Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF083 16C2/003 30.11.2020 11:57 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 533V Rlpe: >30.0MΩ Um: 534V Rnpe: >30.0MΩ Um: 526VUiso: 500V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 26.11.2020 14:08SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 26.11.2020 14:10Zs(rcd)Z: 0.46ΩIsc: 505A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 26.11.2020 14:12Tallberg Elektro A/S Tlf.22796640Side:35GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.242242243243244244245245246246247247248248TEST RAPPORTResultatZ-LINEZ: 0.45ΩIsc: 506A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 26.11.2020 14:14RCD II: 28.5mA