Title: økernvn 94.pdf
Cable ID: T3092 Date / Time: 09/11/2013 05:24:34 Headroom 14.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 45]94 149 11 4.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.1 78.3 34.1 12 19.1 78.3 31.1SR 12-36 14.6 72.5 34.6 36 15.8 78.3 31.1MAIN 36-45 19.1 78.3 34.1 12 19.8 95.3 29.7SR 12-36 15.6 94.3 32.7 36 16.3 94.8 29.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 20.3 76.8 20.9 36 22.0 99.5 15.7