Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The energy consumption quantities do not take into account light scenes and their dimming levels.The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 64Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N | S ’ < Site 1/ Building 1/ Storey 10 / Taiga / ViewsTaigaTaigaDIALux Page 65Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019Site 1/ Building 1/ Storey 10 / Taiga / Results summary, EN 12464Taiga EN 12464-1 Surface Result Average (Target) Min Max Min/average Min/max 1 Visual task area 8 Perpendicular illuminance (adaptive) [Ix] 691 (> 500) 478 832 0.69 0.57 Surrounding area: 0.500 m 2 Surrounding area 8 Perpendicular illuminance (adaptive) [Ix] 596 (= 300) 368 840 0.62 0.44 3 Background area 7 Perpendicular illuminance (adaptive) [Ix] 397 (= 100) 152 656 0.38 0.23Wall zone: 0.500 m