Title: 91879 FDV F13 Kafe.pdf
4134239Delivery program Product rangeDILL Lighting contactorsApplicationContactors for lighting systemsUtilization categoryAC-1: Non-inductive or slightly inductive loads, resistance furnacesRated operational currentAC-5a220 V 230 VIeA18380 V 400 VIeA18AC-5b220 V 230 VIeA21380 V 400 VIeA21AC-1Conventional free air thermal current, 3 pole, 50 - 60 HzOpenat 40 °CIth =IeA40Contact sequenceActuating voltage230 V 50 Hz, 240 V 60 HzNoteSwitchgear for lighting systemsDIL L12 L18 L20 M7 M9 M12 M17 M25 M32 M40 M50 100 220 330 470 470 500 Cmax Permissible [mF] compensation capacitance470 470 470 4780Ie [A]14212767.5101421273342Filament lamp Mercury blended lamps Fluorescent lamps, conventional - reactor – starter – connection Fluorescent lamps, conventional - reactor – starter – connection Fluorescent lamps, duo circuit (series compensated) Ie [A]12 electronic upstream devices andIe [A]12Ie [A]20Ie [A]20