Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36-45 29,9 26,7 3,2 498,00Worst Value: Local: 36-45 28,4 26,7 1,7 499,00Remote: 36-45 29,9 26,7 3,2 498,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 24,7 13,9 10,8 328,00Remote: 45-12 25,1 13,9 11,2 328,00Worst Value: Local: 12-45 22,6 10,9 11,7 460,00Remote: 12-45 22,6 11,0 11,6 457,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 27,1 23,8 3,3 499,00Remote: 36 29,4 23,8 5,6 497,00Worst Value: Local: 45 27,1 23,8 3,3 500,00Remote: 45 29,4 23,8 5,6 500,00PS-ACRF: Pass Worst Margin: Local: 45 19,8 8,0 11,8 459,00Worst Value: Local: 45 19,7 7,9 11,8 460,00Remote: 45 73,0 61,2 11,8 1,00Remote: 45 19,9 8,0 11,9 457,00