Title: DOCA0005EN-12.pdf
DescriptionRMS MeasureThis tab provides power, current, and voltage values as well as frequency and power factor information.Meter StatusThis tab provides information on the settings and status of the digital input, digital outputs and alarms as well as existing power system settings.Configuring the meter using the M-Bus tool1. Select Setup > Config to switch to configuration mode.2. Set the values that you want to change then click Send for that value or section.For example, to change the nominal frequency, select a different value from the list then click Send in Set Wiring.Some values may be unavailable based on existing settings.NOTE: If Com. Protection is enabled, you may receive a message that the configuration failed. Use the HMI to either: 1) configure the meter, or 2) disable Com. Protection then configure the meter using the tool.DOCA0005EN-12105106Communications via M-BusiEM3000 series user manualThe configuration screen has the following sections:Section