Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
Isc: 1.02kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF038 C16/2 10.06.2020 12:52Zs(rcd)Z: 0.20ΩIsc: 1.18kA Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF038 C16/2 10.06.2020 12:53RCD UbUc: 0.1V Rl: 2Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF038 C16/2 10.06.2020 12:53RCD tt: 57.8msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF038 C16/2 10.06.2020 12:54RCD II: 28.5mAUci: 0.1V t: 87.7ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF038 C16/2 12.06.2020 11:53KONTINUITET R: 0.2ΩGrenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:25GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 170170171171172172173173174174175175176176TEST RAPPORTResultat