Title: økernvn 94.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 19.1 61.5 31.0 12 20.1 61.5 28.5SR 12-36 15.0 61.5 31.0 36 16.1 47.3 32.2MAIN 12-45 27.9 250.0 4.7 45 28.6 250.0 2.0SR 36-45 22.2 249.0 4.8 36 22.3 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.5 28.9 18.7SR 36 4.5 174.5 11.6MAIN 36 7.0 250.0 10.0SR 36 4.5 174.5 11.6010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4