Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 52Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Print / Visual task area 10 / Perpendicular illuminance (adaptive)Visual task area 10 / Perpendicular illuminance (adaptive)y X Surface Result Average Min Max Min/average Min/max Visual task area 10 Perpendicular illuminance (adaptive) [Ix] 488 358 593 0.73 0.60 Surrounding area: 0.500 m Surrounding area 10 Perpendicular illuminance (adaptive) [Ix] 327 237 415 0.72 0.57 Background area 9 Perpendicular illuminance (adaptive) [Ix] 155 127 184 0.82 0.69Wall zone: 0.500 mDIALuxPage 53Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10/ Print / Visual task area 10 / Perpendicular illuminance (adaptive)False colors [Ix]295 500 IxScale: 1:12Value grid [Ix]Scale: 1:12