Title: økernvn 94.pdf
RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: D3078 Date / Time: 09/12/2013 10:23:38 Headroom 13.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]95 151 11 4.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.1 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.2 99.8 32.3 36 15.5 82.5 30.7SR 12-36 14.8 72.0 34.6 36 16.4 100.0 29.3MAIN 12-36 13.2 99.8 32.3 36 15.6 99.8 29.3SR 12-36 14.8 99.8 32.3 36 16.4 100.0 29.310080604020NEXT (dB)