Title: +038=433.002-FS026._02-FDV 16490-39.pdf
CharacteristicB, C, D, K, S, ZMax. back-up fuseA gL/gG 125Selectivity Class3lifespanLifespanOperations> 10000Direction of incoming supplyas requiredMechanical Standard front dimensionmm45Enclosure heightmm80Mounting width per polemm17.5MountingIEC/EN 60715 top-hat railDegree of ProtectionIP20, IP40 (when ﬁtted)Terminals top and bottomTwin-purpose terminalsTerminal protectionFinger and back-of-hand proof to BGV A2Terminal capacities2 mm2 mm1 x 252 mm2 x 10Thickness of busbar materialmm0.8 … 2Mounting positionAs requiredDesign veriﬁcation as per IEC/EN 61439 Technical data for design veriﬁcationRated operational current for speciﬁed heat dissipationInA63Heat dissipation per pole, current-dependentPvidW0Equipment heat dissipation, current-dependentPvidW20.8Static heat dissipation, non-current-dependentPvsW0Heat dissipation capacityPdiss