Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
AIR INTAKEFresh air connectionThe fresh air inlets are designed for the insertion of standard 110 x 55 mm rectangular ducts.The air duct is connected quickly and easily. After removing the blank and the insulation inside the unit, the mounting plate is rolled back and the air duct with its V-shaped section must be pushed into the unit (see Figures below). The duct is then fixed to the mounting plate.Note: the fresh air must be filtered.1234MAIN AIR INLETAccessory “Fresh air connection” - Identification CAP - Code 6078005 (see page 14)AIR INTAKEAir distribution - Air distribution connectionTwo air outlets are provided on the side of the unit for connection to separate supply air outlets.AIR OUTLETThey can be used to supply air from the fan coil unit to distant areas of a room or even to a different room.The total air flow does not change.The air flow at high speed depending on the air duct pressure drop is shown in the tables below.Spigot for air distributionAIR INTAKE