Title: +038=360.019-#####._07-360.019 Gold SD-30 Ventilasjonsaggregat Swegon - quickguide.pdf
14582518 3258 2388 1600x800 4,72 16992 5,55 199806.5234005.52 19800 3x400V, 40/50A0703447 3454-37041274786-91190018822837 3580 2740 1800x1000 5,8 20880 6,82 245527.5270006.94 24900 3x400V, 40/63A0803447 3508-39021274813-101090018822837 3580 2740 1800x1000 6,03 21708 7,05 253809.5342006.79 24400 3x400V, 63/80A1003322 4294-488011261046-1314 1070 1101-1126 3740 4283 3440 2400x1200 9,02 32472 10,6 3816011.0396001139600 3x400V, 50/80A1203322 4494-515211261146-1450 1070 1101-1126 3740 4283 3440 2400x1200 9,25 33300 11,05 39780 14.0 5040010.7 38500 3x400V, 80/125ASILVER C unit without control systemSize Top 011-012GOLD RX/HC/HCBSize Top 014-030HBA BBAWL1L1LSFPv≤ 1,50 150 PaSFPv≤ 2,0 200 PaAmount of refi- gerant (kg)B mmLL1Max.A mmCooling capcity (kW)Heating capacity (kW)GOLD RX/HCW mmH mmSFPv≤ 1,5SFPv≤ 2,0Max.Max. EcodesignLL2m3/s m3/h m3/s m3/h m3/s m3/hmmkgmmkgWH