Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.9 147 2 5.17Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]26.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.0 494.0 29.4 36 8.2 494.0 26.5SR 36-45 8.3 494.0 29.4 36 8.2 494.0 26.5MAIN 36-78 9.0 494.0 29.4 36 8.2 494.0 26.5SR 36-45 8.4 497.0 29.3 36 8.3 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 16.2 75.5 27.7 45 14.9 3.4 51.7SR 45-36 16.2 75.5 27.7 45 14.8 3.0 52.7MAIN 78-36 16.9 496.0 11.3 78 17.5 478.0 8.6SR 36-78 17.1 496.0 11.3 45 16.9 471.0 8.80100806040200250 MHzACR-F (dB)