Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 78-36 15.9 485.0 11.5 45 15.2 4.5 49.2SR 36-78 16.2 485.0 11.5 45 15.3 3.8 50.8MAIN 78-36 15.9 485.0 11.5 45 17.6 488.0 8.5SR 36-78 16.2 485.0 11.5 78 17.9 488.0 8.50100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.7 43.5 36.2 45 24.0 43.5 33.8SR 45-78 22.0 46.0 35.5 45 22.5 39.8 34.9MAIN 36-45 31.5 499.0 -12.3 36 32.3 498.0 -15.1SR 36-45 33.8 498.0 -12.3 36 33.5 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 7.2 481.0 8.0SR 12 5.7 498.0 8.0MAIN 12 7.2 481.0 8.0SR 12 5.7 498.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS