Title: +038=30.001-NI003._19-V20-10-01 VVS-anlegg plan 10 - DM1.pdf
ABXCDPlan 1138.62 mPlan 1035.07 m98MM 42 Ned 320.102LD001T Maks:220 m³/h Kjøling: 420 W 0.033 L/s Varme: 290 W 0.007 L/s28 mm +c 3180LD001T Maks:220 m³/h Kjøling: 420 W 0.033 L/s Varme: 290 W 0.007 L/sLD001T Maks:220 m³/h Kjøling: 420 W 0.032 L/s Varme: 290 W 0.007 L/sLD001T Maks:220 m³/h Kjøling: 420 W 0.032 L/s Varme: 290 W 0.007 L/sBaffel tilkobles kun varmeLD002T Q: 200 m³/h Varme: 865 W 0.022 L/s+10 = 320.102 - OE 102 0.124 L/s320.102: 18 mm +c 3283 320.102: 18 mm +c 328328 mm +c 3180320.102: 22 mm +c 3283 320.102: 22 mm +c 3283370.101: 35 mm +c 3273 370.101: 35 mm +c 3273Ned 320.102: 15mm Ned 320.102: 15mm15 mm +c 3283 15 mm +c 3283STAD Dim:09/10 StengtST009T-160-200 200 m³/hForrom 10-401NedNed 320.102: 15mmSF002T-160STAP/STAD DN20SF002T-2005 2 1 3 = K U 0 6 1 ø5 1 1 3 = K U 0 0 2 øSF002T-160 SF002T-160WISE IAQ WISE RTAMøterom 10-0066 4 1 3 = K U 0 6 1 øSF002T-200SF002T-160SF002T-200ø160 UK=3146Korridor 10-302