Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Valves should open only when the fan is working, that is, when one of terminals V1, V2, V3 is energized by L mains supply.When the system is filled with water, verify all couplings for tightness.When the system is filled with water, verify all couplings for tightness.The manufacturer does not accept responsibility for the tightness of the field - installed valve assembly and this is not tested in the factory.He declines any responsibility for non functioning of these assemblies and for damage due to dripping.He declines any responsibility for non functioning of these assemblies and for damage due to dripping.(cid:19)(cid:25)(cid:18)(cid:20)(cid:21)(cid:18)(cid:20)(cid:20)(cid:3)(cid:3)(cid:3)(cid:20)(cid:20)(cid:29)(cid:24)(cid:22)Side knockouts allow connection of fresh air inlet ducts and ducts to deliver conditioned air to an adjacent room.Remove the external prepunched anti-condensate insulation and take away the knockout panels using a punch.