Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 78-45 17.8 5.0 51.3 45 17.6 3.8 50.8MAIN 78-45 18.1 498.0 11.3 78 19.2 500.0 8.3SR 78-45 18.0 498.0 11.3 45 19.2 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 27.3 122.0 20.9 12 28.9 122.0 18.3SR 12-45 27.0 123.0 20.7 45 27.8 91.0 23.2MAIN 36-45 39.1 496.0 -12.1 36 39.3 500.0 -15.3SR 36-45 36.8 496.0 -12.1 36 37.5 496.0 -15.00804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.9 461.0 8.0SR 12 6.3 437.0 8.0MAIN 45 6.9 461.0 8.0SR 12 6.3 437.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS