Title: Simployer - Data testrapport =514.204-FS001.pdf
45.3 mLinkWare™ PC Version 10.4Cable ID: 521.204-UD27 Date / Time: 28/01/2022 10:49:18 Headroom 8.6 dB (NEXT 4,5-7,8) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 4,5]48.7 250 18 8.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]21.1 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 4,5-7,8 8.6 87.8 40.9 4,5 10.6 88.0 38.0SR 1,2-7,8 8.7 33.3 48.0 1,2 9.2 174.0 32.9MAIN 4,5-7,8 10.9 239.0 33.5 7,8 12.1 239.5 30.5SR 1,2-7,8 10.1 248.0 33.2 7,8 10.3 248.0 30.2