Title: økernvn 94.pdf
Cable ID: D4142 Date / Time: 09/10/2013 02:56:28 Headroom 13.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]86 137 10 3.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.7 83.5 33.6 36 16.3 83.8 30.6SR 12-36 15.5 83.5 33.6 36 17.8 87.5 30.3MAIN 12-36 14.2 99.0 32.4 36 16.5 99.0 29.4SR 12-36 15.5 83.5 33.6 36 17.8 87.5 30.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-45 26.9 7.1 41.6 12 27.6 5.5 40.8