Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]18.0 78 1 2.82Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.1 465.0 29.5 36 7.4 477.0 26.1SR 36-45 6.3 465.0 29.5 36 7.0 458.0 27.0MAIN 12-36 8.9 500.0 27.8 36 7.8 496.0 25.2SR 36-45 7.3 497.0 28.0 36 7.3 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.5 9.5 45.7 45 21.2 28.1 33.3SR 45-78 19.5 15.6 41.4 45 21.2 28.1 33.3MAIN 78-45 22.6 500.0 11.3 45 23.2 499.0 8.3