Title: +038=462.001-NB001._05-Battery pack Xstorage Eaton Produktblad.pdf
Recommended operating range20-25°CMaximum relative humidity95 %, non-condensingMaximum altitude2,000 mThe total cooling requirements must be calculated considering:Cooling requirements for each battery rack according to Table 24 • Cooling requirements for each PCS according to Table 25Table 24: Cooling requirements for battery rackBattery technol- ogyMaximum initial cooling requirement per battery rack at 1C (kW)25 % load50 % load75 % load100 % loadGEN 10.150.290.520.84GEN 20.150.310.560.92GEN 30.160.340.641.05GEN 40.230.611.252.14Table 25: Cooling requirements for PCS StandardMaximum cooling requirement per PCS (kW)PCS25 % load50 % load75 % load100 % loadxStorage PCS 20 Standard0.410.751.011.27xStorage PCS 40 Standard0.811.391.952.55Total cooling requirements (kW) = (Battery rack cooling req. in table 24 x Number of battery racks) + (PCS cooling req. in table 25 ).© Eaton 2018. All rights reserved.