Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
Z: 0.35ΩIsc: 650A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:16Tallberg Elektro A/S Tlf.22796640Side:20GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.141141142142143143144144145145146146147147TEST RAPPORTResultatRCD II: 28.5mAUci: 0.1V t: 107.5ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 15.06.2020 14:24RCD II: 27.0mAUci: 0.0V t: 188.1ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF054 C16/2 16.06.2020 10:11R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF055 C16/2 15.06.2020 14:23RCD II: 24.0mAUci: 0.4V t: 19.9ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF056 C16/2 16.06.2020 10:11R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩ