Title: 2 etg del2.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 11.6 50.8 36 8.5 15.5 45.5SR 12-36 6.7 11.6 50.8 12 8.6 11.6 48.4MAIN 36-45 10.2 248.0 4.9 36 10.0 249.0 2.1SR 12-36 10.3 244.5 5.2 36 9.8 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.9 14.1 20.3SR 45 1.4 14.3 20.2MAIN 36 6.9 223.5 10.5SR 45 6.5 224.0 10.5010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1