Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 36] [Pair 36] [Pair 45]15.0 66 2 2.41Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.7 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.3 339.0 32.9 36 6.8 474.0 26.2SR 36-45 6.1 466.0 29.5 36 6.6 453.0 27.3MAIN 36-78 8.3 499.0 27.9 36 7.6 498.0 25.1SR 36-45 6.2 467.0 29.4 36 7.7 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.9 472.0 11.8 45 14.2 2.3 55.2SR 36-45 13.8 472.0 11.8 45 14.3 3.4 51.7MAIN 45-36 14.0 474.0 11.7 36 16.5 474.0 8.7SR 36-45 14.0 479.0 11.6 45 16.4 472.0 8.80100806040200250 MHzACR-F (dB)