Title: etg u1.pdf
SR 12-36 14.4 26.9 41.8 12 15.5 22.5 41.4MAIN 36-45 18.4 248.5 4.8 36 17.8 248.5 2.2SR 12-36 24.0 249.5 4.7 36 23.8 248.0 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 3.7 33.5 18.4SR 45 3.8 33.5 18.4MAIN 36 7.6 240.5 10.2SR 78 8.2 249.5 10.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 ETG.U1 økernveien 2410.flwSite: OKERNVEIEN 94