Title: økernvn 94.pdf
Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 15 09/20/2013 08:45:44 økernveien 94 3 og 4 etg.flw128919 ft 824 824 0 0 0Cable ID: D3001 Date / Time: 09/11/2013 01:24:32 Headroom 14.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]178 284 21 7.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]10.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 19.5 58.0 36.2 12 21.4 95.3 29.7SR 12-36 14.7 95.3 32.7 36 15.5 99.8 29.3MAIN 12-36 20.4 95.5 32.6 12 21.4 95.5 29.6