Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Isc: 474A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:36RCD UbUc: 0.0V Rl: 1Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 08:53RCD II: 28.5mAUci: 0.1V t: 101.4ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 12:47R LOW OhmR: 0.20ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 15.06.2020 12:47R LOW OhmR: 0.24ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF046 C16/2 16.06.2020 09:48R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF047 C16/2 16.06.2020 09:48R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF048 C16/2 15.06.2020 10:14Tallberg Elektro A/S Tlf.22796640Side:15GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT