Title: Ahlsell.pdf
Main: VersivS/N: 2552117 Software Version: V3.0 Build 6 Calibration Date: 12/10/2013 Adapter: DSX-5000 (DSX-PLA004)S/N: 2505094Length (m), Limit 90.0 Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms)[Pair 1,2] [Pair 4,5] [Pair 4,5] [Pair 3,6]12.4 61 1 6.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]34.9 484.0 42.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 9.7 459.0 27.9 7,8 11.4 286.0 31.7SR 1,2-4,5 8.0 291.0 34.2 1,2 9.2 267.0 32.2MAIN 3,6-4,5 10.1 494.0 26.8 3,6 12.2 494.0 23.9SR 3,6-4,5 9.1 493.0 26.9 4,5 10.1 494.0 23.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 19.0 40.3 32.1 4,5 19.9 1.6 57.0SR 7,8-4,5 19.0 40.3 32.1 4,5 19.7 1.1 60.2MAIN 3,6-1,2 20.0 462.0 10.9 1,2 22.4 462.0 7.9