Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Zs (rcd)Z: 0.20QIsc: 1.16kASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AR LOW OhmR: 0.11QRt+: 0.1QR: 0.1QGrenseverdi: 1.0QZLINEZ: 0.44QIsc: 525ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AI a28.5mAUci: 0.2Vt: 86.9msIdn: 30mAtype: ACH,Ulim: 25VKONTINUITETR: 0.0QGrenseverdi:SPENDINGUln: 233VUlpe: 233VUnpe: 0Vf: 50.1HzTEST RAPPORTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTTEST RAPPORTR IS0 GODKJENTR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQSPENDINGUln: 235VUlpe: 235VUnpe: 0V£: 50.0HzZLINE GODKJENTZ2: 0.37QIsc: 627ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0AZs(rcd) GODKJENTZ: 0.31QIsc: 752ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AI 4 GODKJENT28.5mAUci: 0.2Vt: 121.6msIdn: 30mAtype: ACH\Ulim: 25VKONTINUITET GODKJENTR: 0.1QGrenseverdi:R LOW Ohm GODKJENTR: 0.07QR+: 0.1QR: 0.1Q