Title: Våtventil Brukermanual.pdf
The Victaulic Series 752 VdS Retarding Chamber Assembly should be installed in variable pressure applications . NOTE: Victaulic pro- vides specific trim drawings for installations that involve a Series 752 VdS Retarding Chamber Assembly .CAUTIONMake sure no foreign material gets into the valve body, pipe nipples, or valve openings.Make sure no foreign material gets into the valve body, pipe nipples, or valve openings.If using any material other than PTFE thread sealant tape, use extra caution so that no material gets into the trim.If using any material other than PTFE thread sealant tape, use extra caution so that no material gets into the trim.Failure to follow these instructions could cause improper valve operation, resulting in personal injury and/or property damage.Optional Series 760 European Water Motor Alarm Assembly4 .Install the valve, trim, and accessories per the trim drawing .Optional Alarm Pressure Switch