Title: Datablad.pdf
Refrigerant charge for the unit 10,90 kg Number of compressors 2Compressor type ScrollCompressor startup type DirectPlant side heat exchanger Cooling HeatingNumber of exchangers 1Exchanger type PlatesTotal fluid flow rate® 17871 18346 I/h Minimum fluid flow rate 12800 I/h Minimum fluid volume (Comfort) 1309 L Pressure drop 33,5 353 kPaThe plant side exchanger waterflow rate is equal to the standard rating water flow rateWater connections ValueWater connection type Male Gas ThreadWater connection inlet diameter 2"1/2Water connection outlet diameter 2"1/2Pump Cooling HeatingNominal power 1,95 kw Maximum power 1,95 kw Maximum running current 3,43 A Pump available static head 117 113 kPaThe certified performances, conditions and the certification of the software have to be verified in www.eurovent-certification.com Systemair AC SELECT v1.0 | 2022-11-013/12YSAQUAR32HSYSAQUAR32 100.HSYSAQUAR32.100.H.1PSP.ACFan ValueNumber of fans 2Fan type Axial Fans