Title: 1 etg del 2.pdf
SR 36-45 14.7 227.0 17.1 36 16.6 195.0 15.4MAIN 45-36 14.6 246.0 16.4 36 16.6 246.0 13.4SR 45-36 14.7 249.0 16.3 36 16.7 241.0 13.5010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.3 22.5 43.8 12 8.2 14.4 46.3SR 12-36 6.8 16.0 47.5 12 8.7 14.4 46.3MAIN 12-36 14.2 246.0 5.1 36 13.6 246.0 2.4SR 36-45 14.2 248.0 4.9 36 13.6 244.5 2.6010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.4 44.3 17.5SR 45 4.3 11.0 20.8MAIN 45 2.4 44.3 17.5SR 36 8.2 244.5 10.160500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active