Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Tallberg Elektro A/S Tlf.22796640Side:39GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.270270271271272272273273274274275275276276TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 1040V Rlpe: >30.0MΩ Um: 1060V Rnpe: >30.0MΩ Um: 1047VUiso: 1000V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 27.11.2020 10:26SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 26.11.2020 14:33Z-LINEZ: 0.34ΩIsc: 678A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 26.11.2020 14:33Zs(rcd)Z: 0.34ΩIsc: 680A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF089 16C2/003 26.11.2020 14:34RCD II: 28.5mAUci: 0.1V t: 27.8ms Idn: 30mA type: AC Ulim: 50V