Title: Temperaturgiver.pdf
All wiring must be in accordance with local regulations and national rules. • Do not attempt field repairs. If the transmitter is not operating properly, even though it is wired correctly, it should be replaced.3 wires 0...1Vdc Output The TS-6300 Active are 3 wires devices utilizing an RTD sensing element that goes through an amplifier circuit to provide a 0...10Vdc output proportional to the sensed temperature.t°TCOMOUTCom0...10 VdcEPWR15 Vdc or 24 Vdc/Vac2 wires NTC K2 / NTC K10 / PT1000The TS-6300 Series Sensors are two-wire devices utilizing an RTD or thermistor temperature sensing element. The sensing elements have a known response to temperature that provides a predictable and repeatable resistance/ temperature (R/T) characteristic.The RTD sensing elements are thin film platinum SMT chips. They have a positive temperature coefficient and are nearly linear over the operating temperature range.