Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
30.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.0 455.0 30.0 36 8.7 450.0 27.4SR 12-45 10.8 430.0 30.7 36 10.3 471.0 26.4MAIN 36-45 9.3 498.0 27.9 36 8.8 498.0 25.1SR 12-36 11.2 493.0 28.2 36 11.1 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.9 3.8 53.8 45 14.0 2.6 53.9SR 36-45 14.9 3.8 53.8 45 13.9 2.5 54.3MAIN 36-45 16.1 473.0 11.7 45 16.8 499.0 8.3SR 36-45 16.3 473.0 11.7 45 17.1 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 24.2 86.3 26.6 78 26.1 86.0 24.1SR 36-78 25.2 91.5 25.6 45 25.0 85.5 24.2MAIN 36-45 38.8 498.0 -12.3 36 38.7 498.0 -15.1SR 12-36 41.1 493.0 -11.9 36 41.0 498.0 -15.10804000250 MHzACR-N (dB)