Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 36]14.0 61 1 2.22Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]34.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.1 407.0 31.2 36 5.9 458.0 27.0SR 36-45 7.1 468.0 29.4 36 7.8 467.0 26.6MAIN 36-78 8.4 500.0 27.8 36 6.8 500.0 25.0SR 36-45 7.9 493.0 28.2 36 8.1 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.5 6.5 49.0 45 20.7 6.5 46.0SR 45-78 18.5 6.5 49.0 45 20.7 4.9 48.5MAIN 36-12 19.5 410.0 13.0 36 23.7 500.0 8.3SR 12-36 19.4 410.0 13.0 36 21.8 409.0 10.00100806040200250 MHzACR-F (dB)