Title: Data tester Smestad skole - Detaljert.pdf
pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 48,0 68,0 249,0 13,0 8,1Limit 100,0 - 555,0 50,0 25,0Margin 52,0 - 306,0 37,0 16,9Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,9 3,0 2,1 2,80Worst Value: Local: 36 20,4 43,6 23,2 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 24,8 18,3 6,5 34,00Remote: 78 23,0 18,3 4,7 34,00Worst Value: Local: 12 17,6 8,0 9,6 467,00Remote: 78 15,6 8,0 7,6 489,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 498,00Remote: 36-45 29,8 26,7 3,1 500,00Worst Value: Local: 36-45 28,9 26,7 2,2 498,00