Title: V20-04-02 VVS-anlegg plan 4 - DM3-1.pdf
320.102: 28 mm +c 2675320.102: 28 mm +c 2675LD018T Maks:160 m³/h Kjøling: 255 W 0.020 L/s Varme: 440 W 0.011 L/sLD018T Maks:160 m³/h Kjøling: 255 W 0.020 L/s Varme: 440 W 0.011 L/sLD018T Maks:160 m³/h Kjøling: 255 W 0.020 L/s Varme: 440 W 0.011 L/sLD018T Maks:160 m³/h Kjøling: 255 W 0.020 L/s Varme: 440 W 0.011 L/sLD018T Maks:160 m³/h Kjøling: 225 W 0.018 L/s Varme: 495 W 0.012 L/sLD018T Maks:160 m³/h Kjøling: 225 W 0.018 L/s Varme: 495 W 0.012 L/s320.102: 54mmLD018T Maks:160 m³/h Kjøling: 225 W 0.018 L/s Varme: 495 W 0.012 L/sLD018T Maks:160 m³/h Kjøling: 225 W 0.018 L/s Varme: 495 W 0.012 L/s+04 = 320.102 - OE 044 0.094 L/sSTAP/STAD 0.094 L/sLD018T Maks:135 m³/h Kjøling: 620 W 0.050 L/s Varme: 275 W 0.007 L/s+04 = 370.101 - OE 044 0.387 L/sSTAP/STAD DN25LD018T Maks:135 m³/h Kjøling: 620 W 0.050 L/s Varme: 275 W 0.007 L/s370.101: DN 100mmLD018T Maks:140 m³/h Kjøling: 525 W 0.042 L/s Varme: 265 W 0.006 L/s