Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
16 digital inputs, electrically isolated, E0 … E15, (addresses 0 … 15).Tech. data as for PCD2.E610, Source or sink operation selectable via “Q/S” jumper.4 relay outputs, A16 … A19 (addresses 16 … 19),Each with a changeover contact protected with 2 varistors. Tech. data as for PCD2.A200. The 24 V supply to the relay coils is via the screwless terminals “Uext”, located next to the 4 relays.4 analogue outputs, with 8 bit resolution, A32 … A35(base address 32 *, channels 0 … 3) Each channel selectable with “U/I” jumper for voltage 0 … 10 V or current 0 … 20 mA. Tech. data as for PCD2.W410.4 analogue inputs, with 10 bit resolution, E48 … E51(base address 48 *, channels 0 … 3)Each channel can be configured separately with the jumper combinations shown for voltage 0 … 10 V (“U”), current 0 … 20 mA (“I”) or for resistive temperature sensors Pt/Ni 1000 (“T”) for a temperature range from -20 … +100 °C. Tech. data as for PCD2.W2xx.Internal current consumption from+5 V bus V+ bus