Title: +038=433.002-FS034._06-Tavlebyggeren Eaton FDV.pdf
electrical components mechanical components 4,000 operating cycles (In, Un, cos = 0.87)  10,000 operating cyclesMechanical Frame size Device height Device width Mounting Degree of protection switch Degree of protection, built-in Upper and lower terminals Terminal protection Terminal capacity Terminal screw Terminal torque Busbar thickness Operation temperature Storage- and transport temperature Resistance to climatic conditions Line side (supply) Load side45 mm 80 mm 35 mm (2MU) 3-position DIN rail clip, permits removal from existing busbar system IP20 IP40 open mouthed/lift terminals ﬁ nger and hand touch safe, DGUV VS3, EN 50274 1 - 25 mm2 M5 (with slotted screw acc. to EN ISO 4757-Z2, Pozidriv PZ2) 2 - 2.4 Nm 0.8 - 2 mm -25°C to +40°C -35°C to +60°C acc. to IEC 68-2 (25..55°C / 90..95% RH) lower terminals upper terminalsConnection diagram 2-polesDimensions (mm)6EATON CORPORATION xxxxx+xxxx-xxxxENProtective Devices Combined RCD/MCB Devices NdRBM, Technical Data1.7