Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 21,9 10,2 11,7 500,00Remote: 12-45 22,2 10,2 12,0 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,2 23,8 4,4 500,00Remote: 36 28,6 23,8 4,8 498,00Worst Value: Local: 36 28,2 23,8 4,4 500,00Remote: 36 28,6 23,8 4,8 498,00PS-ACRF: Pass Worst Margin: Local: 45 73,1 61,2 11,9 1,00Worst Value: Local: 12 20,1 7,3 12,8 497,00Remote: 12 73,5 61,2 12,3 1,00Remote: 45 20,1 7,2 12,9 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:07Signature:______________________ Page: 93Copper Certification ReportCable Label: 521.002-UD-59 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:25:27 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: