Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Internal current consumption: (from +5 V bus) Internal current consumption: (from V+ bus) External current consumption: Terminals:typically 10 ms; max. 20 ms typically 20 ms; max. 30 ms supplied directly from input current 4 kV under direct coupling 2 kV under capacitive coupling (whole trunk group) 2000 VAC, 1 min 100 MOhm / 500 VDC 2.5 kV Galvanic separation of outputs to Saia PCD®. The channels themselves not are separated. < 1 mA0 mAPluggable 10-pole screw terminal block (4 405 4847 0), for wires up to 1.5 mm²Switch on/off level:250 VAC180 VAC40 VAC0 VAC05-19PCD2.E500LEDs and connection terminalsBus connectorBus interface, Optocoupler, threshold switchInput bleeder chainLEDsScrew terminals9876543210COM COME5E4E3E2E1E0Inputs E0 to E5 0 - 5Common connection for the 6 inputsInput circuits and terminal designation150nF150nFs u B O/ Is u B D C P150nF98765E54E43E32E21E10E0