Title: Avtrekksvifter punktavsug.pdf
Fans with manual thermal contacts (reset by disconnecting the power, motor protection SP1), must be taken into consideration when connecting surrounding equipment with automatic on/off function. Recomended wiring for KT fans (Fig 2).Operation Before initial operation, check the following:Electrical connection has been properly completed.Electrical connection has been properly completed.Protective conductor has been connected. - Motor protection installed. - Safety devices in place (protection grid) - Leftover installation materials and foreign materials have been removed from the casing.When putting into operation, check the following:Connection data corresponds to thespecifications on the nameplate: Maximum voltage +6%, -10%, according to IEC 38. Rated current must not be exceeded with more than 5% at rated voltage.