Title: 2 etg del2.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.2 244.0 5.3 36 7.6 242.5 2.8SR 12-36 8.3 39.8 37.0 36 8.0 237.5 3.3MAIN 36-45 8.3 250.0 4.7 36 7.6 248.5 2.2SR 36-45 9.0 248.5 4.8 36 8.7 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.1 22.5 19.2SR 45 3.2 13.9 20.3MAIN 36 6.5 235.5 10.3SR 36 5.5 194.5 11.1010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1