Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Combined module with digital and analogue inputs and outputs. This module is designed to extend the range of uses for the Saia PCD®. The functions and the technical specification are based on the existing PCD2 modules.This module cannot be installed in the PCD1.The technical details should be taken from the descriptions of these modules.Number and type of inputs/outputs10 digital inputs, E0 … E9 (*addresses 0 … 9)Technical data as for PCD2.E110, but without the option of sink operation,i.e. no “L” connection.6 analogue outputs, A16 … A21 (*base address 16, channels 0 … 5)0 … 10 VDC / 8 bit; remaining tech. data as for PCD2.W400.8 digital outputs, A32 … A39 (*addresses 32 … 39)24 VDC / 0.5 A; remaining tech. data as for PCD2.A400.2 analogue inputs, E48 and E49 (*base address 48, channels 0 … 1)0 … 10 VDC / 10 bit; remaining tech. data as for PCD2.W200.6 analogue inputs, E50 … E55 (*base address 48, channels 2 … 7)Pt/Ni 1000 / 10 bit with data as for PCD2.W220.