Title: Data tester Smestad skole - Detaljert.pdf
Remote: 78 16,5 8,0 8,5 486,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 27,7 26,7 1,0 499,00Remote: 36-45 29,8 26,7 3,1 499,00Worst Value: Local: 36-45 27,7 26,7 1,0 499,00Remote: 36-45 29,8 26,7 3,1 499,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 28,4 17,2 11,2 224,00Remote: 45-12 28,3 17,0 11,3 229,00Worst Value: Local: 36-12 22,6 10,5 12,1 485,00Remote: 12-36 22,0 10,4 11,6 487,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 26,8 23,9 2,9 496,00Remote: 45 28,3 23,8 4,5 499,00Worst Value: Local: 36 26,7 23,8 2,9 499,00Remote: 45 28,3 23,8 4,5 499,00