Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
MERCOR SA – The company reserves the right to make modifications and changes9/21mcr WIP multi-plane fire dampers Cut-off type fire dampers mcr WIP can be also mounted in building partitions of lower fire resistance class. In the case of such mounting, the above mentioned dampers have the fire resistance equal to the fire resistance of the wall with keeping the smoke-proof criterion.6.1. PRE-INSTALLATION INSPECTION ___________________________________________ Each fire damper is inspected before packing and shipment by the manufacturer. After unpacking at the recipient, perform visual inspection to check if the casing has not been deformed and whether the fire damper has not been damaged during transport.6.2. INSTALLATION OPENING __________________________________________________ The minimum size of the opening permitting correct installation of the rectangular fire damper is (B+160+A)x(H+140) mm.Fire damperwith Belimo actuator of series BLF with Belimo actuator of series BF with KW1 mechanism