Title: +038=360.012-#####._06-BA-ESR NI-DV Controller Nicotra Gebhardt - Operating Instruction.pdf
Alarms are either ”Critical” alarms or ”Non-critical” alarms. • ”Critical” alarms stop the motor. • ”Non-critical” alarms reduce motor performance. o The built-in alarm monitor stops the NI-DV. o If the alarm situation passes, the alarm is automatically reset and NI-DV restarted. o If the maximum number of restarts (5 times/60 min) is exceeded,Alarms are either ”Critical” alarms or ”Non-critical” alarms. • ”Critical” alarms stop the motor. • ”Non-critical” alarms reduce motor performance. o The built-in alarm monitor stops the NI-DV. o If the alarm situation passes, the alarm is automatically reset and NI-DV restarted. o If the maximum number of restarts (5 times/60 min) is exceeded,the alarm must be reset manually.o The alarm can be reset by means of a Modbus command. o The alarm is automatically reset if the power is disconnected forlonger than 60 seconds.o Alarms can be read via Modbus, see Modbus protocol. o Alarm overview, see 5-1.Alarm overviewAlarm priority Motor operation/response