Title: 30. Technoporten_Brannalarmutstyr datablad.pdf
ALARMPRE- ALARMFAULT910R2KInput application includes:  Fire Alarm push buttons  Flame, heat or beam detectors with relay contacts  Sprinkler contacts, etc.The output unit contains a potential free contact, which can be activated from a detector or a combination of several detectors or other preconfigured cause and effect relationships. No end-of-line monitoring on output function. The output can be used for:  Door release  Sprinkler control/functions  Control of fire dampers  FPE/FAD without bell patternsFunction IFunction GS1.1 S1.2 S1.3 S1.4 OFF OFF OFF ONS1.1 S1.2 S1.3 S1.4 OFF ON ON OFFFunction: Uncommitted input and independent relay output function.Function: Alarm condition signaling input unit with reset function for external detector. Relay contact activates for a configurable period when the unit is reset. This provides a 5 seconds (configurable) pulse for resetting the external detector.Number of addresses: 1