Title: Kapasitetsmåler Mecon.pdf
Report damage to the carrier and your local sale staff. In such cases, a description of the defect, the type and the serial number of the device is indicated.(cid:1) (cid:1)Information!Unpack the unit carefully to avoid damage.Information!Check the completeness of the delivery against the packing list. Check the rating plate, if the delivered flow meter according to your order.Operating instructions FO Turbo-Lux 3 FM VdSwww.mecon.dePage 5 / 1605/2015 OI_FO_Turbo-Lux 3 FM VdSInstallation and mode of operation2.2 InstallationInstallation of the orifice plateBefore and after the orifice plate a straight calming section is provided as a function of the nominaldiameter (D). When using valves and fittings before the orifice plate, an inlet path of min. 10 x D isalways required.For the standard version an inflow path of min. 10 x D and an outflow zone of min. 5 x D isrequired (please see page 11). The connected pipes have to be of the same size as the orificeplate.