Title: +175=324.001_KA001_Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.Produktinformasjon.pdf
Right of amendment reserved © 2015 Fr. Sauter AGProduct data sheetCombination of VUE with electric actuator with spring return, actuating power 500 NActuatorAVF124F130 AVF124F230AVF125SF132 AVF125SF232Actuating power500 N500 NControl signal3-point2-/3-pt., 0...10 V, 4...20 mARunning time60/120 s60/120 s∆p [bar]Closes against the pressure∆pmax∆ps∆pmaxVUE015F350 VUE015F340 VUE015F330 VUE015F320 VUE015F310 VUE015F3006.016.06.0VUE020F3006.011.06.0VUE025F3006.06.86.0VUE032F3005.25.25.2VUE040F3003.33.33.3VUE050F300 VUE050F2002.02.02.0Closes with the pressureVUE015F350 VUE015F340 VUE015F330 VUE015F320 VUE015F310 VUE015F300 VUE020F3006.016.06.0VUE025F3005.016.05.0VUE032F3004.016.04.0VUE040F3002.516.02.5VUE050F300 VUE050F2001.516.01.5A At temperatures above 100°C, accessories are requiredCombination of VUE with electric actuator, actuating power 1000 NActuatorAVM321F110 AVM321F112