Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
MAIN 36-45 14.4 3.5 54.4 45 14.0 2.9 53.1SR 45-36 14.4 3.5 54.4 45 14.0 2.6 53.9MAIN 45-78 17.0 500.0 11.3 45 17.7 500.0 8.3SR 78-45 16.8 500.0 11.3 45 17.4 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 22.5 76.5 28.4 36 23.7 76.5 25.9SR 36-78 23.6 61.0 31.7 36 24.7 61.3 29.1MAIN 36-45 37.0 482.0 -11.2 36 37.9 498.0 -15.1SR 36-78 36.5 498.0 -12.3 36 36.3 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 7.1 484.0 8.0SR 45 7.1 476.0 8.0MAIN 45 7.1 484.0 8.0SR 45 7.1 476.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASS