Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Installation manual2.3Remote user interfaces (repeaters)The FPMCPU unit has an RS485 BUS which supports up to 15 repeater user interfaces.Each repeater provides the same functions as the FPMCPU module. Each repeater is constituted by an FPMCPU unit housed in an enclosure with a cover plate (PRREP). During the configuration phase each unit must be included in the system as a repeater.For the installation instructions refer to paragraph 5.2 Mounting a PRREP, repeater enclosure; for the electrical connections refer to paragraph 5.16 FPMCPU front-plate module wiring - repeater connection.Repeaters can be connected to the system also through a TCP-IP connection (refer to paragraph 2.6 Control Panels in an IP network).2.4Multi-cabinet control panelsThe capacity of the control panel can be expanded by affixing as many as 4 cabinets together.