Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,7 23,8 3,9 499,00Remote: 45 28,8 23,8 5,0 499,00Worst Value: Local: 36 27,7 23,8 3,9 499,00Remote: 45 28,8 23,8 5,0 500,00PS-ACRF: Pass Worst Margin: Local: 45 19,6 8,1 11,5 451,00Worst Value: Local: 45 19,5 8,0 11,5 454,00Remote: 45 19,6 8,1 11,5 452,00Remote: 45 19,5 8,1 11,4 453,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:12Signature:______________________ Page: 120Copper Certification ReportCable Label: 521.002-UD-92 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:47:49 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: