Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
The fixed power distribution unit must include protection and isolation for the utility supply and the back-up supply. In the event thata residual current device is installed on the UPS input line (optional), this must be located upstream of the power distribution unit.Electrical requirementsUPSThermal-magnetic switch on inputInput leakage currentCable section6 kVA40 C0.1 A type A6 mm210 kVA63 C0.1 A type A10 mm2