Title: +038=433.002-FS031._02-Eaton Tavlebyggeren Produktblad.pdf
Terminal capacities2 mm2 mm1 x 252 mm2 x 10Thickness of busbar materialmm0.8 … 2Mounting positionAs requiredDesign veriﬁcation as per IEC/EN 61439 Technical data for design veriﬁcationRated operational current for speciﬁed heat dissipationInA25Heat dissipation per pole, current-dependentPvidW0Equipment heat dissipation, current-dependentPvidW12Static heat dissipation, non-current-dependentPvsW003/07/2019Eaton 279063 ED2019 V53.0 EN1 / 8Heat dissipation capacityPdissW0Operating ambient temperature min.°C40Operating ambient temperature max.°C75linear, per +1 °C, results in a 0.5% reduction of current carrying capacityIEC/EN 61439 design veriﬁcation10.2 Strength of materials and parts10.2.2 Corrosion resistanceMeets the product standard's requirements.10.2.3.1 Veriﬁcation of thermal stability of enclosuresMeets the product standard's requirements.