Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Z: 0.23ΩIsc: 998A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF054 C16/2 10.06.2020 12:50RCD UbUc: 0.2V Rl: 8Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF054 C16/2 10.06.2020 12:50RCD tt: 57.7msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VTallberg Elektro A/S Tlf.22796640Side:42GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 288288289289290290291291292292293293294294295295TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF054 C16/2 10.06.2020 12:51RCD II: 28.5mAUci: 0.3V t: 24.5ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF054 C16/2 11.06.2020 15:21R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF054 C16/2 11.06.2020 15:32SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.1Hz