Title: Data tester Smestad skole - Detaljert.pdf
Worst Value: Local: 12-45 24,2 10,8 13,4 465,00Remote: 45-12 24,7 10,8 13,9 465,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 30,3 25,3 5,0 452,00Remote: 45 29,1 23,8 5,3 500,00Worst Value: Local: 36 28,9 23,9 5,0 495,00Remote: 45 29,1 23,8 5,3 500,00PS-ACRF: Pass Worst Margin: Local: 45 66,0 54,3 11,7 2,20Worst Value: Local: 45 21,4 8,0 13,4 457,00Remote: 12 66,3 54,3 12,0 2,20Remote: 45 22,3 8,1 14,2 452,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:02Signature:______________________ Page: 56Copper Certification ReportCable Label: 521.002-UD-135 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 12:07:40 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel: