Title: Operating instructions - K3G560PC0401.pdf
Visual inspection At least every6 monthsVisual inspection At least every6 monthsVisual inspection At least every6 monthsVisual inspection At least every6 monthsVisual inspection At least every6 monthsVisual inspection At least every6 monthsCondensation drainage holes for clogging, where necessary Abnormal bearing noise Vibration testVisual inspection At least every6 monthsacousticVibration tester, start-up or deceleration measurementAt least every 6 months Recommended every 6 monthsWhat action? Repair or replacement of deviceReplacement of deviceFastenReplace cablesClean impeller or replace deviceRetighten, replace if damaged Open holesReplace deviceClean impeller or replace device→ Do not use any pointed or sharp-edged objects forcleaning.6.4 Disposal; Completely remove any cleaning agents used.; If severe corrosion is visible on load-bearing or rotating parts, switchoff the device immediately and replace it.