Title: fireray5000_igb.pdf
850 nmRapid obscuration Fault threshold87%Operating Temperature (UL Approved)0 - + 37.8 Deg COperating Temparature (EN54-12 Approved)10 - + 55 Deg CStorage temperature40 - + 85 Deg CRelative Humidity (non condensing)93%IP RatingIP54Relay Contact Voltage30V DCRelay Contact Current100 mAMaximum Cable Length (Controller to Detector)100mCable Gauge24-14 AWG 0.5-1.5 mmHousing Flammability ratingUL94 VOInstallation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 25System InformationParameter Pass Code Power ModeCompensation LevelDefaultDescription User Code required to access Enigneering Menu 1 2 3 4 ‘Hi A’: System will operate at 50mA constant current consumption ‘Lo A’: System will operate at 10mA constant current consumption Range – 50 to + 205. level of amplification applied to compensate for dust build-up and building movement at 75 Auto-optimise is started‘Lo A’