Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD07 Date / Time: 28/01/2022 09:58:59 Headroom 9.2 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]23.3 120 9 5.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]28.5 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 9.3 105.0 39.6 3,6 10.5 180.0 32.6SR 1,2-3,6 9.2 199.5 34.8 3,6 10.6 141.5 34.5MAIN 3,6-7,8 11.3 247.0 33.2 7,8 10.7 223.5 31.0SR 1,2-3,6 9.2 199.5 34.8 7,8 11.0 223.5 31.0PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)