Title: 32 Pumper modbuss teknisk data.pdf.pdf
Reset to factory default Note that the rotary switch must be set in this position for 20 seconds to reset to factory default. During this period, LED1 flashes red and green at the same time to indicate that a reset will occur.Every change of the rotary switch while the module is powered on will cause the module to restart.7.3 Setting the IP addressesThe CIM 500 Ethernet module is by default set to a fixed IP address. You can change the IP address settings from the built-in webserver.Default IP settings used by the webserverIP address:192.168.1.100 Subnet mask: 255.255.255.0 Gateway: 192.168.1.1IP settings for Modbus TCPMake the settings via the webserver.3 1 0 11 3 4 75 0 M TYou can configure CIM 500 using the built-in webserver. To establish a connection from a PC to CIM 500, the following steps are required:Connect the PC and CIM 500 using an Ethernet cable.