Title: 4. Leieavtaler.pdf
2015-01-07: The skylights will have an opening down towards the production and storage area. It was discussed during the project meeting how this can be a challenge for the fire protection. The suggestion is to extend the storage and manufacturing area sprinkler system so that it covers the skylight area using the same heads as those to be installed in the storage area.7. FM Global does not recommend the installation of heat and/or smoke vents in this facility. If required, install manual heat and/or smoke vents in accordance with FM Global Loss Prevention Data Sheet 2-0, Installation Guidelines for Automatic Sprinklers, Section 2.1.1. 7.8. The property for the new facility is planned to be shared with another facility. It is not yet decided what business will be located next to Autronica's facility. Initially the following recommendations should be considered to mitigate the external fire exposure.a. The adjacent building should ideally be protected by an automatic sprinkler protection system.