Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]32.3 140 2 4.97Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.5 459.0 30.0 36 7.5 458.0 27.2SR 12-36 7.2 499.0 29.3 36 7.7 499.0 26.4MAIN 12-36 7.2 499.0 29.3 36 8.1 499.0 26.4SR 12-36 7.2 499.0 29.3 36 7.7 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.7 5.0 51.3 45 17.6 499.0 8.3SR 45-78 16.7 4.9 51.5 45 18.3 500.0 8.3MAIN 78-45 18.1 498.0 11.3 45 17.6 499.0 8.3