Title: 360.002 - Tilluft.pdf.pdf
3. etasje3. etasje3. etasje3. etasje3. etasjeNodeTypeDUCTBEND-30DUCTBEND-45DUCTBEND-45REDUCERDUCTBEND-45DUCTProduct200MAGIB-C4-*-*200200MAGIB-C4-*-*200200MAGIB-C4-*-*200MAGIR-CC1-*-* 200200MAGIB-C4-*-*200200SizeL [m]0,00,40,28,30,4Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]3002,70,0 Sound in:Attenuation: Addition:3002,70,5 Sound in:Attenuation: Addition:3002,70,2 Sound in:Attenuation: Addition:3002,70,7 Sound in:Attenuation: Addition:3002,70,1 Sound in:Attenuation: Addition:3002,70,7 Sound in:Attenuation: Addition:3002,7Sound in:3002,74,3 Sound in:Attenuation: Addition:3002,70,7 Sound in:Attenuation: Addition:3002,70,2 Sound in:Attenuation: Addition:2563 [dB]33.70.0 +11.433.70.0 +11.433.80.0 +11.433.80.0 +11.433.80.0 +11.433.8