Title: 40 Bender brukermanual.pdf.pdf
Power supply unit for supplying up to six W…AB series measuring current transformers. Alternatively, an AN110 power supply unit can also be used.Only if these notes are observed will you obtain a true measurement result.   You must ensure that all live conductors are routed through the measuring current transformer.  Do not use shielded conductors.   Do not route any PE conductors through the meas-uring current transformer!  Commercial measuring current transformers arenot suitable for direct connection to the RCMS460/ RCMS490 systems and must not be used.Additional information is available in our "Transformer installation" manual.30RCMS460-490_D00067_03_M_XXEN/12.2017Installation and connection4.4.5 Connection WF… series measuring current transformersThe connections k and l at the residual current monitor must not be interchanged.RCMS460-490_D00067_03_M_XXEN/12.201731Installation and connectionLegend to W…AB series measuring current transformer connectionW…F