Title: Siemens STA73-eng.pdf
4) Can be set using the DIP switch under the cover on the connecting cable. See Mounting instructions M4884 5) Separate cable, see page 1514 / 16Siemens Building TechnologiesElectrothermal actuators STA..3.., STP..3..CE1N4884en 03.05.2012General ambient conditionsTemperature Temperature for quasi-continuous control HumidityOperation EN 60721-3-3 5…50 °C5…40 °C < 85 % r.h.Transportation EN 60721-3-2 –20…60 °C– < 95% r.h.Connecting cablesConnecting cables w/o 0…10 V moduleASY23..ASY23..BASY23..HF ASY23..LDLength [m] Cross section [mm2]3…102…100.8…15 ≤ 2 m: 0.50 > 2 m: 0.75 24 / 230 1) White, RAL 9016 PVC – –2 / 5 1 m: 0.50 5 m: 0.75 24 White, RAL 9016 PVC – LED See Table on page 40.750.75Operating voltage [V] Housing color24 / 230 1) Black, RAL 9005 PVC – –24 / 230 1) White, RAL 9016 Halogen-free – –Coating Auxiliary switch Indicator Weight 1) AC 230 V with STA23../STP23.., AC/DC 24 V with STA73../STP73..Connecting cables with 0…10 V moduleASY6A..