Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Tighten the connection bolt of the tap-off unit to a torque of 100 N•m to provide the electrical connection (seepage59).10Slide back the bolt access shutter to prevent access to the connection bolt.11Prepare the output cable glands and connect the cables to the tap-off unit.12Close the tap-off unit cover. The system and load are ready to be energised.58QGH3492101-01 11/2018Tap-off UnitsRules for Tightening the Connection Bolt of the Tap-Off UnitCorrect tightening of the bolts of the tap-off unit enables the electrical connection. Follow these rules when tightening the bolts:  The connection bolt must be tightened to a torque of 100 N•m, using the appropriate torque wrench. When the correct tightening torque is reached, the nut head snaps off, freeing a red washer (shear nuts).The freed red washer falls off. The tightening has been done correctly only if the red washer is absent after the procedure.  For dismantling or maintenance operations, the nut has a second head.