Title: 360.001 - Tilluft.pdf
2k [dB]10.90.0 +0.018.40.0 +0.021.621.60.9 +20.523.623.60.2 +20.525.2+29.731.00.1 +20.54k [dB]7.50.0 +0.014.40.0 +0.017.717.70.9 +16.519.719.70.2 +16.521.2+21.724.50.1 +16.58k [dB]3.90.0 +0.08.20.0 +0.011.311.30.9 +9.513.013.00.2 +9.514.4+11.716.30.1 +9.5Lp [dB]LocationLevel2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeTypeProductSILENCERLKR-315-1200DUCTMAGID-C1-315BEND-90MAGIB-C3-90-315DUCTMAGID-C1-315BEND-30MAGIB-C3-30-315DUCTMAGID-C1-315FIREDAMPER FKR-EU/DE/315/ZXXDUCTMAGID-C1-315BEND-90MAGIB-C3-90-315DUCTMAGID-C1-315315315315315315315315315315315SizeSound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]12004,37,712004,312004,30,012004,312004,30,812004,312004,30,012004,312004,31,312004,34311,0 Sound in:Attenuation: