Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
[Pair 45] [Pair 45] [Pair 45]31.7 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 9.6 479.0 28.8 36 9.5 453.0 27.3SR 36-45 7.5 470.0 29.3 45 8.4 465.0 26.7MAIN 12-45 9.7 485.0 28.5 36 10.2 500.0 25.0SR 36-45 7.6 476.0 29.0 36 9.0 478.0 26.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.4 5.9 49.9 45 14.2 3.3 52.0SR 45-78 15.4 5.9 49.9 45 14.2 3.5 51.4MAIN 36-45 17.0 465.0 11.9 45 19.8 476.0 8.7SR 36-45 17.2 470.0 11.8 45 19.3 470.0 8.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 27.0 108.0 23.0 12 28.3 108.0 20.4SR 12-45 28.5 102.5 23.8 12 29.9 120.0 18.6MAIN 36-45 40.8 500.0 -12.4 36 41.0 500.0 -15.3SR 36-45 38.0 476.0 -10.8 45 40.2 492.0 -14.70804000250 MHz