Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
[A] A=S – manual tripping A=24I – electromagnetic tripping – current pulse A=24P – electromagnetic tripping – current break A=230I – electromagnetic tripping – current pulse A=230P – electromagnetic tripping – current break [B] B=0 – no limit switches B=WK1d – one limit switch, signalling the fire damper position state B=WK2d – two limit switches, signalling the fire damper position state [C] C=0 – no additional actuator C=24 – additional actuator for the voltage 24 V DC C=230 – additional actuator for the voltage 230 V AC [D] D=V – execution without thermal trip In the case of no designation, the mechanism will always be executed with the thermal trip 72°C6. INSTALLATION OF THE DEVICE___________________________________NOTE During assembly of the damper and its finishing works one should take into consideration a possibility of future access to the device and removal of the tripping and control mechanism in order to undertake possible service works.