Title: 2wayEPIV_Modbus-Register_en.pdf
www.belimo.comModbus-Register Description2-way EPIV EP..R+MOD P6..W..E-MODContentsModbus General Notes Modbus Register Overview Modbus Register DescriptionModbus-Register 2-way EPIV • en • v1.0 • 05.2018 • Subject to changes2-way EPIV2 3 41 / 62-way EPIVCommunicative characterised control valve with sensor- operated flow control, 2-way (EPIV)Modbus General NotesGeneral information Parameterisation:ZTH EUModbus RTU Protocol:Modbus RTU over RS-485Baud rate:9,600, 19,200, 38,400, 76,800, 115,200 Bd Default: 38,400 BdNumber of nodes:Max. 32 (without repeater)Address:1 ... 247 Default: 1Transmission formats:1-8-N-2, 1-8-N-1, 1-8-E-1, 1-8-O-1 Default: 1-8-N-2Terminating resistor:120 Quick addressing Actuators support quick addressing via the "Address" and "Adaption" buttons. Fordetailed, information please product datasheet (chapter Service).Register implementation All data is arranged in a table and addressed by 1..n (register) or 0..n-1 (address). No