Title: 1 etg del 2.pdf
ACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.1 10.1 21.0SR 36 2.1 21.1 19.4MAIN 36 7.7 238.0 10.2SR 45 7.2 225.0 10.5010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94Cable ID: T1117 Date / Time: 10/21/2013 07:49:36 AM Headroom 14.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0