Title: 05_ListOfVariables_MemoryOrganisation_Smarteh_v25_V6523.xls
"0" = Ok, "1" = Fault read only UV / MARVEL #10 46 MIN. AirFlow 0..10000 1:1 m3/h 47 UV #4 alarm 47 Actual AirFlow 47 UV #4 alarm "0" = Ok, "1" = Fault read only 47 IDLE AirFlow 0..10000 1:1 m3/h 48 Communication alarm 48 Damper Position 48 Communication alarm "0" = Ok, "1" = Fault read only 48 MAX Airflow 0..10000 1:1 m3/h 49 #7 Actuator Alarm 49 Actual Temperature 49 #7 Actuator Alarm "0" = Ok, "1" = Fault read only 49 Actual Pressure #24 0..1000 1:1 Pa read only HOOD 24 50 IR activity 50 Operating Hours#1 50 IR activity "1" = Active read only 50 Damper Position #24 0..10000 100:1 Pa read only HOOD 24 UV / MARVEL #6 51 Pressure alarm UV / MARVEL #11 51 Actual Pressure UV / MARVEL #24 51 Pressure alarm "0" = Ok, "1" = Fault read only UV / MARVEL #11 51 MIN. AirFlow 52 Filter Safety alarm 52 Actual AirFlow 52 Filter Safety alarm "0" = Ok, "1" = Fault read only 52 IDLE AirFlow 53 UV Safety alarm 53 Damper Position 53 UV