Title: 360.002 - Tilluft.pdf.pdf
0.0 +24.329.91.5 +0.04.124.30.0 +8.224.4+0.024.40.0 +8.224.524.50.1 +16.525.13.0 +16.523.10.3 +16.523.7+13.18k [dB]21.60.0 +17.322.91.5 +0.04.117.40.0 +1.217.5+0.017.50.0 +1.217.617.60.1 +9.518.23.0 +9.516.20.3 +9.516.8+3.1Lp [dB]LocationLevel3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasje2. Etasje2. EtasjeNodeTypeDUCTSILENCERDUCTBEND-90DUCT4 T-BRANCHDUCTDUCT5 TAPDUCTProductSize315LKR-315-1200315315MAGIB-C4-*-*315315TCPU_DK-*-*0,0 315/315315315MAGIO-RC-*315/250250L [m]0,00,21,20,80,30,1Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]12004,30,0 Sound in:Attenuation: Addition:12004,311,0 Sound in:Attenuation:12004,30,2 Sound in:Attenuation: Addition:12004,32,8 Sound in: