Title: +039=462.001-NB001._01-ITYS UPS Coromatic Monteringsanvisning Brukerveiledning.pdf
BYPASS FREQUENCY HIGH LIMIT1 to 10 %HE VOLTAGE LOW LIMIT1 to 10 %HE VOLTAGE HIGH LIMIT1 to 10 %HE FREQUENCY LOW LIMIT1 to 10 %HE FREQUENCY HIGH LIMIT1 to 10 %BATTERY QUANTITY19/20/21SET RUNNING TIMEDay:hour:minute:second 0000:0000:00~9999:23:59:59LCD CONTRAST5 to +517. OPERATING MODES17.5. OPERATION WITH MANUAL BY-PASSIf the maintenance bypass is activated using the appropriate procedure, the load is powered directly from the maintenance by- pass, while the UPS is separated from the power supply.WARNING! In this mode continuity is not guaranteed in the event of a mains power failure.This operating mode can be selected for maintenance to be carried out on the system so that the necessary actions can be performed by service personnel without having to disconnect the power supply to the load.17.5-117.5-217.5-317.5-417.5-517.5-617.5-7Wait for the complete shutdown.ITYS 1-10 kVA - Ref.: IOMITYTWXX05-GB 0031H S I L G N E3217. OPERATING MODES