Title: 360.001 - Tilluft.pdf
3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeProductJOINTNPU_SE-*0,1DUCTMAGID-C1-4003 T-BRANCHTCPU-400-315DUCTMAGID-C1-3154 FLOWDAMPER LEO-0-315DUCTMAGID-C1-315BEND-90MAGIB-C3-90-315DUCTMAGID-C1-315SILENCERLKR-315-1200DUCTMAGID-C1-315Size400400400/315315315315315315315315Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]16503,69,316503,616503,61,312004,312004,30,412004,312004,30,112004,312004,30,312004,328Sound in:3,7 Sound in:Attenuation: Addition:10,2 Sound in:Attenuation: Addition:Dividing:0,9 Sound in:Attenuation: Addition:11,5 Sound in:Addition:0,3 Sound in:Attenuation: Addition:2,8 Sound in:Attenuation: Addition:0,1 Sound in:Attenuation: Addition:11,0 Sound in:Attenuation:0,2 Sound in:Attenuation: Addition:63 [dB]37.737.70.6 +24.337.30.0 +35.31.537.90.1 +25.738.1+43.144.30.0 +25.744.3