Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
684 (> 500)622 (2 300)494 (= 100)5373491035043741038128188898078158890.760.580.210.740.600.210.660.430.120.620.460.12The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALuxPage 45Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Pactum / Visual task area 2 / Perpendicular illuminance (adaptive)Visual task area 2 / Perpendicular illuminance (adaptive)PLoX Surface Result Average Min Max Min/average Min/max Visual task area 2 Perpendicular illuminance (adaptive) [Ix] 704 537 812 0.76 0.66 Surrounding area: 0.500 m Surrounding area 2 Perpendicular illuminance (adaptive) [Ix] 602 349 818 0.58 0.43 Background area 2 Perpendicular illuminance (adaptive) [Ix] 491 103 889 0.21 0.12Wall zone: 0.500 mDIALuxPage 46