Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]13.6 58 0 2.29Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]34.3 497.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.4 494.0 28.1 12 8.8 459.0 27.0SR 12-36 5.7 477.0 28.9 36 6.3 479.0 26.0MAIN 12-36 8.4 494.0 28.1 36 9.1 497.0 25.1SR 12-36 6.3 495.0 28.1 36 7.0 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.8 6.5 49.0 78 22.0 5.9 46.9SR 78-45 19.8 6.5 49.0 45 22.1 7.6 44.6MAIN 36-12 23.1 479.0 11.6 36 23.9 486.0 8.5SR 12-36 23.0 479.0 11.6 36 23.7 500.0 8.30100806040200250 MHzACR-F (dB)