Title: 1 etg del 2.pdf
Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.5 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 0.4 * 241.0 35.6 36 0.4 * 250.0 32.7SR 12-36 5.2 205.0 36.8 36 6.9 205.0 34.1MAIN 12-36 0.4 246.5 35.4 36 0.4 250.0 32.7SR 12-36 5.7 242.0 35.6 36 6.9 248.5 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 17.0 224.5 17.2 12 18.0 221.0 14.3SR 36-12 16.7 149.5 20.7 36 17.3 221.0 14.3MAIN 36-12 17.0 225.5 17.1 12 18.0 221.0 14.3SR 36-12 17.2 226.0 17.1 36 17.4 225.5 14.1010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250