Title: etg u1.pdf
Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]128 196 8 5.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]18.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.7 225.5 36.1 78 9.2 225.5 33.5SR 36-78 5.9 171.5 38.0 78 7.7 171.5 35.4MAIN 36-78 7.7 225.5 36.1 78 9.6 246.5 32.8SR 36-78 7.0 237.5 35.7 78 7.8 237.0 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.0 3.9 52.4 45 17.5 3.3 51.0SR 45-78 16.0 3.9 52.4 45 17.6 3.3 51.0MAIN 12-45 18.5 250.0 16.2 45 21.1 250.0 13.2SR 12-45 18.3 249.5 16.2 12 20.8 249.0 13.3010080604020050100150MHz