Title: +038=370.104-OE004T_01-Multical 801 Energimåler Kamstrup - Installasjons- og brukerguide.pdf
8Kamstrup A/S • 5512603_C1_GB_03.2016MULTICAL® 8013.1 Mounting of couplings and short direct sensor mounted inULTRAFLOW® flow partThe short direct sensor from Kamstrup can only be mounted in PN16 installations. The blind plug mounted in the ULTRAFLOW® can be used in connection with both PN16 and PN25. The flow meter can be used in both PN16 and PN25 and can be supplied marked either PN16 or PN25 as desired. Fittings, if supplied, can only be used for PN16. For PN25 installations, fittings suitable for PN25 should be used. In connection with G¾x110 mm and G1x110 mm it shall be checked that the thread run-out is sufficient. See the figures to the right.10 mm12 mmGasketTightening app. 4 Nm Type 65-5-XXAX-XXXGasketTightening app. 4 NmType 65-5-XXHX-XXX