Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD73 Date / Time: 28/01/2022 13:33:42 Headroom 8.0 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]50.4 258 18 9.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]20.8 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 11.3 250.0 33.1 3,6 11.3 157.5 33.7SR 1,2-3,6 8.0 142.5 37.3 3,6 9.5 242.0 30.4MAIN 1,2-3,6 11.3 250.0 33.1 3,6 11.4 250.0 30.2SR 1,2-3,6 8.0 242.0 33.4 3,6 9.5 242.0 30.4PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)