Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Overvoltage protection (W100) Overcurrent protection (W105) Burst protection capacitive coupling (IEC 801-4)see module overview no 12 bits (0 … 4095) differential ≤ 30 µs W100: >10 MΩ W100: ± 0.1 % W100: ± 0.05 % W105: ± 0.2 % ± 1 LSB W100: ± 11 V > 70 dB W100: ± 0.2 % + ± 2 LSB W105: ± 0.3 % + ± 2 LSB ± 60 VDC (permanent) ± 50 mA (permanent) ± 1 kV, with unshielded cables ± 2 kV, with shielded cablesW105: 100 Ω/0.1 % + ± 1 LSB bipolar + ± 1 LSB unipolar + ± 1 LSB unip/bip.W105: ± 8 VTime constant of input filter Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Terminals:3 ms 45 mA typ. 20 mA 15 mA0 mA Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²5-53PCD2.W10xTerminalsBus connector Bus interface +/- 15 VDifferential amplifierA/D converter Analogue multiplexer1 W SU BJumper U: unipolar B: bipolarInput filter9876543210Screw terminalsGroundE3+ Input 3