Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]23.1 100 1 3.43Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]31.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.5 455.0 30.0 36 7.3 450.0 27.4SR 12-36 8.7 450.0 30.2 36 9.0 461.0 26.9MAIN 12-36 8.6 497.0 28.0 36 8.1 497.0 25.1SR 12-36 9.2 497.0 28.0 36 9.2 497.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.4 5.9 49.9 45 20.4 6.5 46.0SR 78-45 18.4 5.9 49.9 45 20.3 5.9 46.9MAIN 36-12 20.4 472.0 11.8 36 22.9 484.0 8.5SR 12-36 20.2 472.0 11.8 36 21.4 474.0 8.70100806040200250 MHzACR-F (dB)