Title: 370.011 Fan coils -42GW200-701C-installasjonsmanual.pdf
Remove the external prepunched anti-condensate insulation and take away the knockout panels using a punch.The optional supplementary fan for fresh air intake (field supplied) has to be connected to terminal block as per diagrams enclosed. Fan motor operation is parallel to the thermo-electric control valve, and the motor stops when the valve shuts off.The optional supplementary fan for fresh air intake (field supplied) has to be connected to terminal block as per diagrams enclosed. Fan motor operation is parallel to the thermo-electric control valve, and the motor stops when the valve shuts off.See fig. 47.The duct lengths and the increase in noise levels caused by these ducts can be calculated in accordance with the “air supply to an adjacent room diagrams ” (also taking into account the flow resistance through air diffusers and fresh air filters).