Title: Data tester Smestad skole - Detaljert.pdf
pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 42,8 68,0 223,0 13,0 7,5Limit 100,0 - 555,0 50,0 25,0Margin 57,2 - 332,0 37,0 17,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 45 0,8 3,0 2,2 2,20Worst Value: Local: 45 18,8 43,7 24,9 499,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 18,2 12,2 6,0 152,00Remote: 12 26,2 18,4 7,8 33,25Worst Value: Local: 78 15,1 8,0 7,1 463,00Remote: 36 17,3 8,0 9,3 463,00dB -2020600Local250500 MHzdB -2020600Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):