Title: Data tester Smestad skole - Detaljert.pdf
Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:09Signature:______________________ Page: 107Copper Certification ReportCable Label: 521.002-UD-100 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:39:19 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 33,6 68,0 174,0 9,0 6,2Limit 100,0 - 555,0 50,0 25,0Margin 66,4 - 381,0 41,0 18,8Wiremap: T568B