Title: 40 Bender brukermanual.pdf.pdf
For each of the 12 measuring channels the reached per cent value of the set alarm value IΔn2 (alarm) and IΔn1 (prealarm) is indi- cated. In case of digital inputs, the status is indicated.3.HistoryDisplays the history (300 data records) with information about messages, acknowledge- ments and associated times. Displays the minimum and maximum residual current after an alarm has occurred, with address and channel.4.HarmonicsDisplays the following for the selected measuring channel: measured value, THF (Total Harmonic Factor) in %; DC compo- nent, fundamental oscillation and harmo- nics in mA.5.Data loggerDisplays the recorded measured values (300 data records) for each measuring channel.6.SettingsSettings for this RCMS… are made here.RCMS460-490_D00067_03_M_XXEN/12.2017Page49495051525347Menu item7.Control8. External devices9.Info48OperationFunctionPageThis menu offers various control options, such as TEST, RESET, Test communication.74