Title: 2 etg del2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]115 182 13 4.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]20.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.4 250.0 35.3 36 1.2 237.5 33.1SR 36-78 7.0 246.5 35.4 36 6.9 237.5 33.1MAIN 36-45 1.4 250.0 35.3 36 1.2 246.5 32.8SR 36-78 7.0 246.5 35.4 36 6.9 237.5 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.9 244.5 16.4 45 16.8 250.0 13.2SR 45-36 15.5 244.5 16.4 36 17.7 244.5 13.4MAIN 36-45 15.9 250.0 16.2 45 16.8 250.0 13.2SR 45-36 15.6 250.0 16.2 36 17.7 244.5 13.4010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)