Title: +038=433.000-NI003._02-Testrapport elektriske anlegg - DM3.E3.433.11.01, Pareto plan 11.pdf
Grenseverdi: 1.0QTEST RAPPORTNr. ResultatR ISO GODKJENTR: 24.1MQ Um: 262VUiso: 250VGrenseverdi: 1MQZLINE GODKJENTZ: 0.63QIsc: 365ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AIGODKJENTI: 28.5mAUci: 0.0V| t: 15.5msIdn: 30matype: ACH\,Ulim: 25VZs (red) GODKJENTZ: 0.40QIsc: 576ASikringstype: CSIKRING I: 16ASIKRING T: 35msIsc_lim: 160.0AKONTINUITET GODKJENTR: 0.1QGrenseverdi:1.0QR LOW Ohm GODKJENTR: 0.02QR+: 0.0QR: 0.0QGrenseverdi: 1.0QSPENDINGUln: 232VUlpe: 232V| Unpe: 0Vf: 50.0HzTEST RAPPORT NG S ResuRat s o e e e R L e SO eR ISO GODKJENTR:48.5MQ Um: 263VUiso: 250VGrenseverdi: 1IMQDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 026 GODKJENT * 12.03.2020 16:26SPENDINGUln: 234VUlpe: 234VUnpe: 0Vf: 50.0HzDronning M.g.1-3 / E.433.11.01 TN-S / Sikring 026 GODKJENT* 12.03.2020RCD T .iDronning M.g.13 /1270852020 _ 1630KONTINUITETR:16527GODKJENT