Title: 32 Pumper modbuss teknisk data.pdf.pdf
CIM 200CIM 260CIM 5009.3 CIM status register blockRegisters in this block can be read by means of function codes 0x03 and/or 0x04. They are read-only. Use this block for various kinds of fault finding.Address Register nameDescription00021GENIbusCRCErrorCntHolds a CRC error counter for the GENIbus connection to the E-pump.00022GENIbusDataErrorCntHolds a data error counter for the GENIbus connection to the E-pump.00023VersionNumberA Grundfos-specific version number. This is an unsigned integer value.00024ActualModbusAddressHolds the current Modbus slave address of the device. Valid value range: 1-247.00025 00026GENIbusTXcountHI GENIbusTXcountLOHolds a transmit counter for the total number of telegrams sent to the E-pump on the GENIbus connection.00027 00028GENIbusRXcountHI GENIbusRXcountLOHolds a receive counter for the total number of telegrams received from the E-pump on the GENIbus connection.00029