Title: Simployer - Data testrapport =514.204-FS001.pdf
Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]35.3 180 12 7.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.2 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 9.2 76.8 41.9 4,5 10.1 76.8 39.1SR 1,2-3,6 8.0 202.0 34.7 3,6 9.9 181.5 32.6MAIN 3,6-7,8 10.6 239.0 33.5 3,6 11.4 239.0 30.5SR 1,2-3,6 8.0 202.0 34.7 3,6 10.2 202.5 31.8PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 18.2 193.0 17.5 4,5 18.3 4.6 47.0SR 7,8-4,5 18.0 202.0 17.1 4,5 18.5 4.6 47.0MAIN 7,8-4,5 18.5 233.5 15.9 4,5 19.0 225.5 13.2