Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
GODKJENTGODKJENTGODKJENT*Nr. 345345346346347347348348349349350350351351TEST RAPPORTResultatDM1-3. Plan 6 / DM1.E5=433.06.04 / XF105 16C2/003 26.11.2020 14:39Z-LINEZ: 0.20ΩIsc: 1.17kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF105 16C2/003 26.11.2020 14:39Zs(rcd)Z: 0.23ΩIsc: 1.01kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF105 16C2/003 26.11.2020 14:39RCD II: 28.5mAUci: 0.1V t: 14.8ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF105 16C2/003 27.11.2020 11:47R LOW OhmR: 0.06ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF105 16C2/003 27.11.2020 11:47KONTINUITET R: 0.0ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF105 16C2/003 27.11.2020 11:47R LOW OhmR: 0.06ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7Ω