Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
typically 5 ms at 24 VDCResistance to interference: acc. to IEC 801-4 Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption:4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 1 … 15 mA typ. 10 mA 0 mAmax. 32 mATerminals:Pluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²1) With external protective diode 2) With reverse voltage protection 3) These ratings are not UL-listedThe Annex, Section A.4 "Relay contacts" contains measurement details and sug- gested wiring for the relay contacts. For safe switching and a long service life, these figures must be observed.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-30Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.A200LEDs and connection terminalsBus connectorBus interfaceRelaysA3A2A1A0Contact protectionLEDs6Screw terminals987A3654 A232 A11