Title: +038=542.001-OS011._02-Previdia Max Brannsentral Nortek Instalasjonsveiledning.pdf
the internal modules, by means of the appropriate screws [E] • the front plate, by means of the wire ([F], paragraph 3.1 - [C]) coming from the soldered end to which the ground wire of the FPMCPU [G] (paragraph 3.4 - [G]) must be connected to.the cable shields, by means of cable-gland screws [H].FGFDACEBHInstallationA35Fire detection and extinguishant systemAGDCFCIn the same way, it is convenient to connect the grounding wires of the cabinets that are attached together.FFor this purpose, use the proper cable supplied with every PRCAB [F] and connect to each other the grounding bars of the two adjacent cabinets ([G], paragraph 3.1 - [L]).BEG5.6IFM24160 module wiringAs well as the terminal board for the mains power supply and the connector for the batteries, the IFM24160 power- supply module also provides two supervised outputs capable of supplying 27.6V in active status and a relay (voltage-free contacts C,NC,NO).5.6.1 Battery connection