Title: +038=360.000-OU045T_05-PCD2.m4160 PLS SBC - User Manual.pdf
26-733Ethernet-TCP/IP26-776RS-485 networks / components26-740Serial interface module PCD7.F1xxx27-664I/O based interface module PCD2.F2xxx27-649User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-2112-1013Dimensions2 5S2X 8B S U2 0X9X2X1E T H 1X7X3E T H 2X6Run1 9HaltError3 1 2I/O BUSX5BATM11 09S1 OX4CSupply 24VPCD2.M4_014270User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-2113-1PCD2.M4160 | PCD2.M456014MountingThere are 2 different types of installation:mounted with screwssnapped on 2 DIN railsUser Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-2114-1Mounting with screws14.1Mounting with screwsScrew diameter:less than Ø 4.9Screw head diameter:less than Ø 8.0125 mmm m 0 0 2User Manual PCD2.M4x60 │ Document 27-648 │ Edition ENG06 │ 2020-10-2114-2Mounting with screws14.1.1Mounting the PCD2.M4x60 and PCD2.C1000: