Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Switch closed: Signal status 'H' = LED on Switch open : Signal status 'L' = LED offM O CM O CleerPhase 115 - 230V 50/60 Hz *)Zero conductor *)) or interchangeable, if the rules permit thisWatchdog: This module can be used on all base addresses; there is no interac- tion with the watchdog on the CPUs. For details, please refer to the “Watchdog” section, which describes the correct use of the watchdog in conjunction with PCD2 components.5-20PCD2.E61x5.3.2PCD2.E61x, 8 digital inputs, electrically isolatedApplicationInput module for source or sink operation with 8 inputs, electrically isolated by optocoupler. Suitable for most electronic and electromechanical switching elements at 24 VDC. The PCD2.E611 differs from the PCD2.E610 in its shorter input delay, typically 0.2 ms.Technical dataNumber of inputs:8 electrically isolated by optocoupler,source or sink operation, all inputs to the module in the same phaseInput voltage E610: E611: E613: E616: