Title: FDV-DOKUMENTASJON.pdf
Heat dissipation capacityPvidPvidProduct range803FAZAASwitchgear for industrial and advanced commercial applicationsLifespanEnclosure heightDirection of incoming supply000V DCHeat dissipation per pole, current-dependentC0.8 … 2Operating ambient temperature min.Rated currentUeUeMounting positionPdiss45IEC/EN 60715 top-hat railMountingInInEquipment heat dissipation, current-dependentTechnicaldata1 x 25IEC/EN 60947-2IEC/EN 60898mmmmmmmm4 poleB, C, D17.5ElectricalRated switching capacity acc. to IEC/EN 60947-2Rated switching capacity acc. to IEC/EN 60947-2IP20, IP40 (when fitted)Static heat dissipation, non-current-dependent48 (per pole)StandardsSelectivity Class7.5> 10000Operational switching capacityTwin-purpose terminals230/400A gL/gGMax. back-up fuse