Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Rl: 11Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF023 C16/2 12.06.2020 12:36KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF023 C16/2 12.06.2020 12:36R LOW OhmR: 0.10ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 10.06.2020 10:46R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 10.06.2020 10:50SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 12.06.2020 11:33RCD II: 27.0mAUci: 0.2V t: 223.0ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 12.06.2020 11:33RCD tt: 57.4msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 12.06.2020 11:34Tallberg Elektro A/S Tlf.22796640Side:6GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.