Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 2 Perpendicular illuminance (adaptive) [Ix] 704 (= 500) 537 812 0.76 0.66 Surrounding area: 0.500 m 2 Surrounding area 2 Perpendicular illuminance (adaplive) [Ix] 602 (z 300) 349 818 0.58 0.43 3 Background area 2 Perpendicular illuminance (adaptive) [Ix] 491 (= 100) 103 889 0.21 0.12 Wall zone: 0.500 m 4 Visual task area 5 Perpendicular illuminance (adaptive) [Ix] 684 (= 500) 504 807 0.74 0.62 Surrounding area: 0.500 m 5 Surrounding area 5 Perpendicular illuminance (adaptive) [Ix] 622 (= 300) 374 815 0.60 0.46 3 Background area 2 Perpendicular illuminance (adaptive) [Ix] 494 (= 100) 103 889 0.21 0.12 Wall zone: 0.500 m # Luminaire ®(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 1 iGuzzini illuminazione - Q497 Laser Blade XS - Downlight HC 12.4W 739 12.4 59.6 24 iGugzini illuminaczione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 14.3HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000K