Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Zs (rcd) GODKJENTZ: 0.42QIsc: 548A14:05Sikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0ARCDDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 039 GODKJENT * 12.03.2020 14:05I:IGODKJENT28.5mAUci: 0.2Vt: 68.0msIdn: 30mAtype: ACA\,Ulim: 25VDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 039 GODKJENT* | 12.03.2020R LOW Chm GODKJENTR:15:150.10QR+: 0.1QR: 0.1QGrenseverdi:1.00QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 039 GODKJENT* 12/:08:2020 15215KONTINUITET GODKJENTR:0.1QGrenseverdi:1.0QTEST RAPPORTNr. ResultatR ISCO GODKJENTR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 040 GODKJENT* 11.08.2020 11:07SPENDINGUln: 234VUlpe: 235VUnpe: 1Vf: 49.9HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 040 GODKJENT* 12.03.2020 14337KONTINUITET GODKJENTR: 0.1QGrenseverdi: 1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 040 GODKJENT * 12.03.2020 13:29R LOW Ohm GODKJENT