Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 27Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Mate 12 / Room summaryMote 12B? PlXNANANANANAy ]L.,Clearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 35.9%, Floor 20.0%, Light loss factor: 0.80EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 4 Perpendicular illuminance (adaptive) [Ix] 502 (= 500) 374 556 0.75 0.67 Surrounding area: 0.500 m 2 Surrounding area 4 Perpendicular illuminance (adaptive) [Ix] 385 (= 300) 220 488 0.57 0.45 3 Background area 4 Perpendicular illuminance (adaptive) [Ix] 240 (= 100) 161 289 0.67 0.56 Wall zone: 0.500 m # Luminaire ®d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 5 iGuzzini illuminazione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 114.3HO plateDALIGeneral LightLED WarmL 1196