Title: økernvn 94.pdf
Cable ID: D3100 Date / Time: 09/11/2013 02:32:34 Headroom 6.6 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]145 228 15 6.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]17.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.3 219.5 36.3 36 9.1 219.5 33.6SR 36-78 6.6 184.5 37.5 78 7.4 184.5 34.9MAIN 12-36 8.3 221.5 36.2 36 9.1 219.5 33.6SR 36-78 6.8 235.5 35.8 36 8.1 235.0 33.210080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 17.0 147.5 20.8 12 17.3 3.1 51.3