Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Venttiilien eritys42 GW19(cid:19)(cid:24)(cid:18)(cid:20)(cid:21)(cid:18)(cid:20)(cid:20)(cid:3)(cid:3)(cid:3)(cid:20)(cid:28)(cid:29)(cid:19)(cid:28)T. VTable V: Operating limitsWater circuitWater- side maximum pressureMinimum entering water temperature: + 4°C1400 kPa (142 m w.c.)Maximum entering water temperature: + 80°CRoom airMinimum temperature: 5°C (1)Maximum temperature 32°CPower supplyNominal single phase voltage230V ~ 50HzOperating voltage limitsmin. 207V – max. 253V min. 216Vmax. 244V (unit with electric heaters)Notes:(1)If the room temperature can go down to 0°C, it is advisable to empty the water circuit to avoid damage caused by ice (see paragraph on water connections).Tabella V: Limiti di funzionamentoCircuito acquaPressione massima lato acquaTemperatura minima acqua entrante: +4°C1400 kPa (142 m c.a.)Temperatura massima acqua entrante: +80°CAria ambienteTemperatura minima: +5°C (1)Temperatura massima 32°CAlimentazione elettrica