Title: økernvn 94.pdf
MAIN 12-36 17.0 49.3 34.1 36 16.8 46.5 32.4SR 12-36 14.4 46.3 35.0 36 14.1 46.8 32.4MAIN 12-36 28.4 247.5 4.9 12 29.3 247.5 2.3SR 36-45 21.4 250.0 4.7 36 21.6 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 1.6 26.0 18.9SR 45 2.6 25.9 18.9MAIN 36 5.2 245.5 10.1SR 45 7.3 249.5 10.0010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 4.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94