Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
26.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.2 452.0 30.2 36 6.7 462.0 27.2SR 36-45 6.5 476.0 29.7 36 7.2 500.0 26.4MAIN 12-36 8.0 500.0 29.2 36 6.8 500.0 26.4SR 36-45 6.6 500.0 29.2 36 7.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.6 408.0 13.0 45 20.7 491.0 8.4SR 78-45 19.6 397.0 13.3 45 20.2 469.0 8.8MAIN 78-45 20.0 448.0 12.2 45 20.7 491.0 8.4SR 78-45 19.9 447.0 12.2 45 20.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.7 41.0 37.0 36 23.6 41.3 34.4SR 12-36 24.0 44.3 36.0 36 23.8 41.3 34.4MAIN 12-36 34.4 500.0 -12.4 36 33.3 500.0 -15.3SR 36-45 33.0 500.0 -12.4 36 33.7 500.0 -15.30804000250 MHzACR-N (dB)