Title: +175=324.001_KA001_Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.Produktinformasjon.pdf
Operating temperature2) Operating pressure10...150 °CPN 16: Up to 120 °C, 16 bar At 150 °C, 14.4 bar PN 10: Up to 120 °C, 10 bar At 150 °C, 9 bar Between 120 °C and 150 °C, a linear interpolation can be performedStandards and directivesPressure and temperature dataEN 764, EN 1333Flow parametersEN 60534 (page 3)Pressure Equipment Directive97/23/EC (fluid group II) No CE label, article 3.3Overview of typesTypeNominal diameterkvs valueWeightVUE015F350DN 150.4 m³/h3.2 kgVUE015F340DN 150.63 m³/h3.2 kgVUE015F330DN 151 m³/h3.2 kgVUE015F320DN 151.6 m³/h3.2 kg1) Air humidity must not exceed 75%. 2) At temperatures below 0 °C, use a stuffing box heater. Use adaptor (accessory) at temperatures above 100 °CRight of amendment reserved © 2015 Fr. Sauter AG10.1VUE032F30056.1151/10Product data sheet2/1056.115TypeNominal diameterkvs valueWeightVUE015F310DN 152.5 m³/h3.2 kgVUE015F300DN 154 m³/h3.2 kgVUE020F300DN 20