Title: 40 Bender brukermanual.pdf.pdf
6.3.2 Alarm and its effect Possible causes of alarm messages:   The value falls below or exceeds the set response value or the prewarn-ing threshold during current or residual current measurement.  Digital input closed resp. open   Fault measuring current transformer or CT connection fault   Device error (see „Display device error“ on page 82)The RCMS460… signals prewarning and/or alarm:   LED "ALARM 1" (prewarning) and/or LED "ALARM 2" (alarm) lightdepending on the type of alarm.  Associated common alarm relays (C…) switch.RCMS490… only: Alarm relays of the individual channel switch.  An alarm message is being sent on the BMS bus.RCMS460-490_D00067_03_M_XXEN/12.201739Operation  An entry is made in the history memory.   An entry is made in the history memory.   RCMS…-D…: An alarm message is shown on the display.ALARM 1/1 Residual current130 mA Addr.: 2 Chan.: 12Line 1:Line 2: