Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 21.2 43.8 36.1 36 21.7 40.0 34.8SR 36-78 22.7 40.5 37.1 36 22.0 40.0 34.8MAIN 36-45 34.1 500.0 -12.4 45 34.0 500.0 -15.3SR 36-45 33.6 500.0 -12.4 36 34.1 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.3 443.0 8.0SR 45 6.5 473.0 8.0MAIN 45 5.3 443.0 8.0SR 45 6.5 473.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: New Project10 Etg tester..flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00435.1 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)