Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]31.8 137 1 4.58Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]27.1 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.8 498.0 29.3 36 6.2 500.0 26.4SR 12-36 7.6 498.0 29.3 36 7.9 497.0 26.4MAIN 12-36 6.8 498.0 29.3 36 6.2 500.0 26.4SR 12-36 7.6 498.0 29.3 36 7.9 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.1 8.0 47.2 45 19.8 500.0 8.3SR 45-78 20.1 8.0 47.2 45 21.7 500.0 8.3MAIN 12-45 20.3 500.0 11.3 45 19.8 500.0 8.3SR 45-12 20.6 500.0 11.3 45 21.7 500.0 8.30100806040200250 MHzACR-F (dB)