Title: +038=433.002-FS032._02-Eaton Tavlebyggeren Produktblad.pdf
Let-through current01/04/2019Eaton 147397 ED2018 V51.0 EN6 / 9Let-through energy01/04/2019Eaton 147397 ED2018 V51.0 EN7 / 9Dimensions① Blow out area, minimum clearance to adjacent parts ② Minimum clearance to adjacent parts01/04/2019Eaton 147397 ED2018 V51.0 EN8 / 901/04/2019Eaton Industries GmbH http://www.eaton.eu © 12/2018 by Eaton Industries GmbH Eaton 147397 ED2018 V51.0 EN9 / 9DATASHEET - NZMN2-4-VE100-BTCircuit-breaker, 4p, 100A, box terminals, selectivity protectionPart no. Catalog No.NZMN2-4-VE100-BT 147396EL-Nummer (Norway)4358841Similar to illustrationTechnical data General StandardsIEC/EN 60947Protection against direct contactFinger and back of hand proof to VDE 0106 Part 100Climatic prooﬁngDamp heat, constant, to IEC 60068-2-78 Damp heat, cyclic, to IEC 60068-2-30Ambient temperatureAmbient temperature, storage°C-40 - + 70Operation°C25 - +70Mechanical shock resistance (10 ms half-sinusoidal shock) according to IEC 60068-2-27