Title: økernvn 94.pdf
Cable ID: T3196 Date / Time: 09/11/2013 06:13:38 Headroom 1.5 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]185 281 8 8.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]13.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 4.4 40.0 48.3 36 6.7 250.0 32.7SR 36-78 1.5 244.5 35.5 78 3.7 244.0 32.9MAIN 36-78 5.6 243.5 35.5 36 6.7 250.0 32.7SR 36-78 1.5 244.5 35.5 78 3.7 244.0 32.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 9.2 1.8 59.3 45 11.0 1.5 57.7