Title: 360.001 - Avtrekk.pdf
29.20.6 +27.331.11.0 +27.331.90.0 +27.38k [dB]14.60.0 +21.522.322.30.1 +14.522.91.5 +14.413.19.19.10.0 +20.320.73.0 +20.322.20.6 +20.324.11.0 +20.324.90.0 +20.3Lp [dB]LocationLevel1. Etasje1. Etasje1. Etasje1. Etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeProductSizeBEND-30MAGIB-C4-*-*315DUCT315BEND-90MAGIB-C4-*-*315DUCT315185 T-BRANCHTCPU_DK-*-*0,0 315/250DUCT250FIREDAMPER FKRS-EU/250/Z 250DUCT250BEND-90MAGIB-C4-*-*250DUCT250L [m]0,70,90,10,30,2Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]19807,13,0 Sound in:Attenuation: Addition:19807,11,3 Sound in:Attenuation: Addition:19807,16,9 Sound in:Attenuation: Addition:19807,11,7 Sound in:Attenuation: Addition:19807,12,6 Sound in:Attenuation: Addition:Dividing:6603,70,1 Sound in:Attenuation: Addition:6603,73,7 Sound in:Addition:6603,7