Title: 32 Pumper modbuss teknisk data.pdf.pdf
DescriptionAmbient humidity30-95 %Operating temperature20 to +45 °CStorage temperature25 to +70 °CBattery, lithium-ionYou can only charge the battery if the battery temperature is between 0 and 45 °C.GENIbus visual diagnosticsLED2Power supply (CIU)24-240 VGENIbus connection type (CIU)RS-485, 3-wire + screenCIU box enclosure classIP54CIU box dimensions (H × W × D) 182 × 108 × 82 mm4.2 CIM 200 Modbus RTUThe table below provides an overview of the specifications for Grundfos CIM 200 and CIU 200. For further details, refer to the specific sections of this functional profile.Modbus RTU specificationsDescriptionModbus connectorScrew-type terminalModbus connection typeRS-485, 2-wire + commonMaximum cable length1200 mSlave address1-247Line terminationOn or OffRecommended cable cross- section0.20 - 0.25 mm2Supported transmission speeds1200*, 2400*, 4800*, 9600, 19200, 38400 bit/sStart bit1Data bits8Stop bits1 or 2Parity bit