Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
2 wire shielded cable Twisted 5/10cm Total maximum capacity 0.5uF Maximum length 2000m Maximum resistance (considering the sum of the positive and negative conductor) 40OhmTotal loop lengthUp to 1000mWire section2 x 1 mm²American Wire Gauge17 AWGIt is necessary to consult the configuration software, Previdia/STUDIO, for the proper cable sizing in relation to the power consumption of the connected devices, or to the following table for a rough estimate:Up to 1500m 2 x 1.5 mm²Up to 2000m2 x 2 mm²16 AWG14 AWGThe cable shield must be connected to the grounding bar at one end only.For the connections of the various devices refer to the instructions supplied with the devices themselves.