Title: DOCA0005EN-12.pdf
Date of manufactureLonWorks firmware major version (for example, 2.xx)nciDevMajVerSCPTdevMajVerThis variable functions with nciDevMinVer to provide the device’s LonWorks firmware versionLonWorks firmware minor version (for example, x.34)nciDevMinVerSCPTdevMinVerThis variable functions with nciDevMajVer to provide the device’s LonWorks firmware versionnciMeterVersionSNVT_str_asc (UCPTMeterVersion)Device firmware version, stored as an ASCII text stringRelated topicsSee “Troubleshooting” on page 125 for more information on the error codes.See “Network propagation rate setup” on page 75 for information on variables that control the network update rate.See “Network propagation rate setup” on page 75 for information on variables that control the network update rate.Energy and energy by tariff measurementsMost energy values are available in both signed 32-bit integer and floating point format. The SNVT is appended with _l for 32-bit integer values and _f for floating point values.