Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
Fusible trip installation instructions ____________________________________________________The fire damper may be delivered in the spring version (mechanism KW1/S or RST) with limit switches. In the KW1/S version the limit switches are mounted on the mechanism itself. The electrical connection consists in connecting the adequately marked wires to the system (see description of the mechanism KW1). The fusible trip is installed on the mechanism. In the RST execution, the limit switches are mounted inside the fire damper casing as independent subassemblies. The fusible trip is located on the fire damper baffle.In order to mount a fire damper in an open position one should:1. Set the fire damper baffle in open position. 2. Put the fusible link on the hooks fixed to the fire damper body and the baffle. 3. Tighten and lock the hook on the fire damper body by tightening the nut.MERCOR SA – The company reserves the right to make modifications and changes19/21mcr WIP multi-plane fire dampers