Title: 360.001 - Tilluft.pdf
3.0 +15.020.30.0 +15.021.4+7.921.60.1 +15.022.450.00.00.2 +15.04k [dB]16.43.0 +11.015.40.1 +11.016.71.0 +11.016.90.1 +11.017.83.0 +11.016.30.0 +11.017.4+0.917.50.1 +11.018.327.00.00.2 +11.08k [dB]9.73.0 +4.08.50.1 +4.09.81.0 +4.010.00.1 +4.010.93.0 +4.09.30.0 +4.010.4+0.910.90.1 +4.011.619.00.00.2 +4.0Lp [dB]Level2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeType79 T-BRANCHDUCT80 SUPPLYREDUCERDUCT81 T-BRANCHDUCT82 SUPPLYDUCT83 PLUGProductTCPU-200-160MAGID-C1-160Tellus-LOV VAV-H-160MAGIR-CC1-200-160MAGID-C1-160TCPU-160-160MAGID-C1-160Tellus-LOV VAV-H-160MAGID-C1-160ESU-160Size200/160160160200/160160160/160160160160160L [m]0,13,20,10,152qv [m³/h]450225225225225225225225v [m/s]4,03,13,12,03,13,13,13,1dpt [Pa]