Title: Data tester Smestad skole - Detaljert.pdf
Pair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36-45 29,0 26,7 2,3 497,00Remote: 36-45 29,3 26,7 2,6 498,00Worst Value: Local: 36-45 29,0 26,7 2,3 497,00Remote: 36-45 29,3 26,7 2,6 498,00dB 0601200Local250500 MHzdB 0601200Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-45 21,9 11,5 10,4 432,00Remote: 45-12 22,3 11,5 10,8 432,00Worst Value: Local: 12-45 21,8 11,4 10,4 434,00Remote: 45-12 22,2 11,4 10,8 434,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 28,6 25,6 3,0 443,00Remote: 45 28,3 23,8 4,5 500,00Worst Value: Local: 36 27,2 23,8 3,4 497,00Remote: 45 28,3 23,8 4,5 500,00PS-ACRF: Pass Worst Margin: Local: 12 20,5 8,5 12,0 432,00Worst Value: Local: 12 20,3 8,4 11,9 436,00Remote: 12 72,6 61,2 11,4 1,00