Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
4. Complete the wiring on the internal module (refer to paragraph 5.5.1 Cable entry and the paragraphs regarding the wiring of each internal module).5.5Control panel wiringAttention:Take care to remove all sources of power, including the batteries before starting any wiring operations.Note:The ends of wires must not be soft soldered in points where they are subject to clamping.5.5.1 Cable entryUse only the provided cable entries (remove the respective cable-entry seals) on the upper and lower parts of the cabinet and on the back [A].AThe cables must run vertically behind the grounding bar (paragraph 3.1 - [L]) and must be secured to the appropriate hooks by cable ties [B].The cable must run level with the terminal board of the module it is to be connected and its shield must be connected to the grounding bar [C]. Conductors without shields must be conveyed to the appropriate terminal board [D].DBThe unused cable entries must be closed by the supplied plastic seals.CB34