Title: økernvn 94.pdf
MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3410 Date / Time: 09/12/2013 12:25:27 Headroom 5.1 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]186 284 10 8.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]13.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.1 229.5 35.9 78 6.3 229.5 33.3SR 12-36 7.9 219.5 36.3 36 8.3 225.5 33.5MAIN 36-78 5.1 229.5 35.9 78 6.6 249.5 32.7SR 12-36 7.9 219.5 36.3 36 8.4 235.0 33.210080604020NEXT (dB)