Title: Aggregatkjøring.pdf.pdf
Unit no. 10Date 18.06.2021Page 11/40Total current, Amp.(2 x 5.60 A) 11.20AVoltage3x400VConsumed power from mains power supply, including speed control3.37kWHeating coil, FluidAir flow15000m³/hPressure drop20PaAir temperature before/after13.6/21.0°CAir relative humidity before/after61/38%Capacity37.10kWFace velocity2.20m/sFluid typeWaterFluid temperature inlet/outlet40.0/25.0°CFluid flow rate0.61l/sFluid pressure drop9.4kPaFluid velocity0.51m/sCoil volume17.5Connection sideService sideConnection size inlet/outlet1 1/4" / 1 1/4"Tube materialCuFin materialAlFin spacing2.5mmNo. of rows2Coil codeGXH-22-W-4-2-11-995-2015-2.5-CU-Al-*-1 1/4Tap for frost guard1pcsThe extract unit consist ofFilterDimensioning pressure drop104PaInitial pressure drop/Final pressure drop54/154PaVelocity, face area2.06m/sVelocity, filter area0.12m/sFilter classF7 - ePM1 60%