Title: 40 Bender brukermanual.pdf.pdf
2:RCMS460-L Exit 1.Alarm/meas.values 2.% Bar graphRCMS460-490_D00067_03_M_XXEN/12.201777OperationThe following menu items are displayed for the RCMS…-L:Menu itemFunctionPageExitExit menu mode1.Alarm/ meas.valuesDisplays the following for each measuring chan- nel, if applicable: prewarning, alarm, measured value, digital input status, response value, chan- nel disabled, CT connection fault.492.% Bar graph For each of the 12 measuring channels, the49reached per cent value of the set alarm value IΔn2 (alarm) and IΔn1 (prewarning) is indicated. In case of digital inputs, the status is indicated.3.HarmonicsDisplays the following for the selected measuring channel: Measured value, THF (Total Harmonic Factor), DC component, fundamental component and harmonics in mA.514.SettingsSettings for this RCMS… are made here.535.ControlThis menu offers various control options, such as TEST, RESET, TEST COMMUNICATION.746.Info