Title: 1 etg del 2.pdf
Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 45]85 135 10 3.685 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]23.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 0.3 * 231.5 35.9 36 0.0 * 247.0 32.8SR 36-78 6.3 211.0 36.5 36 6.2 216.0 33.8MAIN 12-36 0.5 247.0 35.4 36 0.0 247.0 32.8SR 36-78 6.7 234.5 35.8 36 7.0 247.0 32.810080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250