Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]39.1 170 3 5.74Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]24.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.4 500.0 29.2 36 7.8 500.0 26.4SR 36-45 8.0 500.0 29.2 36 7.9 491.0 26.6MAIN 36-45 8.4 500.0 29.2 36 7.8 500.0 26.4SR 36-45 8.0 500.0 29.2 36 8.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-78 14.5 420.0 12.8 45 13.4 2.3 55.2SR 78-36 14.4 420.0 12.8 45 13.3 2.3 55.2MAIN 36-78 14.7 470.0 11.8 45 15.7 468.0 8.8