Title: fireray5000_igb.pdf
Page 23Menu Layout6.5 System Controller SettingsUnits of Measurement  Changes between ’Metric’ and ’Imperial’Change Pass Code  Use to access each digit  Use to change the digit  Press to save the new Pass Code and return to the settings menu  Press to cancel the change and return to the Engineering mneuInstallation, commissioning and operator handbook, FireRay 5000 beam detector 116-P-FIRERAY5000/IGB, 2010-10-28, Autronica Fire and Security ASPage 24System Information7. System Information7.1 Operating Parameters and DimensionsParameterValueOperating Voltage14-28V DCOperating Current – Low Power Mode8-12 mAOperating Current- High Power Mode48-52 mAFire Threshold Range0.45-3.98 dB 10-60%Delay to Fire2-30 sDelay to Fault2-30 sOperating Distance between Detector and Reflector8-100 mMaximum angular misalignment of Detector± 0.3 DegMaximum angular misalignment of Reflector± 5 DegMaximum angular movement of Detector head± 3.5 DegOptical wavelength