Title: 2wayEPIV_PICS_en.pdf
The specified maximum length of writable strings is based on single-byte characters.  Object name 32 char  Location 64 char  Description 64 charThe device supports DeviceCommunicationControl service. No password is required.A maximum of 6 active COV subscriptions with lifetime of 1...28'800 sec. (max. 8 hours) are supportedActuators support quick addressing via the "Address" and "Adaption" buttons. For detailed information, please product datasheet (chapter Service).PICS 2-way EPIV • en • v1.0 • 05.2018 • Subject to changes3 / 52-way EPIVCommunicative characterised control valve with sensor- operated flow control, 2-way (EPIV)BACnet object descriptionObject NameObject Type [Instance]DescriptionCommentValuesFlagsDeviceDevice [Inst.Nr.]0…4'194'302RelPosAI[1]Relative Position in %0…100Overridden = true, if the gear is disengagedAbsPosAI[2]Absolute Position in degree0...max angleThe unit depends on the device: [°] for actuators with rotary movement