Title: +038=30.001-NI003._17-V20-09-01 VVS-anlegg plan 9 - DM1.pdf
800x400 UK=2480 800x400 UK=2480SZ002T 800 x600SF008T-100 60 m³/hPrint/kopi 9-007ø315 UK=2549SR001T Ø100 ø100 UK=2515800x600 UK=2280WISE director (trådløs router)ø200 UK=2685 ø200 UK=2685 ø200 UK=2685ø315 UK=2549ø315 UK=2549ø315 UK=2549ø315 UK=2549LD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sø200 UK=2700LD007T Maks:195 m³/h Kjøling: 640 W 0.051 L/s Varme: 525 W 0.013 L/sSTAP/STAD DN 40+09 = 370.101 - OE 093 0.692 L/s370.101: 54 mm +c 2820 370.101: 54 mm +c 2820320.102: 18 mm +c 2820 320.102: 18 mm +c 2820LD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sLD009T Maks:195 m³/h Kjøling: 640 W 0.051 L/sDN 65 UK = 2802Opp 35 mmOpp 35 mmSTAP/STAD DN 20Servering 9-112Pumpe under vask Grundfos Sololift1:100310.001: PP 40 UK = 2841Møterom 9-11015 mm +c 2820 15 mm +c 2820Møterom 9-109SF002T-160ø160 UK=2735ø160 UK=2704Møterom 9-10815 mm +c 2703 15 mm +c 2703 15 mm +c 2703 15 mm +c 2703ø160 UK=2720