Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
if the module is mounted in the lower aperture and another module is mounted in the upper aperture, the CAN BUS wire must be connected between module port ([D], paragraph 3.4 - [N], paragraph 3.5 - [D], paragraph 3.10 - [N]) and the appropriate port on the upper module ([E], paragraph 3.4 - [O], paragraph 3.5 - [E], paragraph 3.10 - [O])F4. Fit the ferrite ([F], supplied) to the connected CAN BUS cable.5.In the case of an FPMCPU module, complete the wiring on the LAN cable and BUS (refer to paragraph 5.16).InstallationBEDFAFAC33Mounting IFM internal modulesThe internal modules (IFM24160, IFM2L, IFM4R, IFM4IO, IFMDIAL, IFM16IO, IFMNET, IFMLAN, IFMEXT) must be mounted in the special compartment inside the cabinet (paragraph 3.1 - [K]). There are two bars on either side of the compartment for mounting and connecting modules (paragraph 3.1 - [J] - [L]), up to 8 per cabinet.1.