Title: økernvn 94.pdf
Cable ID: D4161 Date / Time: 09/10/2013 05:19:56 Headroom 4.2 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 45]115 173 4 5.9Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]13.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 4.5 85.8 33.4 36 7.2 85.8 30.4SR 12-36 4.2 85.8 33.4 36 6.6 85.8 30.4MAIN 12-36 4.5 85.8 33.4 36 7.2 85.8 30.4SR 12-36 4.2 85.8 33.4 36 6.6 85.8 30.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-12 20.4 4.9 44.9 12 21.3 2.6 47.2