Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
If an emergency occurs, the valve may be manually opened, removing the electric head, unscrewing the ring nut. When the emergency ends, remember to reset the valve to automatic operation, repositioning the electric head; failure to do this can result in condensate formation due the water pipes, even if the unit is switched off.Instructions for field supplied valves Water connection • Install valves following manufacturer's instructions; refer to therelevant figures for connection to the unit.Carefully insulate pipes, valve assemblies and coil connections (cold water side) to avoid condensation forming on the pipes and dripping on the false ceiling.Carefully insulate pipes, valve assemblies and coil connections (cold water side) to avoid condensation forming on the pipes and dripping on the false ceiling.Electrical wiring • Connect the room control following instructions for the control used.ATTENTION: Route the cables through the electrical box as shown in fig. 37.