Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]26.2 114 2 3.98Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]29.4 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 8.3 406.0 31.2 45 9.4 465.0 26.7SR 36-45 6.4 465.0 29.5 36 7.0 453.0 27.3MAIN 12-45 9.7 499.0 27.9 45 10.5 500.0 25.0SR 36-45 7.0 497.0 28.0 36 7.8 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.7 3.5 54.4 45 13.6 2.3 55.2SR 36-45 14.6 3.5 54.4 45 13.4 2.1 55.7MAIN 45-36 15.9 481.0 11.6 45 16.6 499.0 8.3SR 36-45 15.8 482.0 11.6 45 16.5 499.0 8.30100806040200250 MHzACR-F (dB)