Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: D3399 Date / Time: 09/12/2013 12:16:35 Headroom 10.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]232 355 13 10.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]7.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 19.5 39.3 38.9 78 20.5 62.8 32.6SR 12-36 10.4 80.0 33.9 36 11.0 100.0 29.3MAIN 12-78 20.2 87.5 33.3 12 22.0 100.0 29.3SR 12-36 11.0 100.0 32.3 36 11.0 100.0 29.310080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)