Title: TFP151_11_2014.pdf
8.0K UPRIGHT (3/4˝ NPT)TY41516WAX COATED 286°F (141°C) MAX286286°F (141°C)5918.0K PENDENT (3/4˝ NPT)TY42517LEAD COATED360360°F (182°C)5608.0K UPRIGHT (1/2˝ NPT)TY48518WAX-OVER-LEAD 286°F (141°C) MAX000OPEN***5618.0K PENDENT (1/2˝ NPT)TY49519CHROME PLATEDNotes:Eastern Hemisphere sales only ** Available in only 8.0K, 155°F (68°C) or 200°F (93°C); requires lead time to manufactureEastern Hemisphere sales only ** Available in only 8.0K, 155°F (68°C) or 200°F (93°C); requires lead time to manufacture*** Available onlyfor 8.0 K-factor TY4151 and TY4251 (“OPEN” indicates sprinkler assembly without glass bulb, button, and sealing assembly)for usein deluge systemsTABLE C SERIES TY-B UPRIGHT AND PENDENT SPRINKLERS PART NUMBER SELECTIONLimited Warranty For warranty terms and conditions, visit www.tyco-fire.com.Ordering Procedure Contact your for availability. When placing an order, indicate the full product name and Part Number (P/N).