Title: +038=433.000-NI003._07-Testrapport elektriske anlegg - DM1.E7=433.08.05, Pareto plan 08.pdf
Isc: 606A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF026 16/2/C/003 19.11.2020 12:12Zs(rcd)Z: 0.33ΩIsc: 701A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF026 16/2/C/003 19.11.2020 12:12RCD II: 28.5mAUci: 0.1V t: 17.8ms Idn: 30mA type: AC Ulim: 50VTallberg Elektro A/S Tlf.22796640Side:3GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 20202121222223232424252526262727TEST RAPPORTResultatDM1-3. Plan 8 / DM1.E7.433.08.05 / XF026 16/2/C/003 19.11.2020 12:38KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF026 16/2/C/003 19.11.2020 12:38R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF026 16/2/C/003 19.11.2020 14:23R ISOR: >200MΩ Um: 10VUiso: 250V Grenseverdi: 1MΩ