Title: 32 Pumper modbuss teknisk data.pdf.pdf
Fig. 20 CIM 500 connected to a PC via Ethernet cableFor Further information on how to use the webserver, see section 1. Webserver configuration on page 51.You can use both ETH1 and ETH2 to establish a connection to the webserver.You can access the webserver while the selected Industrial Ethernet protocol is active.2 1 7 46 3 4 65 0 M T13)B G(h si lg n El is h(G B)7.5 Status LEDsThe CIM 500 Ethernet module has two status LEDs: LED1 and LED2.See fig. 18.Red and green status LED1 for Ethernet communicationRed and green status LED2 for internal communication between CIM 500 and the Grundfos product.Red and green status LED2 for internal communication between CIM 500 and the Grundfos product.LED1StatusDescriptionOffNo Modbus TCP communication or switched off.Flashing greenModbus TCP communication active.Permanently redCIM 500 module configuration fault. See section 14.3.1 LED status.Permanently red and green