Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF091 Date / Time: 11-03-2020 19:52:28 Headroom 6.2 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 12] [Pair 45]11.7 50 0 2.01Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]35.1 494.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.8 468.0 29.4 36 7.4 468.0 26.5SR 36-45 6.2 458.0 29.8 36 6.7 458.0 27.0MAIN 36-45 7.6 487.0 28.5 36 8.1 488.0 25.5SR 36-45 6.8 476.0 29.0 36 8.2 499.0 25.010080604020NEXT (dB)