Title: økernvn 94.pdf
6040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D4174 Date / Time: 09/09/2013 02:10:36 Headroom 6.7 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]199 305 12 9.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]11.8 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.6 143.0 39.3 36 8.8 210.5 34.0SR 36-78 6.7 162.0 38.4 36 7.7 196.5 34.4MAIN 12-36 8.7 218.0 36.3 36 9.1 247.0 32.8SR 36-78 6.9 249.5 35.4 36 8.4 249.5 32.710080604020NEXT (dB)