Title: +175=574.001_OE001_Manual - Varmemåler M3 - Løs fra rør.Produktinformasjon.pdf
Warning: the pulse value “k” of the heating system flowmeter is settable only once. Once the configuration is confirmed, this parameter is no longer editable.2) The second parameter that has be configured is the enabling/disabling of the anti-tampering contact of the heating system flowmeter (Flow in).By using the T1 button, proceed with the enabling [1] or disabling [0].Confirm the selected parameter by holding the T2 button for more than 3 seconds, thus moving to the next parameter. The enabling of the anti-tampering system requires the connection of a normally closed (NC) contact between terminals 50 and 11. If the contact is opened, a fraud will be recorded.3) The third parameter that has be configured is the pulse value "k" of the C1 cold/hot water meter.The value can be selected by using the button T1: 0.1–0.25–1–2.5–10–25–100–250 L/impConfirm the selected parameter by holding the T2 button for more than 3 seconds, thus moving to the next parameter.