Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
SR 45-78 18.9 496.0 11.3 45 18.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.9 33.5 39.5 36 16.6 33.5 37.0SR 36-45 14.8 33.5 39.5 45 16.0 36.5 36.0MAIN 12-36 32.5 500.0 -12.4 36 33.2 500.0 -15.3SR 12-36 35.0 500.0 -12.4 36 33.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 9.5 451.0 8.0SR 45 8.4 498.0 8.0MAIN 45 9.5 451.0 8.0SR 45 8.4 498.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: SP1 BANK 4 ETGSMN 4 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00437.9 m60Insertion Loss (dB)504030201000250 MHz500100