Title: DM1-3 plan 05 lysberegningsrapport.pdf
Ground area: 79.89 m² | Reflection factors: Ceiling: 70.0 %, Walls: 50.0 %, Floor: 20.0 % | Maintenance factor: 0.80 (fixed) | Clearance height: 2.850 m | Mounting height: 1.700 m - 2.500 m57201104 DM1-3 McKinseyBuilding 1 · Storey 1 · Corridor and reception SummaryResultsSymbolCalculatedWorkplaneĒ272 lxg10.019Visual task areasĒ Task Area960 lxg1 Task Area0.12Ē Surrounding area833 lxg1 Surrounding area0.062Ē Background area311 lxg1 Background area0.087Consumption valuesConsumption[630 - 810] kWh/aLighting power densityRoom5.28 W/m²1.94 W/m²/100 lxUtilisation profile: Places of public assembly - General areas, Entrance hallsLuminaire listpcs.Manufacturer Article No.Article name4IGUZZINIMJ65iN 30 LED 47.3W1IGUZZINIQ497Laser Blade XS - Downlight HC 12.4W11iGuzzini illuminazione S.p.AQ882_B12 G