Title: 2 etg del2.pdf
Wire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.9 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.2 250.0 35.3 36 0.5 * 250.0 32.7SR 12-36 9.9 219.0 36.3 12 9.6 241.0 33.0MAIN 36-45 1.2 250.0 35.3 36 0.5 250.0 32.7SR 12-45 10.5 240.5 35.6 12 9.6 241.0 33.010080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.7 50.3 30.2 45 16.6 43.3 28.5SR 45-36 14.6 50.3 30.2 45 16.5 42.8 28.6MAIN 45-36 16.6 248.0 16.3 36 18.0 247.5 13.3SR 45-36 16.5 250.0 16.2 36 18.0 239.5 13.6010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250