Title: 32 Varmepumpe brukermanual.pdf.pdf
If a MMIGRS2 display is present the preferred way is to connect the M2M2 to the CANterminals on the MMIGRS2 display, as shown below:5M2M2-10, User Guide - Rev. 2020-09-04Direct connectionIf there is no MMIGRS2 display installed, the M2M2 may be directly connected to theAK2 controller as shown below:6M2M2-10, User Guide - Rev. 2020-09-04BACnet/IPConnect the Ethernet interface to your network if you want to integrate the AK2controller as a BACnet/IP device.Modbus TCPConnect the Ethernet interface to your network if you want to integrate the AK2controller as a Modbus TCP slave. By default the M2M2 is using slave id 1.Modbus RTUConnect the RS 485 (Slave) interface to your Modbus RTU network if you want tointegrate the AK2 controlleras as a Modbus RTU slave. By default the M2M2 is usingslave id 1 and running at 19 200 baud with 8 data bits, even parity and 1 stop bit.7M2M2-10, User Guide - Rev. 2020-09-04AdministrationAccessing the web interface