Title: EDM_AQAR32_01-S-2GB.pdf
The minimum water volume requested in cooling mode is 3.5L/kW for application air conditioning and 10L/kW for application process.In heating mode, 12.5L/kW are recommended in order to guarantee homogeneous temperatures during the defrosting cycles (comfort and energy savings).Coil pipes are designed with diameter 7.2 mm , to optimize the unit performances and reduce the amount or R32 refrigerant charge.Finned coils are largely dimensioned in order to optimize performance and defrosting cycles.The condenser can be equipped, as optional, a protective grille to prevent shocks.Modulating fans EC type can be also supplied as factory-fitted option to authorize the unit to operate in cooling mode at low ambient temperature and increase the unit performances.SYSAQUA R32 L and SYSAQUA R32 H units can be supplied in several versions:Fans STD version is provided with axial fans AC type, with two speeds, to increasetheunitefficiencyduringpartloadconditions.