Title: +038=310.101-RF022T_06-multical 62 Vannmåler Kamstrup - Installasjons- og brukerveiledning.pdf
The BACnet module is used for data transfer from MULTICAL® 62 water meters into BACnet sys- tems. The BACnet module transfers meter number (programmable), serial number, accumulated volume flow (V1), actual flow, accumulated values from additional meters with via puls InA, InB as well as info codes from the water meter to the BACnet system. BACnet is a widespread and estab- lished field bus protocol used within building automation. The BACnet module for MULTICAL® 62 ensures simple integration from Kamstrup’s water meters to BACnet based systems. The module can be used as both master or slave, depending on the used MAC address.5.1.12 Modbus RS485 RTU* Slave Module with 2 pulse inputs (VA, VB), type 67-00-67The Modbus base module for MULTICAL® 62 ensures a simple integration from Kamstrup’s water meters into Modbus based systems.Modbus is an open, widespread and well established serial communication protocol used within building automation.