Title: 91290FDV Campus F13 433.04 West elektro.pdf
Energies Active energyReactive energyStart-up current: Start-up voltage ResolutionCurrent Voltage PowerFrequency PF Energies (positive)Energies (negative)AV5: Imin=0.25A; In: 5A, Imax: 6A; Un: 230 to 277 VLN (400 to 480 VLL) From 0.04In to 0.2In: ±(0.5%RDG+1DGT) From 0.2In to Imax: ±(0.5%RDG) In the range Un: ±(0.5% RDG) In the range Un: ±(1% RDG) Range: 45 to 65Hz. From 0.05 In to Imax, within Un range, PF=1: ±(1% RDG) From 0.1 In to Imax, within Un range, PF=0.5L or 0.8C: ±(1% RDG) ±[0.001+1%(1.000 - “PF RDG”)] From 0.05 In to Imax, within Un range, sinphì=1: ±(2% RDG) From 0.1 In to Imax, within Un range, sinphì=0.5L or 0.8C: ±(2% RDG)Class 1 according to EN62053-21 and MID Annex MI-003 Class B (Class B (kWh) according to EN50470-3) Class 2 according to EN62053-23 10mA 90VLN Display/serial communication 0.1/0.001 A 0.1/0.1 V 0.01 kW or kvar/ 0.1 W or var 0.1 Hz/0.1Hz 0.01/ 0.001 0.01 kWh or kvarh / 0.1 kWh or kvarh 0.01 kWh or kvarh / 0.1 kWh or kvarhMemory EnergyProgramming parameters