Title: 360.001 - inntak.pdf
Asplan Viak AsTom Svanberg19.09.2021 20:0113.0 Pa63 [dB]125 [dB]250 [dB]65.073.069.065.073.069.00.0 +22.00.0 +21.00.0 +20.065.073.069.011.013.016.054.060.053.00.0 +22.00.0 +21.00.0 +20.054.060.053.0500 [dB]62.062.00.0 +18.962.019.043.00.0 +18.943.01k [dB]52.052.00.0 +17.952.026.026.00.0 +17.926.62k [dB]46.046.00.0 +16.846.030.016.00.0 +16.819.44k [dB]40.040.00.0 +12.840.020.020.00.0 +12.820.88k [dB]34.034.00.0 +5.834.018.016.00.0 +5.816.4Lp [dB]LocationLevel3. etasje3. etasje3. etasje3. etasjeNodeTypeDUCT185 N-BRANCHDUCT186 CONN.NODEProductEndelokkSize2200x32002100x2400/22002100x24002100x2400L [m]0,70,6Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]136100,50,0 Sound in:Attenuation: Addition:136100,5Sound in:136100,80,0 Sound in:Attenuation: Addition:136100,8Sound in:263 [dB]