Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
MISLYKKESGODKJENTMISLYKKESGODKJENTMISLYKKESNr.6969707071717272737374747575TEST RAPPORTResultatRCD tt: 64.1msUc: 0.2V Idn: 30mA type: AC MUL.: x1 Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 11:17RCD II: >33.0mAUci: 0.5V t: >300ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 11:18Z-LINEZ: 0.42ΩIsc: 542A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 11:18Zs(rcd)Z: 0.42ΩIsc: 545A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 12:20R LOW OhmR: 0.09ΩR+: 0.1Ω R-: 0.1Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF027 C16/2 12.06.2020 12:32KONTINUITET R: 0.1ΩGrenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF028 C16/2 10.06.2020 11:03R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩ