Title: +038=360.000-LC009._05-360 Cassette Fan-coil Samsung - Installasjonsmanual.pdf
Centralized horizontal drain pipe (more than 1/100 slope)360_AirCon_Indoor_IM_ENG_EN.indb 15Step 11 Performing the drainage test1 Do a leak test at the connection part of the flexiblehose and the drian pipe:aConnect a general hose to the connection part of the flexible hose of the indoor unit, and pour in some water.Water leakage check partFlexible hoseHoseb After pouring some water, reassemble the rubber cap on the connection part of a flexible hose of the indoor unit and firmly tighten it with a band to prevent leakage.cCheck the leak test at the part where the adhesive for the flexible hose and the drian pipe is used.CAUTION The leak test must be performed for at least 24 hours.2 Check the condensed water drainage:aPour about 2 liters of water into the indoor unit drain pan as shown in the picture.I n s t a l l a t i o n P r o c e d u r eb When the electric cable connection is completedTurn on the indoor unit and outdoor unit.Operate in the Cool mode.