Title: 05_ListOfVariables_MemoryOrganisation_Smarteh_v25_V6523.xls
32 x byte = 256 100 x word 32 x byte = 256 100 x word Controller Bits Byte Digital statues (discrete inputs) Comments Controller Address Input registers Range Scaling Controller Bits Byte (Digital) Coils Comments Controller Address Holding registers Range Scaling Units UV / MARVEL #1 1 #1 Pressure alarm "0" = Ok, "1" = Fault UV / MARVEL #1 1 Actual Pressure 0..1000 1:1 UV / MARVEL #19 1 #1 Pressure alarm "0" = Ok, "1" = Fault read only UV / MARVEL #1 1 MIN. AirFlow 0..10000 1:1 m3/h 2 Filter Safety alarm "0" = Ok, "1" = Fault 2 Actual AirFlow 0..10000 1:1 2 Filter Safety alarm "0" = Ok, "1" = Fault read only 2 IDLE AirFlow 0..10000 1:1 m3/h 3 UV Safety alarm "0" = Ok, "1" = Fault 3 Damper Position 0..10000 100:1 3 UV Safety alarm "0" = Ok, "1" = Fault read only 3 MAX Airflow 0..10000 1:1 m3/h 4 UV #1 alarm "0" = Ok, "1" = Fault 4 Actual Temperature 0..10000 100:1 4 UV #1 alarm "0" = Ok, "1" = Fault read only 4 Actual Pressure #15 0..1000 1:1 Pa read only HOOD 15 5 UV #2 alarm "0" = Ok, "1" = Fault 5 Operating