Title: +038=370.001-RD001._01-Siemens Differanstrykk væske QBE3000-D6.pdf
25 bar≥ 10 bar50 barBursting pressure1.5 × system pressureDynamic response:Response time< 5 msLoad alternation< 50 HzSuitable mediaAir, mildly corrosive gases, liquidsAdmissible temperature of medium15...85 °CMaintenanceNo maintenance requiredProtection degree of housingIP65 according to EN 60529, mounted and tightenedProtection classIII according to EN 60730-1Connecting cablePlug DIN EN 175301-803-A, plug with seals and PG9cable glands includedPressure connectionsMale-threaded G1/8", With screwded fittings forcopper pipes, 6 mm diameterDifferential Pressure Sensor QBE3000-D.. / QBE3100-D..CE1N1922en 2018-11-19MountingsEnvironmental conditionsDirectives and StandardsEnvironmental compatibilityMaterialsWeightConnection terminalsSiemens Building TechnologiesMounting bracketFor mounting in ducts, on walls or ceilings, in contr.panelsOrientationAny (factory-calibrated with pressure connections atbottom)Perm. ambient temperature