Title: økernvn 94.pdf
40202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: D3192 Date / Time: 09/11/2013 03:09:51 Headroom 3.1 dB (NEXT 36-45) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]123 188 6 5.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]19.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 3.1 43.0 47.8 36 5.0 43.0 45.3SR 36-45 3.2 43.0 47.8 36 4.8 232.0 33.2MAIN 12-36 6.3 245.5 35.5 36 6.1 246.0 32.8SR 36-45 4.6 232.5 35.9 36 4.8 232.0 33.210080604020NEXT (dB)