Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.8 500.0 29.2 36 6.5 466.0 27.1SR 36-45 6.5 500.0 29.2 36 7.1 500.0 26.4MAIN 36-45 7.8 500.0 29.2 36 6.6 499.0 26.4SR 36-45 6.5 500.0 29.2 36 7.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.9 456.0 12.1 45 20.5 500.0 8.3SR 36-12 20.1 150.0 21.7 45 20.9 406.0 10.1MAIN 78-45 20.1 500.0 11.3 45 20.5 500.0 8.3SR 45-78 20.6 500.0 11.3 45 21.3 460.0 9.00100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.8 26.4 42.3 45 21.8 28.3 39.1SR 12-36 24.7 26.1 42.4 36 24.4 26.4 39.9MAIN 36-45 29.8 500.0 -12.4 36 29.0 499.0 -15.2SR 36-45 28.5 500.0 -12.4 36 29.6 500.0 -15.30804000250 MHzACR-N (dB)