Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]39.1 169 2 5.70Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.3 487.0 29.5 36 9.2 485.0 26.7SR 36-45 6.2 495.0 29.3 36 6.1 495.0 26.5MAIN 36-45 10.3 487.0 29.5 36 9.4 500.0 26.4SR 36-45 6.2 495.0 29.3 36 6.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.1 479.0 11.6 45 13.5 8.4 43.8SR 78-45 13.9 435.0 12.5 45 13.5 6.0 46.7MAIN 45-78 14.1 479.0 11.6 78 14.9 473.0 8.7