Title: 1 etg del 2.pdf
ACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.2 14.1 48.8 12 9.8 14.1 46.4SR 12-36 7.8 14.1 48.8 36 9.1 14.1 46.4MAIN 36-45 11.4 249.5 4.7 36 11.1 250.0 2.0SR 36-45 10.4 249.0 4.8 36 10.0 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 1.6 27.5 18.8SR 45 3.2 38.3 18.1MAIN 45 6.6 156.0 12.1SR 45 7.7 236.0 10.3010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1