Title: Innstallasjons manual PS2500.pdf
[l/s] 0,07 0,04 0,08 0,04 0,10 0,06Water temperature: 80/60 °C Room temperature: +18 °COutput *2Outlet air temp.Water ﬂow[kW] 8,8 7,0 16,3 11,7 20,1 16,0[°C] 38,0 41,0 40,8 45,6 40,8 44,1[l/s] 0,11 0,09 0,20 0,14 0,25 0,20TypePA2510WPA2515WPA2520WFan positionMax Min Max Min Max MinAirﬂow[m3/h] 1300 900 2100 1250 2600 1800Supply water temperature:70 °C Room temperature: +18 °C Outlet air temperature: +35 °C*1 OutputWater ﬂowPressure dropReturn water temp. [°C] 54,0 49,0 47,0 41,0 47,0 41,0[l/s] 0,11 0,06 0,13 0,06 0,16 0,09[kW] 7,4 5,3 12,0 7,3 15,0 10,3[kPa] 3,7 1,3 6,7 1,8 12,1 4,1Water temperature: 70/50 °C Room temperature: +18 °COutput *2Outlet air temp.Water ﬂow[kW] 6,8 5,4 12,8 9,2 15,8 12,6[°C] 33,4 35,7 35,9 39,6 35,9 38,5[l/s] 0,08 0,07 0,16 0,11 0,19 0,151) Recommended outlet air temperature for good comfort and optimized output. *2) Nominal output at given supply and return water temperature.Pressure drop[kPa]