Title: økernvn 94.pdf
Cable ID: T4104 Date / Time: 09/11/2013 12:28:39 Headroom 6.5 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]136 209 8 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]17.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.4 222.0 36.2 36 8.2 222.0 33.6SR 36-78 6.5 248.5 35.4 36 6.0 246.5 32.8MAIN 12-36 8.5 232.0 35.9 78 8.2 246.0 32.8SR 36-78 6.5 248.5 35.4 36 6.0 246.5 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 14.4 3.3 54.0 12 16.6 3.3 51.0