 12 15,9 8,5 7,4 357,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,7 26,7 3,0 500,00Remote: 36-45 29,4 26,7 2,7 500,00Worst Value: Local: 36-45 29,7 26,7 3,0 500,00Remote: 36-45 29,4 26,7 2,7 500,00dB 0601200Local250500 MHzdB 0