Title: Ø94, Medistim - innregulering ventilasjon, avtrekk sjakt 2.pdf
AVTREKK MÅLEPROTOKOLLANLEGG:SYSTEM NR.:PLAN:ETGROM/GRENNR. 1 1 1 1NAVN/NR A1 A2 A3 A4SUMANMERKNINGERLUFT KONTROLLØKERNVEIEN 94 Sjakt 2 1 ETGDATO:FREKVENS / TRYKK:SIGNATURKANALPROSJEKTERTMÅLTFORHOLDTempØ.DIM.[m3/h] 1800 1000 300 500[m3/h] 1000 1300 310 520[%] 56 % 130 % 103 % 104 %C3600313087 %12.03.2013H.BANMERKNING