Title: økernvn 94.pdf
RL @ Remote (dB)80604020100002550 MHz75100LinkWare Version 7.4Cable ID: D4163 Date / Time: 09/10/2013 05:23:15 Headroom 9.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 36] [Pair 36] [Pair 45]121 184 5 6.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]12.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.9 99.3 32.4 36 11.3 99.3 29.4SR 12-36 10.6 77.0 34.2 12 12.2 34.8 36.8MAIN 12-36 9.9 99.3 32.4 36 11.3 99.3 29.4SR 12-36 11.6 99.3 32.4 12 12.9 99.3 29.410080604020NEXT (dB)