Title: 36 Siemens GDB181-MO.pdf.pdf
The actuator supports the following re-initialization / reset behavior:Local reset by push-button: cf. section 2.4.2Tool-reset, cf. section 6.2Remote reset: Using “RemoteFactoryReset” command.Effect of reset:Process values: set to ex-works default values.Parameters:Application and actuator parameters are set to factory or OEM defaults,Network parameters are reset only in case of local reset, not by remote reset (otherwise loss of communication).Network parameters are reset only in case of local reset, not by remote reset (otherwise loss of communication).Counters are not reset.Status flags are not reset.Device Information and Factory Data are not reset.10.2.10 Selftestà Register 256 The actuator supports a selftest. When triggered, the selftest runs the actuator to the detected limits and sets the flags in register 769 according to the result (bit 09 = 1à”failed” or bit 10 = 1 à “passed”).