Title: +038=360.000-OU045T_01-PCD2.m4160 PLS SBC - Cables and Adapters Manual.pdf
Sink Operation (negative logic) is not supportedConnection of PCD2.A460For the off connection of PCD2/3.A460 the system cables PCD2.K231 (1 m) or PCD2.K232 (2 m) chapt. 2.1.2 are used. The «+» and the «–» of the Supply must be connected to the «+» and the «–» of the screw-terminal.The supply is only connected to the module when the Jumper JP1 is plugged to the position «Negative Logic»The supply is only connected to the module when the Jumper JP1 is plugged to the position «Negative Logic»3-4PCD2.K551 relay interface3.1.4 PCD2.K551 relay interface with relay type G2RL-1Relay interface to PCD2/3.A460 with 8 plug-in relays. The logical state of the relay is displayed with an LED:Relay switched on Relay switched offLED on LED off128550 1 2 3 4 5 6 7J1 2 4 6 8 10 12 14 16 1/3/ 5/7 9/11/ 13/15I/O 7 6 5 4 3 2 1 0+K0I/OJ1K1K2K3K4K5K6K701 04 02 11 14 12 21 24 22 31 34 32 41 44 42 51 54 52 61 64 62 71 74 72825 3PCD end:Process end: