Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
DM1-3. Plan 6 / DM1.E5=433.06.04 / XF080 16C2/003 30.11.2020 11:57 (ELEKTRIKER)ISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 254V Rnpe: >30.0MΩ Um: 254VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF081 16C2/003 27.11.2020 10:21SPĆNDINGUln: 235V Ulpe: 235V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF081 16C2/003 27.11.2020 10:21Z-LINEZ: 0.42ΩIsc: 545A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF081 16C2/003 27.11.2020 10:21Tallberg Elektro A/S Tlf.22796640Side:32GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.221221222222223223224224225225226226227227TEST RAPPORTResultatZs(rcd)Z: 0.41ΩIsc: 557A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF081 16C2/003 27.11.2020 10:22RCD II: 28.5mA