Title: etg u1.pdf
SR 45-36 18.1 5.6 49.2 45 19.5 4.3 48.6MAIN 45-36 19.1 250.0 16.2 36 21.8 250.0 13.2SR 36-45 19.6 250.0 16.2 45 21.4 249.5 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.7 26.6 41.9 12 11.3 22.5 41.4SR 12-36 9.2 26.6 41.9 36 11.2 26.6 39.5MAIN 36-45 17.3 247.0 5.0 36 17.7 250.0 2.0SR 36-45 17.8 249.5 4.7 36 17.3 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.8 35.0 18.3SR 45 3.4 14.1 20.3MAIN 45 8.3 239.5 10.2SR 45 7.2 220.0 10.6010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active