Title: 360.001 - Tilluft.pdf
16,7LocationLevel2. Etasje2. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. Etasje1. EtasjeNodeTypeProductDUCTLKR-400-400-1869-*122 PLUGLEPR-400-400DUCTLKR-800-500-8098-*DUCTLKR-800-500-8098-*227 TAPMAGIO-RC-*DUCTFIREDAMPER FKRS-EU/200/ZXXDUCTBEND-45MAGIB-C4-*-*DUCTSize800x600800x600800x800800x800200200200200200200Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]0,03,248002,10,648002,13002,70,13002,73002,70,23002,73002,70,43002,753Sound in:Attenuation: Addition:0,2 Sound in:Attenuation: Addition:Sound in:Attenuation: Addition:Dividing:3,4 Sound in:0,0 Sound in:Attenuation: Addition:1,8 Sound in:Addition:0,1 Sound in:Attenuation: Addition:0,7 Sound in:Attenuation: Addition:0,2 Sound in:Attenuation: Addition:63 [dB]40.00.0 +0.042.92.1 +19.240.80.2 +20.915.625.025.00.0 +11.425.1+32.433.1