Title: 370.011 RT400 og RT500 Siemens temperaturfoler.pdf
.. . . . . .DisposalTechnical dataFunctional dataDegree of protectionElectrical connectionsEnvironmental conditionsMaterials and colors5/8Siemens Building TechnologiesThe devices are considered electronics devices for disposal in terms of European Di- rective 2012/19/EU and may not be disposed of as domestic waste.(cid:120) Dispose of the device via the channels provided for this purpose. (cid:120) Comply with all local and currently applicable laws and regulations.Measuring range(cid:16) 30...+125 °C for NTC-Type (cid:16) 30...+130 °C other typesSensing elementRefer to "Type summary"Time constantWith protection pocket Without protection pocketApprox. 30 s Approx. 8 sMeasuring accuracyRefer to "Function"Immersion lengthRefer to "Type summary"Nominal pressureRefer to "Type summary"Protection classIII according to EN 60730-1Protection degree of housingRefer to "Type summary" accordingto EN 60529Screw terminals for1 x 2.5 mm2 or x 1.5 mm2