Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF024 16C2/003 30.11.2020 09:45SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF024 16C2/003 30.11.2020 09:45Z-LINEZ: 0.50ΩIsc: 459A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF024 16C2/003 30.11.2020 09:46Zs(rcd)Z: 0.51ΩIsc: 454A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF024 16C2/003 30.11.2020 09:46Tallberg Elektro A/S Tlf.22796640Side:8GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.5555565657575858595960606161TEST RAPPORTResultatRCD II: 28.5mAUci: 0.6V t: 13.8ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF024 16C2/003 30.11.2020 11:53 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 253V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254V