Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 36] [Pair 45] [Pair 45]12.6 55 2 2.12Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]35.3 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.7 287.0 34.3 36 6.7 297.0 31.5SR 36-45 5.6 454.0 30.0 36 6.1 463.0 26.8MAIN 36-45 8.2 462.0 29.6 36 9.8 499.0 25.0SR 36-45 7.7 500.0 27.8 36 7.5 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.4 477.0 11.7 45 14.0 5.9 46.9SR 36-45 14.4 477.0 11.7 45 13.9 5.0 48.3MAIN 45-36 14.4 477.0 11.7 45 16.9 486.0 8.5SR 36-45 14.4 477.0 11.7 45 17.0 495.0 8.30100806040200250 MHzACR-F (dB)