Title: økernvn 94.pdf
SR 36-45 13.7 54.3 29.5 45 15.3 48.0 27.6MAIN 36-12 17.0 240.5 16.6 12 18.9 242.0 13.5SR 12-36 17.8 240.5 16.6 36 18.9 240.5 13.6010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 14.0 13.3 49.5 36 15.2 13.3 47.1SR 12-36 9.7 13.3 49.5 36 11.4 13.1 47.2MAIN 36-45 17.8 249.5 4.7 36 17.9 250.0 2.0SR 36-45 12.5 249.5 4.7 36 13.0 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 3.1 25.5 19.0SR 36 4.9 11.8 20.6MAIN 45 9.4 150.5 12.2SR 45 7.3 242.0 10.2010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active