Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
The thermo-electric valve must be mounted on the unit after the unit installation. For this operation follow figures, depending on model. Assembly (Fig. 30) With 4–pipes models, first install the valve assembly for the cold circuit followed by the valve assembly for the hot circuit. Connect the valve assemble to the coil and fix it by a 30Nm torque. Insulate the valve assembly.Gasket type Rubber FibreNm 10/12 25/30Fit the actuator on the valve body, route the valve cable through the box and connect it to the terminal block as shown in fig. 37.To connect the steel pipes to the system, ensure they are aligned and supported to avoid excess strain on the unit. If the system is filled with water, check all fitting seals.After ending the hydraulic connections, make sure there are no leaks Insulate the valve using the shell, fix it by means of the clips and make sure that all cold parts are insulated (fig. 29 – 30).