Title: økernvn 94.pdf
SR 36-45 9.2 44.3 35.6 36 10.9 44.0 33.2MAIN 12-36 21.0 232.5 6.4 36 21.0 233.0 3.7SR 36-45 18.9 249.5 4.7 36 18.7 245.5 2.5010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 6.2 36.3 18.2SR 36 6.1 96.5 14.2MAIN 12 7.5 200.5 11.0SR 36 6.1 96.5 14.2010080050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040200050100150MHzProject: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002173 ft60Insertion Loss (dB)50403020100050100150200250MHz100NEXT @ Remote (dB)806040202500050100150200250MHz100ACR-F @ Remote (dB)806040202500050100150200