Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
83 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 027 GODKJENT *12.03.2020 14:02SPENDINGUln: 234VUlpe: 234VUnpe: 0Vf: 50.1HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 027 GODKJENT * 12.03.2020 14:04RCD IGODKJENTI: 28.5mAUci: 0.1Vt: 18.2msIdn: 30mAtype: ACO\,Ulim: 25V5 | Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 027 GODKJENT *12.03.2020 14:04Zs (red) GODKJENTZ: 0.34QIsc: 678ASikringstype: CSIKRING I: 16ASTIKRING T: 35msIsc_lim: 160.0A86Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 027 GODKJENT * 12.03.2020 14:02ZLINE GODKJENTZ: 0.69QIsc: 332ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0A87Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 027 GODKJENT * 124003.2020 13:29R LOW Ohm GODKJENTR: 0.04QR+: 0.0QR: 0.0QGrenseverdi:1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 027 GODKJENT* 12.03.2020 16:30KONTINUITET GODKJENTR: 0.1QGrenseverdi:1.0QR IS0 GODKJENTR: >200MQ Um: 263VUiso: 250V