Title: +038=67.011-##033._01-Ø1_Aggregat.pdf
Ensure that the unit is grounded when replacing components. Like the protection device, use the relay supplied with the compressor only, even if another model number appears to work at any given time. All TECUMSEH compressors are protected by an external or internal protection device, based on temperature/current. As with any protection device, it is normal for the device to cut the power supply to the compressor if it functions outside of the normal operating ranges defined by TECUMSEH. ■ 3.9. Connection of components Please refer to the electrical drawing for the connection of components. - Connect all regulation and safety devices mounted on themachine.Hold any cables in place with the cable ties available on the unit.