Title: økernvn 94.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]168 266 18 6.9168 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.7 * 238.5 35.7 36 0.7 * 248.0 32.8SR 36-78 7.7 243.0 35.5 78 9.4 243.0 32.9MAIN 36-45 0.8 248.5 35.4 36 0.7 248.0 32.8SR 36-78 7.7 243.0 35.5 78 9.4 243.0 32.910080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 9.2 1.8 59.3 36 11.7 1.6 57.0SR 36-45 9.3 1.8 59.3 36 11.8 1.6 57.0MAIN 45-36 13.6 165.0 19.8 36 16.2 164.5 16.9SR 36-45 13.9 165.0 19.8 45 17.8 227.0 14.1010080604020050100150MHzACR-F (dB)200250010080604020