Title: Data tester Smestad skole - Detaljert.pdf
Remote: 45-12 67,5 57,3 10,2 2,20Worst Value: Local: 12-45 21,8 10,2 11,6 500,00Remote: 45-12 22,3 10,2 12,1 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,0 23,8 4,2 497,00Remote: 36 28,5 23,8 4,7 500,00Worst Value: Local: 36 28,0 23,8 4,2 497,00Remote: 36 28,5 23,8 4,7 500,00PS-ACRF: Pass Worst Margin: Local: 12 67,6 56,3 11,3 1,75Worst Value: Local: 45 19,4 7,2 12,2 500,00Remote: 12 72,1 61,2 10,9 1,00Remote: 12 20,2 7,2 13,0 498,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:10Signature:______________________ Page: 112Copper Certification ReportCable Label: 521.002-UD-81 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:43:02 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole Jostein