Title: DM1-3 plan 05 lysberegningsrapport.pdf
Consumption[240 - 390] kWh/aLighting power densityRoom3.97 W/m²Utilisation profile: Offices, Conference and meeting roomsLuminaire listpcs.Manufacturer Article No.Article name4Fagerhult22226-402Notor Rec Delta 3K 2400 white HL Single CLOTarget≥ 500 lx≥ 0.60≥ 300 lx≥ 0.40≥ 100 lx≥ 0.10max. 1800 kWh/aPΦ50.0 W4996 lmCheckLuminous efficacy99.9 lm/W44201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M1/M2 Visual task area 245201104 DM1-3 McKinseyBuilding 1 · Storey 1 · M1/M2 Visual task area 2PropertiesVisual task area 2 Perpendicular illuminance (adaptive) Height: 0.800 m, Surrounding area: 0.500 mSurrounding area 2 Perpendicular illuminance (adaptive) Height: 0.800 mBackground area 2 Perpendicular illuminance (adaptive) Height: 0.000 m, Wall zone: 0.500 mUtilisation profile: Offices, Conference and meeting roomsĒ(Target)583 lx (≥ 500 lx)313 lx (≥ 300 lx)171 lx (≥ 100 lx)Emin223 lx112 lx45.7 lxEmax898 lx750 lx