Title: 2 etg del2.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.9 * 249.5 35.4 36 1.2 249.5 32.7SR 36-450.7 *248.0 35.4 36 0.5 *244.5 32.9MAIN 36-45 0.9 249.5 35.4 36 1.2 249.5 32.7SR 36-45 0.7 248.0 35.4 36 0.5 248.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 11.1 19.1 38.6 45 13.8 2.8 52.4SR 45-36 11.1 19.1 38.6 45 13.6 2.5 53.2MAIN 45-36 16.6 150.5 20.6 36 19.9 189.5 15.6SR 45-36 16.3 152.0 20.6 36 18.4 185.5 15.8010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250