Title: fireray5000_igb.pdf
System Controller, including base Detector, including ‘easy fit’ base Universal Bracket Reflector (Single) Protective CageWidth, in (mm) 7.9 (200)Height, in (mm) 9.3 (235)5.3 (135)5.3 (135)5.3 (135) 5.3 (135) 3.9 (100) 3.9 (100) Ø5.4 (Ø136) 6.2 (157)Depth, in (mm) 2.8 (71)5.3 (135)2.8 (71) 0.4 (10) -Weight, IB (kg) 2.0 (0.9)1.1 (0.5)0.4 (0.2) 0.2 (0.1) 0.3 (0.13)Installation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 26Approval Information8. Approval Information8.1 Territory-Specific Information8.1.1 UL Approval Information UL File Number: S3417Distance between Detector and ReflectorFire Threshold Range8-10m (26.2-32.8ft)10-18%10-15m (32.8-49.2ft)15-25%15-22m (49.2-72.2ft)15-35%22-40m (72.2-131.2ft)25-50%40-60m (131.2-196.8ft)35-50%60-100m (196.8-328.1ft)50%