Title: +038=433.000-NI003._07-Testrapport elektriske anlegg - DM1.E7=433.08.05, Pareto plan 08.pdf
R LOW OhmR: 0.15ΩR+: 0.2Ω R-: 0.1Ω Grenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF026 16/2/C/003 19.11.2020 14:23R ISOR: >200MΩ Um: 10VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF027 16/2/C/003 19.11.2020 12:16SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 8 / DM1.E7.433.08.05 / XF027 16/2/C/003 19.11.2020 12:16Z-LINEZ: 0.38ΩIsc: 612A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF027 16/2/C/003 19.11.2020 12:35KONTINUITET R: 0.1ΩGrenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF027 16/2/C/003 19.11.2020 14:23R ISOR: 154.8MΩ Um: 11VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF027 16/2/C/003 19.11.2020 12:38R LOW OhmR: 0.04ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.7ΩTallberg Elektro A/S Tlf.22796640Side:4GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*