Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Headroom 5.6 dB (NEXT) 7.3 dB (NEXT) 8.6 dB (NEXT) 7.7 dB (NEXT) 8.4 dB (NEXT) 7.7 dB (NEXT) 8.3 dB (NEXT) 6.3 dB (NEXT) 8.8 dB (NEXT) 7.8 dB (NEXT) 8.2 dB (NEXT) 8.0 dB (NEXT) 8.7 dB (NEXT) 7.5 dB (NEXT) 6.6 dB (NEXT) 7.6 dB (NEXT) 7.0 dB (NEXT) 7.5 dB (NEXT) 9.3 dB (NEXT) 8.7 dB (NEXT) 7.9 dB (NEXT) 8.1 dB (NEXT) 7.5 dB (NEXT) 9.0 dB (NEXT) 9.4 dB (NEXT) 8.0 dB (NEXT) 7.7 dB (NEXT) 7.3 dB (NEXT) 7.6 dB (NEXT) 8.7 dB (NEXT) 8.5 dB (NEXT) 8.1 dB (NEXT) 9.6 dB (NEXT) 6.0 dB (NEXT) 5.2 dB (NEXT) 9.3 dB (NEXT) 7.2 dB (NEXT) 7.0 dB (NEXT) 8.7 dB (NEXT) 7.8 dB (NEXT) 7.2 dB (NEXT) 7.8 dB (NEXT) 6.4 dB (NEXT) 7.3 dB (NEXT) 5.5 dB (NEXT) 7.5 dB (NEXT) 7.1 dB (NEXT) 5.7 dB (NEXT) 7.4 dB (NEXT) 6.2 dB (NEXT) 4.8 dB (NEXT) 7.1 dB (NEXT) 7.5 dB (NEXT) 7.9 dB (NEXT) 7.6 dB (NEXT) 7.8 dB (NEXT) 6.6 dB (NEXT) 5.6 dB (NEXT) 5.0 dB (NEXT) 7.1 dB (NEXT) 4.7 dB (NEXT) 6.8 dB (NEXT) 4.6 dB (NEXT) 3.1 dB (NEXT) 4.1 dB (NEXT) 4.2 dB (NEXT) 4.2 dB (NEXT) 4.6 dB (NEXT) 3.4 dB (NEXT) 4.0 dB (NEXT) 1.10 dB (Loss Margin) 1.23 dB (Loss