Title: 360.001 - Tilluft.pdf
19.60.1 +3.719.627.00.00.2 +3.75.21.5 +0.05.40.00.9 +4.15.311.0 +9.79.98k [dB]11.60.3 +0.011.6+14.616.40.1 +0.016.43.0 +0.013.60.1 +0.013.818.00.00.2 +0.02.91.5 +0.05.40.00.9 +0.02.616.0 +2.7 2.916.0 +2.7 2.9Lp [dB]23,0LocationLevel2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeTypeDUCTREDUCERDUCT199 T-BRANCHDUCT200 SUPPLYDUCT201 PLUG202 TAPDUCTProductMAGIR-CC1-*-*TCPU_DK-*-*0,0,1,0Tellus-Lov-H-160ESU_SE-*0MAGIO-RC-*Size250250/200200200/160160160200200315/160160Sound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]0,32301,32301,32,82302,02302,02,72303,22303,20,21001,41,11001,490,0 Sound in:Attenuation: Addition:0,1 Sound in:0,9 Sound in:Attenuation: Addition:3,7 Sound in:Attenuation: Addition:Dividing:2,6 Sound in: