Title: +038=522.000-NI002._03-Testrapport EKOM-anlegg, plan 10 (Pareto, Pactum).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]25.0 109 2 3.80Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]30.3 499.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-45 7.7 419.0 30.9 45 8.1 471.0 26.4SR 36-45 8.0 490.0 28.3 36 7.8 484.0 25.7MAIN 12-45 8.6 499.0 27.9 45 8.9 500.0 25.0SR 36-45 8.0 490.0 28.3 36 8.0 489.0 25.510080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 36-45 15.0 4.0 53.2 45 14.1 2.9 53.1SR 36-45 15.0 4.0 53.2 45 14.1 2.9 53.1MAIN 45-36 16.1 488.0 11.5 45 17.3 484.0 8.5SR 36-45 15.9 484.0 11.5 45 17.1 497.0 8.30100806040200250 MHzACR-F (dB)