Title: Ahlsell.pdf
Cable ID: UD 23 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 10:52:48 AM Operator: Pam Headroom 10.2 dB (NEXT 1,2-4,5) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 3,6] [Pair 4,5] [Pair 4,5] [Pair 3,6]57.3 283 6 9.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]16.2 499.0 43.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 11.5 473.0 27.4 4,5 13.5 473.0 24.6SR 1,2-4,5 10.2 281.0 34.5 4,5 10.9 297.0 31.5MAIN 3,6-4,5 12.2 500.0 26.7 3,6 13.7 500.0 23.8SR 1,2-4,5 11.1 498.0 26.7 4,5 11.4 499.0 23.810080604020NEXT (dB)