Title: fireray5000_igb.pdf
Page 41.2 Fitting the ProductOptions for Detector wiring orientationInstallation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 5InstallationInstallation1.3 Wiring Diagrams Fire Resistor – Contact Fire Control Panel manufacturer for values of Fire Resistor. Some Zone and Switch Interface Modules do not need a Fire Resistor – replace Resistor with a short circuit. Refer to supplied CD for further information. ALWAYS use a seperate screened 2- core cable for each detector head End of Line (EOL) component is supplied by Fire Control Panel manufacturer CAUTION: For system monitoring – Do Check operation of Fire and Fault connectionon Fire Panelnot use looped wire under any terminals. Break wire run to provide monitoring of connections.Installation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 6