Title: 05_ListOfVariables_MemoryOrganisation_Smarteh_v25_V6523.xls
Actuator Alarm "0" = Ok, "1" = Fault read only 19 Actual Pressure #18 0..1000 1:1 Pa read only HOOD 18 20 IR activity 20 Operating Hours#1 20 IR activity "1" = Active read only 20 Damper Position #18 0..10000 100:1 Pa read only HOOD 18 UV / MARVEL #3 21 Pressure alarm UV / MARVEL #5 21 Actual Pressure UV / MARVEL #21 21 Pressure alarm "0" = Ok, "1" = Fault read only UV / MARVEL #5 21 MIN. AirFlow 0..10000 1:1 m3/h 22 Filter Safety alarm 22 Actual AirFlow 22 Filter Safety alarm "0" = Ok, "1" = Fault read only 22 IDLE AirFlow 0..10000 1:1 m3/h 23 UV Safety alarm 23 Damper Position 23 UV Safety alarm "0" = Ok, "1" = Fault read only 23 MAX Airflow 0..10000 1:1 m3/h 24 UV #1 alarm 24 Actual Temperature 24 UV #1 alarm "0" = Ok, "1" = Fault read only 24 Actual Pressure #19 0..1000 1:1 Pa read only HOOD 19 25 #4 UV #2 alarm 25 Operating Hours#1 25 #4 UV #2 alarm "0" = Ok, "1" = Fault read only 25 Damper Position #19 0..10000 100:1