Title: økernvn 94.pdf
237 376 27 10.3237 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]9.4 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 0.9 * 230.0 35.9 36 0.5 * 246.5 32.8SR 12-45 7.0 249.0 35.4 12 8.7 247.5 32.8MAIN 12-36 1.0 247.5 35.4 36 0.5 246.5 32.8SR 12-45 7.0 249.0 35.4 12 8.7 247.5 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-12 15.5 4.4 51.4 45 17.2 3.4 50.6SR 45-12 15.5 4.1 51.9 45 17.1 3.4 50.6MAIN 45-12 16.4 227.0 17.1 45 18.2 230.5 13.9SR 45-36 17.3 250.0 16.2 45 17.9 227.0 14.1010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHz