Title: Aggregatkjøring.pdf.pdf
Initial pressure drop/Final pressure drop54/154PaVelocity, face area2.06m/sVelocity, filter area0.12m/sFilter classF7 - ePM1 60%Filter size6x[592x490x25] + 2x[287x490x25]Filter length520mmFilter descriptionCamfil Hi-Flo II XLTRotary heat exchangerSupplyExtractAir flow1500015000m³/hPressure drop163163PaAir temperature before/after25.0/13.622.0/-16.6°CAir relative humidity before/after90/6140/100%Capacity265.85kWTemperature efficiency82.1%Dry efficiency according to EN 308 at 15000 m³/h82%Humidity efficiency86.8%Heat exchanger typeP - Condensation (Temperature)Temperature efficiencyHigh efficiencyDescriptionP135_340_1-2240*Rotor driveVariable speedElectrical data1x230V, 40W, 0.7AmpOACF1.02Purging sector1pcsTwin fan, PlugAir flow15000m³/hExternal pressure250PaPressure drop22PaStatic pressure (Designed at wet conditions)564Pa