Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E6.433.09.03 / XF057 C16/2 16.06.2020 10:12R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF058 C16/2 15.06.2020 10:18SPĆNDINGUln: 230V Ulpe: 231V Unpe: 1V f: 49.9HzDM1-3. Plan 9 / DM3.E6.433.09.03 / XF058 C16/2 15.06.2020 10:19Tallberg Elektro A/S Tlf.22796640Side:21GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENTGODKJENT*GODKJENT*Nr.148148149149150150151151152152153153154154TEST RAPPORTResultatZ-LINEZ: 0.30ΩIsc: 761A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF058 C16/2 15.06.2020 10:19Zs(rcd)Z: 0.27ΩIsc: 844A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF058 C16/2 15.06.2020 10:19RCD II: 27.0mAUci: 0.4V t: 283.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF058 C16/2 15.06.2020 13:59