Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]45.1 195 2 6.63Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]21.0 496.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.7 485.0 29.5 36 8.6 491.0 26.6SR 12-45 9.4 468.0 29.9 45 9.5 494.0 26.5MAIN 36-45 8.9 500.0 29.2 36 8.8 500.0 26.4SR 12-45 9.7 494.0 29.4 45 9.5 494.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.1 465.0 11.9 45 13.7 465.0 8.9SR 45-78 14.3 465.0 11.9 45 14.3 5.0 48.3MAIN 78-45 14.5 488.0 11.5 45 14.2 496.0 8.3SR 45-78 14.3 465.0 11.9 45 15.2 472.0 8.80100806040200250 MHzACR-F (dB)