Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12-36 21,1 10,5 10,6 483,00Worst Value: Local: 12-36 21,4 10,5 10,9 486,00Remote: 12-36 21,0 10,5 10,5 485,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,8 3,8 497,00Remote: 36 29,2 23,8 5,4 498,00Worst Value: Local: 36 27,6 23,8 3,8 497,00Remote: 36 29,2 23,8 5,4 499,00PS-ACRF: Pass Worst Margin: Local: 12 72,1 61,2 10,9 1,00Worst Value: Local: 12 20,1 7,4 12,7 487,00Remote: 45 71,5 61,2 10,3 1,00Remote: 36 19,7 7,5 12,2 483,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:13Signature:______________________ Page: 131Copper Certification ReportCable Label: 521.002-UD-28 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:06:27 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein