Title: økernvn 94.pdf
050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.4 29.3 40.8 36 12.7 21.5 41.9SR 36-45 16.2 46.0 35.0 36 16.3 21.4 42.0MAIN 36-45 17.4 248.5 4.8 36 16.8 248.0 2.2SR 36-78 23.8 243.0 5.4 36 26.2 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.6 15.4 20.1SR 45 2.1 88.5 14.5MAIN 36 7.3 197.0 11.1SR 45 2.1 88.5 14.5010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.