Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
[Pair 45] [Pair 45] [Pair 45]24.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 6.8 464.0 29.9 45 7.5 479.0 26.8SR 36-45 5.8 500.0 29.2 36 6.5 500.0 26.4MAIN 12-45 6.9 481.0 29.6 45 7.5 479.0 26.8SR 36-45 5.8 500.0 29.2 36 6.5 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.4 4.3 52.7 45 14.1 2.9 53.1SR 36-45 14.4 4.3 52.7 45 14.0 2.6 53.9MAIN 36-78 16.0 488.0 11.5 45 16.1 500.0 8.3SR 78-36 15.9 488.0 11.5 45 15.6 475.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 18.0 42.5 36.5 45 19.0 33.0 37.2SR 12-45 22.6 33.0 39.6 45 23.3 33.0 37.2MAIN 12-45 31.9 500.0 -12.4 45 32.8 500.0 -15.3SR 36-45 30.2 500.0 -12.4 36 31.3 500.0 -15.30804000250 MHz