Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 29,9 25,4 4,5 449,00Remote: 45 28,5 23,8 4,7 500,00Worst Value: Local: 45 28,5 23,8 4,7 500,00Remote: 45 28,5 23,8 4,7 500,00PS-ACRF: Pass Worst Margin: Local: 12 68,2 56,3 11,9 1,75Worst Value: Local: 45 20,9 8,2 12,7 444,00Remote: 12 72,9 61,2 11,7 1,00Remote: 12 20,8 8,5 12,3 429,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:08Signature:______________________ Page: 101Copper Certification ReportCable Label: 521.002-UD-110 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 14:32:46 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result: