Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]18.5 81 2 3.02Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.5 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.1 481.0 28.7 36 7.1 468.0 26.5SR 36-45 6.4 431.0 30.6 45 7.0 434.0 27.8MAIN 36-45 8.9 500.0 27.8 36 8.1 499.0 25.0SR 36-45 7.2 494.0 28.1 45 7.6 486.0 25.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.9 5.0 51.3 45 17.7 3.8 50.8SR 45-78 17.0 5.0 51.3 45 17.8 37.0 30.9MAIN 78-45 19.0 500.0 11.3 45 20.5 500.0 8.3SR 78-45 19.0 500.0 11.3 45 20.0 499.0 8.30100806040200250 MHzACR-F (dB)