Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Watchdog: This module can be used on all base addresses; there is no interaction with the watchdog on the CPUs. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD2 components.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-78Saia-Burgess Controls Ltd.Input/output (I/O) modulesAnalogue combined input/output modules6.12 Analogue combined input/output modulesPCD2.W5254 inputs, 14 Bit, 0…10 V, 0(4)…20 mA, Pt 1000, Pt 500 or Ni 1000 (selectable via DIP switch)and2 outputs, 12 Bit, 0…10 V or 0(4)…20 mA (selectable via software (FBox, FB)6Galvanic separation of outputs to PCD, channels themselves not separatedI/O modules and I/O terminal blocks may only be plugged in and removed when the PCD and the external +24 V are disconnected from the power supply.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-79Saia-Burgess Controls Ltd.