Title: Data tester Smestad skole - Detaljert.pdf
1000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 25,0 14,0 11,0 324,00Remote: 45-12 68,6 57,3 11,3 2,20Worst Value: Local: 12-45 22,8 11,4 11,4 434,00Remote: 45-12 23,2 11,4 11,8 434,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,5 23,9 4,6 494,00Remote: 36 32,1 27,1 5,0 399,00Worst Value: Local: 45 28,4 23,8 4,6 499,00Remote: 45 28,9 23,8 5,1 499,00PS-ACRF: Pass Worst Margin: Local: 12 65,9 54,3 11,6 2,20Worst Value: Local: 12 20,6 8,5 12,1 429,00Remote: 12 65,7 54,3 11,4 2,20Remote: 12 20,6 8,6 12,0 426,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:11Signature:______________________ Page: 115Copper Certification Report