Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF010 16C2/003 30.11.2020 12:01 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF010 16C2/003 30.11.2020 10:46SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 49.9HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF011 16C2/003 30.11.2020 12:06 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF011 16C2/003 30.11.2020 10:48Tallberg Elektro A/S Tlf.22796640Side:2GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.1414151516161717181819192020TEST RAPPORTResultatSPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF012 16C2/003 30.11.2020 12:24 (ELEKTRIKER)ISOLASJON: ALLE