Title: FDV-DOKUMENTASJON.pdf
mm2mm2mm2mm2mm2Total break time at short-circuit< 1050006500StrandedScrew terminalTunnel terminalconnection on rear415 V 50/60 Hz16 x 51-holeCu strip (number of segments x width x segment thickness)ms°CTechnical data for design veriﬁcation24 x 8Box terminalBox terminalBox terminal250Direct on the switchDirect on the switch120max.max.max.Control cablesFlat copper strip, with holesFlat copper strip, with holesCopper busbar (width x thickness)OperationsOperationsOperationsOperationsTerminal capacityStandard equipmentPvidRated operational current for speciﬁed heat dissipation1 x (0.75 - 2.5)2 x (0.75 - 1.5)A1 x 161 x 161 x (10 - 16)2 x (6 - 16)1 x (10 - 16)2 x (6 - 16)M8Al circular conductorScrew connectionOperating ambient temperature min.Optional accessoriesAC--3InEquipment heat dissipation, current-dependentmin.min.min.mmmmmmmmmmmmmmOps/h1 x (25 - 185)1 x (25 - 185)