Title: 2 etg del2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]236 372 24 17.5236 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 241.0 35.6 36 1.0 * 241.0 33.0SR 36-78 9.1 205.0 36.8 36 9.3 205.0 34.1MAIN 36-45 1.3 248.5 35.4 36 1.2 248.5 32.7SR 36-78 10.1 236.0 35.7 36 9.6 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 12.4 50.3 30.2 45 14.7 44.8 28.2SR 36-45 12.5 50.3 30.2 45 14.3 47.5 27.7MAIN 45-36 13.2 196.5 18.3 36 17.6 247.0 13.3SR 36-45 13.4 196.5 18.3 45 16.2 247.0 13.3010080604020050100150MHzACR-F (dB)2002500100806040