Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
SR 36-45 20.4 499.0 11.3 45 20.6 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 28.2 136.5 18.9 36 30.0 136.0 16.4SR 36-45 28.4 137.0 18.8 36 29.9 136.5 16.3MAIN 12-36 40.7 500.0 -12.4 36 39.9 498.0 -15.1SR 12-36 41.5 500.0 -12.4 36 40.8 498.0 -15.10804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.7 489.0 8.0SR 45 7.9 489.0 8.0MAIN 45 5.7 489.0 8.0SR 45 7.9 489.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasjeTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00418.0 m60