Title: DOCA0005EN-12.pdf
Wye: 100 - 277 V L-N, 173 - 480 V L-L ±20%Delta: 173 - 480 V L-L ±20%Maximum current125 AMeasured current1 A to 125 AOverload332 V L-N or 575 V L-LVoltage impedance6 MΩCurrent impedance< 0.2 mΩFrequency50 / 60 Hz ±10%Measurement categoryIIIMinimum wire temperature rating required 105 °C (221 °F)Burden< 10 VA at 125 AWire50 mm2 / 1 AWGWire strip length13 mm / 0.5 inTorque3.5 Nm / 30.9 in•lbWithstand10 A continuous, 20 A at 10 sec/hrDOCA0005EN-12Specifications117Specifications iEM3000 series user manualPower system inputs: iEM32•• metersCharacteristicValueMeasured voltageWye: 100 - 277 V L-N, 173 - 480 V L-L ±20%Delta: 173 - 480 V L-L ±20%Overload332 V L-N or 575 V L-LImpedance3 MΩFrequency50 / 60 Hz ±10%Voltage inputsMeasurement categoryMinimum wire temperature rating requiredIII90 °C (194 °F)Maximum device consumption< 10 VAWire2.5 mm2 / 14 AWGWire strip length8 mm / 0.31 inTorque0.5 Nm / 4.4 in•lb