Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]29.0 126 2 4.31Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]28.6 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.5 497.0 29.3 36 9.0 472.0 26.3SR 36-45 6.5 481.0 29.6 45 7.5 480.0 26.8MAIN 36-45 8.5 497.0 29.3 36 9.3 497.0 25.1SR 36-45 6.6 485.0 29.5 36 9.1 499.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 15.4 500.0 11.3 45 14.5 3.5 51.4SR 36-45 15.8 5.9 49.9 45 14.5 3.8 50.8MAIN 78-45 15.4 500.0 11.3 45 16.8 500.0 8.3SR 78-45 15.8 499.0 11.3 78 16.6 500.0 8.30100806040200250 MHzACR-F (dB)