Title: +038=310.101-RF048._01-Siemens vannmåler WFK40.D080.pdf
CE1N5302en 2016-01-305302Mechanical water metersWFK40.. WFW40..Mechanical water meters to measure the consumption of hot or cold drinking water. • Permanent flow rate Q3 = 2.5 m3/h or 4 m3/h • Pulse add-on modules (optional) • No upstream and/or downstream settling paths required • Optional mounting position (horizontal or vertical) • Totalizer for indication of accumulated consumption in cubic meters andlitersBuilding TechnologiesApplicationFunctionType summaryCold water metersHot water metersAdd-on modules2 / 8Siemens Building TechnologiesThe impeller type cold and hot water meters are of compact design and are used for the physically correct acquisition of cold or hot water consumption. They consist of flow measuring section and processor.The meters measure the consumption of water in …-domestic water systems of residential or non-residential buildings any type of water supply system.Such systems are e.g. installed in ...multi-family houses, -