Title: økernvn 94.pdf
Cable ID: T4037 Date / Time: 09/11/2013 10:03:36 Headroom 12.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]127 201 14 5.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.0 72.3 34.6 36 14.6 72.3 31.6SR 12-36 12.9 72.3 34.6 36 14.3 82.8 30.7MAIN 12-36 13.0 90.5 33.0 36 15.4 90.5 30.0SR 12-36 13.4 90.3 33.0 36 15.4 100.0 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 21.3 3.8 47.1 45 22.9 3.1 45.7