Title: økernvn 94.pdf
Cable ID: D4024 Date / Time: 09/10/2013 12:24:22 Headroom 12.6 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]72 114 8 2.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.4 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.6 95.8 32.6 36 14.2 95.8 29.6SR 12-36 13.9 95.8 32.6 36 15.1 95.8 29.6MAIN 12-36 12.6 95.8 32.6 36 14.2 95.8 29.6SR 12-36 13.9 95.8 32.6 36 15.1 95.8 29.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 20.8 3.3 48.4 45 22.6 3.1 45.7