Title: 2 etg del2.pdf
Cable ID: D2007 Date / Time: 10/10/2013 10:56:11 AM Headroom 7.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]244 374 14 11.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]8.0 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 226.0 36.1 36 7.6 226.5 33.4SR 12-36 7.0 216.5 36.4 36 7.3 249.5 32.7MAIN 36-78 7.4 250.0 35.3 36 7.9 245.5 32.8SR 36-78 7.1 249.5 35.4 36 7.3 249.5 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-78 15.9 191.0 18.6 36 15.9 184.5 15.9