Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Site 1/ Building 1/ Storey 10 / Print / Room summaryPrintiN 7 ]YyClearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 43.7%, Floor 20.0%, Light loss factor: 0.80EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 10 Perpendicular illuminance (adaptive) [Ix] 488 (= 300) 358 593 0.73 0.60 Surrounding area: 0.500 m 2 Surrounding area 10 Perpendicular illuminance (adaptive) [Ix] 327 (= 200) 237 415 0.72 0.57 3 Background area9 Perpendicular illuminance (adaptive) [Ix] 155 (= 66.7) 127 184 0.82 0.69 Wall zone: 0.500 m # Luminaire d(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 2 iGuzzini illuminazione S.p.A - QA85+QB22_B66J iN60 LED: Down LO 1824 16.7 109.5plateDALIGeneral LightLED WarmL 119615W 2400Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 3648 334 109.2Lighting power density: 7.12 W/m? (Floor area of room 4.69 m?) Consumption: 75 kWh/a of maximum 200 kWh/a