Title: 1 etg del 2.pdf
604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 8.1Cable ID: T1218 Date / Time: 10/17/2013 02:22:49 PM Headroom 11.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]69 110 8 2.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.6 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.3 51.8 37.0 36 13.4 99.3 29.4SR 12-36 11.2 99.0 32.4 36 13.3 99.3 29.4MAIN 12-36 11.3 99.0 32.4 36 13.4 99.3 29.4SR 12-36 11.2 99.0 32.4 36 13.3 99.3 29.4