Title: +038=433.000-NI003._28-Testrapport Elektriske Anlegg Pecunia Plan 10 UF 433.10.03.pdf
34343535363637373838Resultat R LOW OhmR: 0.02ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE032 10.02.2020 13:02RCD II: 28.5mAUci: 0.2V t: 36.8ms Idn: 30mA type: AC Ulim: 50VOBJEKT / Plan 10 / FUSE032 10.02.2020 13:04SPÆNDINGUln: 231V Ulpe: 230V Unpe: 2V f: 49.9HzOBJEKT / Plan 10 / FUSE032 10.02.2020 13:04Z-LINEZ: 0.74ΩIsc: 312A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE032 10.02.2020 13:05Zs(rcd)Z: 0.45ΩIsc: 516A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0AOBJEKT / Plan 10 / FUSE032 06.02.2020 09:11R LOW OhmR: 0.04ΩR+: 0.0Ω R-: 0.1Ω Grenseverdi: 1.0ΩOBJEKT / Plan 10 / FUSE033 10.02.2020 13:25TEST RAPPORTSide:6GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.393940404141424243434444ResultatRCD II: 28.5mAUci: 0.2V t: 103.9ms Idn: 30mA type: AC Ulim: 50V