Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
200 300 400500 600 700200 300 4007002-pipe4-pipeq.tyq.tyq.tyq.ty112211bValve 3/4" gas111Valve 1/2" gas1cShell1111d Clips3333e Gasket2244Instructions for mounting of motorized thermo- electric valve assembly (see "Components" table)The thermo-electric valve must be mounted on the unit after the unit installation. For this operation follow figures, depending on model. Assembly (Fig. 30) With 4–pipes models, first install the valve assembly for the cold circuit followed by the valve assembly for the hot circuit. Connect the valve assemble to the coil and fix it by a 30Nm torque. Insulate the valve assembly.