Title: 40 Bender brukermanual.pdf.pdf
Setting range 10…20 mA 25…50 mA 60…200 mA 250…500 mA 600 mA… 2 A 2.5 A…5 A 6 A…10 AResolution of setting 1 mA 5 mA 10 mA 50 mA 100 mA 0.5 A 1.0 AResolution of settings type A(pulsating current sensitive measuring current transformers):Setting range 6…20 mA 25…50 mA 60…200 mA 250…500 mA 600 mA… 2 A 2.5 A…5 A 6 A…20 AResolution of setting 1 mA 5 mA 10 mA 50 mA 100 mA 0.5 A 1.0 A62RCMS460-490_D00067_03_M_XXEN/12.2017Resolution of settings type A (RCMS…-D4/-L4 only, channels k9…k12):Setting range 100…200 mA 250…500 mA 600 mA… 2 A 2.5 A…5 A 6 A…20 A 25 A…50 A 60 A…125 AResolution of setting 10 mA 50 mA 100 mA 0.5 A 1.0 A 5.0 A 10.0 AResolution of settings type Flex.: the same as for type A