Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
27.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.1 467.0 29.9 36 6.6 486.0 26.7SR 36-45 7.6 500.0 29.2 36 7.3 500.0 26.4MAIN 12-36 8.3 498.0 29.3 36 6.9 500.0 26.4SR 36-45 7.6 500.0 29.2 36 7.3 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.9 487.0 11.5 45 18.7 500.0 8.3SR 45-78 17.9 486.0 11.5 45 19.1 498.0 8.3MAIN 78-45 17.9 487.0 11.5 45 18.7 500.0 8.3SR 45-78 17.9 486.0 11.5 45 19.1 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.4 48.0 34.9 45 24.9 48.0 32.5SR 45-78 20.4 48.5 34.8 45 21.4 48.3 32.4MAIN 12-36 35.8 498.0 -12.3 36 34.5 500.0 -15.3SR 36-45 35.0 500.0 -12.4 36 34.9 500.0 -15.30804000250 MHzACR-N (dB)