Title: økernvn 94.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]22.4 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.9 240.0 35.6 36 7.1 208.0 34.0SR 36-450.0 *246.0 35.5 36 0.5 *243.5 32.9MAIN 12-36 5.9 240.0 35.6 36 7.5 250.0 32.7SR 36-45 0.0 246.0 35.5 36 0.5 243.5 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.3 243.0 16.5 36 19.3 119.0 19.7SR 36-45 17.7 243.0 16.5 45 19.1 186.5 15.8MAIN 45-36 17.4 250.0 16.2 36 19.7 249.5 13.2SR 36-45 17.7 250.0 16.2 45 19.4 249.5 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250