Title: økernvn 94.pdf
MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3199 Date / Time: 09/11/2013 03:15:54 Headroom 4.5 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]189 288 9 8.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]13.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 4.5 247.5 35.4 36 5.5 247.5 32.8SR 12-36 4.5 230.0 35.9 36 3.8 236.5 33.1MAIN 36-78 4.5 247.5 35.4 36 5.5 247.5 32.8SR 36-45 4.7 249.0 35.4 36 3.8 236.5 33.110080