Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Digital input modules, electrically isolated from the I/O Bus6.3Digital input modules, electrically isolated from the I/O BusPCD3.E500 PCD3.E610 PCD3.E6136 inputs for 115 … 230 VAC 8 inputs 24 VDC, 10 ms 8 inputs 48 VDC, 9 msElectrical isolation of inputs to the Saia PCD®. The channels are not isolated from each otherDefinition of input signalsfor 5 VDC (on request)for 24 VDC PCD3.E610for 48 VDC PCD3.E6137 VDC 5 VDC2.5 VDC130 VDC 24 VDC15 VDC160 VDC 48 VDC30 VDC11 VDC 0 VDC5 VDC 0 VDC10 VDC 0 VDC0007 VDC30 VDC60 VDCfor 115 – 230 VAC PCD3.E500250 VAC180 VAC40 VAC0 VAC0Installation instructionsFor reasons of safety it is not permissible to connect low voltages (up to 50V) and higher voltages (50 … 250 V) to the same module.If a Saia PCD® module is connected to a higher voltage (50 … 250 V), approved com- ponents for this voltage must be used for all elements that are electrically connected to the system.