Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
[Pair 36] [Pair 36] [Pair 36]24.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.3 500.0 29.2 36 8.7 500.0 26.4SR 36-45 8.0 497.0 29.3 36 7.5 499.0 26.4MAIN 36-45 8.3 500.0 29.2 36 8.7 500.0 26.4SR 36-45 8.1 500.0 29.2 36 7.5 499.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 14.5 370.0 13.9 45 13.8 2.6 53.9SR 45-78 14.7 370.0 13.9 45 13.8 2.9 53.1MAIN 78-36 16.0 471.0 11.8 45 16.7 464.0 8.9SR 36-78 16.1 471.0 11.8 45 15.7 417.0 9.80100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.2 32.8 39.7 45 23.3 35.5 36.3SR 45-78 20.2 38.5 37.8 45 20.6 35.5 36.3MAIN 36-45 33.0 500.0 -12.4 36 33.5 500.0 -15.3SR 36-45 32.8 500.0 -12.4 36 32.2 499.0 -15.20804000250 MHz