Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
MAIN 12-36 8.7 500.0 29.2 36 8.7 500.0 26.4SR 12-36 10.1 467.0 29.9 36 9.0 468.0 27.0MAIN 12-36 8.7 500.0 29.2 36 8.7 500.0 26.4SR 12-36 10.1 467.0 29.9 36 9.4 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.6 488.0 11.5 45 19.6 500.0 8.3SR 78-45 20.4 500.0 11.3 45 19.9 500.0 8.3MAIN 78-45 20.7 500.0 11.3 45 19.6 500.0 8.3SR 78-45 20.4 500.0 11.3 45 19.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.3 33.8 39.4 36 19.5 33.8 36.9SR 36-45 18.7 33.8 39.4 36 19.5 33.8 36.9MAIN 12-36 33.4 500.0 -12.4 36 33.3 499.0 -15.2SR 36-45 35.5 500.0 -12.4 36 34.0 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.5 494.0 8.0SR 45 8.2 441.0 8.0MAIN 45 8.5 494.0 8.0SR 45 8.2 441.0 8.040010080250 MHz