Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
MAIN 36-45 22.0 80.5 27.6 36 22.6 81.0 25.0SR 36-45 20.9 80.3 27.7 45 22.4 80.8 25.1MAIN 12-36 40.1 499.0 -12.3 36 39.9 499.0 -15.2SR 12-36 39.0 499.0 -12.3 36 38.8 499.0 -15.20804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.5 499.0 8.0SR 45 6.1 489.0 8.0MAIN 45 8.5 499.0 8.0SR 45 6.1 489.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: MCKINSEY 4 ETGMcKinsey 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00423.1 m60Insertion Loss (dB)504030201000250 MHz500100NEXT @ Remote (dB)8060402050000250 MHz500100ACR-F @ Remote (dB)8060402050000250 MHz500ACR-N @ Remote (dB)80400500400250 MHz500