Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
30.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.0 444.0 30.4 36 7.4 455.0 27.2SR 36-45 7.6 497.0 28.0 36 7.7 460.0 26.9MAIN 12-36 8.7 496.0 28.0 36 8.0 496.0 25.2SR 36-45 7.6 497.0 28.0 36 8.0 496.0 25.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.4 9.3 45.9 45 20.6 500.0 8.3SR 45-78 19.4 9.8 45.5 45 20.3 499.0 8.3MAIN 78-45 19.9 500.0 11.3 45 20.6 500.0 8.3SR 45-78 20.0 500.0 11.3 45 20.3 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.5 85.8 26.7 45 26.8 86.0 24.1SR 36-45 24.8 85.8 26.7 45 26.6 85.8 24.1MAIN 12-36 38.1 496.0 -12.1 36 37.5 496.0 -15.0SR 36-45 37.2 497.0 -12.2 36 37.5 496.0 -15.00804000250 MHzACR-N (dB)