Title: Hydrauliske beregninger sprinkler Kontorer plan 3 78m².pdf
1613171820191920160152223242525242623272816142333436159k-factor C-factor Height[m]120196.0120200.6120200.6120200.6120200.6120200.6120200.6120200.6120200.6120200.6120200.6120195.8120195.8120195.8120195.8120195.8120195.8120195.8120195.8120195.8120195.8120195.8120195.8120195.8120196.0120196.0120196.0120196.0120196.0120196.0120196.0120196.0120196.0120196.0120196.0120200.6120196.4120196.4120195.4120196.4qv [l/min]12.0301.9128.0173.969.158.9128.064.563.5513.5449.012.66.96.920.15.714.410.14.33.36.810.114.426.918.413.19.05.63.44.19.05.313.118.48.5314.6173.7125.1125.1167.8v [m/s]0.00.60.40.50.20.20.40.20.20.90.80.10.10.10.20.10.10.10.10.10.10.10.10.20.10.10.10.00.1