Title: +038=360.000-LC007T_06-Coadis line 600 Fan-coil CIAT - Teknisk beskrivelse.pdf
0m 20 19 18 17 of the condensate drains). 2m 14 13,5 Condensate flow rate (I/h) = Total P - Sensible P (W) 4m 15 1 10,5 10 680 6m 8,5 75 6,5 I T T10m A I S Y 25Electrical heaters2 single tube 230/1/50 electrical elements inserted into the aluminium housing and bent around the hydraulic coil.Removal of shunt to deactivate a heater@ Temperature limiter with manual reset N (reduction of 300 W)Temperature limiter with automatic resetHEAT PUMPSAIR CONDITIONINGREFRIGERATIONAIR HANDLINGHEAT EXCHANGENA 14696 A 13pp— =>» Comfort unitsCIATCoanda effect cassetteCOADIS LINE 600Operating speed selectionu Asynchronous motor All speeds are connected and wired to the terminal.s PE|PEspeed+ speed3456The customer must cable the speeds for the thermostat at the top of the terminal block between V1 and V5.= HEE motorOperating speed selection:With 010 V control, adjustment via the controllerWith 3