Title: Data tester Smestad skole - Detaljert.pdf
Remote: 45 28,1 23,8 4,3 499,00Worst Value: Local: 36 28,1 23,8 4,3 500,00Remote: 45 28,1 23,8 4,3 499,00PS-ACRF: Pass Worst Margin: Local: 12 71,8 61,2 10,6 1,00Worst Value: Local: 36 19,4 7,2 12,2 500,00Remote: 45 71,1 61,2 9,9 1,00Remote: 45 18,4 7,9 10,5 461,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:57Signature:______________________ Page: 20Copper Certification ReportCable Label: 521.002-UD-017 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 14:07:48 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4