Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:19)(cid:24)(cid:18)(cid:20)(cid:21)(cid:18)(cid:20)(cid:20)(cid:3)(cid:3)(cid:3)(cid:20)(cid:28)(cid:29)(cid:20)(cid:21)Type “A” and “B” controls have a knob to select the temperature, with a range from 10°C to 30°C, and room temperature is maintained at the selected value.NTC ControlPower supply connection (fig. 38-39)IMPORTANT: Make earth connection prior to any other electrical connections.Before proceeding with the unit connection to the mains supply locate live L and neutral N, then make connections as shown in the figures 38-39.Communication bus connection • Use connector “J9” (ref. B) on the card to connect the communication