Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
366465_b / 03.201710/44| Installation InstructionsAvoid highly corrosive or dusty environments. In the event of an extended operations stop, you are strongly recommended to put the refrigerant fluid in the tank if there is one fitted onto the condensation unit. The aim of this operation is to avoid the refrigerant migrating to the compressor and any concentration of fluid within the lubricant that may cause “liquid slugs” during recommissioning.■ 4.1. Circuit leak-tightness Systematically check all connections for any refrigerant leaks with an electronic leak detector suitable for the type of refrigerant used. Leak detection can be carried out before the vacuum purge using a pre-loading of nitrogen and an aerosol (tracer fluids are prohibited). A more accurate check will be carried out after charging to ensure the integrity of the refrigerant circuit using a detector.