Title: økernvn 94.pdf
50100150200250MHzLinkWare Version 7.4Cable ID: T3404 Date / Time: 09/11/2013 06:18:59 Headroom 5.7 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]176 268 9 8.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]13.9 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.6 219.0 36.3 36 7.9 246.0 32.8SR 36-78 5.7 230.0 35.9 36 6.4 219.5 33.6MAIN 12-36 8.2 244.0 35.5 36 7.9 246.0 32.8SR 36-78 5.7 230.0 35.9 36 6.4 219.5 33.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)