Title: 05_ListOfVariables_MemoryOrganisation_Smarteh_v25_V6523.xls
Actuator Alarm "0" = Ok, "1" = Fault read only 39 Actual Pressure #22 0..1000 1:1 Pa read only HOOD 22 40 IR activity 40 Operating Hours#1 40 IR activity "1" = Active read only 40 Damper Position #22 0..10000 100:1 Pa read only HOOD 22 UV / MARVEL #5 41 #6 Pressure alarm UV / MARVEL #9 41 Actual Pressure UV / MARVEL #23 41 #6 Pressure alarm "0" = Ok, "1" = Fault read only UV / MARVEL #9 41 MIN. AirFlow 0..10000 1:1 m3/h 42 Filter Safety alarm 42 Actual AirFlow 42 Filter Safety alarm "0" = Ok, "1" = Fault read only 42 IDLE AirFlow 0..10000 1:1 m3/h 43 UV Safety alarm 43 Damper Position 43 UV Safety alarm "0" = Ok, "1" = Fault read only 43 MAX Airflow 0..10000 1:1 m3/h 44 UV #1 alarm 44 Actual Temperature 44 UV #1 alarm "0" = Ok, "1" = Fault read only 44 Actual Pressure #23 0..1000 1:1 Pa read only HOOD 23 45 UV #2 alarm 45 Operating Hours#1 45 UV #2 alarm "0" = Ok, "1" = Fault read only 45 Damper Position #23 0..10000 100:1 Pa read only HOOD 23 46 UV #3 alarm UV / MARVEL #10 46 Actual Pressure 46 UV #3 alarm