Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
14 bit differential 4 yes, 500 V yes, 500 V no two cables per channel using DIP switches ± 0.2% max. ± 0.05% max. ± 70 ppm/°C ± 50 V min. ± 35 mA min. ± 50 V min. 70 dB min.2 ms 40 dB min. between 49.5 and 50.5 Hz 40 dB min. between 59.5 and 60.5 Hz14 Bit; 0.61 mV per LSB125 Ω 14 Bit; 1.22 µA per LSB 13.7 Bit; 1.22 µA per LSB0.1 °C 0.2 °C 0.1 °C 0,2 Ω 2.5 mW max.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-83Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W525Outputs General: Resolution: Number of channels: Galvanic separation of the PCD: Galvanic separation of external supply: Galvanic separation between channels: Type of connections:12 bit 2 yes yes no two cables per channel