Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
29.8 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.0 441.0 30.4 36 7.4 464.0 26.7SR 12-36 8.5 449.0 30.3 36 9.3 496.0 25.2MAIN 12-36 9.2 500.0 27.8 36 7.9 500.0 25.0SR 12-36 9.1 500.0 27.8 36 9.5 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.8 499.0 11.3 45 19.4 500.0 8.3SR 78-45 17.9 499.0 11.3 45 19.6 499.0 8.3MAIN 78-45 17.8 499.0 11.3 45 19.4 500.0 8.3SR 78-45 17.9 499.0 11.3 45 19.6 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 25.6 68.8 30.0 45 26.8 73.0 26.6SR 36-45 22.4 72.5 29.2 36 24.6 72.5 26.7MAIN 12-36 37.8 500.0 -12.4 36 36.6 500.0 -15.3SR 12-36 37.7 500.0 -12.4 36 38.2 500.0 -15.30804000250 MHzACR-N (dB)