Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
27.2 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 7.2 458.0 30.1 36 6.3 500.0 26.4SR 36-45 5.9 500.0 29.2 36 6.5 500.0 26.4MAIN 36-45 7.3 500.0 29.2 36 6.3 500.0 26.4SR 36-45 5.9 500.0 29.2 36 6.5 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 21.5 12.3 43.5 45 21.4 498.0 8.3SR 45-78 21.5 11.4 44.1 45 21.2 498.0 8.3MAIN 78-45 21.7 499.0 11.3 45 21.4 498.0 8.3SR 78-45 21.8 498.0 11.3 45 21.2 498.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 27.3 66.8 30.4 36 25.7 47.8 32.5SR 45-78 25.5 53.8 33.4 78 26.7 49.5 32.1MAIN 36-45 34.6 500.0 -12.4 36 33.9 500.0 -15.3SR 36-45 33.2 500.0 -12.4 36 34.1 500.0 -15.30804000250 MHzACR-N (dB)