Title: etg u1.pdf
0050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 8.1Cable ID: T0001 Date / Time: 10/22/2013 01:18:49 PM Headroom 9.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]56 90 7 2.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.2 100.0 20.4Worst Case Margin Worst Case ValueN/A Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 10.4 57.8 36.2 36 12.2 98.3 29.4SR 12-36 9.9 57.8 36.2 36 12.0 98.3 29.4MAIN 12-36 10.8 98.3 32.4 36 12.2 98.3 29.4SR 12-36 9.9 98.3 32.4 36 12.0 98.3 29.410080604020NEXT (dB)