Title: 91879 FDV F13 Kafe.pdf
(each switchgear assembly has to be verified individually based on provided design verification reports)StandardsIEC/EN 61439-1/-2/-3, IEC 62208Degree of protectionIP2XC (door opened, closed front cover level)IP55Mechanical impact protectionIK10 (IP55)Form of separationup to Form 4b (in combination with Profi+ installation system)Internal segregationIP2XCRated insulation voltage [Ui]440VACRated voltage [Ue]415VACAmbient air temperature5°C to +40°CPlace of installationIndoor use severity ARated impulse withstand voltage [Uimp]4kVOvervoltage categoryIIIPollution degree3Protection against electric shockProtective earthing (protection class I)Joule integral I²dt for earthing connectionType BPM-F / BPM-OBase frame M8 earthing bolt @ 1,25mm sheet metal - Door M6 earthing bolt @ 1,25mm sheet metal Seismic characteristicsBase frame M8 earthing bolt @ 1,25mm sheet metal - Door M6 earthing bolt @ 1,25mm sheet metal Seismic characteristics1,16x10^7 A²s