Title: DOCA0005EN-12.pdf
– Enable: the alarm is enabled. If you enabled the Overload Alarm, you mustalso configure the Pick Up Value in kW from 1 - 9999999.Select how the digital output functions: – Disable: the digital output is disabled.Digital Output (iEM3235 / iEM3255 / iEM3265)DO FunctionDisablefor Alarmfor Pulse (kWh)– for Alarm: the digital output is associated with the overload alarm. The metersends a pulse to the digital output port when the alarm is triggered.– for Pulse (kWh): The digital output is associated with energy pulsing (active energy). When this mode is selected, you can select the energy parameter and set the Pulse Constant (imp/kWh) and the Pulse Width (ms).NOTE: the iEM3275 does not have a digital output.Select how the digital input functions: – Input status: the digital input records the status of the input, for example, OF,Input StatusSD of a circuit breaker.Digital InputDI FunctionTariff ControlInput Metering