Title: etg u1.pdf
2500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 8.1Cable ID: D0079 Date / Time: 10/21/2013 03:02:06 PM Headroom 13.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]122 193 13 5.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.5 100.0 32.3 36 15.3 99.3 29.4SR 45-78 19.7 78.5 34.0 45 20.3 98.5 29.4MAIN 12-36 13.5 100.0 32.3 36 15.3 99.3 29.4SR 45-78 20.2 91.8 32.9 45 20.3 98.5 29.410080604020NEXT (dB)