Title: +038=30.001-NI003._16-V20-08-02 VVS-anlegg plan 8 - DM3.pdf
LD018T Maks:140 m³/h Kjøling: 335 W 0.027 L/s Varme: 375 W 0.009 L/sLD018T Maks:220 m³/h Kjøling: 410 W 0.033 L/s Varme: 375 W 0.009 L/s7Opp 320.102: 54 mm 320.102: 54 mm8Romregulering - Plan 08ProduktPlan 09 WISE RTA 09 WISE IAQ 09 WISE RTS 09 WISE director (trådløs router)ProduktBørverdiomstiller CO2-, RH- og temperaturgiver Temperaturgiver Wise Director routerKombibaffler-Produktliste, Plan 08System ProduktkodeProduktVersjon360.008 360.008 360.008 360.009 360.018 360.018 360.018 360.018 360.027 360.027 Grand total: 76LD018T LD021T LD022T LD024T LD018T LD021T LD024T LD028T LD018T LD021TWISE Parasol Zenith 1200x600-ø160 kortside WISE Parasol Zenith 1200x600-ø160 kortside WISE Parasol Zenith 600x600-ø160 Parasol Zenith 1200x600-ø160 kortside WISE Parasol Zenith 1200x600-ø160 kortside WISE Parasol Zenith 1200x600-ø160 kortside Parasol Zenith 1200x600-ø160 kortside Parasol Zenith 600x600-ø160 WISE Parasol Zenith 1200x600-ø160 kortside WISE Parasol Zenith 1200x600-ø160 kortside