Title: Kabelspesifikasjoner AutroSafe.pdf
Usability for PowerLoop Most commonly used alternative. Recommended to avoid long parallel paths. Contact Autronica for advice. Not suitable to Powerloop. If foil is a thin metal film this cable shall not be used. One of the foils has to be at least 0,3mm thick copper to be acceptable at the low frequencies. (Aluminium foil has to be 0,5 mm). Well suited.Well suited, especially for long parallel Powerloop cable runs.Conversion table American Wire Gauge (AWG) to mm / mm2AWG No 8 9 10 12 13 15 17 18 24Diam. mm Area mm2 3,260 2,910 2,590 2,050 1,830 1,450 1,150 1,024 0,5118,350 6,620 5,270 3,310 2,630 1,650 1,040 0,8230 0,2050This document specifies the cabling for Autronica’s interactive fire detection systems, and integrated fire and gas detection systems.