Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
2Phase order and label checkCarry out a visual check of the phase order from end to end. Special attention is recommended if phase or neutral crossovers are installed. All labels have to be checked.3Connection check Carry out a visual check on the tightening of the joint block bolts. All shear nuts should have the double-headed bolts snapped off and the red washers absent. If the joint block is dismantled and reassembled for any reason, the 60 N•m torque must be checked again with a torque wrench. Check the PE protective circuit equipotential (according to the standard IEC 61439-1). Using an ohmmeter, check the PE protective circuit continuity by visual inspection and random continuity testing. This test is carried out to detect the wrong mounting of the PE plate, for example, accidental insertion in the phase joint block.4Insulation check (before transformer and switchboard connections) Measure the insulation resistance between each phase or neutral(1) and earth (if the casing