Title: +038=433.002-FS031._02-Eaton Tavlebyggeren Produktblad.pdf
Technical data Electrical Current test marksAs per inscriptionStandardsIEC/EN 61008Rated operational voltageUeVUeV ACRated operating voltageUeV AC230/400Rated frequencyfHz50/60Limit values of the operating voltageTest circuitV AC184 - 440Comment for range of the test button3-phase application without N (400V AC Phase-Phase) not allowedRated fault currentsIΔnmA30, 300Rated non-tripping currentIΔno0.5 x I ∆nSensitivityAC and pulsating DC current sensitiveRated insulation voltageUiV440SensitivityDC and pulsed currentRated impulse withstand voltageUimpkV4Rated short-circuit strengthIcnkA10Maximum max. as short-circuit protective deviceA gLBack-up fuseA gLShort-circuit and overload: 63 A gG/GLlifespanElectricalOperations≧ 4000MechanicalOperations≧ 20000References Auxiliary switch for subsequent installationZ-HK 248432Tripping signal contact for subsequent installationZ-NHK 248434