Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Configuration of operating mode: Accuracy at 25 °C: Repeat accuracy: Temperature drift (0…55 °C) max.: Overcurrent protection: Time constant for filter: Voltage mode: Max. load to maintain specified accuracy: Resolution range 0 … 10 V: Current mode: Operating resistance: Resolution range 0 … 20 mA: Resolution range 4 … 20 mA:using software (FBOX, FB) ± 0.5% max. ± 0.1% max. ± 70 ppm/°C short circuit protected 1 ms> 700 Ω 12 Bit; 2.44 mV per LSB< 600 Ω 12 Bit; 4.88 µA per LSB 11.7 Bit; 4.88 µA per LSB6General details Current consumption at I/O bus +5V: Current consumption at I/O bus V+: Temperature range:max. 40 mA no load 0..0.55 °CExternal power supply (The same power supply can be used as for the PCD without losing the galvanic separation of the inputs/outputs.) Operating voltage: Current consumption:24 V ±4 V smoothed max. 2.5 W (depending on output load)Terminals:Plug-in 14-pole screw clamps (PCD2.W525; item no: 4 405 5002 0, supplied with module), for cables up to 1.5 mm²