Title: +038=360.029-#####._05-360.029 GOLD RXF TOP Ventilasjonsaggregat Swegon - Passivhus sertifisering.pdf
Airflow range540-9000 m³/h at an external pressure of 222-359 PaRequirements non-residentialbuildings (Therefore also applic- able for residential buildings)Heat recovery rateηHR ≥ 84 %Specific electric powerPel,spec 0.45 Wh/m³ 3)Swegon Operations AB Box 300, 535 23 Kvänum, Sweden  +46 (0) 31 89 58 00 |  info@swegon.se |  http://www.swegon.com |DIt n e n o p m o Cle d o mt i n Ug n i t s e Ts t n e m e r i u q e rAirflow rangeMinMaxm³/hm³/hla n r e t x Ee r u s s e r pPac i f i c e p Sc i r t c e el) 1r e w o pWh/m³t a e Hy r e v o c e r%e t a r0558vl0304Non-residential54010002220.45850559vl0305Non-residential54010002220.45850560vl0307Non-residential54018202650.45860561vl0308Non-residential108017802590.45840562vl0311Non-residential108024652810.45850563vl0312Non-residential180026002810.45840564vl0314Non-residential180042853160.45