Title: 1 etg del 2.pdf
LinkWare Version 8.1Cable ID: T1232 Date / Time: 10/17/2013 02:12:19 PM Headroom 3.4 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]57 87 3 2.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]24.6 246.5 30.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 3.4 224.5 36.1 36 4.3 225.0 33.5SR 36-78 4.0 224.5 36.1 36 4.8 225.0 33.5MAIN 36-78 3.4 224.5 36.1 36 4.3 225.0 33.5SR 36-78 4.0 224.5 36.1 36 4.8 225.0 33.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 16.8 3.9 52.4 12 17.8 3.1 51.3