Title: Data tester Smestad skole - Detaljert.pdf
Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 61,3 68,0 318,0 17,0 10,5Limit 100,0 - 555,0 50,0 25,0Margin 38,7 - 237,0 33,0 14,5Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,2 3,0 1,8 2,80Worst Value: Local: 45 25,6 43,6 18,0 497,00dB -2020600Local250500 MHzReturn Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 78 17,3 8,8 8,5 333,00Remote: 78 20,6 15,1 5,5 78,50Worst Value: Local: 12 16,5 8,0 8,5 499,00Remote: 78 15,2 8,6 6,6 346,00dB -2030800Local250500 MHzdB -2030800Remote250500 MHzNEXT: Pass