Title: DOCA0005EN-12.pdf
CT SecondaryCT PrimaryFrequencyFrequencyDateDateTimeTimePulse OutputPulse ConstantPulse WidthMulti TariffsControl modeDisableby Internal ClockScheduleby Digital Inputby 2 Tariffsby Communicationsby 3 Tariffsby 4 TariffsContrastContrastPasswordPasswordReset ConfigReset ConfigDOCA0005EN-123738Front panel display and meter setupiEM3000 series user manualSectionParameterOptionsDescription3PH3W3PH4WType1PH2W L-NSelect the power system type the meter is wired to.Wiring1PH2W L-L1PH3W L-L-NCT3CTs on I1, I2, I31 CT on I12 CTs on I1, I3Define how many current transformers (CT) are connected to the meter and which terminals they are connected to.CT RatioCT Secondary15Select the size of the CT secondary, in Amps.CT Primary1 - 32767Enter the size of the CT primary, in Amps.FrequencyFrequency5060Select the frequency of the electrical power system, in Hz.Date (iEM3210 / iEM3215)DateDD-MMM-YYYY