Title: +038=360.000-OU045T_01-PCD2.m4160 PLS SBC - Cables and Adapters Manual.pdf
m c 0 5 2y r e v e. x o r p p am c0 14 405 5028 0 spring terminal, 8 pole. (strand ends bare, 7 mm)View A (terminal designation)6 strands held together with cable ties, each strand 0.75 mm², 2.5 m long. PCD side: 6 pole, plug-in spring terminal block, type H. Process side: free strands, numbered.Connection configuration PCD3.K861:PCD3.A860 PCD3.K861tu c– Input 0 – Input 1 – +24 VDC6 5 4 3 2 16 5 4 3 2 1s d n e e n Li24 VDCI0I12-13Ribbon/screw terminal adapters3System adapters3.1Ribbon/screw terminal adapters (external terminal blocks)Terminal blocks for mounting on DIN rails at the output from the switching cabinet, to connect Saia PCD I/O modules to the process. The cables configured for this are described in the previous section «System cables with I/O module connections to the Saia PCD».3-1PCD2.K510 and PCD2.K511 adapters3.1.1 PCD2.K510 and PCD2.K511 adaptersRibbon/screw terminal adapters for 8 inputs or 8 outputs.4050J1 I/OJ12 8