Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3009 Date / Time: 09/11/2013 05:01:16 Headroom 14.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]111 177 13 4.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.2 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 20.1 53.0 36.8 36 21.1 53.0 33.8SR 12-36 14.9 52.8 36.9 36 15.8 53.3 33.8MAIN 36-45 21.3 94.8 32.7 36 21.7 94.8 29.7SR 12-36 15.6 97.3 32.5 36 16.0 97.0 29.510080604020NEXT (dB)