Title: 360.013 Hybra Modul A 8,00-2,0 +- 22.800 m³h -Datakjøring Fra leverandør.pdf
220-55 / Default (IE5) / IP55 2 x 4,300 10,00 1.700 3x400 / 50Plug fan Volume flow operating mode Designation Number of width and height Pressure loss external / static (Pa) Pressure loss total / dynamic (Pa) Shaft output / performance class Sound p. suction / pressure dB(A) Efficiency total / static (%) System-efficiency total / static (%) System p. consumption V/E (kW) Speed (U/min) / C-factor Differential pressure (dp at Vn) Operating frequency Maximum frequency Motor Size / Number of terminals Energy class / Protection item x Nominal output (kW) Rated current (A) Nominal speed (U/min) Voltage (V) / Frequency (Hz) revision door with dual hinge22.800 m³/h parallel RLM E0-BE 560 2 x 1 300 / 673 731 / 58 2,920 kW / P1 79,8 / 84,6 79,0 / 73,0 71,2 / 65,6 5,910 / 6,500 1.670 / 242 1.331 Pa 143 Hz 150 Hz220-55 / 4 (IE5) / IP55 2 x 4,300 10,00 1.700 3x400 / 50Inspection window Diameter190 mmHeat wheel Condensation ST1-XL-WV-2375-CS-V1-A1-0,W2477,H2477