Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Uci: 0.2V t: 28.0ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 27.11.2020 12:03R LOW OhmR: 0.20ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 27.11.2020 12:03KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF084 16C2/003 30.11.2020 11:58 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF085 16C2/003 26.11.2020 14:07SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.1HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF085 16C2/003 26.11.2020 14:07Z-LINEZ: 0.49ΩIsc: 469A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF085 16C2/003 26.11.2020 14:07Tallberg Elektro A/S Tlf.22796640Side:36GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENT