Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Side:24GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.167167168168169169170170171171172172173173TEST RAPPORTResultat KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 30.11.2020 09:09Z-LINEZ: 0.36ΩIsc: 640A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 30.11.2020 09:10Zs(rcd)Z: 0.35ΩIsc: 657A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 30.11.2020 09:09SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 30.11.2020 09:45RCD II: 28.5mAUci: 1.6V t: 28.2ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 27.11.2020 11:51R LOW OhmR: 0.16ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7Ω