Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 21,8 11,3 10,5 440,00Remote: 45-12 22,1 11,3 10,8 440,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,2 23,8 4,4 498,00Remote: 36 28,7 23,8 4,9 498,00Worst Value: Local: 36 28,2 23,8 4,4 500,00Remote: 36 28,7 23,8 4,9 500,00PS-ACRF: Pass Worst Margin: Local: 12 67,7 56,3 11,4 1,75Worst Value: Local: 12 20,5 8,3 12,2 440,00Remote: 12 64,9 54,3 10,6 2,20Remote: 12 20,1 8,3 11,8 440,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:11Signature:______________________ Page: 116Copper Certification ReportCable Label: 521.002-UD-85 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:44:50 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: