Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
24.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.5 499.0 29.3 36 5.3 499.0 26.4SR 36-45 7.8 499.0 29.3 36 7.4 500.0 26.4MAIN 36-45 5.5 499.0 29.3 36 5.3 499.0 26.4SR 36-45 7.8 499.0 29.3 36 7.4 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.2 354.0 14.3 45 20.9 392.0 10.4SR 78-45 19.2 388.0 13.5 45 20.1 409.0 10.0MAIN 45-78 19.4 404.0 13.1 45 21.9 459.0 9.0SR 78-45 19.4 404.0 13.1 45 20.1 409.0 10.00100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 24.3 31.0 40.4 45 24.4 30.8 38.1SR 36-45 23.8 31.8 40.1 36 24.8 31.8 37.7MAIN 36-45 29.5 499.0 -12.3 36 29.3 499.0 -15.2SR 36-45 31.8 499.0 -12.3 36 31.5 500.0 -15.30804000250 MHzACR-N (dB)