Title: +038=433.000-NI003._05-Testrapport elektriske anlegg - DM3.E3.433.09.02, Pareto plan 09.pdf
GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTNr.130130131131132132133133134134135135136136137137TEST RAPPORTResultatR ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF202 C16/2 10.06.2020 15:11R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF203 C16/2 10.06.2020 15:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF204 C16/2 10.06.2020 15:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E3.433.09.02 / XF205 C16/2 10.06.2020 15:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13KONTINUITET R: 0.0ΩGrenseverdi: 1.0Ω