Title: +038=433.000-NI003._07-Testrapport elektriske anlegg - DM1.E7=433.08.05, Pareto plan 08.pdf
DM1-3. Plan 8 / DM1.E7.433.08.05 / XF030 16/2/C/003 19.11.2020 11:49Z-LINEZ: 0.51ΩIsc: 448A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF030 16/2/C/003 19.11.2020 11:49Tallberg Elektro A/S Tlf.22796640Side:6GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*Nr.4242434344444545464647474848TEST RAPPORTResultatRCD II: 27.0mAUci: 0.1V t: 97.6ms Idn: 30mA type: AC Ulim: 50VDM1-3. Plan 8 / DM1.E7.433.08.05 / XF030 16/2/C/003 19.11.2020 11:49Zs(rcd)Z: 0.50ΩIsc: 456A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 8 / DM1.E7.433.08.05 / XF030 16/2/C/003 19.11.2020 12:43R LOW OhmR: 0.19ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 0.7ΩDM1-3. Plan 8 / DM1.E7.433.08.05 / XF030 16/2/C/003 19.11.2020 12:43KONTINUITET R: 0.2ΩGrenseverdi: 0.7Ω