Title: 36 Siemens GDB181-MO.pdf.pdf
ASV181.1E/3 with 3P actuator GEB136.1E (15 Nm) GBB136.1E (25 Nm) GLB136.1E (35 Nm)ASV181.1E/3 with 3P actuator GEB131.1E (15 Nm) GBB131.1E (25 Nm) GLB131.1E (35 Nm)GLB181.1E/3 10 NmGDB181.1E/3 5 Nm7 / 40A6V10631862_en--_d 2019-09-138 / 40Siemens Smart Infrastructure2.1.3Version summaryVersionSeries AIdentificationFeatures§ Communication Modbus RTU or BACnet MS/TP § Quasi-static differential pressure sensor. § Simultaneous feedback of actual values ofdamper position and air volume flow.§ Optional adaptive opening range measurement(adaptive positioning).§ HMI with push button and LED.VAV Compact Controller Modbus RTUA6V10631862_en--_d 2019-09-13Main device partsGear train disengagementSiemens Smart InfrastructureThe VAV Compact Controllers consist of a differential pressure sensor, actuator and digitally configurable control electronics. They are intended for mounting on damper shafts of a minimum length of 30 mm. They consist of base and 2-sectional housing.