Title: økernvn 94.pdf
75100100NEXT @ Remote (dB)80604020100002550 MHz75100100ACR-F @ Remote (dB)80604020100002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 7.4Cable ID: T4164 Date / Time: 09/11/2013 12:09:09 Headroom 7.7 dB (NEXT 36-78) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]121 184 5 6.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.7 83.5 33.6 36 9.3 83.5 30.6