Title: DOCA0005EN-12.pdf
In nonvolatile memory, the power meter maintains a maximum operating demand value called peak demand. The peak is the highest value (absolute value) for each of these readings since the last reset.You can reset peak demand values from the power meter display. You should reset peak demand after changes to basic power meter setup such as CT ratio or power system configuration.ResetsThe following resets are available, depending on your meter model:ResetDescriptionPartial energyClears all active and reactive energy accumulated since the last reset.this does not reset the total active and reactive energy accumulation.Input meteringClears all input metering energy data.you can only reset the input metering accumulation using software.Resetting accumulated energy using the display1. Navigate to the Partial Active E or Partial Reactive E screen. The screen displaysthe date of the last reset. For example:A Date of last resetPartial Active E876.223-Apr-2012kWh2. Press and hold