Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: D3063 Date / Time: 09/12/2013 10:11:08 Headroom 13.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]168 265 18 7.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]11.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.2 95.8 32.6 36 14.4 95.8 29.6SR 12-36 13.5 72.3 34.6 36 14.6 95.8 29.6MAIN 12-36 13.2 95.8 32.6 36 14.4 95.8 29.6SR 12-36 13.9 99.5 32.3 36 14.6 95.8 29.610080604020NEXT (dB)