Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Z-LINEZ: 0.50ΩIsc: 457A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:31Zs(rcd)Z: 0.45ΩIsc: 507A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:32RCD UbUc: 0.0V Rl: 1Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:35SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:35Z-LINEZ: 0.52ΩIsc: 441A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:36Tallberg Elektro A/S Tlf.22796640Side:14GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.100100101101102102103103104104105105106106TEST RAPPORTResultatZs(rcd)Z: 0.49Ω