Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 022 GODKJENT* 12.03.2020 14:53ZLINE GODKJENTZ: 0.48QIsc: 477ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 022 GODKJENT* 12,:08r2020 » 1455Zs (rcd) GODKJENTZ: 0.45QIsc: 512ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc lim: 160.0ADronning M.g.1-3 / E.433.11.01 TN-S / Sikring 022 GODKJENT * 1251038.2020 1511RCD T GODKJENTI: 28.5mAUci: 0.1Vt: 88.9%msIdn: 30mAtype: ACO\,Ulim: 25VDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 022 GODKJENT * 12.03.2020 14:48KONTINUITET GODKJENTR: 0.1QGrenseverdi:Dronning M.g.1-3 / E.433.11.01 TN-S / Sikring 022 GODKJENT * 12100352020 15856SPENDINGUln: 233VUlpe: 233VUnpe: 0Vf: 49.9Hz1.0QDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 022 GODKJENT* 12.03.2020 15:34R LOW Ohm GODKJENTR: 0.09QR+: 0.1QR: 0.1QGrenseverdi: 1.0QNr. ResultatR ISOR: >200MQ Um: 263VUiso: 250VGrenseverdi: 1MQ