Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Isc: 628A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF050 C16/2 12.06.2020 10:04Zs(rcd)Z: 0.36ΩIsc: 646A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF050 C16/2 12.06.2020 10:05RCD tt: 64.5msUc: 0.3V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF050 C16/2 12.06.2020 10:06RCD II: 28.5mAUci: 0.1V t: 108.0ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF050 C16/2 12.06.2020 12:19R LOW OhmR: 0.05ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:39GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 266266267267268268269269270270271271272272TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF050 C16/2 12.06.2020 12:19KONTINUITET R: 0.1ΩGrenseverdi: 1.0Ω