Title: FDV-DOKUMENTASJON.pdf
ENZapCharger Pro is an alternating current wall- or column-mounted charging station in accordance with IEC 61851-1, EVSE mode 3. Dimensions and weightH: 392 mm, W: 258 mm, D: 112 mmWeight: approximately 5 kg (including backplate)Installation network TN, IT and TTInstallation circuitMax 63A connected fuse on installation circuit for charging stations.Connection boxCable cross section 2.5-10 mm2Installation network, voltages230VAC ±10%400VAC ±10%Max charging current and power7.36 kW* at 32A single phase22 kW* at 32A three phase (applies only to TN networks)Fuses Built-in 3 x 40A type C fusesCharging socket IEC 62196-2 Type 2 FemaleEarth fault protectionRCD type BSoft startLimits the inrush current at the start of charging.eMeterIntegrated in the charging station with an accuracy of +/-1 % on current and voltage. This enables the user to check the actual power usage. In an installation, the consumption report can be used to distribute the cost based on use.Theft protectionThe front cover of the ZapCharger Pro