Title: 1 etg del 2.pdf
002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 8.1Cable ID: T1215 Date / Time: 10/17/2013 02:20:26 PM Headroom 12.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]101 161 12 4.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.9 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.4 93.3 32.8 36 14.6 96.5 29.6SR 12-36 12.5 61.0 35.8 36 14.7 96.5 29.6MAIN 12-36 12.7 99.8 32.3 36 14.6 96.5 29.6SR 12-36 12.6 99.8 32.3 36 14.7 96.5 29.610080604020NEXT (dB)