Title: V20-06-02 VVS-anlegg plan 6 - DM3.pdf
WISE RTA WISE IAQLD021T Maks:220 m³/h Kjøling: 470 W 0.037 L/sLD021T Maks:220 m³/h Kjøling: 470 W 0.037 L/s28 mm +c 2703WISE RTALD009T Maks:200 m³/h Kjøling: 480 W 0.038 L/sFleksibelt areal 6-1300 9 7 20 9 7 2c + m m 8 2 : 1 0 1 . 0 7 3c + m m 8 2 : 1 0 1 . 0 7 30 3 7 2c + m m 5 1 : 2 0 1 . 0 2 30 3 7 2c + m m 5 1 : 2 0 1 . 0 2 3WISE IAQ370.101: 42 mm +c 2790ø160 UK=2670ø160 UK=2670Åpent landskap-3 6-123-3370.101: 42 mm +c 2680 370.101: 42 mm +c 2680320.102: 18 mm +c 2680320.102: 18 mm +c 2680370.101: 42 mm +c 279054 mm54 mm22mm320.102: 18 mm +c 2790320.102: 18 mm +c 2790ø200 UK=2650 ø200 UK=2650ø200 UK=2650 ø200 UK=2650LD007T Maks:200 m³/h Kjøling: 480 W 0.038 L/s Varme: 410 W 0.010 L/s+06 = 370.101 - OE 065 0.541 L/sLD007T Maks:200 m³/h Kjøling: 480 W 0.038 L/s Varme: 410 W 0.010 L/sSTAP/STAD DN40Opp/ned 370.101: DN 100mm 370.101: DN 100mmLD018T Maks:220 m³/h Kjøling: 470 W 0.037 L/s Varme: 515 W 0.012 L/s