Title: økernvn 94.pdf
PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.4 28.8 41.0 12 11.3 22.5 41.4SR 12-36 9.5 28.8 41.0 12 10.6 22.5 41.4MAIN 36-45 17.3 249.5 4.7 36 17.3 248.0 2.2SR 12-36 17.7 248.5 4.8 36 17.3 249.5 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 2.8 22.4 19.3SR 36 1.8 22.4 19.3MAIN 36 7.8 237.5 10.2SR 36 7.7 249.5 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4