Title: +038=360.000-LC007T_04-Coadis line 600 Fan-coil CIAT - Manual.pdf
Circuit diagrams for customer applications should be based on the diagrams supplied: - Unit wiring for 2-tube systems , without condensate pump (Fig. 10). - Unit wiring for 4-tube systems , without condensate pump (Fig. 11). - Unit wiring for 2-tube systems with an electric heater using 2 heating elements, without condensate pump (P=900 or 1200W max) (Fig. 12). (cid:49)(cid:82)(cid:87)(cid:72)(cid:29) if necessary, the output of the 300W electric heater can be reduced by removing the shunt positioned between terminals 8 and 9. CIAT recommends using a system that controls the unit in relation to the temperature of the water (to actuate the valve(s)) and the use of an electric heater.All electrical connections are fed into the electrics box marked with the symbol . The electrics box is equipped with a cable grommet to facilitate the routing of the cables to the terminal block.