Title: Tørrsprinkler.pdf
Blue360°F (182°C)Mauve1, 2, 3135°F (57°C)Orange155°F (68°C)RedUPRIGHT (TY3155)WITHOUT175°F (79°C)200°F (93°C)YellowGreen1, 2, 3, 4, 5286°F (141°C)Blue360°F (182°C)Mauve1, 2, 3Notes: 1. Listed by Underwriters Laboratories, Inc. (UL), maximum order length of 48 in. 2. Listed by Underwriters Laboratories for use in Canada (C-UL), maximum order length of 48 in. 3. Approved by FM Global (FM Approvals), maximum order length of 48 in. 4. Loss Prevention Certification Board (LPCB) and CE conformity apply to these temperature ratings only 5. Approved by the City of New York under MEA 352-01-E * Frame and deflector only N/A – Not ApplicableTABLE A SERIES DS-1 PENDENT & UPRIGHT DRY-TYPE SPRINKLERS, 5.6K, STANDARD RESPONSE LABORATORY LISTINGS AND APPROVALSPOLYESTER*1, 2, 4, 51, 21, 2, 51, 2, 4, 51, 21, 2, 4, 51, 2TFP500 Page 3 of 10SPRINKLER TYPEESCUTCHEON TYPETEMPERATURE RATINGBULB COLOR CODENATURAL BRASSSPRINKLER FINISHCHROME PLATEDPOLYESTER***