Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
Connection of the batteries before the mains voltage is present will not activate the system. Once the mains voltage is supplied, the power-supply module will connect the batteries automatically and initialize the circuits which manage them.D5. The thermal probe must be positioned on the side of the battery and held in place by a strip of tape ([D]).5. The thermal probe must be positioned on the side of the battery and held in place by a strip of tape ([D]).36InstallationInstallation manual5.6.2 Output connectionEach output of the IFM24160 module can be configured to activate specific conditions. If left at their default settings, the three outputs will be as follows:OUT 1 (paragraph 3.6 - [D]), supervised output which activates in the event of a generic fire alarm • OUT 2 (paragraph 3.6 - [E]), constantly active output (27.6V constant) for powering external devices • RELAY (paragraph 3.6 - [F]), voltage free contact which activates in the event of fault