Title: økernvn 94.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.2 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.0 * 249.5 35.4 36 0.4 * 248.0 32.8SR 36-450.6 *232.5 35.9 36 0.4 *241.0 33.0MAIN 36-45 0.0 249.5 35.4 36 0.4 248.0 32.8SR 36-45 0.7 247.5 35.4 36 0.5 249.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.0 88.5 25.3 45 15.6 111.0 20.3SR 45-36 13.0 82.0 25.9 45 15.4 99.3 21.3MAIN 36-45 15.6 249.0 16.3 45 17.3 241.0 13.5SR 45-36 15.3 249.0 16.3 45 17.7 244.0 13.4010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250