Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 78-45 14.2 492.0 11.4 45 14.7 492.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 20.1 33.0 39.6 45 20.0 33.0 37.2SR 45-78 18.2 33.0 39.6 45 19.3 32.8 37.3MAIN 36-45 35.4 499.0 -12.3 36 34.3 500.0 -15.3SR 36-45 30.7 495.0 -12.1 36 31.1 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.4 449.0 8.0SR 12 6.0 449.0 8.0MAIN 12 7.4 449.0 8.0SR 12 6.0 449.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00439.1 m60Insertion Loss (dB)504030201000250 MHz500