Title: 1 etg del 2.pdf
Cable ID: D1028 Date / Time: 10/17/2013 11:49:07 AM Headroom 10.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]90 142 10 3.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.0 98.8 32.4 36 13.5 98.8 29.4SR 12-36 10.9 98.8 32.4 36 13.3 98.8 29.4MAIN 12-36 11.0 98.8 32.4 36 13.5 98.8 29.4SR 12-36 10.9 98.8 32.4 36 13.3 98.8 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 26.3 7.9 40.7 45 25.9 4.3 43.0