Title: 1 etg del 2.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.5 250.0 4.7 36 5.2 242.0 2.8SR 36-45 6.3 247.5 4.9 36 5.8 242.5 2.8MAIN 36-45 5.5 250.0 4.7 36 5.4 250.0 2.0SR 36-45 6.3 247.5 4.9 36 6.0 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.5 21.6 19.3SR 45 3.5 3.9 21.0MAIN 36 7.3 235.5 10.3SR 36 8.1 235.0 10.360500050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020104030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1