Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.9 499.0 29.3 36 9.0 499.0 26.4SR 36-45 6.3 499.0 29.3 36 6.6 496.0 26.5MAIN 36-45 9.9 499.0 29.3 36 9.0 499.0 26.4SR 36-45 6.4 500.0 29.2 36 6.6 496.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.3 374.0 13.8 45 13.5 2.6 53.9SR 45-78 14.6 388.0 13.5 45 13.4 2.5 54.3MAIN 78-45 15.0 429.0 12.6 45 15.8 475.0 8.7SR 78-45 15.3 429.0 12.6 45 15.5 424.0 9.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.7 32.0 40.0 45 21.4 32.0 37.6SR 45-78 19.2 32.3 39.9 45 19.6 32.0 37.6MAIN 36-45 34.1 499.0 -12.3 36 33.5 499.0 -15.2