Title: TESEO.pdf
This chart indicates Teseo piping diameters calculated at 8 bars pressure and 5% pressure drop from inlet pressure. #110 = indicates pressure drop over 5%APPROXIMATE CHART FOR CHOOSING TESEO PIPING DIAMETER - AP SYSTEMFlow rate3. in l/minLENGTH (in me3.te3.rs)m³/hcfm205010020030040050010001500200022 22 22 22 22 22 22 22 28 28 45 45 45 45 45 54 54 68 68 6822 22 22 22 22 22 22 28 28 45 45 45 45 54 54 68 68 #68 #68 #6822 22 22 22 22 22 28 28 45 45 45 54 54 54 68 68 #68 #68 #68 #6822 22 22 22 22 28 28 45 45 45 54 54 68 68 #68 #68 #68 #68 #68 #6822 22 22 22 28 28 45 45 45 45 54 68 68 68 #68 #68 #68 #68 #68 #6822 22 22 28 28 28 45 45 45 54 68 68 68 #68 #68 #68 #68 #68 #68 #6822 22 22 28 28 45 45 45 45 54 68 68 #68 #68 #68 #68 #68 #68 #68 #6822 22 28 28 45 45 45 45 54 54 68 #68 #68 #68 #68 #68 #68 #68 #68 #6822 28 28 45 45 45 45 45 54 54 #68 #68 #68 #68 #68 #68 #68 #68 #68 #6822 28 45 45 45 45 45 54 54 68 #68 #68 #68 #68 #68 #68 #68 #68 #68 #68