Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
Legend B Coil Q Magneto-thermal input main switch T 90 A AC1 remote contactor 2-pole; 230 V coil1.2.DESCRIPTION OF THE SYMBOLS USED ON LABELS ATTACHED TO THE UNITComply with all precautions and warnings on labels and plates on the inside and outside of the equipment.DANGER! HIGH VOLTAGE (BLACK/YELLOW)GROUND TERMINALREAD THE USER MANUAL BEFORE USING THE UNITITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 005H S I L G N E6Position the UPS on a flat, stable surface in a properly ventilated room, well away from heat sources and avoiding direct exposure to sunlight.Position the UPS on a flat, stable surface in a properly ventilated room, well away from heat sources and avoiding direct exposure to sunlight.Ambient temperature should be kept between 0 to 45 °C, and relative humidity below 90% (without condensation); the optimum temperature to maximise battery lifetime is 15 to 20 °C.