Title: +038=370.001-IK009._01-Dynaciat LG 300 A Varmepumpe EPTEC - Modbus kommunikasjonsguide.pdf
Remote Terminal United Technologies CorporationSCTSaturated Condensing TemperatureSSTSaturated Suction TemperatureTCPTransmission Control ProtocolxxLS..Low SpeedxxHS..High SpeedThis document is the property of CIAT Corporation and is delivered on the express condition that it is not to be disclosed, reproduced in whole or in part, or used for manufacture by anyone other than CIAT Corporation without its written consent, and that no right is granted to disclose or so use any information contained in said document.DATEPAGEDynaCIAT LG/LGN – Modbus CommunicationOriginal03/04/20175 OF 212 CONNECTION CHANNELSHere below sockets available for communication purposes with external devices.sockets identification available for communicationNB: PORT 0 should be used only if it is not already used to connect a gateway integrated in the unit.2.1 RS485 socket details Bus “port0” is intended to Modbus serial line with RS485 (i.e. no control flow)