Title: Data tester Smestad skole - Detaljert.pdf
601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 27,4 16,8 10,6 234,00Remote: 45-12 27,7 16,8 10,9 234,00Worst Value: Local: 12-45 21,5 10,4 11,1 492,00Remote: 12-36 21,4 10,3 11,1 495,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,3 23,8 3,5 498,00Remote: 36 28,3 23,8 4,5 500,00Worst Value: Local: 36 27,3 23,8 3,5 500,00Remote: 36 28,3 23,8 4,5 500,00PS-ACRF: Pass Worst Margin: Local: 45 73,2 61,2 12,0 1,00Worst Value: Local: 12 19,3 7,3 12,0 495,00Remote: 12 65,9 54,3 11,6 2,20Remote: 12 19,6 7,3 12,3 496,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:55Signature:______________________ Page: 7Copper Certification Report