Title: økernvn 94.pdf
Cable ID: D4059 Date / Time: 09/10/2013 01:04:03 Headroom 13.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]289 458 32 12.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]4.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.7 99.0 32.4 36 16.4 98.8 29.4SR 12-36 13.4 22.5 42.8 36 15.2 96.3 29.6MAIN 12-36 14.7 99.0 32.4 36 16.4 98.8 29.4SR 12-36 13.5 96.3 32.6 36 15.2 96.3 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.5 40.0 26.6 36 17.3 40.0 23.6