Title: Data tester Smestad skole - Detaljert.pdf
Margin 63,7 - 367,0 40,0 18,4Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 0,6 3,0 2,4 2,05Worst Value: Local: 36 15,6 43,8 28,2 500,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 17,5 8,9 8,6 326,00Remote: 12 19,6 11,6 8,0 174,50Worst Value: Local: 78 17,2 8,0 9,2 495,00Remote: 36 18,0 8,0 10,0 463,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,6 26,7 2,9 497,00Remote: 36-45 30,0 26,7 3,3 500,00Worst Value: Local: 36-45 29,6 26,7 2,9 497,00Remote: 36-45 30,0 26,7 3,3 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45-12 69,4 59,3 10,1 1,75