Title: EDM_AQAR32_01-S-2GB.pdf
Heating modeWater volume Antifreeze heater COIL Number Frontal surface Number of rows FAN NumberECWater flow Water pressure drop Water flow Water pressure dropm³/h kPa m³/h kPa l W1 / Plate 8.7 31.8 9.3 36.3 6.0 30m21 4.2 21Air flow Rotational speed Power input each fan kWm³/h 21 200 Rpm 780 1.110.6 46.7 10.7 48.1 6.0 301 4.2 21 21 200 780 1.112.2 33.0 12.5 34.4 8.4 2 x 302 5.6 22 30 000 620 0.613.2 38.2 13.9 42.8 8.4 2 x 302 5.6 22 30 000 620 0.6WATER CONNECTIONSEvaporatorDesuperheaterType Inlet diameter Outlet diameter Type Inlet diameter Outlet diameterinch inchinch inchMale gas threaded 2'' 2'' Male gas threaded 1''1/4 1''1/42'' 2''1''1/4 1''1/42'' 2''1''1/4 1''1/42'' 2''1''1/4 1''1/4BUFFER TANK (OPTION) Volume DIMENSIONS Length without/with tank Width Height WEIGHT Operating weight (STD) ACOUSTICAL DATA Sound power level Sound pressure level (*)L300mm mm mm2 180/2 680 1 160 2 034kg554dB(A) 80.7 dB(A) 48.9300