Title: +038=542.001-XZ008T_02-Enea EM411R Konvensjonell Sonemodul Nortek Produktblad.pdf
TECHNICAL SPECIFICATIONS Power supply Current draw in standby status Maximum current draw in alarm status Conventional zone End Of Line Open fault threshold with no load Open fault threshold with load Alarm threshold Short fault thresholdRelay contact ratingOperating temperatureHumidity (without condensation) Height Width (with anchor loca- tions) Width (without anchor locations) Depth (with terminal boards) Depth (without terminal boards) WeightEM411R19-30Vdc1.2 mA60 mA22μF 35v capacitor220 nF2.2 μF12 mA 50 Ohm 1 A / 30 Vdc -5°C/ +40°C95% RH53 mm100 mm78 mm29 mm19 mm66 gDCMIIN4AEM411R-R100-201103162EM411RNO1 NC1C1NO2 NC2C222 μF 35 VInstallationThe module must be connected to the control panel via a 2 pole twisted- shielded cable. This cable carries both the power supply and the two-way digital communications data. Refer to the Installation section for the wiring diagram.