Title: +038=30.001-NI004._02-V62--01 Oppleggskjema varme.pdf
+09=320.102-OE096 0.114 L/sMM 28Pareto4.7 kW, 410 l/hDN20+08=320.102-OE086 0.149 L/sMM 286.2 kW, 536 l/hParetoDN 20+07=320.102-OE076 0.131 L/sMM 22Pareto5.4 kW, 472 l/hDN 20+06=320.102-OE066 0.097 L/sMM 284.0 kW, 349 l/hSB1DN 20+05=320.102-OE056 0.095 L/sMM 224.0 kW, 343 l/hMcKinsey+04=320.102-OE046MM 22n i nx,x kW, xXx l/hVika Invest+03=320.102-OE036MM 22x,x kW, xXx l/hEQTAkse C MM 54Til baffelkurs sydfasade14MM 54GlastadTeatro+U1=320.102-OE90115320.101 Varme ventilasjon Akse A/B16Tak 41.70 mPlan 11 38.25 m+10=360.029-OE901MM 15360.029 2,86 kW, 82,9 l/hPecuniaPlan 1035.07 mPlan 0931.97 mPlan 0828.17 m360.025 5,24 kW, 151 l/hMM 28+07=360.025-OE901MM 18Plan 0725.07 m360.023 5,24 kW, 151 l/h+06=360.023-OE901MM 18Plan 0621.97 mPlan 05MM 2818.87 mMM 28Plan 0415.77 mAkse CPlan 0312.67 mMM 421516Til ventilasjonskursMM 42Plan 028.37 mPlan 01 4.20 m