Title: 10 FR Brannplate - Montasjeanvisning.pdf
≤ Ø 110mm PVC-U & PVC-C ≤ Ø 50mm PVC-U & PVC-C ≤ Ø 110mm PVC-U & PVC-C ≤ Ø 160mm PVC-U & PVC-C ≤ Ø 110mm PE, ABS & SAN+PVC ≤ Ø 50mm PE, ABS & SAN+PVC ≤ Ø 110mm PE, ABS & SAN+PVC ≤ Ø 160mm PE, ABS & SAN+PVC ≤ Ø 90mm PP ≤ Ø 110mm PP ≤ Ø 160mm PPRørveggtykkelse Min. Mansjett høyde Klassifisering 30mm 1.9 – 6.6mm 50mm 1.9 – 3.7mm 50mm 2.1 – 6.6mm 60mm 3.1 – 9.5mm 30mm 3.4 – 10.0mm 50mm 3.0 – 4.6mm 50mm 3.0 – 10.0mm 60mm 3.9 – 9.5mm 50mm 1.8 – 4.6mm 50mm 2.7mm 60mm 3.4 – 9.1mmEI 30 U/C (E 90 U/C) EI 60 U/C (E 120 U/C) EI 60 U/C (E 90 U/C) EI 60 C/C (E 60 C/C) EI 45 U/C (E 60 U/C) EI 60 U/C (E 120 U/C) EI 60 C/C (E 90 C/C) EI 60 C/C (E 60 C/C) EI 60 C/C (E 60 C/C) EI 60 C/C (E 60 C/C) EI 60 C/C (E 60 C/C)1 lag 50mm FR Brannplate 2-SProtecta FR Rørmansjett skrud med 50mm spiral- skruerPLASTRØR BRANNMOTSTAND EI 120-240Maks utsparing ubegrenset bredde med 1200mm høydePlastrør2 lag 60mm FR Brannplate 2-SProtecta Rørstruper på begge sider