Title: Data tester Smestad skole - Detaljert.pdf
Cable Label: 521.002-UD-192 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:28:47 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 29,0 68,0 150,0 8,0 5,3Limit 100,0 - 555,0 50,0 25,0Margin 71,0 - 405,0 42,0 19,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,4 3,0 2,6 1,60Worst Value: Local: 36 12,6 43,8 31,2 500,00dB -2020600Local250