Title: +038=522.000-NI002._05-Testrapport EKOM-anlegg, plan 03 (Uniconsult).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.7 499.0 29.3 36 8.4 500.0 26.4SR 36-45 10.5 499.0 29.3 36 10.2 499.0 26.4MAIN 36-45 8.8 500.0 29.2 36 8.4 500.0 26.4SR 36-45 10.6 500.0 29.2 36 10.2 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.1 447.0 12.2 45 14.6 33.8 31.7SR 45-78 15.1 459.0 12.0 45 14.5 15.6 38.4MAIN 45-78 15.5 498.0 11.3 45 15.5 476.0 8.7SR 78-45 15.5 500.0 11.3 45 15.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.7 42.0 36.7 45 24.8 42.3 34.1SR 36-45 22.0 41.8 36.7 36 22.8 41.8 34.3MAIN 36-45 34.6 500.0 -12.4 36 34.6 500.0 -15.3