Title: 360.001 - Tilluft.pdf
0.1 +3.28k [dB]7.714.0 +16.4 16.414.0 +16.4 16.420.020.00.0 +6.620.21.5 +0.08.110.610.60.6 +8.112.21.5 +0.04.16.90.0 +0.07.71.0 +0.07.50.1 +0.0Lp [dB]22,6Level1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeProductFIREDAMPER FKRS-EU/250/ZXXDUCTMAGID-C1-250161 T-BRANCHTCPU-250-160DUCTMAGID-C1-160162 SUPPLYTellus-LOV VAV-H-160REDUCERMAGIR-CC1-250-160DUCTMAGID-C1-160163 T-BRANCHTCPU-160-160DUCTMAGID-C1-160164 SUPPLYTellus-LOV VAV-H-160Size250250250/160160160250/160160160/160160160L [m]1,50,23,00,156qv [m³/h]450450450225225225225225225225v [m/s]2,52,52,53,13,11,33,13,13,13,1dpt [Pa]1,7 Sound in:Addition:0,5 Sound in:Attenuation: Addition:5,1 Sound in:Attenuation: Addition:Dividing:0,2 Sound in:Attenuation: Addition:66,5 Sound in:Attenuation: Addition: