Title: Ahlsell.pdf
80400500400250 MHz500100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 11.1Cable ID: UD 21 Test Limit: EN50173 PL2 Class Ea Limits Version: V3.0 Date / Time: 05/20/2022 03:41:37 PM Operator: Pam Headroom 5.3 dB (NEXT 3,6-7,8) Cable Type: Cat 6 F/UTP NVP: 70.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.6[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]41.6 202 4 7.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 1,2] [Pair 1,2] [Pair 1,2]21.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 5.3 463.0 30.0 3,6 7.1 461.0 27.2