Title: 1 etg del 2.pdf
MAIN 12-36 8.7 21.0 44.6 36 10.0 21.0 42.2SR 12-36 9.3 19.3 45.5 12 11.2 19.3 43.1MAIN 36-45 16.5 250.0 4.7 36 15.2 243.0 2.7SR 36-45 16.2 248.5 4.8 36 15.6 248.5 2.2010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 5.1 26.3 18.9SR 36 2.8 26.3 18.9MAIN 36 10.0 183.0 11.4SR 36 8.9 238.5 10.2010080050100150MHzRL (dB)20025060500050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-46040204030201000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1Project: OKERNVEIEN 94 1 etg DEL 2 økernveien 2410.flwSite: OKERNVEIEN 94