Title: 2 etg del2.pdf
[Pair 45] [Pair 12] [Pair 12] [Pair 12]219 345 23 9.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 85.5 33.4 36 14.9 85.8 30.4SR 12-36 14.1 48.0 37.5 36 15.0 87.3 30.3MAIN 12-36 14.9 99.0 32.4 36 14.9 85.8 30.4SR 12-36 14.5 90.0 33.1 36 15.2 93.3 29.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 17.2 59.3 23.2 36 19.1 57.8 20.4SR 36-45 17.4 54.3 23.9 36 19.5 59.3 20.2MAIN 45-36 19.7 96.8 18.9 45 21.9 99.0 15.7SR 45-36 19.8 99.0 18.7 45 21.4 95.3 16.001008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 18.3 16.4 37.2 12 20.4 16.3 34.3