Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]33.4 145 2 4.91Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.8 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.0 469.0 29.8 36 7.5 500.0 26.4SR 36-45 5.2 476.0 29.7 36 5.9 500.0 26.4MAIN 36-45 8.1 500.0 29.2 36 7.5 500.0 26.4SR 36-45 5.4 500.0 29.2 36 5.9 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 13.8 411.0 13.0 45 13.8 5.0 48.3SR 36-45 13.8 413.0 12.9 45 13.7 2.6 53.9MAIN 36-78 14.2 474.0 11.7 36 14.9 478.0 8.6