Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF051 C16/2 10.06.2020 11:49SPĆNDINGUln: 231V Ulpe: 232V Unpe: 0V f: 50.1HzDM1-3. Plan 9 / DM3.E2.433.09.01 / XF051 C16/2 11.06.2020 15:20R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF051 C16/2 11.06.2020 15:36Z-LINEZ: 0.39ΩIsc: 592A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF051 C16/2 11.06.2020 15:37Zs(rcd)Z: 0.34ΩIsc: 681A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF051 C16/2 11.06.2020 15:37RCD UbUc: 0.6VRl: 18Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF051 C16/2 11.06.2020 15:37RCD tt: 57.6msUc: 0.1V Idn: 30mA type: AC MUL.: x1 Ulim: 25VTallberg Elektro A/S Tlf.22796640Side:40GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTNr. 273273274274275275