Title: fireray5000_igb.pdf
Installation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 3Installation Check the beam spacing against local regulations  Position beam as high as possible, but with a minimum distance of0.5m from detector to ceiling Mount Detector and Reflector directly opposite each other  Do NOT position detector where personnel or objects can enter thebeam pathInstallation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 41.2 Fitting the ProductOptions for Detector wiring orientation