Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Within the voltage range 5…24 VDC, the load resistance should be at least 48 Ω.Total current per module:4 A on 100% duty cycleOperating mode:Source operation (positive switching)Voltage range:5…32 VDC, smoothed 10…25 VDC, pulsedVoltage drop:≤ 0.4 V at 0.5 AOutput delay:Switch-on delay typ. 10 µs Switch-off delay typically 50 µs (ohmic load 5…500 mA), longer with inductive load, because of the protective diode.Isolation voltage:1000 VAC, 1 minResistance to interference: acc. to IEC 801-44 kV under direct coupling 2 kV under capacitive coupling (whole trunk group)Internal current consumption: (from +5 V bus)1…24 mA typically 15 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption:Load currentTerminals:Plug-in 10-pole spring terminal block (4 405 4954 0) or pluggable 10-pole screw terminal block (4 405 4955 0), both for wires up to 2.5 mm²6-40PCD3.A410LEDs and connection terminalsLED 0...7Terminal 0Terminal01234567