Title: Data tester Smestad skole - Detaljert.pdf
Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-12 21,5 10,4 11,1 488,00Remote: 12-36 21,1 10,4 10,7 488,00Worst Value: Local: 36-12 21,5 10,4 11,1 488,00Remote: 12-36 21,1 10,4 10,7 488,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 30,1 27,1 3,0 400,00Remote: 36 28,3 23,8 4,5 500,00Worst Value: Local: 36 27,5 23,8 3,7 499,00Remote: 36 28,3 23,8 4,5 500,00PS-ACRF: Pass Worst Margin: Local: 12 71,4 60,0 11,4 1,15Worst Value: Local: 12 19,5 7,4 12,1 488,00Remote: 12 19,7 7,5 12,2 484,00Remote: 12 19,7 7,5 12,2 484,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:18Signature:______________________ Page: 164Copper Certification Report