Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Classic: Programming examples for the PCD2.W11x can be found in a separate manual and on the TCS Support site (www.sbc-support.com + getting started). xx7: the firmware reads in the values according to the configuration (I/O Builder)Watchdog: This module can be used on all base addresses; there is no interac- tion with the watchdog on the CPUs. For details, please refer to the “Watchdog” section, which describes the correct use of the watchdog in conjunction with PCD2 components.5-60PCD2.W2x05.8.3PCD2.W2x0, analogue inputs, 8 channels, 10 bit resolutionApplicationWith its short conversion time of <50 µs, this module is universally suitable for recording analogue signals. The only limitations are with weak signals, as with Pt 100 resistive temperature sensors, or with thermocouples.Module overview8 channels for signals 0 … 10 V 8 channels for signals 0 … 20 mA 8 channels for resistive temperature sensors Pt/Ni 1000