Title: Data tester Smestad skole - Detaljert.pdf
PS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,6 24,0 2,6 493,00Remote: 36 27,9 23,9 4,0 494,00Worst Value: Local: 36 26,6 24,0 2,6 493,00Remote: 36 27,8 23,9 3,9 495,00PS-ACRF: Pass Worst Margin: Local: 45 65,6 54,3 11,3 2,20Worst Value: Local: 45 20,1 7,2 12,9 500,00Remote: 12 65,7 54,3 11,4 2,20Remote: 45 20,0 7,2 12,8 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:56Signature:______________________ Page: 9Copper Certification ReportCable Label: 521.002-UD-158 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 10:14:59 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: