Title: BRV Ahlsell No 450 kW.pdf
SINGLE PHASE - QUOTATION Heat Exchanger : B60Hx40/1P-SC-M (2"+2 1/2"+2"+2 1/2")Art No : 14748-040Connection DataF1 - F2 - F3 - F4 -ISO-G 2 1/2" A NON-CASTED(54) ISO-G 2" A NON-CASTED(54) ISO-G 2" A NON-CASTED(54) ISO-G 2 1/2" A NON-CASTED(54)Connection LocationsSide 1: Side 2:F3/F2 (In / Out) F1/F4 (In / Out)Fluid Side 1 : Water Fluid Side 2 : WaterFlow Type : Counter-Current SSP Alias : B60H-LDUTY REQUIREMENTS Heat load Inlet temperature Outlet temperature Flow rate Max. pressure drop Thermal lengthkW °C °C l/s kPaSide 1115,00 60,00 2,012 25,0 1,258PLATE HEAT EXCHANGER Total heat transfer area Heat flux Mean temperature difference O.H.T.C. (available/required) Pressure drop -total* - in ports Port diameterNumber of channels Number of plates Oversurfacing Fouling factor Reynolds number Port velocitym² kW/m² K W/m²,°C kPa kPa mm% m²,°C/kWm/sSide 19,93 0,329 55,0/55,0 (up/down) 19H1976 0,847www.swep.net