Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 500.0 29.2 36 6.7 500.0 26.4SR 36-45 5.8 500.0 29.2 36 6.9 500.0 26.4MAIN 12-36 7.6 500.0 29.2 36 6.7 500.0 26.4SR 36-45 5.8 500.0 29.2 36 6.9 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.7 9.8 45.5 45 20.6 63.5 26.2SR 78-45 18.6 6.9 48.5 45 19.9 500.0 8.3MAIN 78-45 19.1 500.0 11.3 45 21.0 500.0 8.3SR 78-45 19.2 500.0 11.3 45 19.9 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.4 27.8 41.7 36 20.8 33.3 37.1SR 12-36 20.3 36.0 38.6 36 20.8 30.5 38.2MAIN 12-36 31.0 500.0 -12.4 36 30.2 500.0 -15.3SR 36-45 28.7 500.0 -12.4 36 30.4 500.0 -15.30804000250 MHzACR-N (dB)