Title: +038=433.002-FS051._12-Terminalblokk 1 pol Eaton Tavlebyggeren Produktblad.pdf
3) Up to 95 mm² can be connected depending on the cable manufacturer. Al conductors, Cu cable Solid mm2 1 x 16 Stranded mm2 Stranded mm2 1 x (25 - 95) Cu strip (number of segments x width x segment thickness) Box terminal min. mm 2 x 9 x 0.8 max. mm 9 x 9 x 0.8 Copper busbar (width x thickness) mm Bolt terminal and rear-side connection Screw connection M6 Direct on the switch min. mm 12 x 5 max. mm 16 x 5 Control cables mm2 1 x (0.75 - 2.5)2 x (0.75 - 1.5) DesignverificationasperIEC/EN61439 Technical data for design verification Rated operational current for specified heat dissipation In A 32 Equipment heat dissipation, current-dependent Pvid W 9.31 Operating ambient temperature min. °C