Title: +038=433.002-FS031._02-Eaton Tavlebyggeren Produktblad.pdf
Rated short-circuit breaking capacity lcu at 400 V, 50 HzkA25Overload release current settingA40 - 50Adjustment range short-term delayed short-circuit releaseA0 - 0Adjustment range undelayed short-circuit releaseA6 - 10Integrated earth fault protectionNoType of electrical connection of main circuitFrame clampDevice constructionBuilt-in device ﬁxed built-in techniqueSuitable for DIN rail (top hat rail) mountingNoDIN rail (top hat rail) mounting optionalYesNumber of auxiliary contacts as normally closed contact0Number of auxiliary contacts as normally open contact0Number of auxiliary contacts as change-over contact0With switched-oﬀ indicatorNoWith under voltage releaseNoNumber of poles4Position of connection for main current circuitFront sideType of control elementRocker leverComplete device with protection unitYesMotor drive integratedNoMotor drive optionalNoDegree of protection (IP)IP2006/21/2019