Title: 564 SAS_81622 Relemodul 8x16A.pdf
Incandescent lamp load Uncompensated Parallel compensated DUO circuit Inductive transformer Electronic transformer Halogen 230 V Uncompensated Parallel compensated Uncompensated Parallel compensated Maximum peak inrush current Ip (150 µs)Number of ballasts (T5/T8, single ele- ment)Maximum peak inrush current Ip (250 µs) Maximum peak inrush current Ip (600 µs) 18 W (ABB ballast 1 x 18 SF)Energy-saving lamps Rated motor power24 W (ABB ballast T5 1 x 24 CY) 36 W (ABB ballast 1 x 36 CF) 58 W (ABB ballast 1 x 58 CF) 80 W (Helvar EL 1 x 80 SC) LED lampsNoteThe peak inrush current Ip is the typical ballast load current that results during switching. Using the peak inrush current Ip, it is possible to calcu- late the maximum number of switchable bal- lasts at the Switch Actuator output for the vari- ous ballast types. The number of ballasts speci- fied in the table can be only a sample guide value.