Title: Lockzone Ceiling Ventil Swegon - Inreguleringsguide.pdf
GTHTRGdGTHc – tilluft – raka lamellerGTHc – tilluft – lameller 45°StorlekBKLBKL200-100-1257,57,27,37,27,07,1300-100-16012,112,112,311,311,912,1400-100-16016,216,615,415,016,115,0500-100-20021,120,722,120,120,421,1300-150-20019,319,219,719,418,819,2400-150-25026,526,127,925,425,826,6500-150-25034,833,532,933,833,430,9400-200-25038,139,241,237,438,141,1500-200-31550,548,448,348,048,246,4600-200-31560,358,756,657,657,854,4Anslutningsalternativ: B = baksida, K = kortsida, L = långsida Antal mätslangar: 2 Slangfärg: Transparent + Blå26Luftdon med cirkulär anslutningslådaLuftdon med cirkulär anslutningslådaCOLIBRI Free x XXXT / E X T R A C T A I RTomelilla Swedenk = XXkTILLUFT / SUPPLY AIRTILLUFT / SUPPLY AIRqp(cid:31)(cid:30) k p q (cid:30)( )2 kpq