Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 27.11.2020 12:03R LOW OhmR: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 27.11.2020 12:03KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF031 16C2/003 30.11.2020 09:55SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF031 16C2/003 30.11.2020 09:55Tallberg Elektro A/S Tlf.22796640Side:14GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.979798989999100100101101102102103103TEST RAPPORTResultatZ-LINEZ: 0.83ΩIsc: 277A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF031 16C2/003 30.11.2020 09:56Zs(rcd)Z: 0.81ΩIsc: 284A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A