Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 10.06.2020 11:10Tallberg Elektro A/S Tlf.22796640Side:11GODKJENTMISLYKKESMISLYKKESMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESGODKJENTGODKJENT*GODKJENTGODKJENT*Nr.767677777878797980808181TEST RAPPORTResultatSPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 12.06.2020 12:33R LOW OhmR: 0.13ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 12.06.2020 10:22Z-LINEZ: 0.54ΩIsc: 425A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 12.06.2020 10:22Zs(rcd)Z: 0.48ΩIsc: 482A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 12.06.2020 11:25RCD tt: 57.9msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 12.06.2020 11:26RCD I