Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF030 Date / Time: 27-02-2020 20:23:28 Headroom 7.9 dB (NEXT 12-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]11.5 50 1 2.02Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]35.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.8 444.0 30.4 36 8.7 471.0 26.4SR 12-45 7.9 343.0 32.8 45 8.7 343.0 30.1MAIN 36-45 9.9 496.0 28.0 36 8.9 493.0 25.3SR 36-78 9.2 473.0 29.1 36 9.0 473.0 26.310080604020NEXT (dB)