Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 36 27,4 23,8 3,6 500,00Remote: 45 28,9 23,8 5,1 500,00PS-ACRF: Pass Worst Margin: Local: 12 68,1 56,3 11,8 1,75Worst Value: Local: 36 19,9 7,2 12,7 500,00Remote: 45 72,2 61,2 11,0 1,00Remote: 36 19,5 7,2 12,3 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 50Copper Certification ReportCable Label: 521.002-UD-149 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 12:01:16 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software: