Title: 360.002 - Tilluft.pdf.pdf
22.00.3 +17.323.03.0 +17.321.92.0 +17.321.73.0 +17.321.10.0 +17.322.63.0 +17.3Lp [dB]LocationLevelTeknisk etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeProductSizeDUCT5002 T-BRANCHTCPU_DK-*-*0,0 500/400DUCT400FIREDAMPER FKR-EU/DE/400/400DUCT400REDUCERMAGIR-CC1-*-* 400/315DUCT315BEND-90MAGIB-C4-*-*315DUCT3153 FLOWDAMPER LEO-0-315315L [m]0,20,10,00,41,3Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]36005,10,1 Sound in:Attenuation: Addition:36005,116,4 Sound in:Attenuation: Addition:Dividing:12002,70,0 Sound in:Attenuation: Addition:12002,71,1 Sound in:Addition:12002,70,0 Sound in:Attenuation: Addition:12002,70,4 Sound in:12004,30,3 Sound in:Attenuation: Addition:12004,32,8 Sound in:Attenuation: Addition:12004,30,9 Sound in:Attenuation: Addition:12004,311,5 Sound in: