Title: økernvn 94.pdf
100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3204 Date / Time: 09/11/2013 05:57:50 Headroom 3.0 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]116 177 6 5.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]19.5 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 5.2 250.0 35.3 78 6.4 250.0 32.7SR 36-78 3.0 232.0 35.9 78 3.4 196.0 34.5MAIN 36-78 5.2 250.0 35.3 78 6.4 250.0 32.7SR 36-78 3.0 232.0 35.9 78 3.4 196.0 34.510080604020NEXT (dB)