Title: VR-PL-02-003 Gulvvarme Plan 02 Del 1.pdf
EDCFordeler 02.01 10 kurser dT 5 °C 0,28 l/s L=839,5 mBA1101.01 L=96,1 m c/c=20001.06 L=48,1 m c/c=20001.03 L=92,9 m c/c=20001.02 L=98,4 m c/c=20001.10 L=82,3 m c/c=20001.09 L=88,3 m c/c=20001.08 L=95,5 m c/c=20001.07 L=95,0 m c/c=20001.04 L=94,2 m c/c=20001.05 L=47,2 m c/c=2002204.03 L=76,5 m c/c=20004.04 L=94,8 m c/c=20004.09 L=95,1 m c/c=20004.08 L=97,9 m c/c=20002.04 L=92,9 m c/c=20002.03 L=91,6 m c/c=20002.02 L=98,0 m c/c=20002.01 L=96,8 m c/c=20004.07 L=95,8 m c/c=20004.05 L=95,6 m c/c=20004.06 L=99,1 m c/c=2003302.05 L=49,7 m c/c=20002.06 L=48,9 m c/c=200Fordeler 02.02 10 kurser dT 5 °C 0,28 l/s L=847,0 m04.01 L=87,8 m c/c=20004.02 L=91,5 m c/c=20003.01 L=104,2 m c/c=20002.10 L=89,0 m c/c=20002.09 L=95,7 m c/c=20002.08 L=87,2 m c/c=20002.07 L=97,1 m c/c=200445Fordeler 02.03 4 kurser dT 5 °C 0,11 l/s L=338,2 m03.04 L=93,1 m c/c=20003.02 L=53,8 m c/c=2005Fordeler 02.04 10 kurser dT 5 °C 0,27 l/s L=834,0 m