Title: 26 Manual for takslukvakt.pdf.pdf
Use glue/sealer recommended for you roof typePosition the Monitor, including bracket, 40-60 mm from the edge of the drain. If the drain has a leaf guard, the 40-60 mm distance is from the edge of the leaf guard to the bracket.40 mm - 60 mmREV. 02 - MARCH 2021 - BLÜCHER® CONNECTED ROOF 116 CommissioningPrior to commissioning, ensure that all Monitors have been installed and the Gateway is mounted and wired according to the previous chapter. 1. Ensure power is OFF* 2. Remove SD card from the Gateway and open the Config file in an editor 3. Edit the Config file parameters to reflect the application (see appendix 13) 4. Save the Config file and place the SD card in the Gateway 5. Turn power ON* 6. Wait for all the Monitors to connect. This process can take up to 30 minutes. Alternatively,enable Monitor Test mode to reduce time (see capture 7.6)7. Verify that there are no errors or warnings in the display 8. Verify Modbus values and functionality**