Title: 360.002 - Tilluft.pdf.pdf
10.91.5 +0.03.06.86.80.0 +0.07.610.0 +0.52.38.20.0 +0.015.90.3 +9.516.51.5 +0.04.111.00.6 +0.02k [dB]9.90.6 +0.09.81.5 +0.03.05.95.90.0 +0.06.910.0 +0.01.77.20.0 +0.014.50.3 +8.515.21.5 +0.04.19.80.6 +0.04k [dB]6.90.6 +0.07.21.5 +0.03.03.73.70.0 +0.05.28.0 +0.0 1.88.0 +0.0 1.84.90.0 +0.010.60.3 +4.511.31.5 +0.04.16.10.6 +0.08k [dB]3.70.6 +0.04.81.5 +0.03.02.02.00.0 +0.04.18.0 +0.0 1.58.0 +0.0 1.53.10.0 +0.04.60.3 +0.05.71.5 +0.04.11.50.6 +0.0Lp [dB]10,83. etasje2. Etasje2. Etasje2. Etasje3. etasje3. etasje3. etasje3. etasje3. etasje3. etasjeDUCT77 TAPDUCT78 SUPPLYDUCT79 PLUGDUCTBEND-90DUCTBEND-90250MAGIO-RC-*250/250250FKV-250 Cooling250250ESU_SE-*0250315MAGIB-C4-*-*315315MAGIB-C4-*-*315L [m]0,30,10,11,20,4Sound Calculation Reportqv [m³/h]v [m/s]dpt [Pa]230