Title: etg u1.pdf
2550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: T0009 Date / Time: 10/22/2013 01:23:01 PM Headroom 13.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]163 258 18 6.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.4 96.0 32.6 36 15.0 88.0 30.2SR 12-36 14.3 88.0 33.2 36 15.5 88.0 30.2MAIN 12-36 13.5 98.0 32.4 36 15.1 98.0 29.4SR 12-36 14.3 88.0 33.2 36 15.5 90.0 30.110080604020NEXT (dB)