Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36-45 30,2 26,7 3,5 499,00Worst Value: Local: 36-45 29,4 26,7 2,7 499,00Remote: 36-45 30,2 26,7 3,5 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 22,2 11,1 11,1 452,00Remote: 12-45 24,4 13,5 10,9 343,00Worst Value: Local: 12-45 22,0 11,0 11,0 455,00Remote: 12-45 22,3 11,0 11,3 455,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,2 23,9 3,3 496,00Remote: 36 28,8 23,9 4,9 496,00Worst Value: Local: 36 27,2 23,9 3,3 496,00Remote: 36 28,7 23,8 4,9 499,00PS-ACRF: Pass Worst Margin: Local: 36 73,0 61,2 11,8 1,00Worst Value: Local: 45 20,3 8,0 12,3 459,00Remote: 12 72,3 61,2 11,1 1,00Remote: 45 20,8 7,9 12,9 462,00