Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
The procedure for installing the sealing kit is described in the instruction sheet AAV32049 available on the Schneider Electric website.Connecting the Canalis InterfaceThe height of the Canalis interface is defined by the rating of the Trihal transformer.The following graphic shows how the heights of the Canalis interface (J) and the run components (K) are defined.The following table gives the heights of the run components that can be connected to a Canalis interface of a given height:Height of Canalis interface (J) (mm)Height of run component (K) (mm)12474, 104, 124164104, 124, 164204204244204, 244324244, 324404324, 404QGH3492101-01 11/201843Transformer Connections44QGH3492101-01 11/2018Canalis KTSwitchboard ConnectionsQGH3492101-01 11/2018Switchboard ConnectionsChapter 4 Switchboard ConnectionsWhat Is in This Chapter?This chapter contains the following topics:Connection to SwitchboardsConnection to Prisma P and Okken Switchboards