Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Resolution (digital representation): 12 bit (0 … 4095) Measuring principle: Input resistance:non-differential, single-ended W305: W315: W325: ± 0.15 % ± 0.05 % ± 0.25 % ≤ 2 ms W305: W325: W315: yes typically 2.4 ms < 60 mA13.5 kΩ / 0.1 % 120 Ω / 0.1 % 13.7 kΩ / 0.1 %Accuracy at 25°C Repeat accuracy: Temperature error (0 … +55 °C) Conversion time A/D: Overvoltage protection:± 40 VDC (permanent) ± 40 VDC (permanent) ± 35 mA (permanent)Overcurrent protection: EMC protection: Time constant of input filter: Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Terminals:0 mA0 mA Pluggable 14-pole spring terminal block (4 405 5002 0), for Ø up to 1.5 mm²,Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-61Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W3x5Connections6Digital/analogue values Input signals and type PCD2.W305 + 10.0 V + 5.0 V 0 VPCD2.W315 + 20 mA + 10 mA 0 mA