Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
HW2HW3CW1CW2ηs heat 30/35°C & SCOP 30/35°C ηs heat 47/55°C & SCOP47/55°C SEER 12/7°C & SEPR 12/7°C SEPR -2/-8°C IPLV.SI - (1)(2)Eurovent certified values1213Technical characteristicsDYNACIAT LG080090100120130150180200240260300DimensionsLengthmm600600600600600600880880880880880Widthmm10441044104410441044104414741474147414741474Heightmm901901901901901901901901901901901Operating Weight (3)Standard unitkg191200200207212220386392403413441Unit with evaporator with single LP pumpkg250258258263266271431435442449465Unit with condenser with single LP pumpkg250258258263266271431435442449465Unit with evaporator with single variable-speed HP pump + condenser with single variable-speed HP pumpkg305313313321327334513521533544574CompressorsHermetic Scroll 48.3 r/sCircuit AQty11111