Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 36] [Pair 36] [Pair 45]18.7 82 2 3.02Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]32.4 498.0 41.5Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 6.0 452.0 30.1 36 6.9 452.0 27.3SR 36-45 9.4 457.0 29.9 36 9.7 457.0 27.1MAIN 36-45 7.8 497.0 28.0 36 8.3 497.0 25.1SR 12-45 10.9 497.0 28.0 36 10.9 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.3 406.0 13.1 45 14.4 2.6 53.9SR 36-45 15.3 144.0 22.1 45 14.5 16.0 38.2MAIN 36-45 15.4 468.0 11.8 45 18.0 498.0 8.3SR 45-36 15.5 468.0 11.8 45 18.1 498.0 8.30100806040200250 MHzACR-F (dB)