Title: 360.001 - Tilluft.pdf
MAGID-C1-315ESU-315MAGIO-RC-*MAGID-C1-400Size315315/315315315315315315315400400L [m]2,20,10,20,13,827qv [m³/h]30030030030016501650v [m/s]1,11,11,11,13,63,6dpt [Pa]0,1 Sound in:Attenuation: Addition:0,8 Sound in:Attenuation: Addition:Dividing:0,0 Sound in:Attenuation: Addition:9,4 Sound in:Attenuation: Addition:Total Lw:Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:5,7 Sound in:1,5 Sound in:Attenuation: Addition:63 [dB]36.50.2 +0.036.30.0 +0.03.033.30.0 +0.033.312.0 +0.021.333.30.0 +0.039.60.0 +0.037.737.70.3 +24.3125 [dB]31.10.2 +0.030.80.0 +0.03.027.80.0 +0.027.87.0 +0.020.927.80.0 +0.034.20.0 +0.032.332.30.3 +23.3250 [dB]23.40.2 +0.023.20.6 +0.03.019.70.0 +0.019.76.0 +0.013.920.30.0 +0.027.10.0 +0.028.828.80.3 +22.2500 [dB]19.10.4 +0.018.81.2 +0.03.014.60.0 +0.0