Title: 40 Bender brukermanual.pdf.pdf
6.6.5 Menu 5: Data logger Up to 300 data records can be recorded for each of the 12 measuring chan- nels. A new measured value is saved if it differs from the previous measured value by a defined percentage. You define this percentage in the menu "6. Settings-> 5. Data logger -> Change". You also make settings for overwriting and deleting measured values here.Exit 1.Data logger 2.Data logger 3.Data logger52RCMS460-490_D00067_03_M_XXEN/12.20171. Use the Up/Down buttons to select the required measuring channel (measuring channel number k1…k12). Press the "↵" button.271 01.04.16 15:57:03 35mA 270 01.04.16 15:40:10 51mA 269 01.04.16 15:37:15 36mA 268 01.04.16 15:35:01 70mA2. You can use the Up/Down buttons to browse the recorded data records of this measuring channel (data record number, date, time, measured value or digital input).2. You can use the Up/Down buttons to browse the recorded data records of this measuring channel (data record number, date, time, measured value or digital input).