Title: Innstallasjons manual PS2500.pdf
Pot. Unit IDC2 X5C1 X4SIReCC6XX (max 50 m)SIReB1/B2/B1ECPot. Unit IDC2 X5C1 X4SIReCC6XX (max 50 m)SIReB1/B2/B1ECPot. Unit IDC2 X5C1 X416ROOM X3ROOM X3ROOM X3PA2500SD230230V~ACTUATOR SUPPLYN LL~PEN LL=2mL=1,5mSIReCC6XX (max 50 m)SD230230V~ACTUATOR SUPPLYN LL~PEN LSD230230V~ACTUATOR SUPPLYN LL~PEN LSIReRTX (optional)SIReUB1PA2500Output charts water PA2500TypeFan positionAirﬂow[m3/h]Supply water temperature:110 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 OutputWater ﬂowPressure dropReturn water temp. [°C][l/s][kW][kPa]Water temperature: 110/80 °C Room temperature: +18 °COutput *2Outlet air temp.Water ﬂow[kW][°C][l/s]PA2510WPA2515WPA2520WMax Min Max Min Max Min1300 900 2100 1250 2600 18007,4 5,3 12,5 7,4 15,0 10,247,0 46,0 39,0 34,0 36,0 32,00,03 0,02 0,04 0,02 0,05 0,030,3 0,2 0,9 0,3 1,5 0,713,3 10,6 24,4 17,6 30,1 23,948,1 52,8 52,2 59,4 52,0 57,0