Title: 2 etg del2.pdf
Cable ID: D2031 Date / Time: 10/10/2013 12:14:15 PM Headroom 12.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]100 160 12 4.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.0 77.8 34.1 36 14.2 77.8 31.1SR 12-36 12.7 97.3 32.5 36 14.3 77.8 31.1MAIN 12-36 12.3 97.0 32.5 36 14.6 97.3 29.5SR 12-36 12.7 97.3 32.5 36 14.6 97.3 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.6 2.0 52.6 36 19.3 2.0 49.6