Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
100GBASE-LR4 10GBASE-LRM 40GBASE-FR Fibre Channel 1200-SM-LC-L Fibre Channel 400-SM-LC-L Fibre Channel 800-SM-LC-LProject: Uni ConsultUniconsult tester.flwTest Summary: PASS Backscatter Coefficient: -79.5dB (1310 nm) Backscatter Coefficient: -82.0dB (1550 nm)Number of Adapters: 2 Number of Splices: 0 Connector Type: LC Patch Length1 (m): 2.0 Reference Date: 15-06-2020 12:21:59 1 JumperLinkWare™ PC Version 10.1Cable ID: 006 Date / Time: 15-06-2020 12:33:23 Cable Type: OS2 Singlemoden = 1.467000 (1310 nm) n = 1.468000 (1550 nm)Loss (M->R) PASS Date / Time: 15-06-2020 12:33:23 Test Limit: EN50173 Fiber Optic Link Limits Version: 7.1 CertiFiber Pro (2388501 V6.1 Build 3) Module: CFP-QUAD(2440405) Calibration Date: 19-07-2017 certifiber pro remote (2412037 v6.1 build 3) Module: CFP-QUAD(2440413) Calibration Date: 19-07-2017Propagation Delay (ns) Length m Limit 10000.0Result Loss (dB) Limit (dB) Margin (dB)Reference (dBm)206 42.11310 nm PASS 0.15 1.52 1.374.77PASS