Title: 2079500_9070917_9070918_9070531 thePrema, kapper, gitter..pdf
Time delay The time delay enables delayed switching off of HVAC devices and systems after the room is vacated.Room monitoring channel C6 In the room monitoring channel the sensitivity of the presence detection is reduced. A telegram is only sent when a significant movement occurs and indicates the presence of people with a high degree of certainty. A separate time delay is available for the room monitoring.Detection rangeThe square detection area of the presence detector guarantees accurate and simple planning. Square detection areas make it possible to cover a whole room with parallel switching. Note that seated and moving persons can be detected in differently- sized areas. The recommended installation height is 2.0 m – 3.0 m. The sensitivity of the presence detector decreases with higher installation heights. Walking motions are necessary from installation heights of 3.0 m and the detection areas of several detectors should overlap in the marginal zones.