Title: 360.001 - Tilluft.pdf
2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeTypeDUCTBEND-45DUCTBEND-30DUCTBEND-30DUCTBEND-90DUCTBEND-90MAGIB-C4-*-*MAGIB-C4-*-*MAGIB-C4-*-*MAGIB-C4-*-*MAGIB-C4-*-*Product200200200200200200200200200200SizeSound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]0,53002,73002,74,13002,73002,70,13002,73002,71,03002,73002,71,33002,73002,7350,2 Sound in:Attenuation: Addition:0,7 Sound in:Attenuation: Addition:2,1 Sound in:Attenuation: Addition:0,5 Sound in:Attenuation: Addition:0,1 Sound in:Attenuation: Addition:0,5 Sound in:Attenuation: Addition:0,5 Sound in:Attenuation: Addition:1,4 Sound in:Attenuation: Addition:0,7 Sound in:Attenuation: Addition:1,4 Sound in:Attenuation: Addition:63 [dB]34.20.0 +11.434.20.0 +11.434.20.4 +11.433.90.0 +11.433.90.0 +11.433.90.0 +11.433.90.1 +11.433.80.0 +18.734.00.1 +11.4