Title: +135.01=370.004-OE401T_02-320 Datablad Energimåler UH50.._.pdf
Collection of measured values per e-mail, FTP, http, SMS transparent GSM or TCP ● Configurable report templates for manufacturer-specific reports on values, about the system, etc.Configurable per SMS, http, or Telenet ● Updating applications, firmware and resources via GPRS remote controlNOTICEThe module must be plugged into slot 2.19 CE2N5324en 2018-08-1820 Building TechnologiesM-bus The module has a built-in M-bus master, capable of reading up to another 8 M-bus meters. If the bus is overloaded, communication problems with the connected slaves occur. All connected M-bus devices (slaves) must have a unique M-bus secondary address.Power supply The module (WZU-GPRS) is supplied complete with the required power supply module (rated voltage AC 100…240 V).Communication protocols ● E-mail via SMTP with authentication mode HELO, EHLO ● Passive FTP mode with authentication and change of remote directory ● HTTP POST and GET ● GSM data transparent M-bus @ 300 and 2400 baud and GSM data console TCP