Title: +175=737.001_IK001_Brukermanual for Refra varmepumpe.Produktinformasjon.pdf
value of filling. If the temperature of the liquid line does not drop and discharge pressure rises 20.7 - 34.5 kPa by adding 2,2-4,5 kg of refrigerant, it is considered that has reached the maximum filling. Refills can be done at any stable system operation and any outdoor temperature. Before you start filling plant must have worked for at least 5 minutes. In this case, you must be sure that the flow of fluid through the condenser and evaporator, the temperature of the liquid on their inputs on the technical requirements. In the presence of moisture in the circuit (as determined by the indicator sight glass), replace the filter - drier. In the presence of moisture in the system, replace the filter - drier. When necessary refill the system, remove the refrigerant by means of special equipment.