Title: 36 Siemens GDB181-MO.pdf.pdf
Open / Close (depends on opening direction)GoToMin / GoToMax (depends on Min/Max settings)Stop35 / 40VAV Compact Controller Modbus RTUA6V10631862_en--_d 2019-09-1336 / 40Siemens Smart InfrastructureAdaptive positioning on: Any position is commanded and reported relative to the actual minimum and maximum position.Adaptive positioning on: Any position is commanded and reported relative to the actual minimum and maximum position.Example A: The minimum position is 24° and the maximum position is 90°à the absolute position 24° is commanded and reported as 0% à the absolute position 43° is commanded and reported as 29%.Example B: The minimum position is 24° and the maximum position is 60°à the absolute position 24° is commanded and reported as 0%. à the absolute position 43° is commanded and reported as 53% = (43°-24°) /(60°-24°).Using adaptive positioning makes the actuator driving to its end positions at the first startup after activating the adaptive positioning.