Title: TFP510_06_2015.pdf
4-1/4" ± 1/8" (108,0 ± 3,2 mm)3-1/2" DIA. (88,9 mm)3.5°SPRINKLER FITTING (REFER TO DESIGN CRITERIA SECTION)CENTERLINE OF WATERWAY5/16" (7,9 mm)FIGURE 9 TY3335 AND TY3735 HORIZONAL SIDEWALL WITH DEEP ESCUTCHEONFACE OF SPRINKLER FITTINGORDER LENGTHS: 5-1/2" to 48" (139,7 to 1219,2 mm) IN 1/4" (6,4 mm) INCREMENTSMINIMUM 2-1/4" (57,2 mm) DEFLECTOR TO MOUNTING SURFACESPRINKLER FITTING (REFER TO DESIGN CRITERIA SECTION)CENTERLINE OF WATERWAY3.5°5/16" (7,9 mm)FIGURE 10 TY3335 AND TY3735 HORIZONAL SIDEWALL WITHOUT ESCUTCHEONTFP510 Page 5 of 10The configuration shown in Figure 12 is only applicable for wet pipe systems where the sprinkler fitting and water- filled pipe above the sprinkler fitting are not subject to freezing and where the length of the Dry-Type Sprinkler has the minimum exposure length depicted in Figure 11. Refer to the Exposure Length section.