Title: 1 etg del 2.pdf
Measurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: D1193 Date / Time: 10/17/2013 12:50:55 PM Headroom 11.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]108 172 13 4.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.5 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.2 90.5 33.0 36 13.6 96.5 29.6SR 12-36 11.8 75.5 34.3 36 14.0 93.5 29.8MAIN 12-36 11.2 96.8 32.5 36 13.6 96.8 29.5SR 12-36 11.8 96.8 32.5 36 14.1 96.8 29.510080604020NEXT (dB)