Title: økernvn 94.pdf
MHz100RL @ Remote (dB)806040202500050100150200250MHzLinkWare Version 7.4Cable ID: T3405 Date / Time: 09/13/2013 08:32:20 Headroom 4.6 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]247 378 14 11.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]7.7 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 8.2 234.5 35.8 78 8.8 233.5 33.2SR 36-78 4.6 248.5 35.4 36 5.7 249.0 32.7MAIN 36-78 8.2 234.5 35.8 36 9.1 250.0 32.7SR 36-78 4.6 248.5 35.4 36 5.7 249.0 32.710080604020NEXT (dB)