Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 78-45 16.0 488.0 11.5 78 17.0 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.8 52.0 33.9 45 23.3 62.0 29.0SR 12-45 26.6 49.8 34.5 45 25.7 49.8 32.0MAIN 36-45 38.0 497.0 -12.2 36 37.4 500.0 -15.3SR 36-45 34.3 497.0 -12.2 45 35.1 494.0 -14.90804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.2 480.0 8.0SR 12 5.4 499.0 8.0MAIN 45 7.2 480.0 8.0SR 12 5.4 499.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00430.9 m60Insertion Loss (dB)504030201000250 MHz500100