Title: økernvn 94.pdf
SR 36-45 17.9 64.5 28.0 45 19.0 3.9 49.4MAIN 45-12 19.7 229.0 17.0 12 22.0 229.0 14.0SR 45-12 19.3 233.0 16.8 45 22.0 227.5 14.0010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.3 21.9 44.1 12 12.2 25.8 39.9SR 12-36 11.7 37.8 37.6 12 13.2 19.8 42.9MAIN 36-45 16.7 248.0 4.9 36 16.9 250.0 2.0SR 36-45 17.6 246.0 5.1 36 17.5 246.0 2.4010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 2.7 13.6 20.3SR 45 2.4 13.6 20.3MAIN 36 6.8 190.0 11.2SR 45 7.4 244.5 10.1010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active