Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.2 144 2 4.91Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]26.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.1 494.0 29.4 36 8.8 493.0 26.5SR 12-45 9.1 499.0 29.3 36 9.2 499.0 26.4MAIN 36-45 9.1 494.0 29.4 36 8.9 500.0 26.4SR 12-45 9.1 499.0 29.3 36 9.2 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.6 500.0 11.3 45 14.0 2.5 54.3SR 78-45 15.4 498.0 11.3 45 14.0 2.6 53.9MAIN 78-45 15.6 500.0 11.3 45 16.3 498.0 8.3