Title: +038=360.019-#####._05-360.019 Gold SD-30 Ventilasjonsaggregat Swegon - Installasjonsanvisning.pdf
PT-VerSecção4.10noManualdefuncionamentoGOLD,Instalação.NL-ZieSectie4.10indeGOLD-functiehandleiding,Installatie.192013.GOLD SD 004/005, 007/008, 011/012, 014/020, 025/030, 035/040, 050/060, 070/080, 100/120BAA >= 1500 mm B = 7000 mm C = Ø 11 mmABC14.The max. permissible load on the corresponding connection is 16 VA.ABSDDigital inputs, terminals 4-17, are of extra-low voltage type. Analogue inputs, terminals 18-19 have an input impedance of 66 kΩ.Wiring terminalFunctionRemarks1,2,3Connections for EIA -4851= Communication connection A/RT+, 2= Communication connection B/RT–, 3= GND/COM.4,5External stopStops the air handling unit by opening the circuit. On delivery, this function is fitted with a jumper. If the connection is interrupted, the air handling unit will stop.6,7External fire/smoke function 1