Title: 40 Bender Datablad.pdf.pdf
Set response value Menu option “50 Hz” – plant protection: Only evaluates the fundamental component of the residual current. Menu selection “60 Hz”– Plant protection: Only evaluates the fundamental component of the residual current. Menu selection “IEC”– Touch current for let go (protection of persons) in accordance with IEC 60990 Menu selection “None”– Fire protection: Response factor remains the same over the entire frequency range.Residual current monitors LINETRAXX® RCMS460-D/-L – RCMS490-D/-LExample for a design of a – minimum system consisting of an RCMS460-D and 12 measuring points1Example for a system design of – standard system consisting of an RCMS460-D and RCMS460-L and a protocol converter COM465IPCOM465IPCOMTRAXX®1ONETHERNET/IPMODBUS/RTU BMSRCMS460-DRCMS460-LAN420COM465IPUS AC 85…260 VNLDI-1DL2B/N A/PB/N A/P