Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.59596060TEST RAPPORTResultat SPENNING TRMS Uln: 232V Ulpe: 232V Unpe: 1V f: 49.93HzSYS.: TN/TTZ-LINEZ: 0.31ΩIsc: 741A R: 0.31Ω Xl: 0.00Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.0V t: 253.4ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 520V Rnpe: >30.0MΩ Um: 515VUiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF031 C16/2/003 / Mal 2 10.03.2022 14:31 (TomekElektriker)KONTINUITET: R200mA LPER: 0.04ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF031 C16/2/003 / Mal 3 10.03.2022 12:21 (TomekElektriker)SPENNING TRMS Uln: 232V Ulpe: 232V Unpe: 1V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.32ΩIsc: 723A R: 0.32Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0A