Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Plug-on variant modules with switching circuit to generate -15 V, power sources and linearization. Each of the four variants has a module of its own, i.e. amodule with different equipment.The user has access to the 4 potentiometers to set the offset for each individual channel. This can be useful for adjusting the zero value (at -50 °C) for long measurement cables.All modules are set up in pairs (base and variant module) at the factory. The vari- ant modules must not be exchanged.5-58PCD2.W11xThe 4 built-in potentiometers for setting the amplification are not accessible to the user and must not be adjusted.Substitution moduleNot user accessibleBasic moduleAdjustment of offsetTerminals Basic moduleBus connector I/O bus interface+15 VA/D converterAdjustment of amplification (not for users) Digital value = 4095 Temperature = +150°CAnalogue multiplexerInput amplifier Adjustment of offset Digital value = 0 --> Temperature = –50°CInput filter Screw terminals987654