Title: 2 etg del2.pdf
229 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.3 250.0 35.3 36 1.0 * 250.0 32.7SR 36-450.1 *247.0 35.4 36 1.4 234.0 33.2MAIN 36-45 1.3 250.0 35.3 36 1.0 250.0 32.7SR 36-45 0.1 247.0 35.4 36 1.4 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 16.4 54.5 29.5 36 18.3 51.5 27.0SR 36-45 16.4 53.0 29.7 36 18.4 53.3 26.7MAIN 45-12 20.1 215.0 17.5 45 21.1 214.5 14.6SR 45-12 19.8 214.0 17.6 45 21.1 213.5 14.6010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)