Title: FebDoc Netys RT.PDF
UPS Manufacturer Model Performance (kVA/kW)SOCOMEC NRT-U1100C 1.1 kVA / 0.8 kWNominal Voltage Input (V) Output (V)230 V (Ph+N) 230 V (Ph+N)Nominal Current Input (A) Output (A)4.1 A (Full Charged)Static BypassYesNoIf Yes, Maximum allowed I²t (A²s)5000Short circuit capability Short time Current (A) Maximum time (s) Long time Current (A) Maximum time (s)20 A 100 ms20 A 100 msMaximum thermal overload Current (A)4.9 AInstallation data Cable cross-section Mains protection Auxilary Mains protection Common Input protection >discr. ProtectionNoise (dBA) Maximum Heat lossInput 6 x IEC320-C14 / Output 6 x IEC 320-C13 (10 A) 8 A AC Breaker (1 Pole) curve C 8 A AC Breaker (1 Pole) curve C 8 A AC Breaker (1 Pole) curve C 4 A B curve 45 dB(A) 520 Btu/hr4:08 AM