Title: Hardware Installation Guide.pdf
4. Present a Lenel card to the reader. The LED will change from red to amber for about 1 second, then back to steady red when the card is removed.5. Experiment with the maximum distance from the reader at which the card reads. Record the test results.6.If the reader fails to meet Lenel’s specifications, contact Lenel’s Technical Support.Site TestInterchange two MR-1824 readers - Does the problem stay at the location or move with the reader?101.8.3SpecificationsMounting Surface-LPMR-1824: Non-metallic material only (Keep reader at least 3 inches from all metal) LPMR-1824 MC: Metallic material only (Metal plate, sheet or housing with surface at least 12 square inches; reader centered in area)Cable to Controller -5 to 7 conductors (not twisted pairs), stranded, 22 AWG, color-coded insulation, overall 100% shielded (Number of conductors depends upon use of optional features - Beeper, Hold and LED.) Length: up to 500 feetRead Range -LPMR-1824:–