Title: 370.011 RP100, RP400 og RP500 Siemens Trykkfoler.pdf
Nominal pressureRelative pressure as in "Type summary" (measurement of difference from ambient pressure)Max. admissible pressure/ Rupture pressure3 x scale end value of measuring range 0…1 to 0…4 bar 2.5 x scale end value of measuring range 0...6 to 0...60 barMediaAdmissible temperature of mediumNeutral and slightly corrosive liquids and gases (suited for use with oil-contacting media) − 1 5...+ 1 2 5 °CMaintenancemaintenance-freeMounting positionoptionalProtection standardIP 65 to EN 60529Protection classIII according to EN 60730Electric connectionPlug DIN EN 175301-803-A, Cable diameter 6-8 mmScrewed fittingExternal thread G ½", inside thread M5Temperature HumidityO p e r a t i o n − 3 0...+ 85 °C Insensitive to CondensationStorage − 5 0...+ 1 0 0 °C Insensitive to CondensationProduct standardEN 61326-1Electrical equipment for measurement, control and laboratory use. EMC requirements. General requirementsPressure connection