Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.6 477.0 29.7 36 8.3 500.0 26.4SR 36-78 9.0 484.0 29.5 36 8.5 500.0 26.4MAIN 36-45 8.0 499.0 29.3 36 8.3 500.0 26.4SR 36-78 9.0 484.0 29.5 36 8.5 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.6 3.8 53.8 45 14.1 3.4 51.7SR 36-45 14.6 3.8 53.8 45 14.1 3.5 51.4MAIN 45-78 16.3 487.0 11.5 45 17.7 499.0 8.3SR 78-45 16.5 495.0 11.3 45 16.9 486.0 8.50100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 22.5 59.0 32.1 36 24.5 58.5 29.8SR 36-78 22.7 67.5 30.2 36 24.2 71.5 26.9MAIN 36-45 36.4 499.0 -12.3 36 37.1 500.0 -15.3SR 36-78 37.0 484.0 -11.3 36 37.3 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.5 480.0 8.0