Title: økernvn 94.pdf
Cable ID: T4160 Date / Time: 09/10/2013 10:03:43 Headroom 13.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]136 212 11 6.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]12.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 17.2 100.0 32.3 36 17.9 58.5 33.1SR 12-36 13.6 58.3 36.1 36 15.2 82.8 30.7MAIN 45-78 17.2 100.0 32.3 45 18.8 98.5 29.4SR 12-36 14.2 99.5 32.3 36 15.2 94.3 29.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 24.0 8.4 40.2 12 25.7 4.6 42.3