Title: økernvn 94.pdf
Cable ID: T4087 Date / Time: 09/11/2013 12:32:27 Headroom 11.3 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]83 133 10 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]15.7 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 11.3 86.0 33.4 36 13.7 86.0 30.4SR 12-36 11.4 86.0 33.4 12 13.9 70.5 31.8MAIN 12-36 11.4 97.8 32.5 36 13.8 98.0 29.4SR 12-36 11.6 97.8 32.5 36 14.1 97.8 29.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 22.8 92.8 19.3 36 23.0 3.0 46.1