Title: 2 etg del2.pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]8.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 0.4 * 244.0 35.5 36 0.9 * 249.0 32.7SR 36-450.9 *246.5 35.4 36 0.4 *241.0 33.0MAIN 36-45 0.4 244.0 35.5 36 0.9 249.0 32.7SR 36-45 0.9 246.5 35.4 36 0.4 241.0 33.010080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 8.6 50.0 30.2 45 11.4 43.0 28.5SR 45-36 8.5 45.8 31.0 45 11.2 44.3 28.3MAIN 45-36 13.6 247.0 16.3 36 15.9 247.5 13.3SR 45-36 14.0 249.0 16.3 45 16.1 247.0 13.3010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250