Title: V20-01-01 VVS-anlegg plan 1 - DM1 (V20--011)-1.pdf
Reguleringsventil STAD370.101: 28 mm UK = 3292SK001T - 250 500 m³/hDifferansetrykkregulator STAPOppadvente stusser med stoppeventiler og luftepotter+01 = 320.102 - SB 506 0.109 L/s 0.109 L/s +01 = 370.101 - SB 505 0.220 L/s 0.220 L/sStengeventilDN 32= 360.002 - LD009T 220 m³/h Kjøling: 625 W 0.055 L/s Varme: 1145 W 0.027 L/sXMotorventilLD009T 220 m³/h Kjøling: 500 W 0.055 L/s Varme: 1145 W 0.027 L/sKjøkkenhette 2 -1100 m3/h +450 m3/hEndelokkDN 32DN 32+01 = 310.102 - RF 402DN 32B1-B 310.302: Cu 18 UK = 3601LD009T 220 m³/h Kjøling: 500 W 0.055 L/s Varme: 1145 W 0.027 L/sø315 UK=3242320.102: 28 mm UK = 3601310.202: Cu 28 UK = 3596320.102: 28 mm UK = 3601310.102: Cu 28 UK = 3596370.101: 35 mm UK = 3597DN 65370.101: 35 mm UK = 3593X310.302: Cu 18 UK = 3641 310.202: Cu 28 UK = 3636 310.102: Cu 28 UK = 3636ST007T-200-250 200 m³/hEksist. spillvannopplegg28.09.2020 11:21:06SOM BYGGETVANNMÅLERINSTALLASJONVI-G880 m³/h1100 m³/h