Title: økernvn 94.pdf
6040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3207 Date / Time: 09/11/2013 02:59:45 Headroom 5.7 dB (NEXT 45-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]117 180 7 5.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]19.3 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 45-78 5.7 95.8 42.1 78 6.7 201.0 34.3SR 45-78 5.8 153.0 38.8 78 6.6 153.0 36.3MAIN 36-78 6.0 238.0 35.7 78 7.3 247.0 32.8SR 36-78 6.2 207.0 36.7 12 8.5 250.0 32.710080604020NEXT (dB)