Title: Ahlsell.pdf
LinkWare™ PC Version 11.1Cable ID: UD 14 Test Limit: EN50173 PL2 Class Ea Limits Version: V3.0 Date / Time: 05/20/2022 03:44:14 PM Operator: Pam Headroom 8.4 dB (NEXT 3,6-4,5) Cable Type: Cat 6 F/UTP NVP: 70.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 3,6] [Pair 4,5] [Pair 4,5] [Pair 3,6]44.9 218 4 7.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 7,8] [Pair 7,8] [Pair 7,8]19.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 8.4 489.0 29.5 3,6 10.2 489.0 26.6SR 3,6-4,5 9.3 494.0 29.4 3,6 10.0 498.0 26.4MAIN 3,6-4,5 8.4 489.0 29.5 3,6 10.2 489.0 26.6SR 3,6-4,5 9.4 498.0 29.3 3,6 10.0 498.0 26.410080604020NEXT (dB)