Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD2 components.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-28Saia-Burgess Controls Ltd.Input/output (I/O) modulesDigital output modules, electrically isolated6.5Digital output modules, electrically isolatedPCD2.A200 PCD2.A210 PCD2.A220 PCD2.A250PCD2.A4104 make contacts 2 A, 250 VAC | 50 VDC 4 break contacts 2 A, 250 VAC | 50 VDC 6 make contacts 2 A, 250 VAC | 50 VDC 8 make contacts 2 A, 48 VAC | 50 VDC pluggable 14-pole terminal block 8 outputs 0.5 A, 5…32 VDC, electrically isolated from PCD2 busInstallation instructionsFor reasons of safety it is not permissible to connect low voltages (up to 50V) and higher voltages (50 … 250 V) to the same module.6