Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]187 296 20 8.0187 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.2 * 249.0 35.4 36 0.8 * 234.5 33.2SR 36-450.4 *247.5 35.4 36 0.1 *243.5 32.9MAIN 36-45 0.2 249.0 35.4 36 0.8 249.0 32.7SR 36-45 0.4 247.5 35.4 36 0.1 249.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 13.6 51.5 30.0 45 14.4 2.4 53.7SR 45-36 13.4 51.5 30.0 45 14.4 2.4 53.7MAIN 45-12 14.1 201.0 18.1 12 16.8 201.0 15.1SR 45-12 14.0 202.5 18.1 45 18.2 250.0 13.2010080604020050100150MHzACR-F (dB)20025001008060