Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]34.6 151 3 5.23Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]25.9 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 8.8 498.0 29.3 36 8.7 471.0 27.0SR 36-45 8.6 491.0 29.4 36 8.6 488.0 26.6MAIN 36-45 8.8 498.0 29.3 36 8.8 499.0 26.4SR 36-45 8.6 491.0 29.4 36 8.6 488.0 26.610080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 14.9 37.0 33.9 45 14.4 2.6 53.9SR 36-45 15.0 43.5 32.5 45 14.4 2.9 53.1MAIN 78-36 17.8 497.0 11.3 45 17.9 471.0 8.8