Title: Hardware Installation Guide.pdf
Bioscrypt readers wired to IDRC onboard reader ports 1 and/or 2 should be configured in the Readers form as IDRC Onboard Reader 1/2 (Bioscrypt RS-485) alternate readers associated with any type of primary readers. Bioscrypt readers wired to IDRC Onboard Reader ports 1 and/or 2 should be configured in the VeriAdmin Unit Parameters form for Network ID (0) only.29.4Input Circuit WiringTypically, these inputs are used to monitor door position, request to exit, or alarm contacts. Input circuits can be configured as unsupervised or supervised. When unsupervised, reporting consists of only the open or closed states. When configured as supervised, the input circuit will report not only open and closed, but also open circuit, shorted, grounded, and foreign voltage. This implementation exceeds the UL294 Requirement for Grade A Supervision.