Title: Jordfeilautomat 3+N.pdf
placed. Ambient temperature is the temperature inside the enclosure or switchboard in which the circuit breakers are installed.The reference temperature is 30℃Temperature10℃0℃10℃20℃30℃40℃50℃Temperature compensationcoefficient of rated current1.201.151.101.051.000.950.903. Overall and mounting dimensions (mm)49.5±0.31130405850±5.40±54300720.84770.1460℃0.85> >> 02Modular DIN Rail ProductsModular DIN Rail Products RCBORCBO2.2NB310L Residual CurrentStandardIEC/EN 61009-1Operated Circuit BreakerType (wave form of the earth leakage sensed)A, ACwith over-current protectionThermo-magnetic release characteristicB, C(Magnetic)6, 10, 13, 16, 20, 25, 32, 40ARated current In3P+NPoles1. GeneralRated voltage Ue400VRated sensitivity I△nA0.031.1 FunctionRated residual making and breaking capacity I△mA3,000Personnel and fire protection: Cable and line protection against