Title: økernvn 94.pdf
50 MHz75100LinkWare Version 7.4Cable ID: D3019 Date / Time: 09/12/2013 08:44:39 Headroom 11.1 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 36] [Pair 12] [Pair 12] [Pair 12]80 127 9 3.3Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]16.0 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 12.3 94.3 32.7 36 13.2 98.5 29.4SR 12-36 11.1 85.8 33.4 36 12.7 90.0 30.1MAIN 12-36 12.3 94.3 32.7 36 13.2 98.5 29.4SR 12-36 11.3 94.3 32.7 36 12.7 94.0 29.710080604020NEXT (dB)