Title: 40 Bender brukermanual.pdf.pdf
An analysis of the harmonics cannot be carried out in disabled channels or channels with digital input. The display indicates „- - -“ .RCMS460-490_D00067_03_M_XXEN/12.201751Column 1: Column 2:Column 3:Identifies the THF, DC component and harmonics number. Bar graph indication of the THF (% of the r.m.s. value), bar graph of the current value. Current r.m.s. value, THF/residual current of this measuring channel. Harmonics current values are updated in order. Up- dating all harmonics takes up to 15 seconds.Select a measuring channel for displaying the harmonics:– Use the "" button to go to the measuring channel setting. Pressthe "↵" button.– Use the Up/Down buttons to select a measuring channel. Press "↵"to confirm your selection.3. You can use the Up/Down buttons to browse the harmonics current values of this measuring channel.3. You can use the Up/Down buttons to browse the harmonics current values of this measuring channel.