Title: Aggregatkjøring.pdf.pdf
Systemair A/S - Air handling unit design SystemairCAD 2.0 Geniox-2/C2021-04.15.F6 Expired 02.06.2021 | 18.06.2021Quotation no. Project Plant no.brandengen-2 Brandengene 360.002-3/Unit no. 20Date 18.06.2021Page 40/40Terminals for 230 V circulation pump are available in the control cabinet. The pump for the heating circuit will always run, or run when the outdoor temperature is lower than a settable value (+10 °C). At higher outdoor temperatures the pump will run when the heating output is larger than 0 %. The pump has a settable, shortest running time and the pump will be exercised once daily at settable time. Pump is not included in the delivery.Frost protection of the heating coil - water temperature sensor