Title: Eurotester målerestultat.pdf
Testet av: Andreas PedersenSide:2GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr.1313141415151616171718181919TEST RAPPORTResultatRCD II: 22.5mAUc: 8.6V Idn: 30mA type: AC Ulim: 50VBytesteinen 1 / =433.202 / SIKRING9 / CONNECTION1 30.03.2021 13:00:35R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING9 / CONNECTION1 30.03.2021 13:00:53R ISOR: >999MΩ Um: 525VUiso: 500V Grenseverdi: 1MΩBytesteinen 1 / =433.202 / SIKRING9 / CONNECTION1 30.03.2021 13:09:01R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING9 / CONNECTION1 30.03.2021 13:23:54R LOW OhmR: 0.04ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩBytesteinen 1 / =433.202 / SIKRING10 30.03.2021 13:25:13Z-LINEZ: 0.90ΩIsc: 257A Sikringstype: C SIKRING I: 15A SIKRING T: 0.4s Isc_lim: 150.0A Isc(0.38%): 97.7A Isc(0.76%): 195A Isc(1.15%): 296A