Title: Simployer - Data testrapport =514.204-FS001.pdf
Model: DTX-ELT Main S/N: 9862060 Remote S/N: 9862059 Main Adapter: DTX-CHA001 Remote Adapter: DTX-CHA00135.3 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD41 Date / Time: 28/01/2022 12:34:35 Headroom 10.9 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]35.3 180 12 6.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]25.2 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 10.9 128.5 38.1 4,5 10.4 44.8 43.1SR 1,2-3,6 11.2 240.5 33.4 3,6 12.1 240.5 30.4MAIN 1,2-3,6 11.0 247.5 33.2 3,6 12.0 244.0 30.3