Title: +038=433.000-NI003._12-Testrapport elektriske anlegg - DM1.E5=433.06.04, Pareto_SB1 Markets plan 06.pdf
Side:45GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.311311312312313313314314315315316316317317TEST RAPPORTResultatISOLASJON: ALLERln: >30.0MΩ Um: 254V Rlpe: >30.0MΩ Um: 255V Rnpe: >30.0MΩ Um: 253VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 27.11.2020 11:53R LOW OhmR: 0.23ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF094 16C2/003 27.11.2020 11:54KONTINUITET R: 0.2ΩGrenseverdi: 0.7ΩDM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 26.11.2020 14:37SPĆNDINGUln: 232V Ulpe: 232V Unpe: 0V f: 50.0HzDM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 26.11.2020 14:37Z-LINEZ: 0.25ΩIsc: 917A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 6 / DM1.E5=433.06.04 / XF095 16C2/003 26.11.2020 14:37Zs(rcd)Z: 0.27ΩIsc: 865A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0A