Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
27.2 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 9.6 500.0 29.2 36 8.1 500.0 26.4SR 36-45 7.4 500.0 29.2 36 7.2 500.0 26.4MAIN 12-36 9.6 500.0 29.2 36 8.1 500.0 26.4SR 36-45 7.4 500.0 29.2 36 7.2 500.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 20.2 459.0 12.0 45 21.3 500.0 8.3SR 45-78 20.5 459.0 12.0 45 21.8 500.0 8.3MAIN 78-45 20.2 459.0 12.0 45 21.3 500.0 8.3SR 78-45 21.1 500.0 11.3 45 21.8 500.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 21.3 47.5 35.1 36 22.0 47.5 32.6SR 36-45 23.8 47.8 35.0 36 25.0 47.8 32.5MAIN 12-36 36.8 500.0 -12.4 36 35.4 500.0 -15.3SR 36-45 34.6 500.0 -12.4 36 34.5 500.0 -15.30804000250 MHzACR-N (dB)