Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Power supply to all modules Internal current consumption: from +5 V bus (without en- coder) Internal current consumption: from +5 V bus (without en- coder) External current consumption: 0...2 mA (without load current)typically 210 mA, max. 230 mA (250 mA in SSI operation)15 … 20 mA1 A for outputsThe total current consumption for all I/O modules including encoders must not exceed 1.6 A. PCD2.H32x modules should be plugged onto the base unit wherever possible (not the expansion housing). Operational conditions Ambient temperature0 … +55 °C without forced ventilation, -20 … +85 °COperation: Storage: CE mark acc. to EN 61 000-6-3 and EN 61 000-6-2 Based on PCD user program and pre-programmed function blocks (FB). Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²Noise immunity: Programming:Terminals:Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-110Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.H32x