Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
3 screws for securing the module to the grounding bar • Instructions manual[A]Status LEDABC[B]Mini USB portD[C]Relay-xConnection terminals for relay output xE[D]Holes for the grounding bar screws[E]CAN drive connector (opposite)Description of the Previdia Max system partsF27Fire detection and extinguishant systemLED IFM4RColourOn solidFlashingCANBlueActivity on the CAN communication BUSOUTxGreenOutput x activatedIFM4R module - technical specificationsPower supply voltage19-30 Vsupplied by IFM24160 moduleOperating temperaturefrom -5°C to +40°CConsumption @ 27.6Vstand-bymaximum10mA80mAMaximum voltage on outputs5A @ 30V3.13IFM4IO, internal module with 4 input/output terminalsThe IFM4IO module provides 4 input/output channels (IN/OUT 1, ..., IN/OUT 4) each of which, by means of the configuration software, can be configured as: