Title: Brukermanual for Refra varmepumpe.pdf
Attention! Installation place accessible to unauthorized persons and animals must be fenced and marked with warning signs. Machine room must be equipped with warning sign, fire extinguishers (preferably an automatic fire extinguishing system) for electrical equipment, mineral and synthetic oils fighting.We draw your attention to the fact that the machine room must comply with the highest concentrations of toxic refrigerants rates. If local norms do not provide for maximum levels, it is necessary to follow the EN378 regulations. Approximate all HFC refrigerants practical limit may be taken 8 gr/m3.In addition, the installation location must meet the classification under refrigeration equipment localization and by the maximum refrigerant filling.For operation under extreme conditions (e.g. aggressive or corrosive atmospheres, low ambient temperatures etc.) suitable measures must be taken.