Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
100RL @ Remote (dB)8060402050000250 MHz500LinkWare™ PC Version 10.1Cable ID: =521.04.05-UF073 Date / Time: 27-11-2022 14:21:15 Headroom 5.2 dB (NEXT 36-78) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]23.1 101 2 3.65Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]30.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.2 184.5 37.5 78 6.9 184.5 34.9SR 36-78 5.5 183.0 37.6 36 7.2 183.0 35.0MAIN 12-36 8.5 498.0 27.9 36 8.5 499.0 25.0SR 12-36 8.5 462.0 29.6 36 9.2 499.0 25.010080604020NEXT (dB)