Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF043 16C2/003 26.11.2020 13:48SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF043 16C2/003 15.12.2020 10:35 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 255V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF044 16C2/003 26.11.2020 13:53SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF044 16C2/003 15.12.2020 10:35 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 255V Rlpe: >30.0MΩ Um: 256V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF045 16C2/003 26.11.2020 14:28Tallberg Elektro A/S Tlf.22796640Side:27GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.187187188188189189190190191191192192TEST RAPPORTResultatSPĆNDING