Title: Data tester Smestad skole - Detaljert.pdf
Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 36,3 68,0 188,0 10,0 6,0Limit 100,0 - 555,0 50,0 25,0Margin 63,7 - 367,0 40,0 19,0Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 2,05Worst Value: Local: 36 15,5 43,8 28,3 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 19,4 12,5 6,9 141,50Remote: 78 22,3 18,5 3,8 31,75Worst Value: Local: 78 15,2 8,0 7,2 497,00Remote: 36 15,4 8,0 7,4 474,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,5 26,7 1,8 498,00Remote: 36-45 30,0 26,7 3,3 500,00Worst Value: Local: 36-45 28,5 26,7 1,8 498,00Remote: 36-45 30,0 26,7 3,3 500,00dB 0601200Local250500 MHzdB 0