Title: +038=433.000-NI003._25-Testrapport Elektriske Anlegg Plan 5 DM3.E2=433.05.02 Colliers.pdf
Uiso: 500V Grenseverdi: 1MΩColliers Plan 5 / DM3.E2=433.05.02 / XF024 C16/2/003 / Mal 3 10.03.2022 13:53 (TomekElektriker)KONTINUITET: R200mA LPER: 0.19ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.5ΩColliers Plan 5 / DM3.E2=433.05.02 / XF025 C16/2/003 / Mal 1 10.03.2022 11:53 (TomekElektriker)TALLBERG ELEKTRO A/S Stanseveien 4, 0975 Oslo Tlf.22 79 66 40Side:10GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.31313232TEST RAPPORTResultat SPENNING TRMS Uln: 234V Ulpe: 234V Unpe: 1V f: 50.01HzSYS.: TN/TTZ-LINEZ: 0.46ΩIsc: 504A R: 0.46Ω Xl: 0.03Ω Sikringstype: C SIKRING I: 16A SIKRING T: 0.4s Isc_lim: 160.0ARCD: UtlřsningsstrřmI: 27.0mAUci: 0.2V t: 62.3ms Idn: 30mA type: Ulim: 50V SYS.: TN/TTISOLASJON: L-PE,N-PERlpe: >30.0MΩ Um: 521V Rnpe: >30.0MΩ Um: 516VUiso: 500V Grenseverdi: 1MΩ