Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]26.2 113 1 3.90Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.3 471.0 29.2 36 7.0 457.0 27.1SR 36-45 7.1 471.0 29.2 36 7.7 457.0 27.1MAIN 36-45 7.8 498.0 27.9 36 7.6 497.0 25.1SR 36-45 7.9 498.0 27.9 36 8.3 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.3 6.1 49.5 45 21.3 7.4 44.9SR 45-78 19.3 7.4 47.9 45 21.3 6.1 46.5MAIN 12-36 24.3 476.0 11.7 45 25.5 500.0 8.3SR 36-12 24.5 476.0 11.7 45 25.3 500.0 8.30100806040200250 MHzACR-F (dB)