Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 34,7 68,0 180,0 10,0 6,4Limit 100,0 - 555,0 50,0 25,0Margin 65,3 - 375,0 40,0 18,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,6 3,0 2,4 2,80Worst Value: Local: 36 15,0 43,6 28,6 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 12,7 8,0 4,7 475,00Remote: 78 21,1 14,0 7,1 100,50Worst Value: Local: 78 12,7 8,0 4,7 475,00Remote: 78 16,1 8,0 8,1 455,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,1 26,7 2,4 500,00Remote: 36-45 29,5 26,7 2,8 498,00Worst Value: Local: 36-45 29,1 26,7 2,4 500,00Remote: 36-45 29,5 26,7 2,8 498,00dB 060