Title: Simployer - Data testrapport =514.204-FS001.pdf
35.3 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD40 Date / Time: 28/01/2022 12:33:48 Headroom 10.1 dB (NEXT 1,2-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]35.3 181 13 6.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-4,5 10.5 83.5 41.3 1,2 11.8 83.8 38.4SR 1,2-7,8 10.1 59.8 43.7 1,2 10.6 59.8 40.9MAIN 1,2-3,6 12.4 250.0 33.1 1,2 13.1 250.0 30.2SR 1,2-3,6 11.1 229.0 33.8 1,2 11.9 249.5 30.2