Title: Data tester Smestad skole - Detaljert.pdf
Length (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 49,3 68,0 255,0 13,0 8,5Limit 100,0 - 555,0 50,0 25,0Margin 50,7 - 300,0 37,0 16,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,9 3,0 2,1 1,90Worst Value: Local: 45 20,8 43,7 22,9 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 17,3 10,2 7,1 239,00Remote: 78 14,3 8,0 6,3 486,00Worst Value: Local: 12 16,4 9,3 7,1 297,00Remote: 78 14,3 8,0 6,3 486,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,5 26,7 1,8 499,00Remote: 36-45 29,6 26,7 2,9 499,00Worst Value: Local: 36-45 28,5 26,7 1,8 499,00Remote: 36-45 29,6 26,7 2,9 499,00dB 0601200Local250500 MHzdB 0601200