Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
24 VDC (15…30 VDC) smoothed or pulsed 24 VDC (15…30 VDC) smoothedmax. 10 % residual ripple48 VDC (30…60 VDC) smoothedmax. 10 % residual ripple5 VDC (7.5…15 VDC) smoothedmax. 10 % residual rippleSupply voltage: for source operation: for sink operation: Input current: (at input voltage) for source operation: for sink operation: Input delay (0-1/1-0):Resistance to interference: acc. to IEC 801-4E613: 30 V 36 V E613:E611: 15 V 18 V E611:E616: 3 V 3.6 V E616:E610: 15 V 18 V E610: (24 VDC) (24 VDC) (48 VDC) (5 VDC) 5 mA 8.4 mA 5 mA 3.7 mA 6.2mA 3.7 mA E611: E616: E610: 0.2 ms 0.2 ms 10 ms on. off. 1.0 ms 1.0 ms 10 ms 4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group)min. min.2 mA 1.5 mA E613: 9 ms 9 msElectrical isolation voltage: Optocoupler isolation voltage:1000 VAC, 1 min. 2.5 kV Galvanic separation of outputs to Saia PCD®. The channels themselves not are separated.Internal current consumption: (from +5 V bus)1 … 24 mA typ. 12 mA