Title: +135.01=370.003-OE401T_02-320 Datablad Energimåler UH50.._.pdf
– From 5 ms to 100 ms in increments of 5 msA suitable device can be used to receive and evaluate the pulses. Enter the settings in accordance with the controller’s data sheet. Linear pulses are outputted proportionally to the measured value. In the case of scaled pulses, the number of pulses at the upper and lower end of the range can be defined. In this case, the pulse receiving device can detect a wiring error, for example.Pulses nPulsesnmaxnmin0q Flow rate012%100% Flow rateLinear pulsesScaled pulsesDisplay on LCDCE, C2, CV, CT or RIConnection of outputs (standard version):CE2N5324en 2018-08-18Building TechnologiesCL module WZU-CLFunction description The CL module (WZU-CL) can be used to set up a point-to-point link, enabling the meter to be read from a remote location (e.g. from the front door).NOTICEThe CL module can be plugged into either of the 2 slots. The meter can accommodate only 1 CL module.