Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The energy consumption quantities do not take into account light scenes and their dimming levels.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 23Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N l S ’ < Site 1/ Building 1/ Storey 10/ Kontor 5 / ViewsKontor 5Kontor 5DIALux Page 24Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Kontor 5 / Results summary, EN 12464/ENTSKKontor 5 el il i< ———| EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 3 Perpendicular illuminance (adaptive) [Ix] 578 (= 500) 395 669 0.68 0.59 Surrounding area: 0.500 m 2 Surrounding area 3 Perpendicular illuminance (adaptive) [Ix] 422 (= 300) 290 535 0.69 0.54 3 Background area 3 Perpendicular illuminance (adaptive) [Ix] 235 (= 100) 121 350 0.51 0.35Wall zone: 0.500 m