Title: 370.011 LC001 10 kW isvannsenheter UPU 20 B.pdf
at the air supply mouth without sound absorbers på 2 meter i fritt felt (ISO 3744)SOUND PRESS.AND POWER LEV.IN OCTAVE BANDFreq.of the cent.of the oct.band SWL fan discharge SPL front of the unitTot. 72 5263Hz 70 50125Hz 70 50250Hz 71 51500Hz 68 481kHz 62 422kHz 64 444kHz 63 438kHz 60 40OFFER N.: OF 000049 rev. 0 date : 26/08/2016 - A UNIT : Nedblåsende enhet med isvannscoilCUSTOMER : UPU 20bEXTERNAL CONNECTIONSChilled water coil connections Inlet Outlet1 x 1" F 1 x 1" FCondensing drain diameter19x25 mmELECTRICAL CHARACTERISTICSPower supply400/3/50+N+ PEwithin 10 working days from the date of the order confirmation the definite wiring diagram will be sent with the indications of real absorbed power and amperage, the suggested dimensions of the wiring cables and the sizing of the feeding line protection.PHISICAL CHARACTERISTICS