Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 58,5 68,0 304,0 17,0 9,8Limit 100,0 - 555,0 50,0 25,0Margin 41,5 - 251,0 33,0 15,2Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,2 3,1 1,9 3,10Worst Value: Local: 45 24,6 43,8 19,2 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 16,4 13,1 3,3 123,00Remote: 12 14,8 8,6 6,2 350,00Worst Value: Local: 12 14,8 10,2 4,6 241,00Remote: 12 14,6 8,0 6,6 421,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):