Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
250 MHz500LinkWare™ PC Version 10.1Cable ID: 521.11.02-UF072 Date / Time: 27-02-2020 21:11:31 Headroom 8.9 dB (NEXT 36-45) Test Limit: EN50173 PL2 Class Ea Cable Type: Cat 7 S/FTP NVP: 78.0%Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]38.3 166 2 5.70Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]25.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-78 11.5 476.0 29.7 36 10.2 476.0 26.9SR 36-45 8.9 486.0 29.5 36 8.7 476.0 26.9MAIN 36-45 11.7 495.0 29.3 36 10.2 476.0 26.9SR 36-45 8.9 486.0 29.5 36 9.0 497.0 26.410080604020NEXT (dB)