Title: +038=542.001-XZ008T_01-Enea EM3xx IO Enhet Nortek Produktblad.pdf
The module has a short-circuit isolator which, in the event of short-circuit between the two poles of the control panel loop cable, is capable of interrupting the negative pole and thus isolating the section involved in the short- circuit. For the isolator specification, please refer to the “ILP Specification” document.The module should be housed inside an electrical mounting box, as per the diagram, with the following characteristics: • Minimal internal dimensions: 125 x 125 x 40 mm • Protection grade IP44 or higher • Compliant with the established standards and codes relating to the Installation of electrical systemsThe two removable serial number stickers should be taken off the module; one should be attached to the box where the device is to be housed, the other to the installation layout.ATTENTION!