Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 27,9 23,8 4,1 500,00PS-ACRF: Pass Worst Margin: Local: 45 72,8 61,2 11,6 1,00Worst Value: Local: 45 20,5 8,1 12,4 451,00Remote: 45 72,4 61,2 11,2 1,00Remote: 45 20,8 8,1 12,7 449,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:06:55Signature:______________________ Page: 6Copper Certification ReportCable Label: 521.002-ud164 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:16.01.2019 16:31:07 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38