Title: økernvn 94.pdf
200250MHzLinkWare Version 7.4Cable ID: D4169 Date / Time: 09/09/2013 02:08:37 Headroom 5.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]217 333 14 10.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]10.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.7 220.5 36.2 36 9.1 220.5 33.6SR 36-78 5.1 250.0 35.3 36 6.3 250.0 32.7MAIN 12-36 7.7 220.5 36.2 36 9.1 220.5 33.6SR 36-78 5.1 250.0 35.3 36 6.3 250.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)