Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,0 23,8 3,2 498,00Remote: 36 28,5 23,8 4,7 500,00Worst Value: Local: 36 27,0 23,8 3,2 498,00Remote: 36 28,5 23,8 4,7 500,00PS-ACRF: Pass Worst Margin: Local: 45 22,9 10,7 12,2 335,00Worst Value: Local: 45 19,5 7,2 12,3 500,00Remote: 45 71,7 61,2 10,5 1,00Remote: 45 19,4 7,2 12,2 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:06Signature:______________________ Page: 82Copper Certification ReportCable Label: 521.002-UD-208 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:12:18 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: