Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 12-45 20.0 3.5 61.0 45 20.3 4.1 57.6SR 36-45 21.2 3.6 60.8 36 21.1 3.6 58.0MAIN 36-78 45.0 495.0 -12.1 36 44.6 498.0 -15.1SR 36-45 42.7 476.0 -10.8 36 42.6 476.0 -13.70804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.7 492.0 8.0SR 45 3.9 493.0 8.0MAIN 45 3.7 492.0 8.0SR 45 3.9 493.0 8.04060500250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-44030201000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA0045.4 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500100