Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
26.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.2 491.0 29.4 36 7.2 500.0 26.4SR 36-78 6.2 492.0 29.4 36 6.4 493.0 26.5MAIN 36-45 7.2 491.0 29.4 36 7.2 500.0 26.4SR 36-78 6.2 492.0 29.4 36 6.4 493.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.0 427.0 12.6 45 14.2 2.5 54.3SR 45-78 14.2 414.0 12.9 45 14.2 3.9 50.5MAIN 78-45 14.7 484.0 11.5 78 15.3 478.0 8.6SR 78-45 14.7 487.0 11.5 78 15.3 488.0 8.50100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 21.9 42.0 36.7 36 21.8 39.8 34.9SR 36-78 16.6 43.0 36.4 36 17.4 43.3 33.8MAIN 36-45 33.9 500.0 -12.4 36 33.6 500.0 -15.3SR 36-78 32.8 492.0 -11.9 36 32.6 493.0 -14.80804000250 MHzACR-N (dB)