Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Using higher voltage (50…250V), all connections to the relay contacts must be con- nected on the same circuit, i.e. in such a way that they are all protected against one AC phase by one common fuse. Each load circuit may however be fused individually.I/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24V are disconnected from the power supply.6-17PCD3.E5006.3.1PCD3.E500, 6 digital inputs, electrically isolated from the I/O BusApplicationModule with 6 electrically isolated inputs for alternating current. The inputs are set up for source operation and have one common "COM" terminal. Only the positive half- wave of the alternating current is used.Technical dataNumber of inputs6 electrically isolated from the CPU,source operation, all inputs to the module inthe same phaseInput voltageInput current115/230 V 50/60 Hz, sinusoidal (80 to 250 VAC) 115 VAC: 230 VAC: