Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
2 4,6 2,8 3,63 5,4 3,4 4,21 3,8 2,4 3,02 5,1 3,1 4,03 5,8 3,6 4,6NOTE: On heating it must be payed attention to rooms where the floor temperature is particularly low (for example less than 5°C). In this situation the floor can cool the lower layer of air to a level that stop the uniform diffusion of the hot air coming from the unit, decreasing the throw figures shown in the table.12Fresh air supply - Fresh air connectionSkyStarThe cassette is fitted with inlets for fresh air to be mixed with return air inside the unit (Fig. 3).FRESH AIR INLETThe fresh air flow is limited to 20% of the total fan coil air flow at medium speed and 100 m3/h for each treated air inlet.The units feature fresh air inlets on three corners (no inlets on the fourth corner because of the condensate pump inside the unit).AIR INTAKEFresh air connectionThe fresh air inlets are designed for the insertion of standard 110 x 55 mm rectangular ducts.