Title: 370.011 LC001 10 kW isvannsenheter UPU 20 B.pdf
OFFER N.: OF 000049 rev. 0 date : 26/08/2016 - A UNIT : Nedblåsende enhet med isvannscoilCUSTOMER : UPU 20bTECHNICAL SPECIFICATIONSVer. 3.2.1.243 - 04/02/2016Aspirazione in alto,mandata in basso.Struttura in lamiera di acciaio colore grigio scuro (antracite)Metal sheet pannels painted in epoxidic dark grey color. closing pannels with autoextinguishisng th Selfextinguishing thermoacustic insulation material covered by antifriction film.Microprocessor control Survey EVO. Temperature and humidity control. Standard equipped with RS485 (Modbus), terminals for smoke/fire and temperature sensor on supply.Complete electric panel. Door lock main switch. All components are protected against short circuit or overload.POWER SUPPLY400/3/50+N+ PEAltitude[m]0FILTERING SECTIONPanelfilter Trykkvakt for tett filter alarmQuantity Filtering efficency : Suggested final pressure drop Dimensions[n][Pa] [mm]1 G4 250 700 x 640 x 48CHILLED WATER CIRCUITIsvanns coilRegulating valve :