Title: Hardware Installation Guide.pdf
3. Keep power limited wiring separate from non-power limited wiring (115 VAC/60 Hz Input, Battery wires). Minimum 0.25 inch spacing must be provided between power wires.4. Connect devices to be powered to terminals marked (1P-1N, 2P-2N, 3P-3N, 4P-4N) and distribute evenly. Each output is rated at 1.5 amps max.4. Connect devices to be powered to terminals marked (1P-1N, 2P-2N, 3P-3N, 4P-4N) and distribute evenly. Each output is rated at 1.5 amps max.34 — revision 6Hardware Installation GuideNote:It is important to measure output voltage before connecting devices. This helps avoid potential damage. Use 18 AWG or larger wire for all power connections (battery, DC outputs).For UL Access Control applications, batteries are required. When batteries are not used, a loss of AC will result in the loss of output voltage. When the use of stand-by batteries is desired, they must be lead acid or gel type. Connect battery to terminals marked + BAT – (battery leads included).