Title: Data tester Smestad skole - Detaljert.pdf
601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,7 11,0 10,7 459,00Remote: 45-12 21,8 11,0 10,8 459,00Worst Value: Local: 12-45 21,6 10,9 10,7 460,00Remote: 45-12 21,7 10,9 10,8 460,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,4 25,6 3,8 443,00Remote: 45 28,9 23,8 5,1 500,00Worst Value: Local: 36 27,8 23,8 4,0 500,00Remote: 45 28,9 23,8 5,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,6 61,2 11,4 1,00Worst Value: Local: 12 19,8 7,2 12,6 498,00Remote: 12 73,1 61,2 11,9 1,00Remote: 12 19,6 7,2 12,4 499,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:14Signature:______________________ Page: 138Copper Certification Report