Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF096 16C2/003 27.11.2020 10:13SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF096 16C2/003 27.11.2020 10:13Z-LINEZ: 0.39ΩIsc: 589A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF096 16C2/003 27.11.2020 10:13Zs(rcd)Z: 0.40ΩIsc: 580A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF096 16C2/003 27.11.2020 11:45Tallberg Elektro A/S Tlf.22796640Side:47GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.325325326326327327328328329329330330331331TEST RAPPORTResultat KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF096 16C2/003 30.11.2020 12:00 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩ