Title: DOCA0005EN-12.pdf
1. Select Start > Programs > Schneider Electric > Mbus config tool (or navigateto the location where you installed the program) and click SE_iEM3135_3235_3335 Mbus Tool to open the tool. The login screen appears.2. Select the port on your computer that you are using to connect to the meter andselect the baud rate that matches the meter’s configuration.3. Click Test Com to open the communications port.4. Type the device address in the Address field.5. Select the communications mode that you want the tool to start in:– Monitor(Automatic): The tool automatically sends read requests to and receives data from the meter. You can set the interval at which these read requests are sent.– Monitor(Manual): You must manually send a read request to get data from themeter.– Config: The tool opens in configuration mode.You can change the mode from within the tool, if needed.6. Click OK to start the M-Bus tool and access the meter.DOCA0005EN-12103Communications via M-Bus