Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
SR 45-36 15.5 468.0 11.8 45 18.1 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 27.9 122.0 20.9 36 27.6 128.5 17.4SR 36-45 28.6 123.0 20.7 36 29.8 128.5 17.4MAIN 36-45 38.9 497.0 -12.2 36 39.8 497.0 -15.1SR 12-45 42.0 497.0 -12.2 45 42.0 497.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 4.1 127.0 13.0SR 12 3.9 126.5 13.0MAIN 45 5.8 453.0 8.0SR 45 5.2 479.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00418.7 m60Insertion Loss (dB)504030201000250 MHz