Title: 40 Bender brukermanual.pdf.pdf
Press an external test button connected to the RCMS…   Send a test command via the BMS bus.   RCMS…-D… only: Select "TEST" from the control menu. The RCMS… responds as follows:   "ALARM 1" and "ALARM 2" LEDs light up.   All alarm relays switch (this function can be deactivated, refer topage 68).  An alarm message is sent on the BMS bus.   An entry is stored in the history memory with the suffix "TEST".   RCMS…-D…: The progress of the test is indicated on the display.Auto testThe RCMS460…-D then displays the set response value for the highest functioning measuring channel. Press the "" button several times to display the correct functioning of the other measuring channels.TEST 12/12Residual current100 mA Addr.: 2 Chan.: 12RCMS460-490_D00067_03_M_XXEN/12.20174142Operation  RCMS…-L…: All alarm LEDs light for approx. 10 seconds.After successful testing, all LEDs must go out again, with the exception of the LED "ON" and the alarm relays must return to their initial position.