Title: 1 etg del 2.pdf
252 398 27 10.7252 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.6 242.5 35.6 36 1.7 249.5 32.7SR 36-450.9 *249.0 35.4 36 0.6 *249.0 32.7MAIN 36-45 1.6 242.5 35.6 36 1.7 249.5 32.7SR 36-45 0.9 249.0 35.4 36 0.6 249.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.0 52.5 29.8 36 17.2 53.8 26.6SR 36-45 15.1 52.5 29.8 45 17.1 45.3 28.1MAIN 36-45 19.8 250.0 16.2 12 19.9 231.5 13.9SR 45-12 18.8 227.0 17.1 36 18.6 237.5 13.7010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz