Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
PCD2D /D -WD- + + +L+NController24 VDC ±20%L N–Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-25Communication interfacesSerial interfaces - Slots A1 and A21 # t r o P10 11 12 13 14 15 16 17 18 19e c i v e d e i r t e m a r a P T F M5s e v i r d5-16Saia-Burgess Controls Ltd.Communication interfacesSerial interfaces on I/O module slots 0 - 35.5Serial interfaces on I/O module slots 0 - 35.5.1 General remarks on the PCD2.F2xxxSystem properties of PCD2.F2xxx modules:The following points must be observed when using the PCD2.F2xxx interface modules:For each PCD system, up to 4 PCD2.F2xxx modules (8 interfaces) can be used on slots 0…3.The PCD2.M5_ system has a powerful processor which handles the application as well as the serial interfaces. Processing of the interface modules requires the appropriate CPU capacity. To determine the maximum communication capacity per PCD2.M5_ system, note the following:5