Title: +175=324.001_KA001_Motorventiler til kjølebatterier 36.01 og .02 - VUE DN15-50.Produktinformasjon.pdf
Not suitable for drinking water or potentially explosive atmospheres • Valve with flange connection as per EN 1092-2, seal form B, for PN 16 and PN 10 • Regulating valve, free of silicone grease, painted black • Characteristic can be set with SUT (SAUTER Universal Technology) valve actuator to linear, equal- percentage or quadraticThe valve is closed when the spindle is moved out • Closing either against or with the pressure • Valve body and seat made of grey cast iron • Stainless-steel spindle • Plug made of brass with glass-fibre reinforced PTFE sealing ring • Stuffing box made of brass with wiper ring and double O-ring seal made of EPDMTechnical dataParametersNominal pressurePN 16/10ConnectionFlange as per EN 1092-2, form BValve characteristic, control passage F200LinearValve characteristic, control passage F300Equal-percentageControl ratio of valve> 50:1Stuffing boxLeakage rateValve stroke2 EPDM O-rings < 0.05% of kvs value 8 mmAmbient conditions1)