Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF203 16C2/003 30.11.2020 12:03 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / MPE1 / Ventilasjon 27.11.2020 11:29KONTINUITET R: 0.0ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Ventilasjon 27.11.2020 11:29R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Ventilasjon 27.11.2020 11:29R LOW OhmR: 0.01ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Ventilasjon 27.11.2020 11:47R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / MPE1 / Gulv kanal 27.11.2020 11:30Tallberg Elektro A/S Tlf.22796640Side:52GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTMISLYKKESNr.360360361361362362363363364364365365366366367367TEST RAPPORTResultat R LOW OhmR: >1999Ω