Title: økernvn 94.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.4 18.0 46.3 36 10.2 17.9 44.0SR 12-36 8.8 17.9 46.3 12 10.5 17.9 44.0MAIN 36-45 16.0 246.5 5.0 36 15.5 248.0 2.2SR 36-45 16.2 248.5 4.8 36 15.6 246.0 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.5 14.1 20.3SR 45 3.2 14.1 20.3MAIN 45 6.5 147.0 12.3SR 36 5.6 230.5 10.4010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4