Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Loss (R->M) PASS Date / Time: 01-12-2022 12:20:45 Test Limit: EN50173 Fiber Optic Link Limits Version: 7.1 CertiFiber Pro (2388501 V6.1 Build 3) Module: CFP-QUAD(2440413) Calibration Date: 19-07-2017 certifiber pro remote (2412037 v6.1 build 3) Module: CFP-QUAD(2440405) Calibration Date: 19-07-2017Propagation Delay (ns) Length m Limit 2000.0Result Loss (dB) Limit (dB) Margin (dB)Reference (dBm)616 124.9850 nm PASS 0.33 2.54 2.2123.84PASS1300 nm PASS 0.17 2.29 2.1223.42Compliant Network Standards: 10/100BASE-SX 100BASE-FX 10GBASE-LRM 40GBASE-SR4 ATM52 FDDI Fiber Optic Fibre Channel 1200-M5E-SN-I Fibre Channel 200-M5-SN-I Fibre Channel 266SWL Fibre Channel 400-M5F-SN-I1000BASE-LX 100GBASE-SR10 10GBASE-LX4 ATM155 ATM622 Fiber Optic Fibre Channel 100-M5-SN-I Fibre Channel 133 Fibre Channel 200-M5E-SN-I Fibre Channel 400-M5-SN-I Fibre Channel 800-M5E-SN-I