Title: V20-06-02 VVS-anlegg plan 6 - DM3.pdf
Kanaler føres gjennom eksisterende hull i dragerSZ001T Ø125SF002T-125ø125 UK=2668SZ001T Ø125ø125 UK=2708360.013: ø500I dekke plan 06 SZ001T Ø630 SZ001T Ø630FordelerstokkWISE director (trådløs router)ø100ø100ø200 UK=2640SF002T-160ø160 UK=2682ø315 UK=2553ø250 UK=2585ø250 UK=2615370.101: 28 mm +c 2703LD009T Maks:200 m³/h Kjøling: 435 W 0.034 L/sLD007T Maks:220 m³/h Kjøling: 365 W 0.029 L/sMøterom 6-134ø160 UK=2710ø160 UK=2710ø160 UK=2710LD009T Maks:200 m³/h Kjøling: 315 W 0.025 L/s370.101: 28 mm +c 2703LD007T Maks:200 m³/h Kjøling: 435 W 0.034 L/s Varme: 465 W 0.011 L/s320.102: 18 mm +c 2790320.102: 18 mm +c 2790LD009T Maks:200 m³/h Kjøling: 435 W 0.034 L/s320.102: 22 mm +c 2790 320.102: 22 mm +c 2790WISE IAQ3 0 7 2c + m m 5 3 : 1 0 1 . 0 7 33 0 7 2c + m m 5 3 : 1 0 1 . 0 7 3WISE RTA WISE IAQSF002T-160ø160 UK=2682SF002T-160SF002T-160WISE RTAKontor 6-135Print/kopi 6-133Garderobe 6-508SF002T-200ø200 UK=2643