Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 47,8 68,0 249,0 15,0 8,3Limit 100,0 - 555,0 50,0 25,0Margin 52,2 - 306,0 35,0 16,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 2,80Worst Value: Local: 45 20,9 43,6 22,7 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 25,5 18,6 6,9 30,25Remote: 12 16,3 9,9 6,4 260,00Worst Value: Local: 12 16,3 8,8 7,5 328,00Remote: 36 15,1 8,0 7,1 468,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass