Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]23.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.3 475.0 29.7 45 8.2 475.0 26.9SR 36-45 8.6 492.0 29.4 36 9.1 492.0 26.5MAIN 12-45 7.3 475.0 29.7 45 8.2 475.0 26.9SR 36-45 8.7 498.0 29.3 36 9.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.2 4.9 51.5 45 15.3 3.4 51.7SR 78-45 16.1 4.5 52.2 45 15.2 2.9 53.1MAIN 12-45 17.5 497.0 11.3 45 17.1 406.0 10.1SR 12-45 17.5 496.0 11.3 45 17.6 410.0 10.00100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 18.3 28.4 41.4 45 18.9 28.3 39.1SR 36-78 21.1 34.5 39.1 36 21.4 34.3 36.8MAIN 12-45 31.4 500.0 -12.4 45 32.2 500.0 -15.3