Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 12] [Pair 45]14.5 63 1 2.29Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]34.5 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.8 452.0 30.1 36 7.2 452.0 27.3SR 36-45 7.4 470.0 29.3 36 8.0 468.0 26.5MAIN 12-36 8.0 493.0 28.2 36 8.0 500.0 25.0SR 36-45 7.8 486.0 28.5 36 8.6 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.8 6.9 48.5 45 21.6 8.4 43.8SR 45-78 19.8 6.4 49.1 45 21.6 6.0 46.7MAIN 36-45 21.4 500.0 11.3 36 22.8 498.0 8.3SR 45-36 21.5 500.0 11.3 36 22.4 500.0 8.30100806040200250 MHzACR-F (dB)