Title: Data tester Smestad skole - Detaljert.pdf
Remote: 12 17,1 8,3 8,8 374,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 28,5 26,7 1,8 500,00Worst Value: Local: 36-45 28,9 26,7 2,2 500,00Remote: 36-45 28,5 26,7 1,8 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 23,0 11,3 11,7 442,00Remote: 45-12 23,5 11,3 12,2 442,00Worst Value: Local: 12-45 22,9 11,1 11,8 449,00Remote: 45-12 23,4 11,1 12,3 449,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,1 23,8 3,3 500,00Remote: 36 27,9 23,8 4,1 498,00Worst Value: Local: 36 27,1 23,8 3,3 500,00Remote: 36 27,8 23,8 4,0 499,00