Title: +038=360.000-JV042._02-HMa-1,5 Avtrekksvifte R&H - Teknisk spesifikasjon.pdf
1,50-1,0 Exhaust air 4.500 2,17 1.930,0 1.000,0 690,0 151,00Panel outside Panel inside Panel inside bottom assembly material Velocity class SFP (V) Class / Value SFP (E) Class / Value Power class Energy efficiency class Energy efficiency classFilterExhaust air44,00 kgPM1-60-TA-520-KU-CAType airflow [m³/h] Class ISO 16890 Class EN 779 initial pressure drop [Pa] dimensioning pressure drop [Pa] 132 final pressure drop [Pa] 2004.500 ePM1 60% F7 64Bag length [mm] Filter surface [m2] face velocity [m/s] Energy efficiency class Energy consum. [kWh/a] system of filter handling filter media1setrevision door with dual hingeDimensions [mm]OpeningDimensions [mm]1 / 2373169 / 360,xxx 04.03.2021 NOR Oslo Arild Busengdahl04.03.2021T2 TB2 D1 L1 F90,03 0,02 0,000,00 0,789 2018: 230FB RAL7035 (C4) GI GI GI V4 SFP2 / 532 w/(m³/s) SFP2 / 631 w/(m³/s) P1 EUROVENT RLTA h A+132 Pa520,0 9,10 2,40 B 1.101 filter tension device Glassfiber620,0 x 620,0930,0 x 620,004.03.202110:48