Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
System drainage : If the system needs to be emptied, remember that a water head always remains into the coil and it may freeze in case temperature goes below 0° thus causing the heat exchanger failure. The heat exchanger can be totally emptied by opening the valves and blowing in air in each valve for 90 seconds at a minimum pressure of 6 bar.Guide for the owner When installation and tests are completed instruct the Owner on the main operating modes of the air conditioner, such as:Turning the unit ON and OFF. • Changing the operation modes. • Temperature selection.Leave the installation manual with the owner for future use during maintenance operations or for any other needs.3442 GW(cid:20)(cid:21)(cid:28)(cid:43)(cid:28)(cid:23)(cid:66)(cid:42)(cid:37)(cid:16)(cid:22)(cid:17)(cid:76)(cid:81)(cid:71)(cid:71)(cid:3)(cid:3)(cid:3)(cid:22)(cid:23)(cid:19)(cid:24)(cid:18)(cid:20)(cid:21)(cid:18)(cid:20)(cid:20)(cid:3)(cid:3)(cid:3)(cid:20)(cid:28)(cid:29)(cid:20)(cid:21)