Title: økernvn 94.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.5 * 242.5 35.6 36 0.1 * 243.5 32.9SR 36-78 5.5 233.5 35.8 36 6.9 233.0 33.2MAIN 36-45 0.5 242.5 35.6 36 0.1 243.5 32.9SR 36-78 5.5 233.5 35.8 36 6.9 248.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 16.9 248.5 16.3 12 18.3 63.0 25.2SR 45-12 16.4 248.5 16.3 36 18.2 59.0 25.8MAIN 45-12 16.9 248.5 16.3 45 18.6 249.0 13.3SR 45-12 16.4 250.0 16.2 45 18.7 249.5 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250