Title: 4. Leieavtaler.pdf
2015-01-07: As an alternative to the above an FM Approved Water Mist System can be used for the office areas. Please review www.approvalguide.com for FM Approved Water Mist Systems and design the system in accordance with FM Global Property Loss Prevention Data Sheet 4-2, Water Mist Systems and adhere to guidelines for inspection and testing in Data Sheet 2-81, Fire Protection System Inspection.b. Manufacturing areas:Data Sheet 3-26, Fire Protection Water Demand for non-Storage Sprinklered Properties.Based on the existing facility, i.e., electronics manufacturing and assembly, ceiling height up to 9 m with on-floor storage up to a maximum of 1.8 m with movable picking rack containing rigid plastic open top containers the following design can be chosen.