Title: +038=433.000-NI003._03-Testrapport elektriske anlegg - DM1.E5.433.09.04, Pareto plan 09.pdf
R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XQ003 NZM1/4 16.06.2020 09:40R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XQ003 NZM1/4 16.06.2020 08:47SPĆNDINGU12: 402V U13: 400V U23: 402V f: 50.0Hz : 1.2.3DM1-3. Plan 9 / DM1.E5.433.09.04 / XF001 C10/2 10.06.2020 15:07R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF002 C10/2 10.06.2020 15:06R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM1.E5.433.09.04 / XF002 C10/2 15.06.2020 11:36SPĆNDINGUln: 230V Ulpe: 230V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM1.E5.433.09.04 / XF010 C16/2 15.06.2020 08:28Tallberg Elektro A/S Tlf.22796640Side:4GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.28282929303031313232333334343535TEST RAPPORTResultatSPĆNDING