Title: 2 etg del2.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.3 19.5 45.4 12 9.9 15.9 45.2SR 12-36 13.9 19.5 45.4 12 14.1 15.9 45.2MAIN 36-45 15.7 248.0 4.9 36 15.3 248.0 2.2SR 36-78 23.0 237.5 5.9 36 23.8 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.4 15.8 20.0SR 36 3.0 15.9 20.0MAIN 45 7.9 230.5 10.4SR 36 4.9 243.0 10.160500050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1