Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: D3099 Date / Time: 09/11/2013 02:30:56 Headroom 7.0 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]137 217 15 6.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]18.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 235.5 35.8 12 7.8 240.5 33.0SR 36-78 7.0 231.5 35.9 12 7.4 204.0 34.2MAIN 12-36 7.4 235.5 35.8 12 7.8 240.5 33.0SR 36-78 7.0 231.5 35.9 12 8.1 250.0 32.710080604020NEXT (dB)