Title: 40 Bender brukermanual.pdf.pdf
RCMS460-LAN420COM465IPU S AC 85…260 VNDI-1DLB/N A/PB/N A/PLegend to connection exampleRCMS…Residual current monitorsAN420When AC/DC sensitive W…AB series measuring current transformers are used, an AN420 or AN110 power supply unit is required that supplies up to six measuring current transformers of this type. When the supply voltage of AN110-1 is < 30 V, the output power decreases, so that only five measuring current transformers can be connected.COM460IPProtocol converter for connecting the BMS bus (Bender measuring device interface) with a TCP/IP (Transmission Control Protocol/Internet Protocol) network via Ethernet.RCMS460-490_D00067_03_M_XXEN/12.201733Installation and connectionDI-1DLThe DI-1DL repeater only is required when the length of the cable exceeds 1200 m or when more than 32 devices are connected to the bus.CTW…, WR…, WS…, WF…, W…AB series measuring current transformers.