Title: 4. Leieavtaler.pdf
Design Density: HC-2 - 8 mm/min over 230 m2 (wet type system) Sprinkler Head Type: FM Approved (Standard Coverage, Quick or Standard Response, Kl 15, 70°C) Or Extended Coverage, FM Approved (Quick Response, upright or pendent, Kl60EC, 70°C) Sprinkler Linear Spacing: 2.1 - 4.5 m for standard coverage. 3.0- 6.0 m for extended coverage. Sprinkler Area Spacing: 6.5 - 21.0 m2 for standard coverage. 9.0 - 36.0 m2 for extended coverage. Hose Demand: 950 L/min Water Duration 60 minutes.2015-01-07: As the storage and production areas are planned to be in the same area with no subdivisions the best solution with maximum flexibility is to design the sprinkler system for a ceiling only storage protection system in accordance with FM Global Property Loss Prevention Data Sheet 8-9, Storage of Class 1,2,3,4 and Plastic Commodities and item 'e' of this letter.c. Clean Rooms:FM Global Property Loss Prevention Data Sheet 1-56, Cleanrooms.