Title: Ahlsell.pdf
Cable ID: UD 32 Test Limit: TIA Cat 6A Perm. Link Limits Version: V3.0 Date / Time: 05/03/2022 10:47:54 AM Operator: Pam Headroom 9.1 dB (NEXT 3,6-7,8) Cable Type: Cat 6 U/UTP NVP: 69.0%Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 3,6] [Pair 4,5] [Pair 4,5] [Pair 3,6]45.9 226 4 7.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]20.9 500.0 43.8Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-7,8 9.9 4.8 62.9 3,6 11.2 4.6 60.8SR 3,6-7,8 9.1 91.0 42.5 3,6 9.7 91.0 40.0MAIN 3,6-4,5 15.8 500.0 26.7 3,6 16.0 490.0 24.1SR 1,2-3,6 12.1 492.0 26.9 3,6 11.7 493.0 24.010080604020NEXT (dB)