Title: 2 etg del2.pdf
Cable ID: T2163 Date / Time: 10/11/2013 08:16:14 AM Headroom 14.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]61 96 6 11.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.7 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.3 85.5 33.4 36 15.4 97.0 29.5SR 12-36 17.4 97.8 32.5 36 18.7 92.3 29.9MAIN 12-36 14.3 96.8 32.5 36 15.4 97.0 29.5SR 12-36 17.4 97.8 32.5 36 19.0 98.0 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 23.9 5.0 44.6 12 26.6 34.5 24.9