Title: økernvn 94.pdf
80604020002550 MHz75100100ACR-N @ Remote (dB)80604020002550 MHz75100100RL @ Remote (dB)80604020002550 MHz75100LinkWare Version 7.4Cable ID: T3020 Date / Time: 09/12/2013 02:29:57 Headroom 15.8 dB (NEXT 36-45) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]73 116 8 3.1Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.3 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 18.0 100.0 32.3 12 16.0 98.3 29.4SR 12-36 19.6 100.0 32.3 12 15.8 98.3 29.4MAIN 36-45 17.2 98.8 32.4 12 16.0 98.3 29.4SR 36-45 15.8 98.8 32.4 12 15.8 98.3 29.4