Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]35.1 152 2 5.27Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 6.8 469.0 29.8 45 7.6 460.0 27.2SR 36-45 7.6 500.0 29.2 36 7.7 500.0 26.4MAIN 12-45 6.8 469.0 29.8 45 7.9 500.0 26.4SR 36-45 7.6 500.0 29.2 36 7.7 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.3 93.0 25.9 45 14.1 2.9 53.1SR 45-36 15.4 93.0 25.9 45 14.2 3.0 52.7MAIN 78-45 15.8 500.0 11.3 45 15.4 500.0 8.3SR 36-78 15.5 469.0 11.8 45 16.1 500.0 8.30100806040200250 MHzACR-F (dB)