Title: Data tester Smestad skole - Detaljert.pdf
dB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 20,5 11,3 9,2 439,00Remote: 45-12 68,8 59,3 9,5 1,75Worst Value: Local: 12-45 20,4 11,3 9,1 440,00Remote: 12-36 21,1 10,7 10,4 474,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 31,2 27,2 4,0 398,00Remote: 36 27,6 23,8 3,8 498,00Worst Value: Local: 36 27,9 23,9 4,0 494,00Remote: 36 27,6 23,8 3,8 498,00PS-ACRF: Pass Worst Margin: Local: 12 71,4 61,2 10,2 1,00Worst Value: Local: 45 20,3 8,3 12,0 440,00Remote: 45 70,1 61,2 8,9 1,00Remote: 12 19,6 8,2 11,4 446,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:17Signature:______________________ Page: 157Copper Certification Report