Title: +038=360.012-#####._06-BA-ESR NI-DV Controller Nicotra Gebhardt - Operating Instruction.pdf
Displays actual number of days of operation Displays actual number of minutes of operation Displays actual output current Displays actual input voltage Displays actual temperature inside NI-DV l or external input has higher priority than "Normal".Exit SETTINGControlReturn to main menu DESCRIPTION Choice of control signal Control = Modbus NI-DV controlled via OJ-DV Hterm. External signals are ignored, incl.: Start/stop signal (ON/OFF), and external control signal on terminals (0-10 V in). Control = 0-10 V DC NI-DV controlled according to external control signals, incl.: Start/stop signal (ON/OFF), fire mode signal and external control signal (0-10 V in). External stop and stop from hand terminal have higher priority than start from hand terminal. Setting rotation directionRotationMin. rpmSetting minimum revolutions (fig. 9-7)Max. rpmSetting maximum revolutions (fig. 9-7)Up Ramp Down Ramp Switch Hz ExitReset AlarmAlarm stopVoltage lowVoltage highPhase errorCurrent high