Title: Hardware Installation Guide.pdf
The second reader port can accommodate a read head that utilizes Wiegand or magnetic stripe signaling, one or two-wire LED controls, and buzzer control (one-wire LED mode, only). Two Form-C relay outputs may be used for door strike control or alarm signaling. The relay contacts are rated at a 5 Amp @ 30 VDC, dry contact configuration. Four (4) inputs are provided for monitoring the door contacts, exit push buttons, and alarm contacts. The LNL-1300e requires power from PoE or local 12 VDC.Notes:An alternative configuration of the LNL-1300e is available where no reader ports are used, and the device is deployed as an alarm panel with 4 inputs and 2 relay outputs.This product has been evaluated by UL for access control applications only.The LNL-1300e may be mounted in a UL Listed 3-gang switch box (a mounting plate is supplied with the unit). The controller may be mounted in an enclosure; the supplied mounting plate has mounting holes that match the LNL-1300 mounting footprint.65.1