Title: etg u1.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.6 46.5 34.9 36 13.4 46.8 32.4SR 12-36 16.0 46.5 34.9 36 17.4 46.5 32.4MAIN 12-36 20.8 245.0 5.2 36 21.0 245.0 2.5SR 12-36 26.8 227.5 6.9 12 27.1 227.5 4.3010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.1 28.4 18.7SR 36 3.4 28.4 18.7MAIN 36 7.5 226.0 10.5SR 36 6.8 250.0 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1