Title: +038=370.001-IK009._03-Dynaciat LG 300 A Varmepumpe EPTEC - Teknisk datablad.pdf
7 LG 180 8 LG 200 9 LG 240 10 LG 260 11 LG 3009080706050012345678 9 10 117Water flow rate, l/sDYNACIAT LG, sizes 360-600220210200190180a P k170160, d a e h150140e r u s s e r P13012011012 LG 360 13 LG 390 14 LG 450 15 LG 480 16 LG 520 17 LG 600100908070605001234567891011 13 12 13 14 15 16 171214Water flow rate, l/s2829Hydraulic specifications ■ Available static system pressure Units with hydraulic module (dual variable-speed high pressure pump)Data applicable for: - Pure water at 20°C - Refer to the section "Evaporator water flow rate" for the minimum and maximum water flow rate values - If brine is used, the maximum water flow rate is reduced.■ EvaporatorDYNACIAT LG, sizes 360-600240230220210a P k200190, d a e h180170e r u s s e r P1601501401301201101009034651 LG 360 2 LG 390 3 LG 450 4 LG 480 5 LG 520 6 LG 6008001234567