Title: +038=360.025-#####._10-360.025 Kjølebatteri DX Kondensatorbatteri CD R&H - Materialspesifikasjon.pdf
Væske mengde Trykkfall Gasshastighet i rør N°1 Batteri Cu-Al-FeZn P25COND 7R-16T-1000A-2.0pa 6C 28 mm 22 mmTEKNISKE DATA: Rør Cu Finner Al Ramme FeZn Sugestokk matr. Cu9.90 x 0.30 mm Vekt 0.10 1.50 / 1.50 mm Tot. utv. overflate PED 2014/68/UE Maks. Tillatte trykk Maks. Tillatte temp.mm Innv. volum34 Kg 10 dm355.13 m2 Article 4.3 26.0 bar -10/55 °CTILLEGGReduced tolerance calculation - CounterflowWed Sep 29 10:08:34 2021€29/09/2021Rel. 6.4.5 25-03-2021kg/h m/s Pa0.00 2.13 94°C °C °C °C45.00 2.00 37.62 0.185 122,00 stk.1/1Spiro Ø630 both sidesTILLEGGSVERDIERRef:Type P25 ED 3R-25T-650A-3.0pa-6C-Cu/Al/FeZn1 Pos.1 - Høyre / Right 407cR12kW 7 /45°C \ C=r_DX_Rf_DRFordamperbatteri: Flensramme Dryppanne650 A 650a1a2 40406 Øi / Øu= Kap Ø5 750mm50 D 14516 / 28AG 730835 FTA 835B 625b1b2 45401n/a 2n/a 3n/a710 FTB 710310 S 500Øi 16Øu 28Ødr R1/2