Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0017. OPERATING MODESSECOND LEVELTHIRD LEVELBUZZER MUTEBuzzer Mute: noSINGLE UPS BATTERY TESTStatus: battery test Schedule battery test: noCLEAR EPO STATUSStatus EPO active Clear: noRESET FAULT STATEStatus: Fault active Reset fault: noCLEAR EVENT LOGTotal events: 50 Clear event log: noRESTORE FACTORY SETTINGSReset: noUSER PASSWORDenabled/disabledAUDIO ALARMenabled/disabledRATED OUTPUT VOLTAGE208/220/230/240 VOUTPUT FREQUENCYautosensing 50/60 HzPOWER STRATEGYnormal/high efﬁ ciency/ converterDC STARTenabled/disabledSITE WIRING ALARMenabled/disabledAMBIENT TEMPERATURE WARNINGenabled/disabledAUTOMATIC BATTERY TESTS PERIOD 0 to 31daysAUTO RESTARTenabled/disabledAUTOMATIC OVERLOAD RESTARTenabled/disabledAUTO BYPASSenabled/disabledSHORT CIRCUIT CLEARANCEenabled/disabledBYPASS VOLTAGE LOW LIMIT110 to 215 VBYPASS VOLTAGE HIGH LIMIT245 to 276 VBYPASS FREQUENCY LOW LIMIT1 to 10 %