Title: +038=432.001-XQ001._02-NZMN3-4-AE630 Eaton Produktblad.pdf
With XFI earth-fault release: - NZM1, N1, NZM2, N2: vertical and 90° in all directions with plug-in unit - NZM1, N1, NZM2, N2: vertical, 90° right/left with withdrawable unit: - NZM3, N3: vertical, 90° right/left - NZM4, N4: vertical with remote operator: - NZM2, N(S)2, NZM3, N(S)3, NZM4, N(S)4: vertical and 90° in all directionsas requiredIn the operating controls area: IP20 (basic degree of protection)With insulating surround: IP40 With door coupling rotary handle: IP66Tunnel terminal: IP10 Phase isolator and strip terminal: IP00Temperature dependency, Derating63080006000690III/31000≦ 6901871057453408550352520855035135Maximum back-up fuse, if the expected short-circuit currents at the installation location exceed the switching capacity of the circuit-breaker.3.33.3A1500050002 / 10415 V 50/60 Hz690 V 50/60 HzAC--3400 V 50/60 Hz415 V 50/60 Hz690 V 50/60 HzMax. operating frequencyTotal break time at short-circuit