Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Check that the protection device is switched off and carefully inspect the tap-off unit for tools and objects that may have been left inside the tap-off unit.54QGH3492101-01 11/2018Tap-off UnitsStepAction6Position the rear of the tap-off unit on the run component.7Plug the tap-off unit into the run component.8Lock the tap-off unit on the run component using the locking handle located inside the tap-off unit (seepage56).9Secure the tap-off unit on the run component using the fixing mechanism.10Close the tap-off unit cover. The system and the load are ready to be energized.Procedure for Installing Plug-In Tap-Off Units With Automatic Clamping SystemThe procedure for installing plug-in tap-off units with automatic clamping system is described in instruction sheets available on the Schneider Electric website. The list of instruction sheets can be found in the following table:Device installed in plug in-tap-off unit with automatic clamping systemTap-off unit rating