Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Switching capacity: *) (contact lifetime)> 12 V, > 100 mA 2A, 48 VAC AC1 0.7 x 106 operations 1 A, 48 VAC AC11 1.0 x 106 operations 2 A, 50 VDC DC1 0.3 x 106 operations 3) 1 A, 24 VDC DC110.1 x 106 operations 1)3)Relay coil supply: 2)nominal 24 VDC smoothed or pulsed, 8 mA per relay coilVoltage tolerance, dependent on ambi- ent temperature:20°C: 17.0…35 VDC 30°C: 19.5…35 VDC 40°C: 20.5…32 VDC 50°C: 21.5…30 VDCOutput delay:typically 5 ms at 24 VDCResistance to interference: acc. to IEC 801-44 kV under direct coupling 2 kV under capacitive coupling (whole trunk group)Internal current consumption: (from +5 V bus)1…25 mA typically 15 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption:max. 64 mATerminals:Pluggable 24-pole spring terminal block (4 405 4956 0), for Ø up to 1 mm²,1) With external protective diode 3) These ratings are not UL-listed2) With reverse voltage protection