Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
R LOW OhmR: 0.06ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Gulv kanal 16.06.2020 11:12R LOW OhmR: 0.16ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 16.06.2020 11:12KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 16.06.2020 11:12R LOW OhmR: 0.16ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 16.06.2020 10:25KONTINUITET R: 0.0ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 16.06.2020 11:13R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 16.06.2020 11:11R LOW OhmR: 0.17ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / MPE1 / Kabel bru 15.06.2020 13:34Tallberg Elektro A/S Tlf.22796640Side:47MISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESNr.329329330330331331332332333333334334335335336336TEST RAPPORT