Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]14.3 62 1 2.40Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 2.5 463.0 29.6 36 3.8 463.0 26.8SR 12-36 3.5 455.0 30.0 36 5.0 454.0 27.2MAIN 12-36 2.5 463.0 29.6 36 5.3 496.0 25.2SR 12-36 5.3 497.0 28.0 36 6.2 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 17.0 472.0 11.8 12 18.5 472.0 8.8SR 12-36 17.5 472.0 11.8 36 19.0 472.0 8.8MAIN 36-12 17.1 473.0 11.7 12 18.5 472.0 8.8