Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
QGH3492101-01 11/2018TopicPage464945Switchboard ConnectionsConnection to SwitchboardsIntroductionThe Canalis KT system can be connected to switchboards in the following ways:  Directly to the connection bars.  Using flexible links or connection bars, with a KTB••••CR• protective cover: In a vertical arrangement.  In a horizontal arrangement.Examples of connection arrangements:Procedure for Direct ConnectionThe procedure for direct connection to switchboards is described in instruction sheets available on the Schneider Electric website:  For connecting Canalis KTA1000-4000/KTC1350-5000 to switchboard: AAV17625.  For Canalis KTA5000/KTC6300 horizontal incomer arrangement: PHA44577.  For Canalis KTA5000/KTC6300 vertical incomer arrangement: PHA44578.StepAction1Check that the weight of the components does not rest on the switchboard. (seepage22)2Check the phase order of the components in the installation, the end feed unit, and the switchboard (seepage15).3