Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
The following connection diagram shows a typical layout for tempera- ture sensors with the PCD2.W340,  … W350 and  … W360 Modules.9876543210COME7E6E5E4E3 E2E1E0m cDistributor *)0 2. x a mEarthing bar) potential freeThe reference potential for temperature measurements is the “COM” terminal, which should not have any external earth or GND connection.The reference potential for temperature measurements is the “COM” terminal, which should not have any external earth or GND connection.If screened cables are used, screening should be continued to an external earthing bar.If screened cables are used, screening should be continued to an external earthing bar.Unused temperature inputs are to be connected to the logical ground.Mixed operation9876543210COME7E6E5E4E3 E2E1E0Distributor ‘V’ and ‘C’Distributor Temp.5-70PCD2.W3x0Connection concept for two-wire transducersInput filterPressureE2ρ+0...20 mA