Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
NOTE: In tap-off units with PEN, you can remove the connection between the neutral and earth if needed.4Remove the IP protection on the outlet of the run component.5Prepare the output cable glands and connect the cables to the tap-off unit.6Check that the protection device is switched off and carefully inspect the tap-off unit for tools and objects that may have been left inside the tap-off unit.7Place the tap-off unit on the rear pivots and click it into the disconnected position on the clamping system. (seepage56)8Unlock the clamping system by pulling the attached flap and push the tap-off unit in the run component. The tap-off unit is in the connected position (seepage57).9Secure the tap-off unit onto the run component using bolts.10Lock the tap-off unit on the run component using the locking handle located inside the tap-off unit (seepage56).11Close the tap-off unit cover. The system and the load are ready to be energized.QGH3492101-01 11/201855Tap-off Units