Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
22.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 6.5 468.0 29.9 36 6.0 500.0 26.4SR 12-36 7.9 499.0 29.3 36 8.7 500.0 26.4MAIN 36-78 6.9 500.0 29.2 36 6.0 500.0 26.4SR 12-36 8.0 500.0 29.2 36 8.7 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.9 346.0 14.5 45 20.8 357.0 11.2SR 78-45 19.9 341.0 14.6 45 21.6 366.0 11.0MAIN 12-45 20.4 422.0 12.7 45 21.4 403.0 10.1SR 45-12 20.6 422.0 12.7 12 21.9 423.0 9.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.6 26.5 42.2 36 20.5 26.5 39.8SR 36-45 17.2 26.4 42.3 36 18.9 26.4 39.9MAIN 36-78 29.3 500.0 -12.4 36 28.3 500.0 -15.3SR 12-36 30.2 500.0 -12.4 36 31.0 500.0 -15.30804000250 MHzACR-N (dB)