Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 59,8 68,0 311,0 18,0 10,4Limit 100,0 - 555,0 50,0 25,0Margin 40,2 - 244,0 32,0 14,6Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 1,2 3,0 1,8 2,80Worst Value: Local: 36 25,1 43,6 18,5 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 18,1 12,2 5,9 152,50Remote: 78 20,1 18,1 2,0 37,75Worst Value: Local: 78 16,2 8,0 8,2 470,00Remote: 36 14,4 8,0 6,4 474,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):