Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 23,1 11,3 11,8 441,00Remote: 45-12 23,4 11,3 12,1 441,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 30,6 27,3 3,3 395,00Remote: 36 31,1 27,3 3,8 395,00Worst Value: Local: 36 27,1 23,8 3,3 499,00Remote: 45 28,1 23,8 4,3 498,00PS-ACRF: Pass Worst Margin: Local: 45 72,4 61,2 11,2 1,00Worst Value: Local: 45 22,1 8,1 14,0 451,00Remote: 36 72,9 61,2 11,7 1,00Remote: 45 22,3 8,1 14,2 451,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:56Signature:______________________ Page: 12Copper Certification ReportCable Label: 521.002-UD-073 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:17.01.2019 11:32:57 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: