Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
10 … 50 mA 10 … 40 mA24 V connection (Uext): This is located next to the 4 relays as screwless terminal“Uext”. The 24 V supply is common to the relay coils and the external supply to the analogue outputs.Current consumption:9 mA per relay 20 mA per analogue output(when the module is installed on sockets 1 … 4 on the PCD2).5-50PCD2.G410LEDs and connection terminalsThe terminal numbering refers to the use of the module on sockets 1 … 4 (top) on the PCD2. If the module is installed on sockets 5 … 8 (bottom), the value 64 must be added to the addresses given. When using the module in the PCD2.C100 expansion housing, the same logic applies, with the value 128 to be added to the ‘top’ and 192 to the ‘bottom’.A16A17A18A19COM E0E1E2E3E4E5E6E7E8E9 E10E11E12 E13 E14 E15----A32 A33 A34 A35----E48 E49 ----E50 E510123456789012345678901234567890123456789E610A200W410W2..U I