Title: Aggregatkjøring.pdf.pdf
Fuse for supply air fan (in main cabinet)16AFuse for extract air fan (in main cabint)16ARated fuse PSCC max (in main cabinet)10kAMax. consumed current25.4AMax. consumed current in neutral wire3.0AMinimum fuses for unit (L1-L2-L3)32AMinimum fuses for unit (L1-L2-L3-N)32AThe electrical installation (wiring, mounting of components, connection plugs, etc.) for the unit is done as an machineinstallation according to 60204-1The supply unit consist ofDamperPressure drop2PaDamper bladesStandardActuator force21NmNumber of shafts1Empty sectionPressure drop3PaLength100mmSystemair ASTelephone :+47 51969700 www.systemair.no mailbox@systemair.noSystemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.001-1/Unit no. 10Date 18.06.2021Page 10/40FilterDimensioning pressure drop104Pa