Title: økernvn 94.pdf
Cable ID: D3087 Date / Time: 09/12/2013 10:35:43 Headroom 13.5 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]126 200 14 5.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]13.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.6 57.0 36.3 36 15.3 98.5 29.4SR 12-36 13.5 57.0 36.3 36 15.6 95.8 29.6MAIN 12-36 14.1 98.5 32.4 36 15.3 98.5 29.4SR 12-36 13.7 95.8 32.6 36 15.6 95.8 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 24.3 6.0 43.1 12 26.5 5.0 41.6