Title: 1 etg del 2.pdf
75100LinkWare Version 8.1Cable ID: T1228 Date / Time: 10/17/2013 02:21:15 PM Headroom 20.0 dB (NEXT 12-78) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]92 140 5 4.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]15.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-78 20.0 100.0 32.3 12 21.1 85.3 30.4SR 36-78 21.5 67.3 35.1 36 20.9 92.8 29.8MAIN 12-78 20.0 100.0 32.3 78 21.2 100.0 29.3SR 12-36 21.8 99.5 32.3 36 20.9 92.8 29.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)