Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Uln: 234VUlpe: 234VUnpe: 0Vf: 49.8HzR ISO GODKJENTR: >200MQ Um: 263VUiso: 250VGrenseverdi:1MQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 020 GODKJENT * 1150822020 10:20SPENDINGUln: 235VUlpe: 235VUnpe: 0Vf: 50.0HzR ISO GODKJENTR: 24.4MQ Um: 263VUiso: 250VGrenseverdi:1MQTEST RAPPORTSPENDINGUln: 232VUlpe: 233VUnpe: 1Vf: 50.1HzZLINE GODKJENTZ: 0.56QIsc: 407ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AR LOW Chm GODKJENTR: 0.11QR+: 0.1QR: 0.1QGrenseverdi: 1.0QKONTINUITET GODKJENTR: 0.1QGrenseverdi: 1.0QZs (rcd) GODKJENTZ: 0.13QIsc: 1.80kASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AI GODKJENT: 28.5mAUci: 0.1Vt: 27.9msIdn: 30mAtype: ACHN,Ulim: 25VR LOW Ohm GODKJENTR: 0.03QR+: 0.0QR: 0.0QGrenseverdi: 1.0QTEST RAPPORTR IS0R: 46.7MQ Um: 263VUiso: 250VGrenseverdi:GODKJENT1MQ