Title: Våtventil Brukermanual.pdf
Failure to follow these instructions can cause product failure, resulting in serious personal injury and/or property damage.GENERALMAINTENANCE AND TESTING2 .1 . Read and understand all instructions and refer to the trimdiagrams before proceeding with the installation, maintenance, and testing of this Victaulic Series 751 FireLock European Alarm Check Valve Station.Inspect the shipment. Make sure all components are included in the shipment and that all necessary tools are available for installa- tion .3 . Use only recommended accessories. Accessories and equipment that are not approved for use with this alarm check valve may cause improper system operation .4 . Wear safety glasses, hardhat, foot protection, and hearing pro-tection. Wear hearing protection if you are exposed to long periods of noisy job-site operations .2 .