Title: V62--01 Oppleggskjema varme.pdf
10Tak 41.70 mPlan 11 38.25 mPlan 1035.07 mEndret effekt etter ny kjøring fra R&H, 18.12.19Plan 0931.97 m+08=360.008-OE901360.008 15 kW, 440 l/hMM 28Plan 0828.17 m+07=360.007-OE901360.007 15 kW, 440 l/hMM 28Plan 0725.07 m+06=360.006-OE901360.006 15 kW, 440 l/hMM 28Plan 0621.97 m+05=360.005-OE901360.005MM 2815 kW, 440 l/hPlan 0518.87 m+04=360.004-OE901360.004 15 kW, 440 l/hMM 28Plan 0415.77 mPlan 0312.67 mAkse CMM 42Til ventilasjonskursMM 42+02=320.101-OE907Lompen1TianlaiSeasport2320.102 Kombibaffel varme Akse A/ nordDN20+11=320.102-OE111 0.193 L/sMM 28Pareto8,0 kW, 695 l/hDN20+10=320.102-OE101 0.129 L/sMM 28Pactum5,4 kW, 465 l/hDN20+09=320.102-OE091 0.104 L/sMM 28Pareto3,5 kW, 306 l/hDN20+08=320.102-OE081 0.112 L/sMM 284,6 kW, 405 l/hPareto+07=320.102-OE071MM 28Pareto4,7 kW, 408,1 l/hDN20+06=320.102-OE061 0.090 L/sMM 28Pareto Bank3,74 kW, 325 l/h