Title: +038=370.101-OE002T_02-Multical 801 Energimåler Kamstrup - Teknisk beskrivelse.pdf
Flow meter coding (CCC-table)Kamstrup A/S · Technical Description · 5512-571_R1_GB _11.2016B1 2 3 4 5CCC (V1)CCCMULTICAL® 801CCC (V1)CCC15MULTICAL® 8013.3.1 CCC-TABLE FOR MULTICAL 801The CCC-tables are divided into quick codes (CCC=4XX and 1XX) for electronic meters, e.g. ULTRAFLOW, and slow codes for e.g. reed contacts (CCC=0XX).CCC= 4XXElectronic meters with quick and bounce-free pulses as well as info codes for ULTRAFLOW X4 Max. pulse frequency: 128 HzMax. integration frequency: 1 HzCCC= 1XXElectronic meters with quick and bounce-free pulsesMax. pulse frequency: 128 HzMax. integration frequency: 1 HzCCC= 0XX Mechanical meters delivering slow pulses with bounce (flow sensor type "L")Max. pulse frequency: 1 HzMax. integration frequency: 1 HzMax. integration frequency is 1 Hz for all types. The CCC-codes have been so composed that qs+20 % (or Qmax+20 %) does not exceed an integration frequency of 1 Hz.