Title: +038=522.000-NI002._04-Testrapport EKOM-anlegg, plan 11 (Pareto).pdf
SR 36-45 16.9 473.0 11.7 45 18.0 460.0 9.00100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 35.8 278.0 4.3 45 36.3 278.0 1.7SR 36-45 35.5 279.0 4.2 45 35.7 288.0 0.8MAIN 12-36 45.4 494.0 -12.0 36 44.7 496.0 -15.0SR 12-45 45.8 500.0 -12.4 36 45.1 496.0 -15.00804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 5.1 500.0 8.0SR 45 4.3 500.0 8.0MAIN 45 5.1 500.0 8.0SR 45 4.3 500.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: PARETOTester 11 etg.flwTest Summary: PASSModel: DSX-5000 Main S/N: 2420901 Remote S/N: 2420696 Main Adapter: DSX-PLA004 Remote Adapter: DSX-PLA00411.7 m60Insertion Loss (dB)504030201000250 MHz500100