Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
KONTINUITET R: 0.3ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF043 C16/2 12.06.2020 12:07R LOW OhmR: 0.29ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:32GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 218218219219220220221221222222223223224224TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 10.06.2020 11:24R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 10.06.2020 11:28SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 11.06.2020 16:28Z-LINEZ: 0.63ΩIsc: 366A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF044 C16/2 11.06.2020 16:28Zs(rcd)Z: 0.59ΩIsc: 389A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A