Title: DM1-3 plan 09 lysberegningsrapport.pdf
Room 4Summary, Room 4Result overview, Evaluation area 1[m] 5.5N5.04.54.03.53.02.52.01.51.00.50.00.50.0 0.6 1.2 1.8[m]Illuminance [lx]2003005007501000General Calculation algorithm used Height of luminaire plane Maintenance factorAverage indirect fraction 2.50 m 0.80Total luminous flux of all lamps Total power Total power per area (14.18 m²)7000.00 lm 92.4 W 6.52 W/m² (1.37 W/m²/100lx)Evaluation area 1 User profileEm Emin Emin/Em (Uo) Emin/Emax (Ud) UGR (4.9H 1.8H) PositionReference plane 1.1 Offices 5.26.5 (EN 12464-1, 8.2011) Conference and meeting rooms (Ra >80.00) Horizontal 476 lx 363 lx 0.76 0.57 <=17.9 0.75 m(>= 500 lx)(>= 0.60)(< 19.00)Major surfaces M 1.5 (Ceiling) M 1.1 (Wall) M 1.2 (Wall) M 1.3 (Wall) M 1.4 (Wall)Em 33 lx 81 lx 39 lx 62 lx 45 lx(>= 30 lx) (>= 50 lx) (>= 50 lx) (>= 50 lx) (>= 50 lx)Uo 0.78 0.30 0.57 0.38 0.49(>= 0.10) (>= 0.10) (>= 0.10) (>= 0.10) (>= 0.10)191015 test plan 9.rdf