Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
SR 45-78 21.3 450.0 12.2 45 20.8 500.0 8.3MAIN 78-45 21.0 500.0 11.3 45 21.6 500.0 8.3SR 45-78 21.4 500.0 11.3 45 20.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.5 26.4 42.3 45 17.5 26.4 39.9SR 36-45 16.5 26.4 42.3 36 18.4 26.4 39.9MAIN 36-78 30.6 500.0 -12.4 36 29.5 500.0 -15.3SR 12-36 29.3 498.0 -12.3 36 30.4 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 6.8 497.0 8.0SR 12 9.2 86.0 14.7MAIN 45 6.8 497.0 8.0SR 45 10.2 500.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: I arkTester for DM 1-3.flw Floor: 03 etasjeTest Summary: PASS