Title: Bytesteinen 1 - =514.202-FS001.pdf
Operator: ANDREAS PEDERSEN Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]46.4 235 14 7.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]22.4 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-4,5 8.4 228.5 33.8 4,5 8.2 229.0 30.8SR 3,6-4,5 8.3 76.0 41.9 4,5 8.8 74.0 39.3MAIN 1,2-4,5 8.4 228.5 33.8 4,5 8.2 229.0 30.8SR 1,2-3,6 8.6 242.0 33.4 1,2 9.7 242.0 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 14.6 226.5 16.2 4,5 15.5 210.5 13.8SR 7,8-4,5 14.3 226.5 16.2 4,5 15.9 204.0 14.1