Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Side:16GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTNr. 116116117117118118119119120120121121122122123123124124TEST RAPPORTResultatDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:35KONTINUITET R: 2.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:30R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:39R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:39KONTINUITET R: >1999ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:17KONTINUITET R: >1999ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 15.06.2020 13:17R LOW OhmR: >1999ΩR+: >1999Ω R-: >1999Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:13R LOW OhmR: 0.06ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0Ω