Title: Hardware Installation Guide.pdf
Up to 128 Outputs - eight Output Control ModulesUp to 128 Inputs - eight Input Control ModulesElevator Control RoomElevator Reader (inside cab)revision 6 — 297LNL-1200 Output Control Module53ConfigurationThe Output Control Module board contains 8 DIP switches and 3 jumpers that must be configured for your system.53.1Setting DIP SwitchesDIP Switches (shown in factory default position: Address 00; 38400 bps)ONON12345678The following chart describes the use of each DIP switch.DIP SWITCH(ES)USED TO CONFIGURE:1, 2, 3, 4, 5Device communication address (0 - 31)6, 7Communication baud rate8Downstream encryption (available with OnGuard 2009 or later)53.1.1Device AddressTo configure the device communication address, set DIP switches 1, 2, 3, 4, and 5 according to the following table.ADDRESSDIP SWITCH1:2:3:4:5:0offoffoffoffoff1ONoffoffoffoff2offONoffoffoff3ONONoffoffoff4offoffONoff