Title: Aggregatkjøring.pdf.pdf
brandengen-2 Brandengene 360.002-3/Unit no. 20Date 18.06.2021Page 32/40Twin fan, PlugAir flow14713m³/hExternal pressure250PaPressure drop21PaStatic pressure (Designed at wet conditions)535PaTotal pressure553PaFan speed1484RPMMaximum fan speed1950RPMTotal efficiency by static pressure, incl. motor and speed control69.5%Total efficiency by total pressure, incl. motor and speed control71.9%K-factor (p=1.2 kg/m³)(2 x 280) 560Fan type - 2xLargeGR50I-ZID.GG.CRErP efficiency n(stat,A)75.2%ErP efficiency class N(actual)/ N(target)80.0 / 62ErP-conformityYesDirect driveMotorMotor typesEC motorMotor types-sizeZID.GG.CRMotor protectionTotal power(2 x 3.50 kW) 7.00kWSpeed (nominal)1950RPMTotal current, Amp.(2 x 5.60 A) 11.20AVoltage3x400VConsumed power from mains power supply, including speed control3.15kWEmpty sectionPressure drop2PaLength200mmDamperPressure drop2Pa