Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
To complete the installation, all non-insulated ducts must be covered with anti-condensate insulation (ex. expanded neoprene, 6 mm thickness).If these instructions are not observed, condensate may drip. The manufacturer will not be held responsible for any damage caused.corresponding with the duct is closed, using the air supply outlet obstruction kit supplied. The kit cannot be used in units equipped with electric heater. An air inlet grille must be fitted (if possible near the floor) between the air conditioned room (where the unit is situated) and the adjacent room or, alternatively, the door must be undercut, as shown in the drawing.The duct lengths can be calculated in accordance with the “air distribution to an adjacent room” diagram, also taking into account the pressure drop through air diffusers and fresh air filters.