Title: etg u1.pdf
Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]64 102 8 2.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.7 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.1 81.5 33.8 36 13.9 96.3 29.6SR 36-45 14.7 96.8 32.5 36 15.5 96.8 29.5MAIN 12-36 13.2 96.3 32.6 36 13.9 96.3 29.6SR 36-45 14.7 96.8 32.5 36 15.5 96.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 23.0 4.1 46.3 45 24.3 3.4 45.0SR 36-45 23.0 4.1 46.3 45 24.2 3.4 45.0MAIN 45-36 24.0 99.3 18.7 45 26.5 97.0 15.9SR 36-45 24.1 99.3 18.7 45 26.3 99.3 15.701008060402002550 MHzACR-F (dB)