Title: Data tester Smestad skole - Detaljert.pdf
Length (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 38,8 68,0 201,0 11,0 6,9Limit 100,0 - 555,0 50,0 25,0Margin 61,2 - 354,0 39,0 18,1Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 0,7 3,0 2,3 2,80Worst Value: Local: 36 16,6 43,6 27,0 498,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 17,3 11,7 5,6 170,00Remote: 78 17,8 11,7 6,1 170,50Worst Value: Local: 78 16,1 10,1 6,0 247,00Remote: 78 16,8 8,0 8,8 398,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-36 32,4 29,9 2,5 400,00Remote: 36-45 29,6 26,7 2,9 500,00Worst Value: Local: 36-45 29,6 26,7 2,9 498,00Remote: 36-45 29,6 26,7 2,9 500,00dB 0601200Local250500 MHzdB 0601200