Title: +038=433.002-FS024._02-Eaton Tavlebyggeren Produktblad.pdf
DATASHEET - NZMN2-4-VE160-BTCircuit-breaker, 4p, 160A, box terminals, selectivity protectionPart no. Catalog No.NZMN2-4-VE160-BT 147397EL-Nummer (Norway)4358842Similar to illustrationTechnical data General StandardsIEC/EN 60947Protection against direct contactFinger and back of hand proof to VDE 0106 Part 100Climatic prooﬁngDamp heat, constant, to IEC 60068-2-78 Damp heat, cyclic, to IEC 60068-2-30Ambient temperatureAmbient temperature, storage°C-40 - + 70Operation°C25 - +70Mechanical shock resistance (10 ms half-sinusoidal shock) according to IEC 60068-2-27g20 (half-sinusoidal shock 20 ms)Safe isolation to EN 61140Between auxiliary contacts and main contactsV AC500between the auxiliary contactsV AC300Weightkg3.5Mounting positionVertical and 90° in all directions