Title: 2wayEPIV_PICS_en.pdf
Initiate FunctionInitiation of actuator functions for service and test. After command is sent, value returns to None(1). With Reset(4) all status in StatusActuator MO[106] can be reset.1: None 2: Adaption 3: Test 4:ResetUnitSelFlowMV[121] Unit Selection FlowThe selected unit is valid for AI[19] and AV[104]1:m3/s 2:m3/h 3:l/s 4:l/min 5:l/h 6:gpm 7:cfmSpSourceMV[122] Setpoint SourceIf Analog(1) then actuator is controlled by analog signal 0...10V on wire 3. If Bus(2) then setpoint via bus SpRel AO[1]1:Analog 2:BusControlModeMV[123] Control Mode1:PosCtrl 2:FlowCtrlSens1TypeMV[220] Sensor 1 TypeIf SpSource MV[122] is Analog(1) then Out_Of_Service is TRUE1:None 2:Active / Hybrid 3:- 4:- 5:Switch 6:- 7:- 8:- 9:- 10:- 11:-Access: R = Read, W = Write, C = Commandable with priority array * All Status Information except the "Gear disengaged" need a reset command to go back to normal operationwww.belimo.comPICS 2-way EPIV • en • v1.0 • 05.2018 • Subject to changes