Title: økernvn 94.pdf
Cable ID: T4097 Date / Time: 09/11/2013 12:38:08 Headroom 11.8 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]97 154 11 4.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.8 94.5 32.7 36 14.3 94.5 29.7SR 12-36 11.9 94.5 32.7 36 14.2 94.3 29.7MAIN 12-36 11.8 94.5 32.7 36 14.5 98.0 29.4SR 12-36 11.9 94.5 32.7 36 14.2 94.3 29.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 19.1 98.0 18.8 45 21.1 2.4 48.1