Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]21.3 92 1 3.34Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.4 480.0 28.8 36 7.8 463.0 26.8SR 36-45 4.9 464.0 29.6 36 6.3 464.0 26.7MAIN 36-45 9.1 497.0 28.0 36 8.4 496.0 25.2SR 36-45 5.2 492.0 28.2 36 6.6 492.0 25.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.7 500.0 11.3 45 17.5 3.4 51.7SR 78-45 17.7 500.0 11.3 45 17.5 3.8 50.8MAIN 78-45 17.7 500.0 11.3 45 18.9 500.0 8.3SR 78-45 17.7 500.0 11.3 45 19.0 499.0 8.30100806040200250 MHzACR-F (dB)