Title: Hardware Installation Guide.pdf
294 — revision 6Hardware Installation GuideThe RS-485 communication is asynchronous, half-duplex, using 1 start bit, 8 data bits, 1 stop bit.LNL-1200 series 2 upstream controller communication wiring: 2-wire (port 1)RS-485 2-WIRE COMMUNICATIONS2 WTR +TR -SGT+ T- SGEarth GroundWire with 24 AWG stranded twisted pair with shield52.1.3Relay OutputsThe Output Control Module contains sixteen (16) form-C dry-contact relay outputs, Output 1 through Output 16, which each provide up to 5A 30 VDC, or 125 VAC current (resistive). Each output is an SPDT (single pole, double throw) contact.To wire the Output 1 - Output 16 relay contacts, use sufficiently large wires for the load to avoid voltage loss.Transient clamping must be provided to protect the output contacts and to reduce EMI emissions. For AC- powered devices, use MOV across the load. For DC-powered devices, use a diode across the load.revision 6 — 295LNL-1200 Output Control ModuleRelay Output Wiring (Ports 2-5)NCFUSEC