Title: +175=325.001_IK001_FDV luft_vann varmepumpe teknisk rom terapibasseng Manual-P-serien.Produktinformasjon.pdf
Adjusting the bypass Adjusting the bypass can be achieved in a number of ways. One of the easiest ways can be summarized as follows:1. Before adjusting the bypass, first check that the pool’s filter system has been cleaned for maximum flow.2. Open all the valves3. Check the inlet and outlet temperatures, parameters A and B on the display. See Section 3.3. Check the inlet and outlet temperatures, parameters A and B on the display. See Section 3.4.If the difference is above 2 degrees, gradually close the bypass valve until the difference is between 1 and 2 degrees.If the display shows “E03”, this means that the flow through the pool heat pump is too low. The bypass valve must then be closed further in order to increase the flow through the pool heat pump.68First open all the valves to simplify adjustment of the bypass.Electrical installation