Title: Climate Controls Ltd - MG Series 2000.pdf
useful when setting up and commissioning the motor. It should be noted that this is a legalrequirement in some countries.Overload and short-circuit protection devices can be incorporated in a motor control system orindividual products such as motor thermal-magnetic circuit breakers which are specifically designed forthe protection of electric motors.Climate Controls can supply various combination motor relay units fitted with suitable protectiondevices. These units are generally fully compatible with third party control systems. Thermal-magnetic circuit breakers can be supplied in individual water resistant enclosures.Wiring ConnectionsDetails of wiring connections are supplied with the motorgearboxes and are also described at the endof this manual. The cable feeding the main power supply to the electric motor should be a minimum of4 x 1.5mm wires. The wires between the control or relay box and the limit switches should normallybe 3 x 0.8mm wires.