Title: 26 Manual for takslukvakt.pdf.pdf
Modbus If connection to a Modbus RTU BMS system is required, a suitable RS485, cable must be used and connected to A, B, GND. If connection to a Modbus RTU BMS system is required, a suitable RS485 cable must be used and connected to A, B, GND.REV. 02 - MARCH 2021 - BLÜCHER® CONNECTED ROOF 95.2 MonitorWe recommend that one Monitor is installed next to each drain on your roof. Monitors should be installed at the primary drainage system and not at emergency outlets and drains. This gives the system the best conditions to evaluate the performance of the drainage system.10 BLÜCHER® CONNECTED ROOF - REV. 02 - MARCH 2021The Monitor should ideally be installed at the same invert level as the roof drain, giving the system the best conditions to measure the right water level. If this is not possible, and the Monitor ends up higher/lower than the roof drain, you will need to offset the water levels on the Monitor in the config file (see chapter 7.5).1. Clean Bracket 2. Clean Roof 3. Glue