Title: Simployer - Data testrapport =514.204-FS001.pdf
Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]55.0 283 21 9.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.4 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 9.4 45.3 45.7 3,6 10.5 203.0 31.7SR 3,6-7,8 8.2 249.5 33.1 3,6 9.7 225.5 30.9MAIN 3,6-7,8 10.0 203.0 34.7 3,6 10.5 203.0 31.7SR 3,6-7,8 8.2 249.5 33.1 7,8 10.1 250.0 30.2PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 7,8-4,5 16.6 134.5 20.7 4,5 17.5 134.5 17.7SR 7,8-4,5 16.8 129.0 21.0 4,5 17.8 4.8 46.7MAIN 7,8-4,5 17.0 250.0 15.3 4,5 19.7 250.0 12.3