Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
typ. 10 ms; max. 20 ms typ. 20 ms; max. 30 ms supplied directly from input current 4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 2,000 VAC, 1 min. 100 MOhm / 500 VDC 2.5 kVInternal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Terminals:Electrical isolation of outputs to the PCD. The channels are not isolated from each other < 1 mA0 mAPluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²Switch on/off level:250 VAC180 VAC40 VAC0 VAC0Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-15Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.E500LEDs and connection terminalsBus connectorBus interface, Optocoupler, threshold switchInput bleeder chainLEDs6Screw terminals9876543210COM COME5E4E3E2E1E0Inputs E0 to E5 0 - 5Common connection for the 6 inputs