Title: 1 etg del 2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]209 331 23 8.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.2 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.4 249.0 35.4 36 1.1 236.5 33.1SR 36-78 7.9 250.0 35.3 78 9.1 250.0 32.7MAIN 36-45 1.4 249.0 35.4 36 1.1 250.0 32.7SR 36-78 7.9 250.0 35.3 78 9.1 250.0 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 16.7 171.5 19.5 36 18.2 242.5 13.5SR 45-36 16.5 171.5 19.5 36 17.6 190.0 15.6MAIN 45-36 17.3 242.5 16.5 36 18.2 242.5 13.5SR 45-36 17.6 246.0 16.4 36 18.5 242.5 13.5010080604020050100150MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.0 14.0 48.9 36 11.1 18.6 43.5