Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Special temperature sensors or any other resistances up to 2.5 kΩ can be connected to the PCD3.W220. The digital value can be calculated as follows:DV =4092 • R(7500 + R)where 0 ≤ DV ≤ 1023 and R = the resistance to be measured in Ω.6-63PCD3.W3x06.8.2PCD3.W3x0, analogue inputs, 8 channels, 12 bit resolutionApplicationHigh-speed input module for general use with 8 channels, each with 12 bit resolution. Different variants for voltage 0…10V, current 0…20 mA and the use of different resistance thermometers are available.Module overviewresolution *)PCD3.W300: PCD3.W310: PCD3.W340:2,442 mV 4,884 µAVoltage 0..0.10V Current 0…0.20 mA General purpose module 0…10V 0…20 mA Pt/Ni1000 (default) Pt1000: -50…+400°C Ni1000: -50…+200°C Temperature sensor Pt/Ni 100 Pt100: Ni100: Temperature sensor Pt1000 -50…+150°C Method of linearization for temperature inputs: by software *) Resolution = value of least significant bit(LSB)2,442 mV 4,884 µA0.14…0.24°C 09…0.12°C.PCD3.W350: