Title: økernvn 94.pdf
SR 45-36 7.6 66.3 27.8 45 10.5 60.3 25.6MAIN 45-36 11.2 244.5 16.4 36 14.0 244.5 13.4SR 45-36 11.5 247.5 16.3 45 12.6 208.0 14.8010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.7 17.4 46.6 36 9.6 19.3 43.1SR 12-36 8.2 19.1 45.6 36 9.2 19.1 43.2MAIN 36-45 15.6 249.5 4.7 36 15.4 249.0 2.1SR 36-45 15.7 249.5 4.7 36 15.7 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.4 15.6 20.0SR 45 2.8 15.5 20.0MAIN 36 8.5 171.0 11.7SR 36 8.7 242.5 10.2010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active