Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Cable ID 008 009 010 011 012Page 2 24-06-2020 21:16:14 Uniconsult tester.flwSummary PASS PASS PASS PASS PASSTest Limit EN50173 Fiber Optic Link EN50173 Fiber Optic Link EN50173 Fiber Optic Link EN50173 Fiber Optic Link EN50173 Fiber Optic LinkLength 42.2 m 42.1 m 42.1 m 42.2 m 42.2 mHeadroom 1.21 dB (Loss Margin) 1.34 dB (Loss Margin) 1.36 dB (Loss Margin) 1.26 dB (Loss Margin) 1.17 dB (Loss Margin)Date / Time 15-06-2020 12:33 15-06-2020 12:33 15-06-2020 12:33 15-06-2020 12:34 15-06-2020 12:34Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 3 24-06-2020 21:16:14 Uniconsult tester.flw2216.6 m 82 82 0 0 0Cable ID: 521.03.03-UF001 Date / Time: 06-05-2020 15:40:32 Headroom 5.6 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017