Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
32.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.0 447.0 30.3 36 8.6 440.0 27.6SR 36-45 8.6 473.0 29.1 36 8.3 463.0 26.8MAIN 12-45 9.4 493.0 28.2 36 9.4 492.0 25.4SR 36-45 8.9 484.0 28.6 36 9.2 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.5 109.0 24.5 45 14.4 3.0 52.7SR 36-45 15.5 228.5 18.1 45 14.4 3.0 52.7MAIN 45-36 16.1 468.0 11.8 36 18.7 475.0 8.7SR 36-45 16.3 474.0 11.7 45 18.3 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 26.5 108.0 23.0 45 26.8 108.0 20.4SR 36-45 27.3 108.5 22.9 36 28.9 114.0 19.5MAIN 12-45 40.3 493.0 -11.9 36 40.9 498.0 -15.1SR 36-45 40.7 500.0 -12.4 36 40.3 498.0 -15.10804000250 MHzACR-N (dB)