Title: økernvn 94.pdf
MAIN 36-78 22.0 229.5 6.7 12 23.0 242.5 2.8SR 36-78 21.4 247.0 5.0 78 22.1 247.5 2.3010080604020050100150MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.3 19.3 19.6SR 36 3.6 41.5 17.8MAIN 36 4.3 212.5 10.7SR 45 5.5 216.5 10.606050050100150MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4403020100050100150MHzProject: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94200200200200Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002170 ft60Insertion Loss (dB)50403020100050100150200250MHz100NEXT @ Remote (dB)806040202500050100150200250MHz100ACR-F @ Remote (dB)806040202500050100150200250MHz100ACR-N @ Remote (dB)80