Title: DM1-3 plan 09 lysberegningsrapport.pdf
Result overview, Evaluation area 1[m] 2.5N2.01.51.00.50.00.50.00.51.01.52.02.53.03.54.04.55.05.56.0[m]Illuminance [lx]2003005007501000General Calculation algorithm used Height of luminaire plane Maintenance factorAverage indirect fraction 2.50 m 0.80Total luminous flux of all lamps Total power Total power per area (19.26 m²)10500.00 lm 138.6 W 7.19 W/m² (1.47 W/m²/100lx)Evaluation area 1 User profileEm Emin Emin/Em (Uo) Emin/Emax (Ud) UGR (2.6H 4.7H) PositionReference plane 1.1 Offices 5.26.5 (EN 12464-1, 8.2011) Conference and meeting rooms (Ra >80.00) Horizontal 491 lx 332 lx 0.68 0.46 <=17.8 0.75 m(>= 500 lx)(>= 0.60)(< 19.00)Major surfaces M 1.5 (Ceiling) M 1.1 (Wall) M 1.2 (Wall) M 1.3 (Wall) M 1.4 (Wall)Em 44 lx 59 lx 45 lx 54 lx 46 lx(>= 30 lx) (>= 50 lx) (>= 50 lx) (>= 50 lx) (>= 50 lx)Uo 0.76 0.51 0.72 0.54 0.67(>= 0.10) (>= 0.10) (>= 0.10) (>= 0.10) (>= 0.10)191015 test plan 9.rdf