Title: Hardware Installation Guide.pdf
7. Connect appropriate trouble reporting devices to AC Fail and Low Battery supervisory relay outputs marked NC, C, NO. Use 22 AWG to 18 AWG for AC Fail and Low Battery reporting. AC Failure will will report in 2 minutes; 2 hours if jumper is cut. For a six-hour delay on reporting, cut resistor R1.7. Connect appropriate trouble reporting devices to AC Fail and Low Battery supervisory relay outputs marked NC, C, NO. Use 22 AWG to 18 AWG for AC Fail and Low Battery reporting. AC Failure will will report in 2 minutes; 2 hours if jumper is cut. For a six-hour delay on reporting, cut resistor R1.revision 6 — 33To install multiple Lenel hardware panels into a single enclosure, the following guidelines must be used for certified UL installations.All wire connections that cross over the hinge side of the door must be wire wrapped or tie wrapped together.All wire must be routed behind the hardware panel so that the wires are secure from movement when opening and closing the door.