Title: +038=453.004-LZ001._03-Installasjonsveiledning Varmematter Devi.pdf
The subfloor construction must be secure to avoid relative movement after installation.Prepare the installation site properly by removing sharp objects, dirt, etc.Prepare the installation site properly by removing sharp objects, dirt, etc.If walking on the elements is necessary during installation and carefully purring of screed, only use soft shoes.Do not place objects that will cause a thermal block e.g. furniture, thick carpets, etc. Min. 6 cm air space is required. • The flooring must not have a thermalDo not place objects that will cause a thermal block e.g. furniture, thick carpets, etc. Min. 6 cm air space is required. • The flooring must not have a thermalinsulation value of more than R < 0.18 m2K/W corresponding to 1.8 Tog. • Keep thin mats clear of insulation material, other heating sources and expansion joints.Position the thin mat so that it is at least half the C-C distance from obstacles.In case of a wooden subfloor, the maxi- mum installed output is 100 W/m².