Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Uiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF064 C16/2 16.06.2020 10:13R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF065 C16/2 16.06.2020 09:49R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF066 C16/2 16.06.2020 09:50R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF067 C16/2 16.06.2020 09:50R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF068 C16/2 16.06.2020 11:00R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / MPE1 / Ventilasjon 16.06.2020 11:13R LOW OhmR: 0.00ΩR+: 0.0Ω R-: 0.0Ω Grenseverdi: 1.0ΩTallberg Elektro A/S Tlf.22796640Side:23GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTNr. 163163164164