Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
InstallationEnsure that the network cable runs along a separate path and that it does not interfere with any other cables.BThis panel must be connected to a separate line on the Electrical Switchboard (Mains power supply). The line must be protected by a sectioning device which must be labeled and of “16A curve C” type.CThe installation must be constructed, arranged and installed in compliance with the local laws in force regarding electrical safety.Cables: Connection cable type NYM 3 x 1.5 mm2 or similarProtected by ferrites (supplied)5.5.3 Connection of system grounding conductorsConnect the mains earth conductor to the screw that must be inserted in the proper hole of the IFM24160 power-supply module (, [A], paragraph 3.6 - [I]).The earth conductor must be connected to earth on the electrical panel which supplies the control panel.