Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Inside the compartment, find the position of the module that corresponds to one of the connectors on the PCB bar (paragraph 3.1 - [N]). If you are installing an IFM24160 power-supply module, you must use the first connector at the top (paragraph 3.1 - [R]). When installing any other type of internal module, you can use this or any other connector that is free (paragraph 3.1 - [S]).2. Position the module in such a way that it is on level with the desired connector on the bar hen insert it in place by pushing it carefully to the left.3. Affix the module to one of the holes on the grounding bar (paragraph 3.1 - [L]) using one of the supplied screws.3. Affix the module to one of the holes on the grounding bar (paragraph 3.1 - [L]) using one of the supplied screws.4. Complete the wiring on the internal module (refer to paragraph 5.5.1 Cable entry and the paragraphs regarding the wiring of each internal module).