Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF089 Date / Time: 11-03-2020 19:38:38 Headroom 7.3 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]17.3 75 1 2.80Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.4 457.0 29.9 45 9.2 409.0 28.4SR 36-45 7.3 457.0 29.9 36 7.8 457.0 27.1MAIN 36-45 8.9 476.0 29.0 36 10.3 499.0 25.0SR 36-45 8.9 497.0 28.0 36 8.5 498.0 25.110080604020NEXT (dB)