Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 27,6 23,8 3,8 500,00Worst Value: Local: 36 28,3 23,9 4,4 494,00Remote: 36 27,6 23,8 3,8 500,00PS-ACRF: Pass Worst Margin: Local: 45 65,8 54,3 11,5 2,20Worst Value: Local: 12 20,1 7,4 12,7 490,00Remote: 45 65,4 54,3 11,1 2,20Remote: 12 20,5 7,3 13,2 493,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:04Signature:______________________ Page: 68Copper Certification ReportCable Label: 521.002-UD-167 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 13:44:00 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4