Title: Data tester Smestad skole - Detaljert.pdf
Margin 48,5 - 287,0 34,0 15,9Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,0 3,0 2,0 2,80Worst Value: Local: 45 22,5 43,7 21,2 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 23,0 15,6 7,4 68,75Remote: 36 13,5 8,0 5,5 480,00Worst Value: Local: 12 17,0 9,3 7,7 294,00Remote: 36 13,5 8,0 5,5 480,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,2 26,7 2,5 500,00Remote: 36-45 30,5 26,7 3,8 500,00Worst Value: Local: 36-45 29,2 26,7 2,5 500,00Remote: 36-45 30,5 26,7 3,8 500,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-36 21,5 10,6 10,9 480,00