Title: 40 Bender brukermanual.pdf.pdf
2. Use the Up/Down buttons to select a relay (1, 2) or both relays (1…2). Press "↵" to confirm your selection.Set a single relay:Relay: 1 Exit 1.Mode of opera- tion:N/OSet both relays:Relay: 1..2 Exit 1.Op.mode 2.Alarm: --RCMS460-490_D00067_03_M_XXEN/12.2017Operation1. Relay mode Set the relay mode of operation:N/O N/C N/O-TN/O operation. Relay only switches in the event of an alarm. N/C operation. Relay only switches in the event of an alarm. N/O operation. Relay switches when there is an alarm or a test. N/C operation. Relay switches when there is an alarm or a test. Contacts of the relay are always open*. Contacts of the relay are always closed*.N/C-Toff on * This function can also be activated via the BMS bus. By sending the command "off" or "on" via the BMS bus, the switching of the relay can be activated. This relay does not respond to alarms. It only serves as a signal converter (BMS-bus signals/ relay contact signal.2. Alarm on off