Title: etg u1.pdf
250PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.4 22.4 43.9 12 11.1 18.6 43.5SR 12-36 8.6 22.4 43.9 12 10.6 22.4 41.5MAIN 36-45 16.5 249.0 4.8 36 16.0 249.0 2.1SR 12-36 16.2 249.0 4.8 36 15.9 249.0 2.1010080604020050100150MHzACR-N (dB)200250010080604020050100150200MHzACR-N @ Remote (dB)250PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 4.2 32.3 18.5SR 45 3.8 32.3 18.5MAIN 36 8.1 244.5 10.1SR 36 6.7 159.0 12.0010080050100150MHzRL (dB)200250010080050100150MHzRL @ Remote (dB)200250Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-460402060402000501001502002500050100150200250MHzMHzMeasurement is within the accuracy limits of the instrument.LinkWare Version 8.1