Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
After installing the run component, use mortar or fire-resistant plaster to fill the hole around and outside the fire-barrier kit. The material used to fill the hole must meet the applicable requirements in force (for example, DIN 1045 and DIN 1053-1) to maintain the fire-resistance rating of the partition wall or floor slab.QGH3492101-01 11/201865Specific ComponentsFire Barrier PositionTake note of the following points when installing the fire-barrier kit:  The fire-barrier kit must be positioned more than 200 mm from any joint block.  The position of the fire-barrier kit on a horizontal or vertical run component can be adjusted with respectto the partition wall or floor slab as indicated in the following graphic.Installing KTA5000/KTC6300 Fire Barriers