Title: økernvn 94.pdf
Cable ID: T4013 Date / Time: 09/09/2013 03:15:44 Headroom 0.7 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]138 220 16 5.9138 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]18.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.2 210.5 36.6 12 8.8 210.5 34.0SR 36-450.7 *245.5 35.5 36 1.2 250.0 32.7MAIN 12-36 7.4 225.0 36.1 12 8.9 248.5 32.7SR 36-45 0.7 250.0 35.3 36 1.2 250.0 32.71008060