Title: Hardware Installation Guide.pdf
LNL-2210 Intelligent Single Door Controller27SpecificationThe interface is for use in low voltage, Class 2 circuits only, and it is for use with UL Listed access control or burglar alarm power limited power supplies. The installation of this device must comply with all local fire and electrical codes.Power Input: - -PoE power input 12.95W, compliant to IEEE 802.3af or 12 VDC ± 10%, 900 mA maximumNote:For UL installations, PoE powered devices are not evaluated by UL. Power for these devices must be provided by a UL 294 or UL 603 Listed power supply, or the LNL-AL400ULX or LNL-AL600ULX-4CB6 Power Supply/Charger (12 VDC).Power Output (thermally protected) - - -Reader port 1:12 VDC @ 150 mA Reader port 2: use AUX power port AUX power port: used to power reader 2 and/or strike, not to exceed 650 mASRAM Backup Battery: rechargeable battery (Panasonic part number ML920S) with battery life up to 10 years to be replaced by authorized service personnel only.