Title: DOCA0005EN-12.pdf
Check the wire connections and correct the wiring settings if needed.Metering continues.205Date and Time have been reset due to a loss of power.Set the Date and Time.206Metering continues.Pulse is missing due to overload on energy pulse output.Check the energy pulse output settings and correct if needed.207Metering continues.Abnormal internal clock function.Restart the meter by powering off and powering on again then reset the date and time.1 Not all diagnostic codes apply to all devices.126DOCA0005EN-12iEM3000 series user manualPower, energy and power factorChapter 11 Power, energy and power factorNOTE: The descriptions in this section assume that you are an electrical energy consumer, not a supplier.Power (PQS)A typical AC electrical system load has both resistive and reactive (inductive or capacitive) components. Resistive loads consume real power (P) and reactive loads consume reactive power (Q).