Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 57,4 68,0 297,0 16,0 9,6Limit 100,0 - 555,0 50,0 25,0Margin 42,6 - 258,0 34,0 15,4Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,1 3,0 1,9 2,35Worst Value: Local: 36 24,2 43,6 19,4 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 15,7 9,2 6,5 304,00Remote: 78 22,7 16,4 6,3 57,25Worst Value: Local: 36 15,1 8,0 7,1 492,00Remote: 12 15,0 8,6 6,4 349,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: Pass