Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan 4 SMN.pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 45] [Pair 45]30.4 132 2 4.62Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]27.3 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 6.0 496.0 29.3 36 7.5 496.0 26.5SR 12-36 8.6 469.0 29.8 36 9.0 500.0 26.4MAIN 12-36 6.0 496.0 29.3 36 7.6 500.0 26.4SR 12-36 8.8 500.0 29.2 36 9.0 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.2 8.0 47.2 45 21.1 5.9 46.9SR 45-78 20.2 8.3 46.9 45 21.1 6.0 46.7MAIN 78-45 21.7 490.0 11.4 45 22.1 500.0 8.3