Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 36]21.3 92 1 3.30Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]31.1 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.2 456.0 29.9 36 8.4 465.0 26.7SR 36-45 6.0 454.0 30.0 36 7.0 455.0 27.2MAIN 36-45 10.0 497.0 28.0 36 9.3 499.0 25.0SR 36-45 7.4 497.0 28.0 36 8.4 500.0 25.010080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 16.6 5.0 51.3 45 17.1 3.5 51.4SR 78-45 16.6 5.0 51.3 45 17.3 84.8 23.7MAIN 78-45 17.9 499.0 11.3 45 19.8 499.0 8.3SR 45-78 18.3 499.0 11.3 36 19.5 473.0 8.70100806040200250 MHzACR-F (dB)