Title: Data tester Smestad skole - Detaljert.pdf
Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,7 25,3 3,4 450,00Remote: 36 28,3 23,9 4,4 494,00Worst Value: Local: 45 27,4 23,8 3,6 498,00Remote: 36 28,2 23,9 4,3 495,00PS-ACRF: Pass Worst Margin: Local: 45 65,5 54,3 11,2 2,20Worst Value: Local: 12 22,4 8,7 13,7 419,00Remote: 12 64,5 54,3 10,2 2,20Remote: 45 21,9 9,1 12,8 400,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:04Signature:______________________ Page: 71Copper Certification ReportCable Label: 521.002-UD-169 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 13:48:26 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: