Title: 1 etg del 2.pdf
RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 8.1Cable ID: T1090 Date / Time: 10/17/2013 03:07:49 PM Headroom 11.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]307 486 33 13.2Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.5 16.9 44.9 36 16.6 84.3 30.5SR 12-36 11.0 72.5 34.6 36 13.6 72.3 31.6MAIN 12-36 14.8 93.8 32.8 36 16.9 100.0 29.3SR 12-36 11.1 84.3 33.5 36 13.6 84.3 30.510080604020NEXT (dB)