Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF080 16C2/003 27.11.2020 10:23Z-LINEZ: 0.40ΩIsc: 580A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF080 16C2/003 27.11.2020 10:23Tallberg Elektro A/S Tlf.22796640Side:31GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.214214215215216216217217218218219219220220TEST RAPPORTResultatZs(rcd)Z: 0.40ΩIsc: 577A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF080 16C2/003 27.11.2020 10:24RCD II: 28.5mAUci: 0.3V t: 22.3ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF080 16C2/003 27.11.2020 11:48R LOW OhmR: 0.15ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF080 16C2/003 27.11.2020 11:49KONTINUITET R: 0.1ΩGrenseverdi: 0.7Ω