Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,3 23,8 3,5 500,00Remote: 36 28,6 23,9 4,7 496,00Worst Value: Local: 36 27,3 23,8 3,5 500,00Remote: 36 28,6 23,8 4,8 497,00PS-ACRF: Pass Worst Margin: Local: 12 66,7 56,3 10,4 1,75Worst Value: Local: 12 21,8 8,1 13,7 452,00Remote: 45 72,0 61,2 10,8 1,00Remote: 45 22,0 8,1 13,9 451,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:06Signature:______________________ Page: 86Copper Certification ReportCable Label: 521.002-UD-65 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:19:12 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software: