Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]44.0 190 2 6.26Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]21.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.8 449.0 30.3 36 7.4 500.0 26.4SR 12-36 7.8 496.0 29.3 36 7.9 495.0 26.5MAIN 12-36 7.7 500.0 29.2 36 7.4 500.0 26.4SR 12-36 7.8 496.0 29.3 36 7.9 495.0 26.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 18.2 461.0 12.0 45 20.3 494.0 8.4SR 78-45 18.4 455.0 12.1 45 19.8 453.0 9.1MAIN 78-45 18.3 500.0 11.3 45 20.4 500.0 8.3SR 78-45 18.7 500.0 11.3 45 20.0 500.0 8.30100806040200250 MHzACR-F (dB)