Title: Igangkjøringsprotokoller på sirkulasjonspumper V.2017.08.28.pdf
Address: Vargveien 1, 1488 Hakadal, - Operational Manager: Audrius DaniulisPhone/e-mail: +370 676 19634 / audrius.daniuIis@ensopro'!ects.wm~ Required flow (designed): 34 m¥hRequired head (designed): 10m Water temperature: 10°C Fluid: MEG 30% Operation mode: Open loop / Differencial pressureeProduct No. : 2120874Marking in the system: 370.010-JP402Nom. flow; Nom. Pressure; 13.6mMax. Liquid temp. : -25..140 °C Head max: 16.5m{?E.l;pj “ ‘: i S -~ ‘:"? |Check expansion joints installed: ok Check vibration damper installed: ok Check air locks are avoided (suction side): ok Check for pipes adequate support: ok Check mechanical seal for leaks: okReal setp0|nt (head pmssure) 8.5m Flow at preseted setpoint (all valves opened): 35.08m3/h Power consumption W: 1521W Head pressure at regular working cond. : 2.55m Flow at regular working cond. : 8.03m3/h i Name Audnus Daniulis_Signature: %