Title: 40 Bender brukermanual.pdf.pdf
6.3.5 Displaying standard information This function is only available in RCMS…-D. Press the "INFO" button. You will now see information relating to the device and software on the RCMS…-D dis- play. Use the "" arrow button to scroll all the information. Please have this information to hand if you should need to contact us for assistance by tele- phone.RCMS460-D 10.03.16 12:59 Address :2 Software: D233V2.50Line 1: Line 2: Line 3: Line 4:Line 5: Line 6:Line 7: Line 8…10: Line 11:Device type Date, time BMS bus address of the RCMS Software version D233V… for measuring technology proc- esses Date of the measurement technique software version Software version D216/D256/D339/D403… for communication processes Date of communication software version Bender address, homepage Exit. Exit standard information.RCMS460-490_D00067_03_M_XXEN/12.201743