Title: Simployer - Data testrapport =514.204-FS001.pdf
Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]45.3 233 17 8.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]22.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 8.8 58.5 43.9 3,6 10.3 58.5 41.1SR 1,2-3,6 8.1 176.0 35.7 1,2 10.0 176.0 32.8MAIN 1,2-3,6 9.8 228.0 33.8 3,6 10.6 228.0 30.9SR 1,2-3,6 9.9 227.5 33.8 3,6 11.6 232.0 30.7PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 18.0 151.0 19.7 4,5 18.5 161.5 16.1SR 7,8-4,5 18.0 154.5 19.5 4,5 18.9 166.0 15.9MAIN 1,2-4,5 20.3 248.0 15.4 4,5 21.4 248.0 12.4