Title: Aggregat_360,002_SPC.pdf
Condenser coil Volume flow Air speed Heating output (kW) Temperature air intake / outlet °C Medium type Evaporation temperature Pipe rows / Pressure loss, air (Pa) Blade spacing (mm) / Content (l) Number of coils vertically / horizont. Connection nom. width, inlet / outlet Material pipes / blades / framework connection decoupled (temperature/structure-borne sound) Dimensions WxD (mm) Material7.600 m³/h 2,2 m/s 42,0 26,0 / 42,5 R407C 45 °C 7 / 99 2,0 / 23,4 1 / 1 Stk 1 1/8" / 7/8" CU / AL / GV1.240 / 930 galvanized steelDamper Pressure loss / Air speed (m/s) material Frame / Blade Total torque / Number of axes Dimensions WxD (mm)3 Pa / 2,1 VZ/AL 125 - Kl. 2 7,4 Nm / 1 1.240 / 9307.600 m³/h 2,2 m/s 21,8 34,0 25,0 / 60 15,7 / 85 R407C 10°C 3 / 48 2,5 / 10 1 / 1 Stk 7/8" / 1 3/8" CU / AL / GVstainless steel 304 cranked / DN 32ePM1 60% F7 52 / 200 Pa 126 Pa 18,2 / 2,0