Title: 1 etg del 2.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.9 10.1 52.1 12 8.3 10.1 49.8SR 12-36 6.3 24.3 43.0 36 8.4 16.5 44.8MAIN 36-45 10.1 246.5 5.0 36 9.5 247.0 2.3SR 36-45 9.5 250.0 4.7 36 9.2 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.7 32.3 18.5SR 45 4.1 38.8 18.1MAIN 36 8.6 249.0 10.0SR 36 6.2 195.0 11.1010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1