Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD08 Date / Time: 28/01/2022 09:59:34 Headroom 8.2 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]23.3 120 9 5.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]28.5 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 3,6-4,5 9.5 106.0 39.5 3,6 9.3 152.5 33.9SR 1,2-3,6 8.2 152.0 36.8 3,6 8.6 152.5 33.9MAIN 1,2-3,6 9.8 242.0 33.4 3,6 10.4 242.5 30.4SR 1,2-3,6 10.1 242.5 33.3 3,6 10.0 242.5 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)