Title: 4. Leieavtaler.pdf
?"'""' by ,m,;a-, •• """ d • .,;,;;., oo ,.;., , ;,..,., 11,,1,..,;ucy orFM c,,..,,. """"'" ••~'" ~;'"-}Design Dens ity: 8 mm/min over 280 m2 (wet type system - avoid dry pipe or preaction systems)n, n:por1 is provided to you for infonnational purposes only to reduce lhe possibility of loss to insured property by bringing to your attention certain potential m rds or conditions Li&, safety, or health issues are not addressed. You must make the decision whether to take wiy action. FM Global undertakes no duty toPage 6 of9Sprinkler Head Type: FM Approved (Standard Coverage, Quick Response, Pendant, 57 - 77°C - Do not use concealed ceiling sprinklers) Sprinkler Line Spacing: 2.1 - 4.5 m2 Hose Demand: 950 L/min Water Duration: 60 minutes2015-01-07: Clean rooms will not be used in this facility.d. Data Center Facilities:FM Global Property Loss Prevention Data Sheet 5-32, Data Centers and Related Facilities.