Title: +038=30.001-NI003._14-V20-07-02 VVS-anlegg plan 7 - DM3.pdf
ABXCD11Plan 0725.07 mOpp/ned 320.102: 54mm 320.102: 54mm0LD022T Maks:100 m³/h Kjøling: 645 W 0.051 L/s Varme: 485 W 0.012 L/s1LD018T Maks:220 m³/h Kjøling: 435 W 0.035 L/s Varme: 275 W 0.007 L/sLD018T Maks:220 m³/h Kjøling: 435 W 0.035 L/s Varme: 275 W 0.007 L/sLD018T Maks:220 m³/h Kjøling: 435 W 0.035 L/s Varme: 275 W 0.007 L/s2LD018T Maks:220 m³/h Kjøling: 435 W 0.035 L/s Varme: 275 W 0.007 L/sLD018T Maks:230 m³/h Kjøling: 250 W 0.020 L/s Varme: 200 W 0.005 L/sLD018T Maks:230 m³/h Kjøling: 250 W 0.020 L/s Varme: 200 W 0.005 L/sLD022T Maks:130 m³/h Kjøling: 250 W 0.020 L/s Varme: 200 W 0.005 L/s28mmø160 UK=2685 ø160 UK=2685ø200 UK=2650 ø200 UK=2650320.102: 28 mm +c 2790320.102: 28 mm +c 2790LD018T Maks:160 m³/h Kjøling: 595 W 0.047 L/s Varme: 200 W 0.005 L/s28 mm +c 271028 mm +c 2710Kontor 7-012SF002T-160WISE RTASF002T-160SF002T-160WISE IAQ WISE RTA370.101: 28 mm +c 2790 370.101: 28 mm +c 2790SF002T-200SF002T-200Spiserom 7-010