Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12 13,6 8,7 4,9 335,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,8 26,7 3,1 500,00Remote: 36-45 29,0 26,7 2,3 499,00Worst Value: Local: 36-45 29,8 26,7 3,1 500,00Remote: 36-45 29,0 26,7 2,3 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 29,3 18,7 10,6 188,50Remote: 45-12 29,9 18,7 11,2 187,50Worst Value: Local: 12-45 22,8 10,5 12,3 484,00Remote: 12-45 23,7 10,5 13,2 484,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,2 23,8 4,4 499,00Remote: 45 28,1 23,8 4,3 499,00Worst Value: Local: 36 28,2 23,8 4,4 499,00Remote: 45 28,1 23,8 4,3 499,00