Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 35,8 68,0 186,0 10,0 6,4Limit 100,0 - 555,0 50,0 25,0Margin 64,2 - 369,0 40,0 18,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 2,05Worst Value: Local: 36 15,7 43,5 27,8 496,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 19,8 12,8 7,0 132,50Remote: 12 15,6 10,5 5,1 225,50Worst Value: Local: 36 16,8 8,0 8,8 484,00Remote: 12 14,2 8,0 6,2 451,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,8 26,7 2,1 497,00Remote: 36-45 29,1 26,8 2,3 496,00Worst Value: Local: 36-45 28,8 26,7 2,1 497,00Remote: 36-45 29,1 26,8 2,3 496,00dB 0601200Local250500 MHzdB 0