Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 26.11.2020 14:38RCD II: 28.5mAUci: 0.0V t: 15.1ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 27.11.2020 11:54Tallberg Elektro A/S Tlf.22796640Side:46GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.318318319319320320321321322322323323324324TEST RAPPORTResultat R LOW OhmR: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 27.11.2020 11:53KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 15.12.2020 10:13 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 27.11.2021 10:43ISOLASJON: ALLERln: >30.0MΩ Um: 253V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩ