Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]25.0 109 2 3.84Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]30.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.4 467.0 29.4 45 10.5 467.0 26.6SR 36-45 8.0 467.0 29.4 36 8.3 490.0 25.5MAIN 36-45 11.5 500.0 27.8 36 11.1 500.0 25.0SR 36-45 8.4 500.0 27.8 36 8.5 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.4 102.0 25.1 45 14.3 6.5 46.0SR 36-45 15.4 102.0 25.1 45 14.3 4.0 50.2MAIN 36-45 17.9 473.0 11.7 45 18.8 500.0 8.3