Title: økernvn 94.pdf
6040202500050100150200250MHz60RL @ Remote (dB)50403020102500050100150200250MHzLinkWare Version 7.4Cable ID: T4185 Date / Time: 09/11/2013 12:47:42 Headroom 7.6 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]105 159 5 4.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]20.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.7 142.5 39.3 36 8.7 90.5 40.0SR 36-78 7.6 242.5 35.6 36 8.0 200.5 34.3MAIN 12-36 9.8 232.5 35.9 36 10.1 239.0 33.0SR 36-78 7.6 242.5 35.6 36 8.3 248.5 32.710080604020NEXT (dB)