Title: +038=360.000-LD051._03-Paragon Fan-coil Swegon - Installasjon, innregulering og vedlikehold.pdf
C O N D U C T O RW4.1, PSFor US and Canada market WARNING: The power feeding to the system shall be a Low Voltage class 2 circuit.PARAGONc (L)PARAGONc (L)W4.1, 2xPSCONDUCTOR / LUNA32417Grilles assembly / GallermonteringDCBACEFG8Commissioning / Injustering1.2.3.Room 203 PARAGON 1300 22 l/sPARAGON 1300StorlekDystryckLuftflödeKplDysinställning(mm)(Pa)(l/s)90050 - 150 Pa10,6 - 18,41,5L / L90050 - 150 Pa12 - 20,81,7L / M90050 - 150 Pa13,4 - 23,11,89M / M90050 - 150 Pa16,8 - 292,37L / H90050 - 150 Pa18,2 - 31,52,57M / H90050 - 150 Pa22,9 - 39,73,24H / H110050 - 150 Pa13,7 - 23,81,94L / L110050 - 150 Pa15,5 - 26,82,19L / Mq=15.7 - 31.4 (l/s) k=2,22 q=L/Lq = k · √pi [l/s] pi = (q/k)2 [Pa]4.5.LMHL=900, 1300L=775, 1100, 1500MHMHLMHM HLM HLLMHM HM H9Length / LängdpiAirflow / LuftflödeKplNozzle / Dysa(mm)(Pa)