Title: Aggregat_360,002_SPC.pdf
7.600 m³/h RQM F3-4550-BI-YG 320 / 855 896 / 41 2,350 kW / P1 77,7 / 82,6 80,0 / 77,0 72,9 / 69,5 2,350 / 2,600 1.835 / 178 960 Pa 153 Hz 184 Hz220-55 / Default (IE5) / IP55 4,300 10,00 2.200 3x400 / 50Inspection window Diameter190 mmInspection window Diameter190 mmPlate exchanger with bypass flap / Aluminium SV-120/AX/1237/BSK137Heating mode: Volume flow, external air Pressu. loss external / Width byp intake Temperature °C / humi. % outlet Temperature °C / humi. % Efficiency rate humid / dry Heating output / Frost limit air Energy efficiency class7.600 m³/h 192 Pa / 14 cm -20,0 / 80 13,3 / 6 79,3 / 73 % 84,8 kW / -10,0 °C H2Heating mode: Volume flow, extraction air Pressure loss, extraction air intake Temperature °C / humi. % outlet Temperature °C / humi. %7.600 m³/h 198 Pa 22,0 / 30 -5,1 / 100Cooling mode: intake Temperature °C / humi. % outlet Temperature °C / humi. % Efficiency rate humid / dry Cooling output25,0 / 60 22,8 / 68 73,8 / 73,8 % 5,8 kW