Title: +038=67.005-##003._03-Ø4 og Ø5 MR fordamper.pdf
For low temperature refrigerated rooms, defrost termination and fan delay thermostat with single-pole, double throw switch at +12 °C (±3 K) and +2 °C (±3 K). Supplied with a sensor and a fitting clamp.APPLICATIONtA1 +10+2510MR...4,23 mmModelsMR75110135210270R404A SC 2 (1) DT1 = 8 KCapacityQ0mW6801070127020602620Surfacem23,353,666,1010,0513,40Circuit vol.dm30,580,631,051,732,30Air flowm3/h2906505808701160Air throw (2)m33,73,544,5Fan 230 V/1/50-60 Hz 1500 r.p.m.Ø 200 mmNo12234W max A max (3)1 x 38 1 x 0,242 x 38 2 x 0,242 x 38 2 x 0,243 x 38 3 x 0,244 x 38 4 x 0,24Net weightkg37,59,51520