Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 45] [Pair 45]27.8 121 2 4.22Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]28.4 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 8.8 496.0 29.3 36 9.2 500.0 26.4SR 36-45 9.0 488.0 29.5 36 9.1 500.0 26.4MAIN 12-36 8.9 500.0 29.2 36 9.2 500.0 26.4SR 36-45 9.0 488.0 29.5 36 9.1 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 21.3 469.0 11.8 45 21.4 500.0 8.3SR 36-45 21.4 469.0 11.8 45 21.3 500.0 8.3MAIN 45-36 21.6 499.0 11.3 45 21.4 500.0 8.3SR 36-45 21.5 499.0 11.3 45 21.3 500.0 8.30100806040200250 MHzACR-F (dB)