Title: 2 etg del2.pdf
20002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: T2020 Date / Time: 10/11/2013 09:33:42 AM Headroom 3.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]85 129 4 4.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]22.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 5.1 227.5 36.0 36 6.8 227.5 33.4SR 12-36 3.5 219.5 36.3 12 5.6 219.5 33.6MAIN 12-36 5.1 227.5 36.0 36 6.8 227.5 33.4SR 12-36 3.5 219.5 36.3 12 5.6 219.5 33.610080604020NEXT (dB)