Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Tallberg Elektro A/S Tlf.22796640Side:44GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.304304305305306306307307308308309309310310311311TEST RAPPORTResultatR ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF075 C16/2 11.06.2020 15:33SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF076 C16/2 10.06.2020 11:51SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF076 C16/2 10.06.2020 11:56R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF077 C16/2 10.06.2020 11:51SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF077 C16/2 10.06.2020 11:57R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0Ω