Title: økernvn 94.pdf
Cable ID: D3108 Date / Time: 09/11/2013 02:41:22 Headroom 9.2 dB (NEXT 36-78) Test Limit: EN50173 PL Class E Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]178 282 20 7.7Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]14.4 250.0 30.7Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 9.2 232.5 35.9 36 9.2 233.0 33.2SR 36-45 9.9 36.0 49.0 36 10.1 246.0 32.8MAIN 36-78 9.2 232.5 35.9 36 9.2 233.0 33.2SR 36-78 10.2 250.0 35.3 36 10.1 246.0 32.810080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.6 108.0 23.5 12 16.6 3.1 51.3