Title: +038=360.019-#####._05-360.019 Gold SD-30 Ventilasjonsaggregat Swegon - Installasjonsanvisning.pdf
GOLD SD 008 cap. var. 2, 011 cap. var. 2, 012 3-phase, 5-wire, 400V -10/+15%, 50HzL1L2L 1L 2GOLD SD 008 cap. var. 2 10A GOLD SD 011 cap. var. 2 10A 10A GOLD SD 012L3L 3NNPEP E230V400V151610.GOLD SD 014/020, 025/030, 035/040, 050/060, 070/080400VGOLD SD 014/020, 025/030, 035/040, 050/060, 070/080 3-phase, 5-wire, 400V -10/+15%, 50HzL 1L 2L 3NP EL1L2L3NPE10A GOLD SD 014 10A GOLD SD 020 10A GOLD SD 025 10A GOLD SD 030 10A GOLD SD 035 16A GOLD SD 040 cap. var. 1 GOLD SD 040 cap. var. 2 20A GOLD SD 050 cap. var. 1 16A GOLD SD 050 cap. var. 2 20A GOLD SD 060 cap. var. 1 16A GOLD SD 060 cap. var. 2 25A GOLD SD 070 cap. var. 1 16A GOLD SD 070 cap. var. 2 25A GOLD SD 080 cap. var. 1 25A GOLD SD 080 cap. var. 2 40A10.GOLD SD 100/120GOLD SD 100/120 3-phase, 5-wire, 400V -10/+15%, 50HzL 1L 2L 3L1L2L3GOLD SD 100 cap. var. 1 25A GOLD SD 100 cap. var. 2 40A GOLD SD 120 cap. var. 1 40A GOLD SD 120 cap. var. 2 63ANNP EPE171811.