Title: 1 etg del 2.pdf
604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz7510060RL @ Remote (dB)5040302010002550 MHz75100LinkWare Version 8.1Cable ID: D1212 Date / Time: 10/17/2013 11:41:36 AM Headroom 9.4 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]86 136 9 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.4 80.0 33.9 12 11.8 80.0 30.9SR 12-36 10.3 91.5 32.9 36 12.6 91.5 29.9MAIN 12-36 10.0 99.3 32.4 12 12.1 99.3 29.4SR 12-36 10.6 99.3 32.4 36 12.9 99.3 29.4