Title: Simployer - Data testrapport =514.204-FS001.pdf
55.0 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD79 Date / Time: 28/01/2022 13:37:47 Headroom 9.0 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]55.2 284 21 9.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]19.3 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 10.1 199.5 34.8 3,6 11.7 231.0 30.8SR 4,5-7,8 9.0 26.1 49.7 7,8 10.7 26.0 47.1MAIN 1,2-3,6 10.1 199.5 34.8 3,6 11.7 231.0 30.8SR 4,5-7,8 9.1 203.0 34.7 4,5 10.8 203.0 31.7