Title: +135.01=370.002-LC001T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
Water flow l/h 139 113 83 156 127 103 493 365 291 569 449 291EmissionkW 1,61 1,32 0,97 1,82 1,48 1,20 4,33 3,27 2,67 6,61 5,22 3,39Water flow l/h 213 173 127 241 195 157 554 416 340 633 501 340EmissionkW 2,48 2,01 1,47 2,80 2,27 1,83 6,44 4,84 3,95 7,36 5,83 3,95Water flow l/h 288 233 170 326 263 212 736 552 450 843 666 450EmissionkW 3,35 2,71 1,98 3,79 3,06 2,46 8,56 6,42 5,23 9,80 7,74 5,23Water flow l/h 363 294 214 411 332 266 919 689 561 1053 831 561EmissionkW 4,22 3,42 2,49 4,78 3,86 3,10 10,69 8,01 6,52 12,24 9,66 6,52Emission correction factors for different working conditions. Multiply the factors by the emission figures in the 7-12°C table above.Water (°C) 7/12 °C 10/15 °C 14/18 °CTotal emissionAir (°C) K K K25-18 26-18.5 28-20 Water (°C) 0,82 0,56 0,350,89 0,63 0,411,11 0,82 0,527/12 °C 10/15 °C 14/18 °CSensible emission Air (°C) K K K25-18 26-18.5 28-20 1,06 0,94 0,9 0,78 0,72 0,580,9 0,72 0,5Note: