Title: Data tester Smestad skole - Detaljert.pdf
Limit 100,0 - 555,0 50,0 25,0Margin 52,9 - 311,0 37,0 17,0Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 2,80Worst Value: Local: 36 20,0 43,8 23,8 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 15,3 8,0 7,3 456,00Remote: 78 23,2 16,1 7,1 62,25Worst Value: Local: 12 15,3 8,0 7,3 456,00Remote: 78 18,6 8,0 10,6 449,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 499,00Remote: 36-45 29,3 26,7 2,6 499,00Worst Value: Local: 36-45 28,9 26,7 2,2 499,00Remote: 36-45 29,3 26,7 2,6 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):