Title: 564 DGS_x6411 Dali Gateway Basic.pdf
Cable cross-section 1,5 mm2KNXDALI outputs and Mains voltageTightening torqueButtonPush button/LED(red)LED(green)LED(yellow)IP 20IIOvervoltage categoryPollution degreeSELV 24 V DCTypical 16 V DC (12…20.5 V DC)No-load voltageLowest supply current at 12 V DCHighest supply currentOperationStorageTransportEN 62386 Parts 101ed2 and 103ed1100 – 240 V AC85…265 V AC, 50/60 Hz 110…240 V DCDG/S 1.64.1.1DG/S 2.64.1.1maximum 6 Wmaximum 11 Wmaximum 25 mAmaximum 48 mAmaximum 2 Wmaximum 4 Wmaximum 10 mAmaximum 210 mWDG/S 1.64.1.1DG/S 2.64.1.112230 V ACMaximum 64 per output to EN 62386; DALI devices for emergency lighting with individual battery to EN 62386-202 are supported.1)100 m2)150 m2)200 m2)300 m2)KNX connection terminal, 0.8 mm Ø, single coreScrew terminal, universal head 0.2…4 mm2 0.2…6 mm2fine stranded single coreMax. 0.6 NmDALI output testFor allocation of the physical KNX addressOperation readiness indicator