Title: Data tester Smestad skole - Detaljert.pdf
601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 23,4 12,4 11,0 390,00Remote: 12-45 23,6 12,3 11,3 394,00Worst Value: Local: 12-45 22,6 10,2 12,4 500,00Remote: 12-45 22,8 10,2 12,6 500,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,3 24,0 4,3 493,00Remote: 45 28,6 23,8 4,8 500,00Worst Value: Local: 36 28,2 23,9 4,3 495,00Remote: 45 28,6 23,8 4,8 500,00PS-ACRF: Pass Worst Margin: Local: 12 73,9 61,2 12,7 1,00Worst Value: Local: 45 21,0 7,2 13,8 500,00Remote: 12 66,1 54,3 11,8 2,20Remote: 45 20,8 7,2 13,6 500,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:08Signature:______________________ Page: 100Copper Certification Report