Title: +038=442.002-UP020T_14-UP20 Driver 60W Tridonic Produktblad.pdf
4.6 Maximum loading of automatic circuit breakersAutomatic circuit breaker typeC10C13C16C20B10B13B16B20Inrush currentInstallation ØLCA 60W 24V one4all SC PRE1.5 mm2131.5 mm2182.5 mm2234 mm2301.5 mm281.5 mm2112.5 mm2144 mm218Imax 32.2 Atime187 μsTypical values for MCB from ABB series S200 as reference. Actual values can differ due to used MCB types and installation environment.4.7 Harmonic distortion in the mains supply (at 230 V / 50 Hz and full load) in %LCA 60W 24V one4all SC PRETHD 43. 45. 17. 29. 111. 14.8 Dimming5. Interfaces / communicationDimming range 1 % to 100 % Digital control with: • DSI signal: 8 bit Manchester CodeSpeed 1 % to 100 % in 1.4 s5.1 Control input (DA/N, DA/L)Digital DALI signal or switchDIM can be wired on the same terminals (DA/N and DA/L).