Title: +038=433.000-NI003._07-Testrapport elektriske anlegg - DM1.E7=433.08.05, Pareto plan 08.pdf
Tallberg Elektro A/S Tlf.22796640Side:5GODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*GODKJENT*Nr.3535363637373838393940404141TEST RAPPORTResultatZ-LINEZ: 0.38ΩIsc: 601A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF029 16/2/C/003 19.11.2020 12:24Zs(rcd)Z: 0.32ΩIsc: 708A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF029 16/2/C/003 19.11.2020 12:25RCD II: 28.5mAUci: 0.2V t: 108.3ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 8 / DM1.E7.433.08.05 / XF029 16/2/C/003 19.11.2020 13:10KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF029 16/2/C/003 19.11.2020 14:24R ISOR: 108.4MΩ Um: 10VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF030 16/2/C/003 19.11.2020 11:49SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 49.9Hz