Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Cable ID =521.04.04-UF078 =521.04.04-UF079 =521.04.04-UF080 =521.04.04-UF081 =521.04.04-UF082 =521.04.04-UF083 =521.04.04-UF084 =521.04.04-UF086Page 2 15-01-2023 21:39:43 SMN 4 etg.flwSummary PASS PASS PASS PASS PASS PASS PASS PASSTest Limit EN50173 PL2 Class Ea EN50173 PL2 Class Ea EN50173 PL2 Class Ea EN50173 PL2 Class Ea EN50173 PL2 Class Ea EN50173 PL2 Class Ea EN50173 PL2 Class Ea EN50173 PL2 Class EaLength 43.0 m 47.0 m 47.0 m 13.6 m 13.3 m 13.6 m 13.6 m 30.4 mHeadroom 6.5 dB (NEXT) 7.1 dB (NEXT) 9.0 dB (NEXT) 5.3 dB (NEXT) 5.1 dB (NEXT) 5.7 dB (NEXT) 7.1 dB (NEXT) 6.0 dB (NEXT)Date / Time 10-12-2022 15:59 10-12-2022 16:00 10-12-2022 16:00 10-12-2022 16:01 10-12-2022 16:02 10-12-2022 16:02 10-12-2022 16:02 10-12-2022 16:04Total Length: Number of Reports: Number of Passing Reports: Number of Failing Reports: Number of Warning Reports: Documentation Only:Page 3 15-01-2023 21:39:43 SMN 4 etg.flw2512.4 m 85 85 0 0 0