Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
27.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.2 500.0 29.2 36 6.4 500.0 26.4SR 36-45 6.8 497.0 29.3 36 6.7 498.0 26.4MAIN 36-45 7.2 500.0 29.2 36 6.4 500.0 26.4SR 36-45 6.8 497.0 29.3 36 6.7 498.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.2 445.0 12.3 45 19.3 461.0 9.0SR 78-45 17.2 440.0 12.4 45 19.4 453.0 9.1MAIN 78-45 17.6 468.0 11.8 45 19.7 500.0 8.3SR 78-45 17.3 449.0 12.2 45 19.7 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 24.2 47.5 35.1 45 24.4 47.8 32.5SR 36-45 25.0 47.8 35.0 45 26.0 48.0 32.5MAIN 36-45 34.4 500.0 -12.4 36 33.9 500.0 -15.3SR 36-45 34.0 497.0 -12.2 36 34.0 498.0 -15.10804000250 MHzACR-N (dB)