Title: økernvn 94.pdf
SR 36-45 13.4 78.5 26.3 45 15.8 3.3 51.0MAIN 36-45 15.2 233.5 16.8 45 15.9 218.5 14.4SR 45-36 14.6 218.0 17.4 45 15.9 221.0 14.3010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.6 22.9 43.6 12 10.2 23.0 41.2SR 12-36 9.1 22.9 43.6 36 10.2 22.8 41.3MAIN 36-45 16.3 246.5 5.0 36 15.9 246.5 2.4SR 36-45 16.3 242.5 5.4 36 15.7 240.5 3.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.1 24.8 19.0SR 36 1.6 24.8 19.0MAIN 36 8.6 181.5 11.4SR 36 4.7 247.0 10.1010080050100150MHzRL (dB)20025006050050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active