Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
PCD2.W3x0Connection concept for two-wire transducersInput filterPressureE2ρ+0...20 mA24 VDCE1ϑTempera- tureE04...20 mA*GNDPCD2.W310/3404...20 mA over user programTwo-wire transducers need a 24 VDC-supply in the measuring trunk.Block diagram E0 E1 E2 E3 E4 E5 E6 E7r e i f i lr e t l i fp m at u p n Id n aX U MADDatas u B O/ I/IOOUITIODIN/IOWRITEIODOUTI/MS0IOA0IOA1IOA2IOA3s u B D C PGNDRsourceVoltage Source 10.000VRef. Voltage 2.500V+5V GNDW340, W350, W360 onlyProgrammingClassic: Programming examples for the PCD2.W3x0 can be found in a separate man-xx7: