Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]19.9 87 2 3.16Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.0 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.8 476.0 29.0 36 8.0 464.0 26.7SR 36-45 6.2 493.0 28.2 36 6.8 492.0 25.4MAIN 36-45 8.6 499.0 27.9 36 8.9 499.0 25.0SR 36-45 6.2 493.0 28.2 36 6.9 493.0 25.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.0 5.9 49.9 45 17.9 4.4 49.4SR 45-78 18.1 8.0 47.2 45 17.9 3.5 51.4MAIN 78-45 18.8 500.0 11.3 78 19.5 490.0 8.4SR 78-45 18.8 500.0 11.3 36 19.7 490.0 8.40100806040200250 MHzACR-F (dB)