Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
Max. water-side operating pressure with hydraulic modulekPa400400400400400400Water connections with or without hydronic moduleVictaulic®Connectionsinch2,52,52,5333External diametermm73737388,988,988,9Casing paintColour code: RAL 7035 / RAL 7024(3) Values shown are a guideline only. Please refer to the unit nameplate (4) On delivery, the vessels are preinflated to a standard value, which may not be the optimum one for the installation. To enable the water volume to be varied as desired, adapt the inflation pressure to a value close to that which corresponds to the static height of the installation. Fill the installation with water (bleeding out any air) at a pressure more than 10 to 20 kPa higher than the vessel pressure.16Water chillersHeat pumpDYNACIAT LGElectrical specificationsDYNACIAT LG - Standard unit (without hydraulic module)080 090 100 120 130 150 180 200 240 260 300 360 390 450 480 520 600Power circuitNominal voltageV-ph-Hz