Title: +039=335.001-NT001._01-2016_001.pdf
Prosjekt: Mckinsey & Company INC NorwayProsjektnummer:223188Ansvarlig:Roy MortensenFIRESAFE/Type dokument:Driftsog vedlikeholdsmanualUtfert av:Roy MortensenDato:15.12.2021Engineering data sheetINERGEN Mono orifice nozzleGeneralNazzle for use in land based INERGEN-systems. The nozzle is designed to control the flow using a single orifice withdimensions from @1mm to @36mm.The nozzle is designed to disperse the flow laterally (360°) and slightly away from the mounting surface (cefling/wall).The nozle orifice must be calculated specifically for each installation. Each nozzle must be calibrated and marked individually and permanentlywith the orifice dlameter.An uncalibrated nozzle is delivered with a 3 mm orifice.A calibrated nozzie can be ordered with a -8 after the item no.For example 2102048 is an IN15 IS0 Nozzle Calibrated.IMT-calculation or info on the needed orifice diameter must follow ordersfor8 item nos.General specifications