Title: 442.26.pdf
covered by heat-insulating material. The lateral distance between recessed luminaire and building parts must be at least 50 mm. Necessary built-in depth 100 mm Ceiling cut-out Ø 170 mm Remove glass with frame ring by turning it counter-clockwise. Unlock the bar from the connection compartment with a screw driver and unplug it. Open the connection compartment, dismantle the main supply cable max. 45 mm and strip the wires max. 8 mm. Make electrical connection to the plug. Click the cover into the plug and fix it with the screws. Plug the connection compartment together until it is locked. Place luminaire into ceiling cut-out. Tighten fixing screws by turning it clockwise. When tightening the screws the fixing claws will turn onto the false ceiling and the luminaire will be fixed. The thickness of the false ceiling has to be between 3 and 45 mm. If turned counter clock-wise the fixing claws will turn back and the luminaire can be removed from the ceiling cut-out. Insert lamp. Install glass with frame ring with