Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]39.3 171 3 5.72Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]24.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.5 467.0 29.9 36 7.8 500.0 26.4SR 12-36 8.8 496.0 29.3 36 9.0 496.0 26.5MAIN 36-78 9.1 500.0 29.2 36 7.8 500.0 26.4SR 12-36 8.8 496.0 29.3 36 9.1 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 19.3 350.0 14.4 45 20.0 426.0 9.6SR 45-78 19.3 350.0 14.4 45 19.4 409.0 10.0MAIN 12-45 19.9 456.0 12.1 45 20.4 455.0 9.1SR 45-12 20.1 455.0 12.1 45 19.4 409.0 10.00100806040200250 MHzACR-F (dB)