Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.9 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.9 461.0 30.0 36 9.5 492.0 26.5SR 36-45 6.7 489.0 29.5 36 7.2 486.0 26.7MAIN 12-45 10.0 479.0 29.6 36 9.5 492.0 26.5SR 36-45 6.7 489.0 29.5 36 7.3 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 16.6 9.8 45.5 45 15.2 4.5 49.2SR 36-45 16.6 37.0 33.9 45 15.0 3.8 50.8MAIN 78-36 17.0 500.0 11.3 45 17.4 466.0 8.9SR 36-78 17.3 500.0 11.3 78 17.8 477.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 22.6 34.5 39.1 45 22.4 34.0 36.9SR 36-45 25.0 33.5 39.5 45 25.2 36.8 35.9MAIN 36-45 35.5 499.0 -12.3 36 34.3 492.0 -14.7