Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
SR 36-45 16.0 488.0 11.5 45 15.1 498.0 8.30100806040200250 MHzACR-F (dB)N/A Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 21.6 3.6 60.8 12 21.7 3.9 58.0SR 12-45 21.9 5.5 57.8 12 21.5 4.0 57.8MAIN 36-45 41.5 474.0 -10.7 36 41.6 475.0 -13.6SR 36-45 41.0 475.0 -10.7 36 41.8 475.0 -13.60804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 12 4.3 493.0 8.0SR 12 4.1 493.0 8.0MAIN 12 4.3 493.0 8.0SR 12 4.1 493.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: Uni ConsultUniconsult tester.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420696 Remote S/N: 2420901 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA0044.2 m60Insertion Loss (dB)504030201000250 MHz500