Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 45-36 17.2 476.0 11.7 45 18.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 29.5 99.0 24.4 36 29.6 128.0 17.5SR 36-78 28.2 99.0 24.4 45 28.6 101.0 21.5MAIN 36-45 40.3 500.0 -12.4 36 40.6 497.0 -15.1SR 36-45 39.1 500.0 -12.4 45 39.7 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.8 445.0 8.0SR 12 6.0 445.0 8.0MAIN 12 7.8 445.0 8.0SR 12 6.0 445.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00420.6 m60Insertion Loss (dB)504030201000250 MHz500100