Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 109109110110111111112112113113114114115115TEST RAPPORTResultatDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 10.06.2020 11:04R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 10.06.2020 11:11SPĆNDINGUln: 233V Ulpe: 233V Unpe: 0V f: 49.9HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 11:33RCD II: 27.0mAUci: 0.2V t: 223.0ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 11:33RCD tt: 57.4msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 11:34Z-LINEZ: 0.60ΩIsc: 386A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF032 C16/2 12.06.2020 11:36Zs(rcd)Z: 0.58ΩIsc: 396A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A