Title: 2 etg del2.pdf
Cable ID: D2058 Date / Time: 10/10/2013 10:49:27 AM Headroom 13.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]303 479 33 13.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 88.5 33.2 36 16.0 91.8 29.9SR 12-36 13.8 84.3 33.5 36 15.3 99.3 29.4MAIN 12-36 14.5 99.5 32.3 36 16.2 99.5 29.3SR 12-36 14.2 99.5 32.3 36 15.3 99.5 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.1 44.8 25.6 36 17.9 44.8 22.6