Title: Spjeldventil.pdf
Cold and warm water, water with glycol up to max. 50% vol. -20...120°C 1600 kPa Leakage rate A, tight (EN 12266-1) 90° Upright to horizontal (in relation to the stem) In accordance with ISO 7005-2 and EN 1092-2 Maintenance-freeMaterials BodyClosing element Stem Stem seal Stem bearing SeatEN-JS1030 (GGG 40), epoxy-powder coating 1.4301 (stainless steel) 1.4005 (stainless steel) O-ring EPDM RPTFE EPDMSafety notes!The valve has been designed for use in stationary heating, ventilation and air- conditioning systems and must not be used outside the specified field of application, especially in aircraft or in any other airborne means of transport.The valve has been designed for use in stationary heating, ventilation and air- conditioning systems and must not be used outside the specified field of application, especially in aircraft or in any other airborne means of transport.