Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
+ 2 LSB - 2 LSBFor these two values, the measurement error = 0.5-57Deviation (LSB)+6 +5 +4 +3 +2 +1 0 +1 +2 +3 +4 +5 +6Measurement50 00 1024+50 2047.5+100 3071+150 4095°C LSBTypical linearity error for W111/113 (Ni 100/Ni 1000)Deviation (LSB)+6 +5 +4 +3 +2 +1 0 +1 +2 +3 +4 +5 +6Measurement50 00 1024+50 2047.5+100 3071+150 4095°C LSBOn cable break On short circuit→ →Measurement Measurement4095 0Base and variant modulesEach module comprises 2 individual modules.Base module with input filters, A/D converter, I/O port. Same module with same fittings for all 4 variants.Base module with input filters, A/D converter, I/O port. Same module with same fittings for all 4 variants.Plug-on variant modules with switching circuit to generate -15 V, power sources and linearization. Each of the four variants has a module of its own, i.e. a