Title: Data tester Smestad skole - Detaljert.pdf
dB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 31,8 29,2 2,6 348,00Remote: 36 34,0 29,1 4,9 350,00Worst Value: Local: 36 28,0 23,9 4,1 495,00Remote: 36 28,9 23,8 5,1 497,00PS-ACRF: Pass Worst Margin: Local: 12 66,0 54,3 11,7 2,20Worst Value: Local: 12 20,7 8,3 12,4 442,00Remote: 12 71,5 60,0 11,5 1,15Remote: 12 20,8 8,2 12,6 446,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:59Signature:______________________ Page: 31Copper Certification ReportCable Label: 521.002-UD-156 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:37:04 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: