Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
[Pair 12] [Pair 12] [Pair 12]29.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 6.9 476.0 29.0 45 7.6 477.0 26.1SR 36-45 8.8 474.0 29.1 45 8.4 482.0 25.8MAIN 12-45 7.0 477.0 28.9 45 7.6 477.0 26.1SR 12-45 9.1 481.0 28.7 45 8.7 490.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.6 3.5 54.4 45 13.9 2.6 53.9SR 36-45 14.6 3.5 54.4 45 14.0 2.6 53.9MAIN 45-78 16.9 500.0 11.3 45 17.3 489.0 8.4SR 78-45 16.6 500.0 11.3 45 17.1 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 21.3 72.0 29.3 36 21.6 67.5 27.7SR 36-45 23.0 71.3 29.5 36 22.4 71.5 26.9MAIN 12-45 35.5 477.0 -10.9 45 37.4 500.0 -15.3SR 36-45 38.1 492.0 -11.9 45 37.0 490.0 -14.60804000250 MHz