Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 21,5 10,2 11,3 498,00Remote: 12-45 21,5 10,2 11,3 499,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,8 3,3 498,00Remote: 36 28,1 23,9 4,2 496,00Worst Value: Local: 36 27,1 23,8 3,3 500,00Remote: 36 28,0 23,8 4,2 497,00PS-ACRF: Pass Worst Margin: Local: 45 65,4 54,3 11,1 2,20Worst Value: Local: 45 20,5 7,3 13,2 495,00Remote: 45 67,4 56,3 11,1 1,75Remote: 45 20,8 7,5 13,3 483,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:07Signature:______________________ Page: 89Copper Certification ReportCable Label: 521.002-UD-68 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:21:01 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: