Title: +038=360.000-NI001._70-DM1-3. 360.012 (Toaletter) R&H - Målerapport.pdf
MÅLEPROTOKOLLVersjon nr 3Dato 17.02.01Blankett nr.: 68-091ANLEGG : SYSTEM :Dronning Mauds gate 1-3 360.012 ToaletterDato : Ref. :TILLUFTROM NR.7-405 WC 7-406 WC 7-407 HCWC 7-408 Forrom 7-409 WC 7-410 WC 7-411 WC 7-412 BKTILLUFT Prosjektert Målt m3/hm3/h650595Avtrekk Avvik Prosjekt Målt m3/h m3/h 100 100 100%91 92 918100 100 100 5092 92 93 46Avvik %9 -8 -98 -8 -7 -86-430 Forrom 6-431 WC 6-432 WC 6-433 HCWC 6-434 WC 6-435 WC 6-436 WC 6-437 WC BK7506809100 100 100 100 100 100 100 5091 92 91 91 91 92 91 469 -8 -9 -9 -9 -8 -9 -85-408 Forrom WC WC HCWC3002758100 100 10091 91 929 -9 -8Total1 7001 55091 7001 5568KVALITETSHÅNDBOK Randem Hübert A/S - Stansevn. 11, 0975 OSLO - Telefon: 22 90 07 00 - Telefax: 22 90 07 10 E-mail: service@hybra.no02.12.2021T.AntonsenANMERKNING