Title: Hardware Installation Guide.pdf
98.1WiringThe reader has an RJ-45 modular jack for easy field connection. A small piece of pre-terminated cable is supplied with each standard reader for field wiring. The pre-terminated cable has non-standard color. Refer to pin number if the pre-terminated cable is not used. Cable with wires of 24 AWG or larger, 6 conductor (Belden 9536 or equivalent) are recommended for field wiring.98.2Mounting the ReaderFind a suitable location to anchor the reader mounting bracket. The reader may be mounted vertically or horizontally. See recommended orientation. The mounting of the reader does not require a junction box. However, rigid conduit is required for outdoor application. A single gang junction box may used to provide transition to rigid conduit. If a single gang junction box is used, a wall plate (optional) may be used to cover the junction box. The reader is then secured to the mounting bracket using a screw. Refer to figures for reader dimensions and typical junction box usage.Recommended