Title: 40 Bender brukermanual.pdf.pdf
ALARM 1/1 Residual current130 mA Addr.: 2 Chan.: 12Line 1:Line 2:ALARM, PREWARNING or FAULT Alarm 1 of 1 pending alarms Alarm status and alarm text: (e.g. residual current, digital in- put, no Master, CT connection). No alarm Prewarning Alarm, faultLine 3: Line 4:r.m.s. value BMS bus address of the RCMS and measuring channel on which the alarm has occurred.  RCMS…-L…: The alarm LED of the affected measuring channel lightsup.RCMS…-D4/-L4 only (channels 9…12): When measuring the load current, a prewarning is indicated in case of overcurrent only. In case of undercurrent a prewarning is not indicated.40RCMS460-490_D00067_03_M_XXEN/12.2017OperationTest procedure6.3.3 A test serves to check the device function (hardware components) of the RCMS. A test can be activated as follows:   Select standard display and then press the "TEST" button on the RCMSfront panel for at least one second.