Title: etg u1.pdf
SR 36-12 18.7 7.1 47.1 12 19.4 88.0 22.3MAIN 36-45 19.3 246.5 16.4 45 19.9 246.5 13.4SR 45-36 19.1 246.5 16.4 45 20.3 250.0 13.2010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.0 49.5 34.0 12 14.4 33.0 36.9SR 12-36 16.8 37.0 37.9 12 16.8 32.0 37.2MAIN 36-45 20.7 249.5 4.7 36 20.6 249.0 2.1SR 36-78 27.7 239.0 5.8 36 27.7 238.5 3.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.4 22.5 19.2SR 36 3.5 22.5 19.2MAIN 36 7.4 246.0 10.1SR 36 5.0 250.0 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active