Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
E2974755Technical specificationConnection key PC1001OUT33 4 3 4OUT1OUT29 1 N C6 N CHLOUT4OUT5AC-NPC10011 N C2 N CV 2 1T E ND N G1 0 DID N G2 0 DID N G3 0 DID N G4 0 DID N G5 0 DID N G6 0 DID N GNr.LabelDescription1OUT1Control signal to compressor relay (230 VAC)2OUT2Control signal to circulation pump (230 VAC)3OUT3Control signal to four way valve (230 VAC)4OUT4Control signal to fan motor (230 VAC)5OUT5Control signal - not used (230 VAC)6AC-NNeutral conductor (230 VAC)7CN1/CN2Power input (12 VAC)8NET/GND/12VDisplay controller9DI01/GNDRemote On/Off switch (digital input)10DI02/GNDFlow switch (digital input)11DI03/GNDLow pressure pressostat signal (digital input)12DI04/GNDHigh pressure pressostat signal (digital input)13DI05/GNDMode input (digital input)14DI06/GNDSensor terminal - not used (digital input)15AI01/GND