Title: økernvn 94.pdf
RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: D4026 Date / Time: 09/10/2013 12:26:37 Headroom 10.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]67 106 8 2.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.7 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.9 44.3 38.1 36 13.5 44.3 35.1SR 12-36 10.8 44.3 38.1 36 13.3 44.3 35.1MAIN 12-36 11.3 98.3 32.4 36 13.6 98.3 29.4SR 12-36 11.3 98.3 32.4 36 13.3 98.5 29.410080604020NEXT (dB)