Title: Simployer - Data testrapport =514.204-FS001.pdf
[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]53.1 273 20 9.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]20.0 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 8.9 33.3 48.0 7,8 9.8 33.3 45.3SR 3,6-7,8 5.9 33.3 48.0 7,8 7.7 33.3 45.3MAIN 1,2-3,6 10.0 248.0 33.2 3,6 10.7 248.0 30.2SR 3,6-7,8 7.9 250.0 33.1 3,6 9.4 250.0 30.2PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 16.3 133.0 20.8 4,5 18.1 139.5 17.4SR 7,8-4,5 16.2 127.0 21.2 4,5 18.2 4.9 46.5MAIN 7,8-4,5 17.1 243.5 15.5 4,5 19.6 242.0 12.6SR 7,8-4,5 17.1 246.0 15.4 4,5 20.1 246.0 12.4PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 13.0 11.5 48.6 3,6 11.5 3.6 57.2SR 3,6-7,8 12.0 3.6 59.7 3,6 11.3 3.6 57.2