Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
Clearance height: 2.600 m, Reflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 8 Perpendicular illuminance (adaptive) [Ix] 691 (= 500) 478 832 0.69 0.57 Surrounding area: 0.500 m 2 Surrounding area 8 Perpendicular illuminance (adaptive) [Ix] 596 (= 300) 368 840 0.62 0.44 3 Background area 7 Perpendicular illuminance (adaptive) [Ix] 397 (= 100) 152 656 0.38 0.23 Wall zone: 0.500 m # Luminaire ®(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 12 iGuzzini illuminazione S.p.A - QA85+QB54_B38K iN60 LED: Down 2812 246 114.3HO plateDALIGeneral LightLED WarmL 119622W 3700Im3000KInitial moduleFrame DownGeneral LightL 1208Total via all luminaires 33744 295.2 114.3Lighting power density: 6.13 W/m? (Floor area of room 48.18 m?) Consumption: 510 - 810 kWh/a of maximum 1700 kWh/a