Title: 365 R›ykmeldere i ventilasjon monteringsveiledning.pdf
The UG-3-A5O model shall be power supplied thru a disconnect device, next to the smoke detector, marked: ”Disconnect device for smoke detector UG-3-A5O”.Test of detector.Check the detector with smoke detector tester RDP-300.Open the "test hole plug" and briefly release a spray of aerosol. When alarming the LED lits red on the printed circuit board and the detector, and when service alarming it lits yellow on the printed circuit board and green on the smoke detector.Open the "test hole plug" and briefly release a spray of aerosol. When alarming the LED lits red on the printed circuit board and the detector, and when service alarming it lits yellow on the printed circuit board and green on the smoke detector.Reset by pressing the black reset button in the cover over the printed circuit board.Reset by pressing the black reset button in the cover over the printed circuit board.IMPORTANT!Reassemble the "test hole plug".