Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Units with electric heaters The electric heaters are activated by the CARRIER type “B” control. The unit is equipped with two safety thermostats: one automatic reset thermostat and one manual reset thermostat which can be re-activated, fig. 32 (ref. A) to protect the unit against overtemperature caused by dirty filters or clogged air flow. The manual thermostat must be reset by skilled personnel only after the cause for which the intervention was required has been removed.The use of hot water and electric heaters is allowed only if the “Booster Heating” option is active (control B + 42N9084 kit).,they contain electrical and electronic components, connected to 230V power supply.WARNING: • Disconnect the power supply before opening the control cover • All inputs (external contact, seasonal changeover etc.) must beelectrically insulated consistent with 230V requirements.Tipo A (cid:30)Tipo B (cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)(cid:30)