Title: Hardware Installation Guide.pdf
624 — revision 6Hardware Installation GuideNotes:Make sure you connect from TR2+ to TA- and from TR2- to TB+. This reversed polarity wiring is different from other panel types.Jumpers 19 & 20 must be ON.TerminationThe typical recommendation calls for termination at each end of the line. The link between the LNL-500W and the Schlage Wireless devices is fairly short. There may be a need for termination in some unusual cases.Notes:For Port 2, you MUST always remove the RS-485 terminator (J11) for each device that is not an end-of-line device.The wireless reader gateway can be located anywhere along the RS-485 line.Remove the RS-485 terminator for each device that is not an end-of-line device.Access Control Panel ConnectionConnectorSignalAccess Panel Signal DescriptionJ2J2 (1)J2 (2)+ 12 or 24 VDCDC GroundPIM400-485 inputs for 12 or 24 VDC power. Draws 250mA maximum.