Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
GODKJENT*GODKJENTGODKJENTGODKJENTGODKJENT*Nr.107107108108109109110110111111112112113113TEST RAPPORTResultatSPĆNDINGUln: 233V Ulpe: 233V Unpe: 1V f: 50.0HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF048 C16/2 15.06.2020 10:15Z-LINEZ: 0.39ΩIsc: 596A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF048 C16/2 15.06.2020 10:15Zs(rcd)Z: 0.33ΩIsc: 693A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF048 C16/2 15.06.2020 10:16RCD II: 28.5mAUci: 0.1V t: 84.6ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF048 C16/2 16.06.2020 09:48R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF048 C16/2 16.06.2020 09:55R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 15.06.2020 08:37SPĆNDINGUln: 232V Ulpe: 232V Unpe: 1V f: 50.0Hz