Title: 2 etg del2.pdf
Cable ID: T2007 Date / Time: 10/11/2013 07:58:15 AM Headroom 8.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]240 366 13 11.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]8.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.1 248.5 35.4 78 9.0 244.0 32.9SR 12-78 9.8 211.5 36.5 78 9.0 237.0 33.1MAIN 36-78 8.1 248.5 35.4 78 9.0 244.0 32.9SR 12-36 10.3 245.0 35.5 78 9.0 237.0 33.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.4 102.5 24.0 36 17.5 3.8 49.7