Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 45,2 68,0 235,0 13,0 7,9Limit 100,0 - 555,0 50,0 25,0Margin 54,8 - 320,0 37,0 17,1Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,9 3,1 2,2 3,10Worst Value: Local: 36 19,2 43,6 24,4 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 14,2 9,8 4,4 261,00Remote: 12 16,4 12,0 4,4 160,00Worst Value: Local: 78 14,2 9,8 4,4 261,00Remote: 78 15,9 8,0 7,9 447,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,8 26,7 2,1 498,00Remote: 36-45 28,5 26,7 1,8 498,00Worst Value: Local: 36-45 28,8 26,7 2,1 498,00Remote: 36-45 28,5 26,7 1,8 498,00dB 0501000Local250500 MHzdB 0