Title: Innstilt effektbryter hovedfordeling.pdf
VerninnstillingerOverbelastning Kortslutningkorttid Kortslutningmomentan JordfeilFabrikatBryterenhetUtlgserenhetIn[A]Kurs nr.EATON Strom: Ir 1,000/ 210,0 A Strom: li 10,000/2000,0 A NZM2 NZM2 A 200,00 EATON ,. Strgm: Ir 1,000/ 107,0 A Stram: li 6,000/ 600,0 A \nstil I oX 2 uwﬂuu A80-100 i m—SJ100,00 P%\ow -2L k;%@ Q% EATON Strom: Ir 1,000/ 168,0 A Stram: Ii 6,000/ 960,0 A oL LE oKnzmz Sim nhoxgNZM2 A160,00 U%\U 2-1) L>&3 Q% EATON Strgm: Ir 0,800/ 134,4 A Strgm: li 6,000/960,0 A NZM2 NZM2 A 160,00 EATON Strgm: Ir 0,800/68,5 A Strgm: li 6,000 /480,0 A NZM_1 NZM_1-A63-80 80,00Anleggets adresse: Anlegg: Dato: 28.02.2022 12:37:07MELLOm400 VBgifot Elektro ASBytesteinen 1. 6517 Kristiansund NBytesteinen 13 COIFOT Kunde, eier:s ELEKTROVENTILASION Ziko Gruppen AS6517 KRISTIANSUND N Nedte Enggate 14 Tel: 71404050Fordeling:HOVEDFORDELING 400V 432.001FEB91418 VTNCSVs. 6.0.223S FebdoK e oros20m6509 Kristiansund N