Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
6-88Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.H100Programming:Count modes: Terminals:Based on PCD user program and pre-programmed function blocks (FB). Selectable with jumper Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²LEDs and connection terminalsBus connectorGAL*) for adressingSC x1 x2GAL*) for count modes6Jumper for count modesCCOBAEnLEDsScrew terminals9876543210CCOBA(*) GAL = Generic Array Logic)Input “A” Input “B”1 “A” “B” 2 “En” (Enable) Counter active 0 “CCO”Output “CCO” 3Changing the jumpersOn this circuit board there are components that are sensitive to electrostatic discharges. For further information, refer to Appendix B, "Icons"Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-89Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.H100Count modesSC (Single Count):AAND