Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Galvanic separation:noResolution (digital representation):10 bit (0 … 1023)Measuring principle:non-differential, single-endedInput resistance:0 … 10 V: 0 … 20 mA: Pt/Ni 1000: NTC 10:80 kΩ / 0.15 % 125 Ω / 0,1 % 7,5 kΩ / 0,1 % 10 kΩ / 0,1 %Maximum measurement current for resistance measurement with W220: Accuracy: (of measured value) Repeating accuracy (under same conditions): Temperature error:1.5 mA± 3 LSBwithin 1 LSB± 0,3 % ( ± 3 LSB)(over a temperature range from 0° … +55 °C)Conversion time A/D:<50 µsOvervoltage protection:W200/220:± 50 VDCOvercurrent protection:W210:±40 mABurst protection: (IEC 1000-4-4) Time constant of input filter:± 1 kV, with unshielded cables ± 2 kV, with shielded cables W200: typically 5 ms W210: typically 1 ms W220 : typically 10 msInternal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption:8 mA (W200/210/220)5 mA (W200/210) 16 mA (W220) 0 mATerminals: