Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
53,9 78,1 78,1 80,9 86,9 108,4 96,8 97,9 104,1 112,3 137,4 127,3 137,7 166,4 150,5 163,1 195,4(1) Maximum instantaneous starting current (maximum operating current of the smallest compressor(s) + locked rotor current of the largest compressor). (2) Power input, at the unit’s permanent operating limits (indication given on the unit’s name plate). (3) Standardised EUROVENT conditions, water type heat exchanger input/output = 12°C/7°C, outdoor air temperature = 35°C. (4) Maximum unit current at 400V, during non-permanent operation (indication given on the unit’s name plate) (5) Maximum unit current at 360V, during non-permanent operation ■ Short circuit current withstand capability (TN system(1))DYNACIAT LG080 090 100 120 130 150 180 200 240 260 300 360 390 450 480 520 600Value without upstream protectionShort time assigned current (1s) - IcwkA eff333333333335,55,55,55,55,55,5Allowable peak assigned current - IpkkA pk666666666662020