Title: +038=66.009-##003._02-5DB - Brukermanual.pdf
parameters. number display type. View with decimal point. y = yes; n = no. CAlibration 1. Positive or negative temperature value added to the value read by probe 1. efrost display Lock. Viewing mode during defrosting. 0 = shows the temperature read by the room probe; 1 = locks the reading on the temperature value read by room probe when defrosting starts, and until the next time the Setpoint value is reached; 2 = displays the label “dEF” during defrosting, and until the next time the Setpoint value is reached. display read-out. Select °C or °F for displaying the temperature read by the thermostat probe.(0 = °C, 1 = °F). PLEASE NOTE: the switch between °C and °F DO NOT modify setpoint, differential, etc. (for example set=10°C become 10°F) Selection of type of value to be displayed. 0 = Setpoint; 1 = cold room probe (Pb1); 2 = evaporator probe (Pb2) CONFIGURATION Stand-by operating mode. 0 = display switch off; 1 = display switch off, loads and alarms stopped; 2 = display with OFF label, loads and alarms