Title: 40 Bender brukermanual.pdf.pdf
Settings on devices externally connected to the BMS bus (e.g. RCMS460-D/-L, RCMS490-D/-L).76Information on the device. The same display is obtained by pressing the INFO button in the operating mode (refer to „Displaying standard information“ on page 43).79RCMS460-490_D00067_03_M_XXEN/12.2017Operation6.6 The main menu6.6.1 Menu 1: Alarm/meas. values RCMS…-D… displays the following for each measuring channel: alarm, measu- red value, response value.I(d) I(dn) 1. 4mA 10mA 2. 120mA 20mA 3. Channel disabledColumn 1: Column 2:Channel number 1…12 Alarm status:No alarm Prewarning Alarm, faultColumn 3:Column 4:I(d): The currently measured r.m.s. value of the residual cur- rent IΔ, the load current or the status of the digital input. I(dn): Set response value (rated residual operating current) IΔn, digital input or "Channel disabled“ or "CT connected“.