Title: +038=360.000-LC007T_04-Coadis line 600 Fan-coil CIAT - Manual.pdf
The coil can be partially drained, however precautions must be taken during winter if the installation is shut down. To drain completely, air must be blown through the circuit. If the hydraulic connections are completed, it is not necessary to insulate the valves to prevent condensation (unless they are specific valves). A naturally inclined ABS auxiliary condensate drain pan is supplied with the unit. This recovers condensate from the valves and coil (from the main pan) and drains it via gravity or using a condensate drain pump supplied as an option.N 11.47 F(cid:40)(cid:49)(cid:3)(cid:16)(cid:3)(cid:23)(cid:121) Installation