Title: 2 etg del2.pdf
100002550 MHz75100100ACR-N @ Remote (dB)80604020100002550 MHz75100100RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 8.1Cable ID: T2013 Date / Time: 10/11/2013 08:04:21 AM Headroom 4.3 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]134 204 7 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]18.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.6 29.9 50.3 36 8.9 29.9 47.9SR 36-78 4.3 197.5 37.0 36 6.1 197.0 34.4MAIN 36-78 9.6 240.5 35.6 36 10.0 238.0 33.1SR 36-78 4.3 197.5 37.0 36 6.1 197.0 34.4