Title: etg u1.pdf
0050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 8.1Cable ID: D0204 Date / Time: 10/22/2013 12:20:23 PM Headroom 4.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]175 269 11 8.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]14.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.5 146.5 39.1 36 8.8 146.5 36.6SR 12-36 4.7 248.0 35.4 36 4.6 248.5 32.7MAIN 36-78 8.1 243.5 35.5 36 9.1 243.5 32.9SR 12-36 4.7 248.0 35.4 36 4.6 248.5 32.710080604020NEXT (dB)