Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]11.7 51 1 2.04Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]35.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 449.0 30.3 36 9.1 450.0 27.4SR 12-36 6.0 469.0 29.3 36 8.1 470.0 26.4MAIN 12-36 8.4 500.0 27.8 36 9.7 500.0 25.0SR 12-36 6.6 500.0 27.8 36 8.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.2 500.0 11.3 36 21.6 428.0 9.6SR 45-36 20.2 499.0 11.3 36 21.4 488.0 8.5MAIN 36-45 20.2 500.0 11.3 36 21.9 479.0 8.6SR 45-36 20.2 499.0 11.3 36 21.6 497.0 8.30100806040200250 MHzACR-F (dB)