Title: Eurotester målerestultat.pdf
Rapport opprettet01.06.2021GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr.778899101011111212TEST RAPPORTResultat R LOW OhmR: 0.28ΩR+: 0.3Ω R-: 0.3Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING5 30.03.2021 14:41:02RCD II: 22.5mAUc: 8.7V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING6 30.03.2021 14:43:04RCD II: 21.0mAUc: 9.0V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING7 30.03.2021 14:43:27RCD II: 25.5mAUc: 9.7V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING8 30.03.2021 14:44:01RCD II: 25.5mAUc: 8.5V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING9 / CONNECTION1 30.03.2021 12:53:24Z-LINEZ: 0.78ΩIsc: 296A Sikringstype: C SIKRING I: 15A SIKRING T: 0.4s Isc_lim: 150.0A Isc(0.38%): 113A Isc(0.76%): 225A Isc(1.15%): 341ABytesteinen 1 / =433.202 / SIKRING9 / CONNECTION1 30.03.2021 12:59:54