Title: Temperaturgiver.pdf
Place the sensor far enough away from bends, junctions or section changes in the duct to ensure an accurate reading.XXInstall the sensor in the middle of the duct.The preferred placement of the sensor is away from turbulent air caused by filters, rectifiers and coolers.X<6D6DPlace the sensor in front of diffusers or confusers.X3D<6DFilters and coolers calm the air flow.X5Mounting Method12Ø 7 mmCeiling Mount Model (TS-63x0C): Two M4.5 or M4 (#10 or #8) screws, not included. A seal ring is provided to seal around the probe between the enclosure and mounting surface.34Duct/Immersion Model (TS-63x0D): Two M4.5 or M4 (#10 or #8) screws, not included. A seal ring is provided to seal around the probe between the enclosure and duct. Duct Flange Kit is available as accessory for positioning TS-63000 inside the duct.R 1/2” G 1/2”For immersion applications, direct mount to TS-6300W series thermowells. An adapter is required to retrofit TS-63 sensors to TS-9100 thermowells.