Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
4242434344444545464647474848TEST RAPPORTResultatZ-LINEZ: 0.60ΩIsc: 386A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 12.06.2020 11:36Zs(rcd)Z: 0.58ΩIsc: 396A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 12.06.2020 12:37R LOW OhmR: 0.13ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF024 C16/2 12.06.2020 12:38KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 10.06.2020 10:46R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 10.06.2020 10:50SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF025 C16/2 12.06.2020 11:41RCD II: 28.5mAUci: 0.1V t: 105.3ms Idn: 30mA type: AC Ulim: 25V