Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,3 26,7 2,6 500,00Remote: 36-45 29,5 26,7 2,8 500,00Worst Value: Local: 36-45 29,3 26,7 2,6 500,00Remote: 36-45 29,5 26,7 2,8 500,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 24,6 13,3 11,3 351,00Remote: 12-45 24,8 13,3 11,5 351,00Worst Value: Local: 12-45 21,9 10,3 11,6 493,00Remote: 12-45 22,3 10,4 11,9 490,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,6 23,8 3,8 500,00Remote: 45 28,4 23,8 4,6 498,00Worst Value: Local: 36 27,6 23,8 3,8 500,00Remote: 45 28,4 23,8 4,6 498,00PS-ACRF: Pass Worst Margin: Local: 78 70,1 58,0 12,1 1,45Worst Value: Local: 45 20,2 7,2 13,0 499,00Remote: 45 73,1 61,2 11,9 1,00