Title: DOCA0005EN-12.pdf
16Stop characterTelegram information for meter configurationYou can use the information provided in this section to write to the meter using a SND_UD function.NOTE: If Com. Protection is enabled, you may receive an error response when you try to configure the meter over communications.You can also configure the meter using the M-Bus tool available from www.schneider- electric.com.Supported VIFE codes for meter configurationNOTE: E denotes the extension bit; the hex value assumes E = 0.VIFE codeActionDescriptionbinhexE000 000000Write and replace Replaces the old value with the new value.E000 011107ClearResets an accumulated value to 0 (zero).Related topicsSee “Configuration mode menus” on page 31 for information on enabling and disabling Com. Protection.See “Configuration mode menus” on page 31 for information on enabling and disabling Com. Protection.