Title: 2 etg del2.pdf
SR 45-36 11.5 57.0 29.1 36 14.0 55.8 26.3MAIN 36-45 15.0 234.5 16.8 45 17.8 250.0 13.2SR 45-36 15.1 236.5 16.7 36 16.7 213.0 14.6010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.0 13.9 49.0 36 10.2 13.8 46.7SR 12-36 8.4 13.9 49.0 12 10.3 13.9 46.6MAIN 36-45 10.8 244.0 5.3 36 11.8 244.0 2.6SR 36-45 11.9 250.0 4.7 36 11.8 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.6 12.4 20.5SR 36 4.7 12.3 20.6MAIN 36 7.3 237.0 10.3SR 36 5.9 239.0 10.260500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active