Title: Simployer - Data testrapport =514.204-FS001.pdf
LinkWare™ PC Version 10.4Cable ID: 521.204-UD21 Date / Time: 28/01/2022 10:23:20 Headroom 7.7 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]34.0 175 13 6.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.4 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 8.3 53.0 44.6 4,5 8.9 55.0 41.5SR 1,2-3,6 7.7 196.0 34.9 1,2 8.4 158.5 33.6MAIN 1,2-3,6 9.8 247.5 33.2 3,6 9.7 222.0 31.1SR 1,2-7,8 8.0 244.5 33.3 1,2 8.8 247.0 30.2