Title: 10 FR Brannplate - Montasjeanvisning.pdf
FR Rørstruper 50 x 1.8mm (1 lag) 50 x 1.8mm (1 lag) 50 x 1.8mm (1 lag) 50 x 3.6mm (2 lags) 50 x 3.6mm (2 lags) 50 x 3.6mm (2 lags) 50 x 7.2mm (4 lags) 50 x 7.2mm (4 lags) 50 x 7.2mm (4 lags) 50 x 10.8mm (6 lags) 50 x 10.8mm (6 lags) 50 x 10.8mm (6 lags) 75 x 10.8mm (6 lags) 75 x 10.8mm (6 lags) 75 x 10.8mm (6 lags) 75 x 18.0mm (10 lags) 75 x 18.0mm (10 lags) 75 x 28.8mm (16 lags) 75 x 28.8mm (16 lags)Klassifisering EI 240 U/C (E 240 U/C) EI 240 U/C (E 240 U/C) EI 240 U/C (E 240 U/C) EI 240 U/C (E 240 U/C) EI 240 U/C (E 240 U/C) EI 240 C/C (E 240 C/C) EI 240 U/C (E 240 U/C) EI 240 U/C (E 240 U/C) EI 240 C/C (E 240 C/C) EI 240 U/C (E 240 U/C) EI 240 U/C (E 240 U/C) EI 240 C/C (E 240 C/C) EI 180 C/C (E 180 C/C) EI 180 C/C (E 180 C/C) EI 180 C/C (E 180 C/C) EI 120 C/C (E 120 C/C) EI 120 C/C (E 180 C/C) EI 120 C/C (E 120 C/C) EI 120 C/C (E 120 C/C)LINEÆRE FUGER BRANNMOTSTAND EI 180 (E 240)LINEÆRE FUGER BRANNMOTSTAND EI 120 (E 240)Maks 120mm bredt mellom gulvplater eller mellom gulvplate og vegg