Title: 369.02 EX Vifte Spesialavtrekk lakkrobot.pdf
Voltage controllable external rotor motor, vibration-free mounted, the motor is placed inside the air flow for cooling. PTC. Supply cable, led out.Suitable to transport explosive atmospheres of the zone 1. category 2G and zone 2, category 3G. The fans are applicable for zone 1 and 2 and for temperature classes T1, T2, and T3. Ignition type "e" increased safety EExe II, T3.32815 | Version: 32815 32815 DVEX 400D4 EX TAKVIFTE 230/400 | Artikkelnummer: 32815 DVEX 400D4 EX TAKVIFTE 230/400 DVEX 400D4 EX TAKVIFTE 230/400 Navn: DVEX 400D4 EX TAKVIFTE 230/400Produktkatalog 20160418 | Generated by: Produktkatalog Produktkatalog Produktkatalog 20160418 20160418 Product card | Document date: 20160418 Product card Product card Document type: Product card3 / 4Tested acc. to ATEX Directive 94-9-EC.For outdoor installation. Vertical installation position.