Title: Data tester Smestad skole - Detaljert.pdf
1200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,6 10,2 10,4 500,00Remote: 12-45 20,7 10,2 10,5 499,00Worst Value: Local: 12-45 20,7 10,2 10,5 500,00Remote: 12-45 20,6 10,2 10,4 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,4 24,0 3,4 493,00Remote: 45 28,1 23,8 4,3 500,00Worst Value: Local: 36 27,3 23,8 3,5 499,00Remote: 45 28,1 23,8 4,3 500,00PS-ACRF: Pass Worst Margin: Local: 12 72,6 61,2 11,4 1,00Worst Value: Local: 45 19,2 7,2 12,0 499,00Remote: 12 71,3 61,2 10,1 1,00Remote: 12 18,8 7,3 11,5 494,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:05Signature:______________________ Page: 77Copper Certification Report