Title: økernvn 94.pdf
Cable ID: D4175 Date / Time: 09/09/2013 02:11:01 Headroom 3.0 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]215 328 12 10.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]10.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-78 7.5 163.0 38.4 78 8.2 202.5 34.2SR 36-45 3.0 238.5 35.7 36 3.5 240.0 33.0MAIN 12-78 7.7 242.0 35.6 78 8.2 247.0 32.8SR 36-45 3.0 240.0 35.6 36 3.5 240.0 33.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 16.7 162.5 20.0 45 16.9 236.5 13.7