Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 30.11.2020 10:16SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 30.11.2020 10:16Tallberg Elektro A/S Tlf.22796640Side:13GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.9090919192929393949495959696TEST RAPPORTResultatZ-LINEZ: 0.70ΩIsc: 328A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 30.11.2020 10:17Zs(rcd)Z: 0.71ΩIsc: 323A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 30.11.2020 10:29RCD II: 28.5mAUci: 0.2V t: 103.8ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF030 16C2/003 30.11.2020 11:53 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254V