Title: 360.001 - Tilluft.pdf
MAGID-C1-315Size315/315315315/315315315315315/315315315315L [m]1,10,12,20,10,244qv [m³/h]1200600600300300300300300300v [m/s]4,32,12,11,11,11,11,11,11,1dpt [Pa]11,5 Sound in:Attenuation: Addition:Dividing:0,2 Sound in:Attenuation: Addition:2,9 Sound in:Attenuation: Addition:Dividing:0,0 Sound in:Attenuation: Addition:1,5 Sound in:Attenuation: Addition:Total Lw:0,1 Sound in:Attenuation: Addition:0,8 Sound in:Attenuation: Addition:Dividing:0,0 Sound in:Attenuation: Addition:3,1 Sound in:Attenuation: Addition:Total Lw:Sound in:Attenuation: Addition:63 [dB]48.30.0 +25.63.045.30.1 +10.645.20.0 +3.43.042.20.0 +0.042.212.0 +0.030.242.20.2 +0.041.90.0 +0.03.038.90.0 +0.038.912.0 +0.026.938.90.0 +0.0125 [dB]43.00.0 +21.63.040.10.1 +9.639.9