Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
t : 57.2ms t : 67.8ms t : 28.4ms t : 29.8ms t : >300ms t : >300ms I I: 28.5mA : 28.5mAUc: 0.1V Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE037 06.02.2020 15:12Z-LINEZ: 0.70ΩIsc: 327A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE037 06.02.2020 15:13Zs(rcd)Z: 0.35ΩIsc: 658A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE037 06.02.2020 09:14R LOW OhmR: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE038 06.02.2020 14:48Z-LINEZ: 0.92ΩIsc: 249A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE038 06.02.2020 14:52TEST RAPPORTSide:10GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTMISLYKKESGODKJENTMISLYKKESNr.63636464656566666767ResultatRCD II: 28.5mAUci: 0.2V t: 108.1ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE038 06.02.2020 14:58Z-LINE dUdU: 7.5%