Title: økernvn 94.pdf
111 176 13 4.8111 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]20.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.0 227.5 36.0 36 5.8 227.5 33.4SR 36-450.3 *249.5 35.4 36 0.7 *239.5 33.0MAIN 12-36 6.0 227.5 36.0 36 5.8 227.5 33.4SR 36-45 0.3 249.5 35.4 36 0.8 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 17.2 238.0 16.7 12 19.3 243.5 13.5SR 12-45 17.6 240.5 16.6 45 19.3 238.5 13.6MAIN 45-12 17.2 243.5 16.5 12 19.3 246.5 13.4SR 12-45 17.6 243.5 16.5 45 19.3 249.0 13.3010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz