Title: 564 DGS_x6411 Dali Gateway Basic.pdf
The lamps are variably controlled via KNX per DALI output via • Broadcast (all lamps jointly) • 16 lighting groups • 64 individual lamps • 16 scenes • 64 self-contained emergency lightsThe fault status (lamps, ballasts or emergency light- ing converters) of each DALI device or of the lighting group is sent on the KNX by a variety of KNX group objects.In addition to the standard functions, e.g. switching, dimming and brightness value setting with the cor- responding feedback, the DALI gateway has Stair- case lighting, Scene, Slave, Forced operation and Block functions. The lighting groups or individual lamps can be integrated into an energy-efficient building automation system via a KNX presence de- tector or light controller.Function, duration and partial duration tests and battery tests for emergency lighting systems with individual batteries to EN 62386-202 can be trig- gered and stopped via KNX. The results are provided on the KNX.