Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
2.5Control panels in a Hornet+ networkThe system can be expanded by simply connecting other control panels (maximum 48) in such a way as to constitute a system with increased capacity (Hornet+ network).When connecting two or more control panels in a Hornet+, it will be necessary to install an IFMNET module inside each control panel. These modules provide two RS485 ports for the loop (for the wiring description refer to paragraph 3.11 IFMNET, internal network connection module).For further information regarding the method used for connecting control panels in a network refer to the Previdia Max Networking Guide available at www.inim.biz2.6Control Panels in an IP networkSeveral control panels or Hornet+ networks of control panels can be connected together by means of a TCP- IP connection.InternetLANEach node in a connection of this type is identified as a “cluster”. Each cluster can consist of a single control panel, a Hornet network of control panels or a repeater.Router