Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
[Pair 12] [Pair 12] [Pair 12]25.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.7 500.0 29.2 36 10.4 496.0 26.5SR 36-45 7.3 493.0 29.4 36 8.1 493.0 26.5MAIN 36-45 10.7 500.0 29.2 36 10.4 496.0 26.5SR 36-45 7.5 500.0 29.2 36 8.1 493.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.2 494.0 11.4 45 14.1 2.5 54.3SR 45-78 14.2 476.0 11.7 45 14.1 2.6 53.9MAIN 78-45 14.2 494.0 11.4 45 15.3 494.0 8.4SR 45-78 14.3 493.0 11.4 78 15.2 475.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.3 48.3 34.9 45 23.5 38.5 35.3SR 45-78 20.3 46.5 35.4 45 21.7 36.5 36.0MAIN 36-45 36.0 500.0 -12.4 36 35.8 496.0 -15.0SR 36-45 32.8 500.0 -12.4 36 33.8 499.0 -15.20804000