Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,2 23,9 3,3 496,00Remote: 36 28,4 23,8 4,6 500,00Worst Value: Local: 36 27,1 23,8 3,3 498,00Remote: 36 28,4 23,8 4,6 500,00PS-ACRF: Pass Worst Margin: Local: 45 66,4 54,3 12,1 2,20Worst Value: Local: 45 20,2 7,2 13,0 498,00Remote: 12 71,4 60,0 11,4 1,15Remote: 12 20,5 7,2 13,3 498,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:14Signature:______________________ Page: 139Copper Certification ReportCable Label: 521.002-UD-38 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 15:16:20 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: