Title: Data tester Smestad skole - Detaljert.pdf
Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,4 11,2 10,2 446,00Remote: 12-45 21,9 11,3 10,6 441,00Worst Value: Local: 12-45 21,4 11,2 10,2 446,00Remote: 12-36 21,6 10,5 11,1 486,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,3 23,9 2,4 494,00Remote: 36 27,3 23,9 3,4 496,00Worst Value: Local: 36 26,3 23,9 2,4 494,00Remote: 36 27,3 23,9 3,4 496,00PS-ACRF: Pass Worst Margin: Local: 12 24,9 12,8 12,1 264,00Worst Value: Local: 45 20,8 8,3 12,5 440,00Remote: 45 66,3 54,3 12,0 2,20Remote: 36 19,5 7,3 12,2 495,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:03Signature:______________________ Page: 66Copper Certification Report