Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
MAIN 45-78 19.5 9.6 45.6 45 21.0 495.0 8.3SR 45-78 19.5 9.6 45.6 45 20.4 500.0 8.3MAIN 36-12 20.9 472.0 11.8 45 21.0 495.0 8.3SR 12-36 20.7 472.0 11.8 45 20.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 30.3 136.0 19.0 45 30.4 136.0 16.4SR 12-36 33.9 214.0 10.1 36 34.0 135.0 16.5MAIN 36-78 40.0 498.0 -12.3 36 39.7 500.0 -15.3SR 12-36 40.6 496.0 -12.1 36 40.5 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.8 491.0 8.0SR 45 5.5 491.0 8.0MAIN 45 4.8 491.0 8.0SR 45 5.5 491.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasje