Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
MAIN 36-45 10.0 116.0 40.8 36 10.6 408.0 28.4SR 36-45 7.6 458.0 29.8 36 8.2 458.0 27.0MAIN 36-78 11.8 490.0 28.3 36 11.9 489.0 25.5SR 36-45 8.9 500.0 27.8 36 9.2 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 15.3 3.9 53.5 45 14.2 3.5 51.4SR 36-45 15.3 3.9 53.5 45 14.2 2.9 53.1MAIN 45-36 16.1 474.0 11.7 36 19.2 500.0 8.3SR 36-45 15.9 474.0 11.7 45 18.6 474.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.0 115.5 21.8 36 27.2 116.0 19.2SR 36-45 29.4 116.0 21.7 45 31.0 116.0 19.2MAIN 36-78 42.9 490.0 -11.7 36 43.8 500.0 -15.3SR 36-45 39.8 500.0 -12.4 36 40.4 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.9 492.0 8.0SR 12 6.3 500.0 8.0MAIN 45 7.9 492.0 8.0SR 12 6.3 500.0 8.040010080250 MHz