Title: Data tester Smestad skole - Detaljert.pdf
Insertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,8 3,0 2,2 1,90Worst Value: Local: 45 19,4 43,6 24,2 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 16,9 9,1 7,8 311,00Remote: 78 18,4 12,8 5,6 132,50Worst Value: Local: 12 16,6 8,0 8,6 452,00Remote: 78 15,9 8,4 7,5 363,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,1 26,7 2,4 499,00Remote: 36-45 29,6 26,7 2,9 497,00Worst Value: Local: 36-45 29,1 26,7 2,4 499,00Remote: 36-45 29,6 26,7 2,9 497,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 68,9 59,3 9,6 1,75Remote: 45-12 67,8 57,3 10,5 2,20