Title: 40 plena talevarsling.pdf.pdf
ancedSensitivity200 mVImpedance22 kohmS/N (flat at max volume)>70 dBS/N (flat at min volume/muted) >75 dBHeadroom>25 dBTrigger Inputs12 x (6 EMG, 6 business)ConnectorsMC1,5 / 14-ST-3,5AktiveringProgrammerbarOvervåkningPå EMG inngangene, programmerbarOvervåknings metode Serie / parallell motstand100 V input ConnectorMSTB 2,5 /16-STforsterker effekt kapasitet1000 WTape utgang1 xTilkobling Nominal level ImpedanceCinch, 2 x mono 350 mV <1 kohmHøyttaler utganger Tilkobling 100 V utgang Volume override types 3-wire, 4-wire (24 V), 4-wire failsafeMSTB 2,5 /16-ST, floating 700 W rated per zoneBGM sone utgang70 / 50 /35 /25 / 18 / 13 V forAttenuation0 / -3 / -6 / -9 / -12 / -15 dB120 / 60 / 30 / 15 / 8 /4 WUtgangskontakterKontakt type RatingMC 1,5/14-ST-3,5 250 V, 7A, potensial frieEmergency aktiverings rele NO / COM / NCall aktivisrings releNO / COM / NCFeil releNO / COM / NC normally energized (fail-safe)generelt releNO / COM