Title: Tappevann - VV.pdf
REDUCER KR001TMAGI-CU-R1 28/221. EtasjePIPEKR001TMAGI-CU-22 221. EtasjeBEND-90KR001TMAGI-CU-B1-221. EtasjePIPEKR001TMAGI-CU-22 221. EtasjeBEND-90KR001TMAGI-CU-B1-22Domestic Water Pressure Calculation ReportCalculation date:09.05.2022 13:30Project number:633146-01Client name:Drammen KommuneOrganization name:Asplan Viak AsAuthor:Tom SvanbergFluid type:WaterTotal pressure:400.0 kPaFluid density:983 kg/m3Network volume:36.7 lThermal conductivity:20.00000 W/m*K:20.00000 W/m*K:L [m]Insulationqv sum [l/s]qv dim [l/s]v (dim) [m/s]dp/L [Pa/m]dp (flow) [kPa]K factordp Hst [kPa]0,2 BI016T/306,900000,740531,441316,20,2BI016T/306,900000,740531,441,01.0000,30,1 BI016T/306,700000,730921,421282,80,21,3BI016T/306,700000,730921,420,50.4910,33,2 BI016T/306,700000,730921,421282,84,0BI016T/306,700000,730921,420,20.2450,10,4 BI016T/306,700000,73092