Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Check for any changes in the environment that can affect the busbar trunking system operation. Thesecould include the presence or appearance of water, moisture, high temperature, corrosive gas, excessive vibration, dust, air circulation, or new hot air sources. Inspect the external appearance of tap-off units.  Remove dust, water, oil deposits, and all other conductive bodies from the sensitive zones.  The contacts between the busbar trunking system and tap-off units do not need specific maintenance.The contacts consist of sprung silver plated contact jaws to ensure optimum contact quality.Procedures for Critical InstallationsMore specific maintenance procedures must be performed when the busbar trunking system feeds critical applications or in case of unfavorable environmental conditions.