Title: økernvn 94.pdf
60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.6 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.0 * 249.5 35.4 36 1.1 247.0 32.8SR 36-450.9 *249.5 35.4 36 1.5 250.0 32.7MAIN 36-45 1.0 249.5 35.4 36 1.1 247.0 32.8SR 36-45 0.9 249.5 35.4 36 1.5 250.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 9.0 44.3 31.3 36 11.9 44.3 28.3SR 36-45 9.2 44.3 31.3 45 11.6 37.8 29.7MAIN 36-45 10.8 243.0 16.5 45 13.7 243.0 13.5SR 45-36 10.3 248.5 16.3 36 13.5 243.0 13.5010080604020050100150MHzACR-F (dB)200250010080604020050100150200MHzACR-F @ Remote (dB)250