Title: Data tester Smestad skole - Detaljert.pdf
Remote: 45 27,7 23,8 3,9 500,00Worst Value: Local: 36 27,6 23,8 3,8 500,00Remote: 45 27,7 23,8 3,9 500,00PS-ACRF: Pass Worst Margin: Local: 12 72,7 61,2 11,5 1,00Worst Value: Local: 45 20,3 7,2 13,1 499,00Remote: 12 72,8 61,2 11,6 1,00Remote: 12 19,2 7,2 12,0 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 46Copper Certification ReportCable Label: 521.002-UD-145 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:55:10 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4