Title: etg u1.pdf
Project: OKERNVEIEN 94 ETG.U1 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: D0020 Date / Time: 10/21/2013 02:54:58 PM Headroom 14.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]168 266 19 7.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.6 91.5 32.9 36 15.7 92.0 29.9SR 12-36 18.2 25.1 42.1 36 19.7 27.3 38.5MAIN 12-36 15.1 99.5 32.3 36 16.1 99.8 29.3SR 12-36 19.4 83.8 33.6 12 20.7 83.8 30.610080604020NEXT (dB)