Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
TEST RAPPORTResultatZ-LINEZ: 0.31ΩIsc: 748A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF031 C16/2 11.06.2020 15:46Zs(rcd)Z: 0.27ΩIsc: 852A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF031 C16/2 11.06.2020 15:46RCD II: 28.5mAUci: 0.0V t: 17.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF031 C16/2 11.06.2020 15:47RCD tt: 58.1msUc: 0.4V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF031 C16/2 11.06.2020 15:47RCD UbUc: 0.3VRl: 11Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF031 C16/2 12.06.2020 12:23R LOW OhmR: 0.11ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF031 C16/2 12.06.2020 12:23KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:16GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*