Title: bn303_cgb.pdf
Refer to specification for Autroprime or AutroSafeMaximum input cable length10m, non-shielded or shielded. End termination 2kohms +/-5%Maximum cable capacitance10nFResponse time<= 1 secondThresholdShort-circuit: 0-235 Ω Activate: 260-1000 Ω Normal: 1200-4800 Ω Open circuit: 5400-∞ ΩApprovalsSee Autronica’s website0333Autronica Fire and Security AS, N-7483 Trondheim 08 0333-CPR-075249EN 54-17:2005 Short circuit isolators EN 54-18:2005 Input/output devicesProduct name BN-303Part number 116-BN-303Description Single monitored input unit6571-011.6020116-6571-011.6020Membrane gland TSS M20, greyOptional6571-011.1920116-6571-011.1920Gland IP676531-006.1920116-6531-006.1920Backnut for glandAutronica Fire and Security AS | Tel.: +47 90 90 55 00 | E-mail: info@autronicafire.no | www.autronicafire.com | Page 2Single Monitored Input Unit – BN-303Dimension (mm)ConnectorsTerminal 1Description AL_Com In (+)2AL_Com In (-)3AL_Com Out (+)4