Title: økernvn 94.pdf
Cable ID: D3208 Date / Time: 09/12/2013 12:06:40 Headroom 3.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]136 214 14 5.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]18.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.0 136.0 39.7 36 7.2 236.5 33.1SR 12-36 3.7 236.5 35.7 36 2.5 236.5 33.1MAIN 36-78 7.5 246.5 35.4 36 7.2 236.5 33.1SR 12-36 3.7 236.5 35.7 36 2.5 246.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.8 209.5 17.8 12 17.3 3.1 51.3