Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Description of the Previdia Max system partsHDGDH13Fire detection and extinguishant system[N]PCB CAN driveO[O]to the CAN drive bar of an upper cabinetPR[P]CAN connectorto the module on the front plateNS[Q]to the CAN drive bar of a lower cabinetS[R][S]Connector for IFM internal moduleto the power- supply module, if present or any modulefor all modules except the power supply moduleSSSPRACAB - technical specificationsDimensions433 x 563 x 187 mmWeight10KgSProtection ratingIP30QSAccepted Batteries2 x 12V 24Ah, NPL24-12I or equivalent or 2 x 12V 17 Ah, NP 17 -12-FR or equivalent3.2PRCABSP, PRCABRK, accessories for mounting the cabinetThe PRCABSP kit allows you to distance the cabinet 5cm from the wall thus creating a space between the cabinet and its placement. Consists of three pieces to be assembled together before mounting the control panel cabinet.