Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]39.8 172 2 5.77Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]24.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.9 500.0 29.2 36 7.5 500.0 26.4SR 36-45 7.9 500.0 29.2 36 7.9 485.0 26.7MAIN 36-45 7.9 500.0 29.2 36 7.5 500.0 26.4SR 36-45 7.9 500.0 29.2 36 8.0 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.0 472.0 11.8 45 14.0 8.9 43.3SR 78-45 15.2 4.0 53.2 45 14.0 13.0 40.0MAIN 78-45 15.3 500.0 11.3 45 14.8 500.0 8.3SR 45-78 15.8 500.0 11.3 45 14.8 476.0 8.70100806040200250 MHzACR-F (dB)