Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF030 C16/2 10.06.2020 11:03R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF030 C16/2 10.06.2020 11:11SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF030 C16/2 12.06.2020 11:19Z-LINEZ: 0.47ΩIsc: 489A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF030 C16/2 12.06.2020 11:20Zs(rcd)Z: 0.45ΩIsc: 512A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF030 C16/2 12.06.2020 11:20Tallberg Elektro A/S Tlf.22796640Side:14GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.9696979798989999100100101101102102TEST RAPPORTResultatRCD II: 28.5mAUci: 0.4V t: 41.3ms Idn: 30mA type: AC Ulim: 25V