Title: 320.004-LV003  115 kW B28x96.pdf
°C cP cP kg/m³ kJ/kg,°C W/m,°C K °C °C W/m²,°C °C m/s Pakg kg dm³ dm³ mm mm mm mm mm mm mm mm kgbar bar ºC F1 F2 F3 F4 in/outA B C D E F G P RSWEP International AB Box 105, Hjalmar Brantings väg 5 SE-261 22 Landskrona, Sweden www.swep.netSSP G7 - (v 7.0.3.55)Side 1 35,00 0,720 0,756 994,1 4,178 0,6233Side 2 27,50 1,79 1,59 1043 3,670 0,46140,7326,81 38,41 12900 32,59 0,255 41,826,08 38,04 6750 32,11 0,188 30,0Side 1Side 217,8 29,1 5,45 5,57 33,0 33,0 33,0 33,0 36,0 36,0 36,0 36,0 125 AISI 316 25/22 40 155/225ISO-G 1 1/4" A AISI 304(27) ISO-G 1 1/4" A AISI 304(27) ISO-G 1 1/4" A AISI 304(27) ISO-G 1 1/4" A AISI 304(27) F2/F4F3/F1mm mm mm mm mm mm mm mm mm526 +/-2 119 +/-1 470 +/-1 63,0 +/-1 27,1 +/-1 219 +/-2% 6,00 +/-1 15 23,0Date 2016-06-01Page 2(3)SWEP International AB Box 105, Hjalmar Brantings väg 5 SE-261 22 Landskrona, Sweden www.swep.netSSP G7 - (v 7.0.3.55)