Title: økernvn 94.pdf
Cable ID: D4082 Date / Time: 09/10/2013 01:19:39 Headroom 13.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]149 236 16 6.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.2 61.3 35.8 36 15.1 98.8 29.4SR 12-36 13.4 61.3 35.8 36 15.6 98.5 29.4MAIN 12-36 14.1 98.8 32.4 36 15.1 98.8 29.4SR 12-36 14.0 92.0 32.9 36 15.6 98.5 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.6 82.8 20.3 45 24.5 68.5 18.9