Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
SR 45-12 18.9 499.0 11.3 45 18.5 490.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.5 34.3 39.2 36 17.7 34.5 36.7SR 36-45 17.1 34.5 39.1 36 18.8 34.5 36.7MAIN 12-36 33.0 499.0 -12.3 36 33.5 500.0 -15.3SR 12-36 32.1 499.0 -12.3 36 31.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.5 426.0 8.0SR 45 6.1 480.0 8.0MAIN 45 8.5 426.0 8.0SR 45 6.1 480.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: MCKINSEY 4 ETGMcKinsey 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00437.2 m60Insertion Loss (dB)504030201000250 MHz