Title: etg u1.pdf
50 MHz7510060RL @ Remote (dB)5040302010100002550 MHz75100LinkWare Version 8.1Cable ID: T0023 Date / Time: 10/22/2013 01:30:59 PM Headroom 13.0 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]140 222 16 6.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]12.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 13.0 74.8 34.4 36 14.1 97.8 29.5SR 12-36 13.9 74.8 34.4 36 15.5 88.5 30.2MAIN 12-36 13.5 100.0 32.3 36 14.1 97.8 29.5SR 12-36 14.3 93.3 32.8 36 15.5 97.8 29.510080604020NEXT (dB)