Title: økernvn 94.pdf
Cable ID: T3081 Date / Time: 09/12/2013 03:47:16 Headroom 10.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]92 145 10 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.1 100.0 32.3 36 13.8 100.0 29.3SR 12-36 10.3 100.0 32.3 36 13.0 100.0 29.3MAIN 12-36 11.1 100.0 32.3 36 13.8 100.0 29.3SR 12-36 10.3 100.0 32.3 36 13.0 100.0 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 24.9 6.0 43.1 45 25.7 4.1 43.3