Title: Kapasitetsmåler Mecon.pdf
the air bubbles can escape. Then the bypass meter has to be positioned vertically and the unionnut has to be tightened once again.Attention:Before pressure test in pipes, the bypass meter has to be disassembled and the connection of the orifice plate has to be screwed pressure-tight with the cap.Page 8 / 16www.mecon.deOperating Instructions FO Turbo-Lux 3 FM VdS05/2015 OI_FO_Turbo-Lux 3 FM VdSStart-upRead the exact valueOn the scale the flow is printed in lpm (liters per minute), USGPM (U.S. gallons per minute) and as percentage (100% = rated power of the pump) for each nominal size and range.The following table provides more information about the scale display.SizePumpUSGPMlpmratingFlow rangeStepGradu-Flow rangeStepGradu-USGPMUSGPMationlpmation2"/ DN 505020 - 10010575 - 3755052½"/ DN 6510040 - 200204150 – 37510053"/ DN 8015060 - 300505220 - 110020043"/ DN 8020080 - 400505300 - 15002004