Title: Temperaturgiver.pdf
Ø 90 6 2 /0 6 2 /2x Ø 3Ø 90 0 2/ 0 5 1 /0 0 2/ 0 5 1 /Ø 8.50 2 10 2 1Ø 9Ø 911Technical SpecificationsPower Supply0...10Vdc 15 Vdc ± 10% 24 Vac ±20% 24 Vdc ±15%K2 NTC Thermistor ---K10NTC Thermistor ---PT100 RTD ---PT1000 RTD ---Output Signal0...10 Vdc2252 ohm @ 25 °C10 kohm @ 25 °C, Johnson Controls Type II100 ohm @ 0 °C, per EN 607511000 ohm @ 0 °C, per EN 60751Output Accuracy± 1% FS or 0.5 °C± 0.2 C° (± 0.36 F°), from 0 to 70 °C± 0.5 C° (± 0.9 F°), from 0 to 70 °CEN 60751, Class A, ± (0.15 + 0.002 * | T °C |)EN 60751, Class A, ± (0.15 + 0.002 * | T °C |)Measurement Current*5 mA Maximum0.1 mA Recommended 1 mA Maximum0.1 mA Recommended 2 mA Maximum1 mA Recommended 5 mA Maximum0.3 mA Recommended 2 mA MaximumMax Operating Temperature for Enclosure w/PWAOperating Temperature -40 to 70 °C (-40 to 158 °F)Storage Temperature -40 to 70 °C (-40 to 158 °F)Transit Temperature -40 to 70 °C (-40 to 158 °F)Humidity