Title: økernvn 94.pdf
MAIN 12-36 13.8 64.5 30.3 12 14.7 46.0 32.6SR 12-36 13.3 58.3 31.8 12 14.5 46.0 32.6MAIN 36-45 21.6 247.5 4.9 36 21.9 250.0 2.0SR 36-45 21.8 247.5 4.9 36 22.2 250.0 2.0010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 78 3.8 31.8 18.5SR 78 4.0 32.0 18.5MAIN 36 5.2 149.5 12.3SR 45 7.8 234.5 10.306050050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-44030201060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 7.4Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94