Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF002 16C2/003 30.11.2020 09:34SPĆNDINGUln: 235V Ulpe: 234V Unpe: 0V f: 50.0Hz66DM1-3. Plan 6 / DM1.E5=433.06.04 / XF006 16C2/003 30.11.2020 12:02 (ELEKTRIKER)Tallberg Elektro A/S Tlf.22796640Side:1Rapport opprettet06.01.2021GODKJENTGODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.7788991010111112121313TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 255V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF006 16C2/003 30.11.2020 09:44SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF007 16C2/003 30.11.2020 12:01 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF007 16C2/003 30.11.2020 09:45SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 50.0Hz