Title: Ahlsell.pdf
N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 11.6 3.6 61.4 3,6 13.0 3.6 58.6SR 3,6-7,8 10.1 3.4 61.7 3,6 11.8 3.4 58.7MAIN 3,6-4,5 28.7 490.0 -16.3 3,6 29.6 500.0 -20.0SR 1,2-3,6 24.3 478.0 -15.3 3,6 27.6 499.0 -19.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 4,5 5.2 12.0 20.6SR 4,5 5.0 17.1 19.8MAIN 3,6 8.3 417.0 8.0SR 3,6 7.1 485.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Ahlsell Site: Not Set Floor: Not Set Rack: Not Set Untitled1Building: Not Set Room: Not Set Patch: Not SetPage 8Test Summary: PASSRemote: Versiv S/N: 2552311 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013Adapter: DSX-5000R (DSX-PLA004)S/N: 250509557.5 m60Insertion Loss (dB)5040