Title: økernvn 94.pdf
Model: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002185 ft60Insertion Loss (dB)50403020100050100150200250MHz100NEXT @ Remote (dB)806040202500050100150200250MHz100ACR-F @ Remote (dB)806040202500050100150200250MHz100ACR-N @ Remote (dB)806040202500050100150200250MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3198 Date / Time: 09/11/2013 06:14:50 Headroom 4.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 78] [Pair 45] [Pair 45] [Pair 45]187 285 9 8.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)