Title: 2 etg del2.pdf
Cable ID: D2197 Date / Time: 10/10/2013 12:58:49 PM Headroom 11.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]221 349 23 9.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.3 26.5 41.7 36 15.9 84.5 30.5SR 12-36 11.8 81.5 33.8 36 14.1 96.5 29.6MAIN 12-36 14.9 99.3 32.4 36 16.0 99.3 29.4SR 12-36 12.0 96.3 32.6 36 14.1 96.5 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.4 57.3 23.5 36 20.2 57.3 20.5