Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
Isc: 475A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF021 C16/2 15.06.2020 13:16R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF021 C16/2 15.06.2020 13:03Tallberg Elektro A/S Tlf.22796640Side:6GODKJENTGODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.4444454546464747484849495050TEST RAPPORTResultat KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF021 C16/2 15.06.2020 09:54Zs(rcd)Z: 0.40ΩIsc: 577A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF021 C16/2 15.06.2020 09:39Zs(rcd)Z: 0.41ΩIsc: 565A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM1.E5.433.09.04 / XF021 C16/2 16.06.2020 09:44R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩ