Title: 360.001 - Tilluft.pdf
1k [dB]35.441.00.01.8 +21.521.53.0 +21.523.30.0 +21.525.51.0 +21.526.30.2 +21.527.4+18.027.90.0 +21.528.83.0 +21.527.10.3 +21.52k [dB]31.350.00.01.8 +20.520.53.0 +20.522.20.0 +20.524.51.0 +20.525.20.2 +20.526.3+13.326.50.0 +20.527.53.0 +20.526.00.3 +20.54k [dB]25.145.00.01.8 +16.516.53.0 +16.518.30.0 +16.520.51.0 +16.521.20.2 +16.522.3+3.422.40.0 +16.523.43.0 +16.521.90.3 +16.58k [dB]17.032.00.01.8 +9.59.83.0 +9.511.30.0 +9.513.51.0 +9.514.30.2 +9.515.4+2.115.60.0 +9.516.53.0 +9.515.00.3 +9.5Lp [dB]2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeType86 T-BRANCHDUCT87 T-BRANCHDUCT88 SUPPLYDUCT89 T-BRANCHDUCT90 SUPPLYDUCTProductTCPU-315-315MAGID-C1-315TCPU-315-315MAGID-C1-315FKV-315 CoolingMAGID-C1-315TCPU-315-315MAGID-C1-315FKV-315 Cooling