Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 12] [Pair 12] [Pair 12]30.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.7 423.0 30.8 36 9.1 476.0 26.1SR 12-45 10.1 423.0 30.8 36 9.8 456.0 27.1MAIN 36-45 10.4 500.0 27.8 36 9.4 496.0 25.2SR 36-78 10.9 500.0 27.8 36 10.5 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.9 3.8 53.8 45 13.7 2.3 55.2SR 45-78 14.9 4.0 53.2 45 13.6 2.3 55.2MAIN 78-45 15.7 499.0 11.3 45 17.0 500.0 8.3SR 45-78 15.9 499.0 11.3 45 17.1 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 25.0 78.8 28.0 45 25.1 82.8 24.7SR 36-45 22.9 82.5 27.3 36 24.5 82.8 24.7MAIN 36-45 39.8 500.0 -12.4 36 38.9 496.0 -15.0SR 36-78 40.5 500.0 -12.4 36 40.1 500.0 -15.30804000250 MHz