Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Watchdog: This module can interact with the watchdog, if it is used on base address 240. In this case, the last input with address 255 cannot be used. For details, please refer to the "Watchdog" section, which describes the correct use of the watchdog in conjunction with PCD3 components.6-86Analogue output modules, electrically isolated from the I/O Bus6.11Analogue output modules, electrically isolated from the I/O BusPCD3.W605 PCD3.W615 PCD3.W6256 electrically isolated analogue outputs 10 bit, 0…10 V 4 electrically isolated analogue outputs 10 bit, 0…20 mA 6 electrically isolated analogue outputs 10 bit, -10 V…+10 VGalvanic separation of outputs to Saia PCD®, channels themselves not separatedI/O modules and I/O terminal blocks may only be plugged in and removed when the Saia PCD® and the external +24?V are disconnected from the power supply.6-87PCD3.W6x56.11.1PCD3.W6x5, analogue outputs electrically isolated from the I/O Bus, 6(4) channels, 10 Bit resolutionApplication