Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 10.0 461.0 29.7 36 9.7 461.0 26.9SR 36-45 7.1 474.0 29.1 36 8.2 475.0 26.2MAIN 36-45 11.4 500.0 27.8 36 10.5 499.0 25.0SR 36-45 7.4 496.0 28.0 36 8.5 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.0 3.5 54.4 45 13.7 2.6 53.9SR 36-45 14.0 3.5 54.4 45 13.7 2.3 55.2MAIN 36-45 14.5 473.0 11.7 45 17.0 491.0 8.4SR 45-36 14.5 473.0 11.7 36 16.7 490.0 8.40100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.2 66.0 30.6 36 23.5 66.8 27.9SR 12-45 25.7 67.3 30.3 12 27.3 67.3 27.8MAIN 36-45 39.4 500.0 -12.4 36 38.5 499.0 -15.2