Title: +038=522.000-NI002._01-Testrapport EKOM Anlegg Plan 4 McKinsey.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]34.6 150 2 5.19Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.7 488.0 29.5 36 7.7 495.0 26.5SR 12-36 6.7 499.0 29.3 36 6.6 499.0 26.4MAIN 36-45 8.9 500.0 29.2 36 7.7 495.0 26.5SR 12-36 6.7 499.0 29.3 36 6.6 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 18.2 7.6 47.6 45 18.8 499.0 8.3SR 78-45 17.7 491.0 11.4 45 18.9 498.0 8.3MAIN 45-78 18.4 495.0 11.3 45 18.8 499.0 8.3