Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]35.3 153 2 5.20Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.7 487.0 29.5 36 7.8 500.0 26.4SR 36-45 7.7 480.0 29.6 36 8.1 494.0 26.5MAIN 36-45 7.7 487.0 29.5 36 7.8 500.0 26.4SR 36-45 7.7 480.0 29.6 36 8.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.5 3.8 53.8 45 13.6 2.3 55.2SR 36-45 14.6 4.5 52.2 45 13.5 2.3 55.2MAIN 78-45 16.1 475.0 11.7 45 16.5 500.0 8.3SR 78-45 16.1 475.0 11.7 45 16.3 478.0 8.60100806040200250 MHzACR-F (dB)