Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]26.0 112 1 4.01Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]29.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.3 472.0 29.2 36 7.7 463.0 26.8SR 36-78 11.8 94.3 42.3 36 11.2 471.0 26.4MAIN 36-45 8.8 498.0 27.9 36 8.5 500.0 25.0SR 12-36 12.2 500.0 27.8 36 12.2 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.4 5.9 49.9 45 20.3 500.0 8.3SR 45-78 18.5 6.3 49.3 45 20.5 500.0 8.3MAIN 78-45 19.8 500.0 11.3 45 20.3 500.0 8.3SR 78-45 20.0 500.0 11.3 45 20.5 500.0 8.30100806040200250 MHzACR-F (dB)