Title: Hardware Installation Guide.pdf
RS-485 is “Not Evaluated by UL” and therefore cannot be used in UL installations.Each field-wiring terminal is suitable for single conductor (wire) only. For detailed mounting instructions, refer to the Hardware Installation Guide (DOC-600).For use with separately Listed compatible control units and accessories as indicated in the installation instructions of the end-use application.Environmental for UL installations: -Temperature: -10 to +49°C (14 to 120°F) operating Humidity: 85+/-5% at 30+/-2°C (86°F)360 — revision 6Hardware Installation Guide72SpecificationThe interface is for use in low voltage, Class 2 circuits only.Power Input: - -PoE powered at 12.95 watts, compliant to IEEE 802.3af or 12 VDC ± 10%, 900 mA maximum power supplyPower Output: - - -12 VDC @ 650 mA maximum (reader and AUX outputs combined) Reader 1 (TB3) 12 VDC (10.3 through 12.6) @ 150 mA maximum AUX (TB5) 12 VDC (10.7 through 13.0) @ 650 mA maximumNote: