Title: økernvn 94.pdf
Project: OKERNVEIEN 94 3.ETG DEL 2 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 94Cable ID: T3055 Date / Time: 09/12/2013 03:02:05 Headroom 14.7 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]249 396 29 10.8Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]6.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 15.0 95.8 32.6 36 15.9 95.8 29.6SR 12-36 14.7 72.0 34.6 36 16.0 80.0 30.9MAIN 12-36 15.0 95.8 32.6 36 15.9 95.8 29.6SR 12-36 15.4 99.8 32.3 36 16.2 99.8 29.310080604020NEXT (dB)