Title: 360.001 - Tilluft.pdf
Project InformationProject name:Brandengen skoleProject address:ProsjektadresseProject issue date:24.05.2016Organization description:RivSoftware version:MagiCAD for Revit 2021 UR-1.1Project Calculation DataSystems:/ - / - / -Total flow:16080 m³/hHighest LpA (10 m2 sab):37.6 dBCalculation Input ValuesOut of dp-range warning tolerance:0 %Calculation Results / SupplyLocationLevelNodeTypeProduct3. etasje183 AHE/AHUGeniox 22 360.001-210602/3. etasjeDUCT3. etasjeBEND-90LBR_SE-*-*-*-*-*-*-*-*1,1,13. etasjeDUCT3. etasjeSILENCERLKK-3209D H=1000Size2000x10001000x20002000x10002000x1000Sound Calculation ReportProject number:633146-01Client name:Drammen KommuneOrganization name:Asplan Viak AsAuthor:Tom SvanbergCalculation date:19.09.2021 19:58Total pressure:161.7 PaL [m]qv [m³/h]v [m/s]dpt [Pa]63 [dB]125 [dB]16080+250,0Total Lw:71.081.00,2160802,20,0 Sound in:71.081.0