Title: DOCA0005EN-12.pdf
See “Communications via M-Bus” on page 79 for information on M-Bus communications.122DOCA0005EN-12SpecificationsBACnet communicationsCharacteristicValueMetersNumber of ports1Labels0V, D0/-, D1/+(shield)Baud rate9600, 19200, 38400, 57600, 76800Isolation4.0 kV rmsiEM3165 / iEM3265 / iEM3365 /iEM3465 / iEM3565Wire2.5mm2 / 14 AWG shielded twisted pairWire strip length7 mm / 0.28 inTorque0.5 Nm / 4.4 in•lbRelated topicsSee “Communications via BACnet” on page 107 for information on BACnet communications.See “Communications via BACnet” on page 107 for information on BACnet communications.DOCA0005EN-12123124Specifications iEM3000 series user manualDOCA0005EN-12TroubleshootingChapter 10 TroubleshootingThe meter does not contain any user-serviceable parts. If the meter requires service, contact your local Schneider Electric representative.NOTICERISK OF DAMAGE TO THE METERDo not open the meter case.