Title: FDV 16678-4.pdf
25 - +70 Terminal capacities mm2 Solid mm2 0.75 - 2.5 Stranded mm2 0.5 - 2.5 Flexible with ferrule mm2 0.5 - 1.5 Contacts Rated impulse withstand voltage Uimp V AC 6000 Rated insulation voltage Ui V 500 Overvoltage category/pollution degree III/3 Control circuit reliability at 24 V DC/5 mA HF Faultprobability < 10-7 (i.e. 1 failure to 107 operations) at 5 V DC/1 mA HF Faultprobability < 5 x 10-6 (i.e. 1 failure in 5 x 106 operations) Max. short-circuit protective device Fuseless Type PKZM0-10/FAZ-B6/1 Fuse gG/gL A 10 Switchingcapacity Rated operational current Ie A AC-15 115 V Ie A 6 220 V 230 V 240 V Ie A 6 380 V 400 V 415 V Ie A 4 500 V Ie A 2 DC-13 24 V Ie A 3 42 V Ie A 1.7 60 V Ie A 1.2mm2mm2500Max. miniature circuit-breakerIth = IeDifferentratedoperationalcurrents when used as auxiliary contact for NZMcircuit-breakerOperating times1 x (0,75 - 2,5)2 x (0,75 - 2,5)0.311/06/2016216376 - HPL-ED2016 V26.0 EN3 / 5Terminal capacitiesV AC