Title: +038=30.001-NI003._16-V20-08-02 VVS-anlegg plan 8 - DM3.pdf
LD021T Maks:200 m³/h Kjøling: 260 W 0.020 L/sSTAP/STAD DN 20LD018T Maks:200 m³/h Kjøling: 260 W 0.020 L/s Varme: 600 W 0.014 L/s370.101: 22 mm +c 3450370.101: 22 mm +c 3450Overstrømning til åpent landskap0 5 4 30 5 4 3c + m m 8 2 : 1 0 1 . 0 7 3c + m m 8 2 : 1 0 1 . 0 7 3STAP/STAD DN 25320.102: 18 mm +c 3520 320.102: 18 mm +c 3520Møterom 8-010ø160 UK=33800 0 5 5 4 4 3 3SF002T-160SF002T-160SF002T-160SF002T-160WISE RTA WISE IAQSF002T-160SF002T-160WISE IAQ WISE RTAc c + + m m m m 2 2 2 2 : : 1 1 0 0 1 1 . . 0 0 7 7 3 3SF002T-160SF002T-160ø160 UK=3399 ø160 UK=3399 ø160 UK=3399 ø160 UK=3399Møte/revisor 8-011ø160 UK=3405LD018T Maks:165 m³/h Kjøling: 270 W 0.021 L/s Varme: 220 W 0.005 L/sLD018T Maks:165 m³/h Kjøling: 270 W 0.021 L/s Varme: 220 W 0.005 L/sLD021T Maks:150 m³/h Kjøling: 450 W 0.036 L/sWISE IAQ WISE RTAø160 UK=3399SF002T-160SF002T-160SF002T-160Møterom 8-126SF002T-160WISE RTA