Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]29.2 127 2 4.38Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]28.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.0 488.0 29.5 36 9.6 483.0 25.8SR 36-45 8.4 500.0 29.2 36 8.5 465.0 26.7MAIN 36-45 9.0 488.0 29.5 36 9.8 495.0 25.2SR 36-45 8.4 500.0 29.2 36 8.7 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.3 3.5 54.4 45 13.3 2.3 55.2SR 36-45 14.2 3.5 54.4 45 13.3 2.1 55.7MAIN 78-45 16.0 498.0 11.3 45 16.5 494.0 8.4