Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]8.7 37 0 1.55Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]36.9 495.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.7 449.0 30.3 36 9.7 496.0 25.2SR 12-45 7.3 449.0 30.3 36 7.8 482.0 25.8MAIN 12-45 10.3 491.0 28.3 36 9.8 497.0 25.1SR 36-45 7.3 481.0 28.7 45 8.1 493.0 25.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 15.9 3.8 53.8 45 14.3 2.5 54.3SR 45-78 15.9 4.8 51.7 45 14.2 2.4 54.7MAIN 12-45 17.1 500.0 11.3 45 16.7 500.0 8.3SR 45-12 17.0 498.0 11.3 45 16.5 471.0 8.80100806040200250 MHzACR-F (dB)