Title: +038=534.001-RA001._02-Porttelefon Siedle Systemanvisning.pdf
Functional Viewing/monitoring a certain area using an Access indoor call station set up for the purpose. Each camera is specifically selected via the ATLC 670-… The number of cameras/Access users is limited by the server used. Using the buttons defined during configuration, each camera can be selected. This function must be con- figured for every authorized user.Notes on the circuit diagram p) Camera in continuous operation The camera used must be suit- able for continuous operation. Alternatively, the camera must be used in switching operation. (For detailed information, see page 80) • In addition, the camera should only be used in continuous opera- tion within its permitted operating parameters (e.g. ambient tempera- ture). (For detailed information, see page 35)y) Distance between the camera and AIVS 670-… max. 10 m13310.5 Camera connection External camera with video distributoro e d Vi1 V2 V+ –O 1 VO 2 VI 1 VI 2 V3 V4 V5 V6 VS / L1 V2 V3 V4 V5 V6 VS / L