Title: økernvn 94.pdf
LinkWare Version 7.4Cable ID: T3192 Date / Time: 09/11/2013 06:10:19 Headroom 1.7 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]123 187 6 5.4Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]19.1 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 5.8 43.3 47.7 36 7.0 43.3 45.3SR 36-78 1.7 249.0 35.4 36 2.0 249.5 32.7MAIN 12-36 7.9 249.0 35.4 36 7.0 249.5 32.7SR 36-78 1.7 249.0 35.4 36 2.0 249.5 32.710080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.5 246.5 16.4 45 10.4 246.5 13.4