Title: +135.01=564.001-RB001T_01-Montasje 258_2DB12_2582EB22_bma_bev_Norsk.pdf
Hanging lights cause shadows in the catchment area if they are mounted in the immediate vicinity of the presence detec- tor.Interference factors to be avoided: · Rapid temperature changes in the vicinity of the detector, caused by fan heaters being switched on or off, fans, etc., simulate motion.Lights being switched on or off in the immediate catchment area (mainly incandescent and halogen lamps) simulate mo- tion.Moving objects such as machines, robots, hanging posters, falling flower petals, hot paper from laser printers, animals, etc.The mounting site must not be exposed to vibrations or mo- tion.The mounting site must not be exposed to vibrations or mo- tion.3 / 4Bild 10 / figure 10Technical Support' +49 (911) 895-72227 +49 (911) 895-7223support.automation@siemens.comwww.siemens.de/automation/support-requestL1V30049867A DS02Technische DatenSpannungsversorgung erfolgt über die Buslinie Stromaufnahme ca. 10 mAAnschlüsse · Busklemme KNX