Title: økernvn 94.pdf
250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D4150 Date / Time: 09/10/2013 04:57:48 Headroom 11.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 45] [Pair 45] [Pair 45]211 314 3 9.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 78] [Pair 78] [Pair 78]6.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 90.0 33.1 36 16.0 98.3 29.4SR 12-36 11.7 99.8 32.3 36 14.0 99.8 29.3