Title: 36 Siemens GDB181-MO.pdf.pdf
5 5.1 Mechanical installation / mountingFor mounting and limitations on mounting (location / position), consulting the mounting instruction [2] is mandatory.The permissible ambient temperature and ambient humidity must be observed (cf. chapter 9).The actuator may only be manually operated when separated from power supply.If required, the angular rotation can be set by appropriate adjustment of the adjusting screw.Connection of PC tool ACS931 / ACS941 to G..B181.1E/MO124AST1131 PC (with ACS931 or ACS941)2 G..B181.1E/MO3 Strain release stripConnection of VAV handheld tool AST20 to G..B181.1E/MO1231 AST202 G..B181.1E/MO3 Strain release stripVAV Compact Controller Modbus RTUA6V10631862_en--_d 2019-09-13Permissible cable lengths and cross- sectional areasNotePermissible voltage dropNoteL/P chart for AC 24 VNote on chartBasic diagram: Voltage drop on the supply linesSiemens Smart Infrastructure