Title: 370.011 LC001 10 kW isvannsenheter UPU 20 B.pdf
3 way ball valveCHILLED WATER CIRCUIT PERFORMANCESPerformance are declared according EN 14511 (at gross of the heat generated by the fan)Fluid 100 % recirculation Re-suction air Re-suction air Discharge air Discharge air Total cooling capacity: Sens.cooling capacity: EER (Energy Effinciency Ratio)[°C] [%] [°C] [%] [kW] [kW]50,0Water + Glycole 0,0%WB [°C]24,0 17,0 12,7 99,9 10,8 10,2 27,69[°C] [°C] [l/h] [kPa] [kPa] [kPa]Water temp.inlet: Water temp.outlet: Chilled water flow : Coil pressure drop . Valve pressure drop Total pressure drop : EER = total cooling capacity / fans power input.10,0 16,0 1.540 10,5 6,0 16,5VENTILATING SECTIONPlug fan EC type, air flow control according cooling capacity EC type plug fan for supply air flow regualtion inAvailable static pressure : Total air flow : Fan[Pa] [m3/h] [n]30 2.700 1Total power input R.P.M.[kW]0,39 73 %ACOUSTIC PERFORMANCESSWL fan discharge SPL front of the unit[dB(A)] [dB(A)]72 52