Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 34,1 68,0 177,0 10,0 6,3Limit 100,0 - 555,0 50,0 25,0Margin 65,9 - 378,0 40,0 18,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,5 3,0 2,5 1,60Worst Value: Local: 36 14,7 43,6 28,9 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 14,1 8,0 6,1 460,00Remote: 12 21,0 15,0 6,0 79,00Worst Value: Local: 12 14,1 8,0 6,1 460,00Remote: 12 17,4 8,7 8,7 337,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):