Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Resistance0 … 2500 Ω, resolution 0.2 ΩEach channel can be configured to have a software-based filter with 50 Hz/ 60 HzOutputs, 12 Bit2 outputs. Each channel has three operating modes (configurable via software)Voltage0 … 10 V, resolution: 2.44 mV per LSB (12 Bit)Current0 … 20 mA, resolution: 4.88 μA per LSB (12 Bit) 4 … 20 mA, resolution: 4.88 μA per LSB (11.7 Bit)High impedance:MiscellaneousAll I/O channels are electrically isolated from the external power supply. (but all channels are electrically connected to each other).Each channel has two connections.Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-256-80Saia-Burgess Controls Ltd.Input/output (I/O) modulesPCD2.W525ConfigurationModule connections/LEDsThe module connections are as follows:Description of LED: ● ● ●Off: On: Flashing slowly:Flashing quickly: