Title: etg u1.pdf
[Pair 36] [Pair 12] [Pair 12] [Pair 12]88 139 10 3.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.6 74.8 34.4 36 13.2 74.8 31.4SR 12-36 10.3 74.8 34.4 36 12.8 74.8 31.4MAIN 12-36 11.1 93.5 32.8 36 13.7 97.5 29.5SR 12-36 10.6 97.3 32.5 36 13.0 97.5 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 20.3 3.3 48.4 36 22.5 3.0 46.1SR 36-45 20.4 3.1 48.7 45 22.3 3.3 45.4MAIN 45-36 20.6 97.3 18.9 45 22.9 98.0 15.8SR 36-45 20.6 97.3 18.9 45 22.6 97.3 15.901008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 23.9 74.8 17.0 12 26.5 74.8 14.0