Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]33.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.0 458.0 29.8 36 7.6 458.0 27.0SR 36-45 8.9 458.0 29.8 36 8.8 459.0 27.0MAIN 36-45 8.6 500.0 27.8 36 8.7 500.0 25.0SR 36-45 10.3 499.0 27.9 36 10.0 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.4 4.3 52.7 45 14.2 5.9 46.9SR 78-45 15.4 3.8 53.8 45 14.2 3.9 50.5MAIN 36-45 17.2 477.0 11.7 45 19.3 476.0 8.7SR 45-36 17.5 477.0 11.7 36 19.5 477.0 8.70100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-78 29.8 146.0 17.7 36 31.1 153.0 14.2SR 36-78 27.8 140.0 18.4 36 30.0 146.5 15.0MAIN 36-45 40.3 500.0 -12.4 36 40.8 500.0 -15.3