Title: 2 etg del2.pdf
SR 36-45 9.2 22.6 43.7 36 10.7 22.6 41.3MAIN 36-45 6.4 247.0 5.0 36 6.1 245.5 2.5SR 36-78 13.3 240.5 5.6 12 13.8 242.5 2.8010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.9 22.3 19.3SR 36 3.1 19.9 19.5MAIN 45 5.7 170.5 11.7SR 36 3.8 249.5 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVN.94 2.ETG DEL 2 wennevolds økernvn 111013.flwSite: OKERNVEIEN 94