Title: 2 etg del2.pdf
LinkWare Version 8.1Cable ID: D2014 Date / Time: 10/10/2013 11:54:42 AM Headroom 4.5 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]69 106 4 10.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]23.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.4 210.5 36.6 36 6.8 210.5 34.0SR 36-78 4.5 211.0 36.5 36 6.1 211.0 33.9MAIN 36-78 5.4 210.5 36.6 36 6.8 210.5 34.0SR 36-78 4.5 211.0 36.5 36 6.1 211.0 33.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.2 3.6 53.0 12 17.3 2.9 52.0