Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]18.5 80 1 2.87Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]32.8 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.7 297.0 34.1 45 8.8 296.0 31.5SR 36-45 8.4 449.0 30.3 36 9.4 473.0 26.3MAIN 12-45 9.9 500.0 27.8 45 10.5 500.0 25.0SR 36-45 8.8 495.0 28.1 36 9.6 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 14.5 3.5 54.4 45 14.0 12.5 40.3SR 45-78 14.5 3.5 54.4 45 13.9 3.5 51.4MAIN 45-36 16.1 472.0 11.8 36 19.2 499.0 8.3SR 36-45 16.0 472.0 11.8 45 18.8 500.0 8.30100806040200250 MHzACR-F (dB)