Title: økernvn 94.pdf
20100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: T3083 Date / Time: 09/12/2013 03:48:55 Headroom 12.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]94 148 10 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.2 91.0 33.0 36 14.3 91.3 30.0SR 12-36 12.1 91.0 33.0 36 14.8 80.5 30.9MAIN 12-36 12.2 91.0 33.0 36 14.3 91.3 30.0SR 12-36 12.1 91.0 33.0 36 14.9 98.3 29.410080604020NEXT (dB)