Title: 360.001 - Tilluft.pdf
18.91.5 +0.03.014.50.0 +7.715.313.0 +10.511.116.00.0 +0.024.824.80.2 +20.526.0+27.930.00.1 +20.54k [dB]15.61.0 +3.714.91.5 +0.03.010.60.0 +3.711.414.0 +11.011.212.00.0 +0.021.021.00.2 +16.522.2+19.924.20.1 +16.58k [dB]9.21.0 +0.08.81.5 +0.03.05.10.0 +0.06.217.0 +10.5 10.517.0 +10.5 10.56.40.0 +0.014.514.50.2 +9.515.5+9.916.60.1 +9.5Lp [dB]16,7LocationLevel3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeProductSILENCERLKR-315-1200DUCTMAGID-C1-315BEND-90MAGIB-C3-90-315DUCTMAGID-C1-315BEND-30MAGIB-C3-30-315DUCTMAGID-C1-315FIREDAMPER FKR-EU/DE/315/ZXXDUCTMAGID-C1-31546 T-BRANCHTCPU-315-315DUCTMAGID-C1-315Size315315315315315315315315315/315315Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]12004,31,912004,312004,30,012004,3