Title: +038=67.005-##003._03-Ø4 og Ø5 MR fordamper.pdf
HIGH PERFORMANCE HEAT EXCHANGER MR range finned coils, are designed with corrugated aluminium fins (fin spacing: 4.23 mm) and grooved internal structure copper tubes. The refrigerant distributors are Venturi type for models MR 210 - MR 270 and MRE 135 - MRE 210 - MRE 270.DEFROST 230 V /1 tubular electric heater connected to a junction box (MRE only) is inserted in slots, under the coil which facilitates easy maintenance and ensures equal heat distribution through the coil. So, defrost is perfect. Defrost water is collected in an intermediate drain pan then drained through a Ø 1” G threaded polyamid drain fitting.VENTILATION 50-60 Hz fan assembly (Ø 200 mm) used for MR and MRE models, is designed with an enclosed frame, class B, impedance protected, life lubricated motor, connected to the junction box (except for MR 75). Fan guards conform to safety regulations.OPTIONAL FEATURESMRE range: