Title: 360.001 - Tilluft.pdf
3. etasje3. etasje3. etasjeNodeTypeProduct17 PLUGESU-315REDUCERMAGIR-CC1-400-200DUCTMAGID-C1-200BEND-90MAGIB-C3-90-200DUCTMAGID-C1-200BEND-30MAGIB-C3-30-200DUCTMAGID-C1-200BEND-90MAGIB-C3-90-200DUCTMAGID-C1-200FIREDAMPER FKRS-EU/200/ZXXSize315400/200200200200200200200200200Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]4501,01,34504,04504,00,34504,04504,00,64504,04504,00,04504,04504,032Sound in:1,4 Sound in:Attenuation: Addition:2,7 Sound in:Attenuation: Addition:0,3 Sound in:Attenuation: Addition:0,9 Sound in:Attenuation: Addition:0,6 Sound in:Attenuation: Addition:2,7 Sound in:Attenuation: Addition:0,0 Sound in:Attenuation: Addition:4,2 Sound in:Addition:63 [dB]34.034.00.1 +20.234.00.0 +31.836.10.0 +20.236.20.0 +20.236.30.1 +20.236.30.0 +31.837.60.0 +20.237.7+42.9125 [dB]29.529.50.1 +19.129.7