Title: Instructions manual - THGT fan.pdf
Environment Equipment is adequately protected against corrosion, weather, vibration and other adverse factors. No undue accumlation of dust and dirt. Electrical insulation is clean and dryCompetent Inspector name, sign / stamp:Refer: IEC EN 60079-14: Explosive atmospheres - Electrical installations design, selection and erection.IEC EN 60079-14: identifies initial inspection schedules, derived from IEC EN 60079-17: Electrical installations inspection and maintenance.IEC EN 14986:2007 Section 7, requires supplier manual to contain; "forms for check sheet quality system"IEC EN 14986:2007 Section 7, requires these to be signed and returned to fan supplier.36Ex tAnnex 4: Table of Vibration levels.FancategoryBalance gradeMountingManufacture Workshop mm/s rmsStart up mm/s rmsIn situAlarm mm/s rmsShutdown mm/s rmsBV-3G 6.3Rigid Flexible2.8 3.54.5 6.37.1 11.89 12.5Notes: All vibration levels - Velocity mm/s rms. Refer ISO 14694:2003