Title: Økernveien 94.pdf
Loss (M->R) PASS Date / Time: 10/16/2013 01:29:42 PM Test Limit: TIA-568-C Multimode Limits Version: 1.9300 Operator: JK DTX-1800 (2395065 v2.7400) Module: DTX-MFM2(9339068) Calibration Date: 07/30/2010 DTX-1800R (2395066 v2.7400) Module: DTX-MFM2(1126209) Calibration Date: 03/15/2011Propagation Delay (ns) Length ft Limit 6562Result Loss (dB) Limit (dB) Margin (dB)Reference (dBm)97 65850 nm PASS 0.48 2.17 1.6923.25PASS1300 nm PASS 0.41 2.13 1.7223.73Compliant Network Standards: 10/100BASE-SX 100BASE-FX 10GBASE-LRM 40GBASE-SR4 ATM52 FDDI Fiber Optic Fibre Channel 1200-M5-SN-I Fibre Channel 200-M5-SN-I Fibre Channel 266SWL1000BASE-LX 100GBASE-SR10 10GBASE-LX4 ATM155 ATM622 Fiber Optic Fibre Channel 100-M5-SN-I Fibre Channel 1200-M5E-SN-I Fibre Channel 200-M5E-SN-I Fibre Channel 400-M5-SN-I1000BASE-SX 10BASE-FL 10GBASE-SR ATM155SWL ATM622SWL Fiber Optic Fibre Channel 100-M5E-SN-I Fibre Channel 133 Fibre Channel 266 Fibre Channel 400-M5E-SN-IProject: DEFAULT Untitled1Site: WE