Title: Økernveien 94 Sprinklerberegning U2.pdf
Project Name : Økernveien 94Drawing No. :Design AreasDesign Area NameCalc. Mode (Model)DesignArea_1Demand (HW)Date 29.05.2018OccupancyCALCULATION SUMMARYProject Location:City:Area of ApplicationTotal Water Pressure @SourceMin. DensityMin. Pressure(m²)(l/min)(bar)(l/min/m²)(bar)149.6862.9Required 1.625.70.5File: D:\Dokumentert\Kunder\Møller eiendom\Dokumentasjon\Økernvn 94 U2.tyc3Copyright © 2002-2012 Tyco Fire Protection ProductsMin. Flow(l/min)56.57Calculated Heads#15Hose Streams(l/min)0Margin To Source(bar)1.62Page 1HYDRAULIC CALCULATIONS forJob InformationProject Name : Økernveien 94Contract No. :City:Project Location:Date: 14.05.2018Contractor InformationName of Contractor: Dokumentert ASAddress: PB 1036City: Oslo, NO 0218Phone Number:E-mail: anders@dokumentertas.noName of Designer: Anders SandmælAuthority Having Jurisdiction: R2BDesignRemote Area NameDesignArea_1Remote Area Location