Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 15.12.2020 10:28 (Elektriker)KONTINUITET: R200mA NPER: 0.04ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 0.5ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 27.11.2021 10:41Tallberg Elektro A/S Tlf.22796640Side:25GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.174174175175176176177177178178179179TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF041 16C2/003 15.12.2020 15:07 (Elektriker)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF042 16C2/003 30.11.2020 08:49SPĆNDINGUln: 234V Ulpe: 234V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF042 16C2/003 30.11.2020 08:50Z-LINEZ: 0.58Ω