Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The procedure for connecting oil-immersed transformers is described in instruction sheets available on the Schneider Electric website:  For connecting Canalis KTA1000-4000/KTC1350-5000 to oil-immersed transformers: AAV17625.  For Canalis KTA1000-4000/KTC1350-5000 vertical incomer arrangement: PHA12477.  For Canalis KTA1000-4000/KTC1350-5000 horizontal incomer arrangement: PHA12478.  For Canalis KTA5000/KTC6300 horizontal incomer arrangement: PHA44577.  For Canalis KTA5000/KTC6300 vertical incomer arrangement: PHA44578.StepAction1Remove the cable box if the transformer is equipped with a cable box.2Install the KTB••••CR• protective cover on the transformer.3Install the end feed unit with its supports.4Check that the weight of the run components does not rest on the transformer (seepage22).5Check the phase order of the run components in the installation, the end feed units, and the transformer (seepage15).6Open the protective cover.7