Title: 26 Manual for takslukvakt.pdf.pdf
Time in minutes between samplesBLOCKED_SENSOR_LIMIT_FACTOR BLOCKED_DRAIN_LIMIT_FACTORSensitivity of the algorithm: Higher value = Lower sensitivity Lower value = Higher sensitivityBLOCKED_SENSOR_ALARM_SET_COUNTER BLOCKED_DRAIN_ALARM_SET_COUNTERCounter of incidents that activate an alarmBLOCKED_SENSOR_NOALARM_RESET_COUNTER BLOCKED_DRAIN_NOALARM_RESET_COUNTERNumber of no incidents to set counter to 0.ALARM_TEMPERATURE_LIMIT:Roof alarms deactivated when temperature is < 5°C on any Monitor. This is to avoid false alarms due to ice and snow. The roof alarms will reactivate when the temperature is >5°C on all Monitors. The temperature limit can be configured in the config file.AUTOMATIC_ALARM_REMOVINGIf set to YES, alarms will automatically clear when alarm conditions are no longer present. If set to NO, alarms will remain active until manually cleared via INFO button or via Modbus.