Title: Igangkjøringsprotokoller på sirkulasjonspumper V.2017.08.28.pdf
Real setp0|nt (head pressure): 26.50m Flow at preseted setpoint (all valves opened): 49.4m3/h Power consumption W: 5661W Head pressure at regular working cond. : 24.23m Flow at regular working cond. : 27.88m3/h [ vfnirie,nr me ; :Name: Audr|us Dan|u||s3 NSignature: =UAB ENSO PROJEETS REGISTRATION CODE 301340546, VAT LT1 00003637612 TILZES ST 41, IBAN LT35401 0042501594250, DNB BANKAS, SWIET AGBLL2XLT-47 182 KAUNAS, LITHUANIA TeL. : +370 37 322 258 WWW.ENSDBALTIC.COMIENSL]ENGINEERING SOLUTIONSPRE-STARTup check-list - CIRCULATION PUMPS Commissioning report No. DO 2 Date: [3/02/ ¥Service partner:Data : tallation AT G 3 Name of nstala n: Nltedal Do|| Address: Vargveien 1, 1488 Hakadal, Operational Manager: Audrius Daniulis Phone/e-mail: +370 676 19634 / audrius.daniulis@ensoprojects.com Required flow (designed): 50 m¥h [heating mode] Required head (designed): 10m Water temperature: 10°C Fluid: MEG 30% Operation mode: Open loop, delta TS T ILe5M10312Product No. : 97924318