Title: V20-09-02 VVS-anlegg plan 9 - DM3.pdf
ABXCDLD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/sLD007T Maks:180 m³/h Kjøling: 550 W 0.044 L/s Varme: 465 W 0.011 L/s01235 mm +c 2820 35 mm +c 2820ø160 UK=2713WISE IAQWISE RTAWISE IAQSF002T-160SF002T-160Møterom 9-02022 mm UK = 280922 mm UK = 280922 mm UK = 280922 mm UK = 2809LD001T Maks:210 m³/h Kjøling: 585 W 0.047 L/s Varme: 600 W 0.014 L/s15 mm +c 2820 15 mm +c 2820STAD Dim:10/09 StengtÅpent kontorlandskap 9-01828 mm +c 2805 28 mm +c 2820LD006T Maks:140 m³/h Kjøling: 110 W 0.009 L/s Varme: 130 W 0.000 L/sSF002T-160WISE RTAMøterom 9-019WISE IAQø160 UK=2705ø160 UK=2705 SF002T-160LD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sLD009T Maks:180 m³/h Kjøling: 550 W 0.044 L/sø160 UK=2675Fancoil 2 kW Tilknyttes kombibaffelkursNed MA 110NedSjakt 9-515.1-sDN25 0,17 L/sPatcherom 9-306Sjakt 9-515.2-sWISE IAQSF002T-160MA 110 +c 2759Opp MA 1101:100 WISE RTAø160 UK=2675ø160 UK=2705 SF002T-160