Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
26.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.5 480.0 29.6 36 7.6 499.0 26.4SR 36-45 7.2 500.0 29.2 36 7.1 500.0 26.4MAIN 12-36 8.6 495.0 29.3 36 7.6 499.0 26.4SR 36-45 7.2 500.0 29.2 36 7.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.9 402.0 13.2 45 19.6 462.0 8.9SR 78-45 18.0 398.0 13.2 45 19.8 472.0 8.8MAIN 78-45 18.3 447.0 12.2 45 19.9 491.0 8.4SR 78-45 18.5 446.0 12.2 45 20.0 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.8 45.8 35.6 45 22.9 45.8 33.1SR 36-45 23.7 42.8 36.4 45 23.2 42.8 34.0MAIN 12-36 35.4 495.0 -12.1 36 34.7 500.0 -15.3SR 36-45 33.9 500.0 -12.4 36 34.1 500.0 -15.30804000250 MHzACR-N (dB)