Title: +135.01=244.003-DI002T_01-FDV Branngardiner Nittedal ungdomsskole.pdf
Side 9 av 15GF/85226FDV 813.1.7 Dimensjoner og målskisser (Dimensjoner i millimeter)Prepared holes in the cabinet for fixing.Always leave at least the indicated space in front of the cabinet for opening.3.1.8 LedningstilkoblingerInn (1,2,3) Ut (4,5,6,7,8) Signal(9,10)Dimensjon (mm2) 2,5 42,5tiltrekking (Nm) 0,5-0,6 0,8-10,5-0,6Avisolering (mm) 7 777Side 10 av 15GF/85226 3.1.9 Kobingsskjema1 2 3 4 5 6 89Power sourceL N PE+ - + -BATTERIESPower Source: 1 - Output 24Vdc 2 + Output 24Vdc - Battery Charger Output 3 4 + Battery Charger Output Signal Common 5 Power failure( N.C.) 6 Signal Common 8 Battery failure( N.C.) 9 L Fase 230Vac N Neutro 23Vac PE GroundingControl board 1 + Input 24Vdc 2 - Input 24Vdc 3 + Output 24Vdc - Output24Vdc 4 Signal Common 5 Power failure( N.C.) 6 7 Battery failure( N.C.) 8 Alarm 9 AlarmConnection clamps 1 Fase 230Vac 2 Neutro 230Vac 3 4 + Output 24Vdc 5 + Output24Vdc 6 7 8 9 Alarm NC 10 Alarm NCPEPE - Output 24Vdc - Output 24Vdc