Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-255-13Saia-Burgess Controls Ltd.Communication interfacesSerial interfaces - Slots A1 and A2Not all manufacturers use the same connection configuration, so the data lines may need to be crossedThe potential difference between PGND and the data lines Rx-Tx, /Rx-/Tx (and SGND) is limited to 50 V by a suppressor capacitor.For installation details, see manual 26/740 “Installation components for RS485 networks”5Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-255-14Saia-Burgess Controls Ltd.Communication interfacesSerial interfaces - Slots A1 and A25.4.5 MP-Bus with PCD7.F180, Port#1 & Port#2PCD7.F180:Connection module to MP-BusThe user can connect an MP-Bus line with 8 drives and sensors.Connections5Steckplatz A2PCD7.F1802t r o P, 3 x0 1 2 3 4 5 6 7 8 90, (0) - 1, (1) MP 2, (2) ,MFT’ 3, (3) ,IN’ 4, (4) GND 5, (5) -