Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
Switching capacity Relay type changeover (O 0, 1):RE 01 4024, SCHRACKOperating mode:> 12 V, > 100 mAMax. switching current:5 A, 250 VAC AC1Contact lifetime *):5 A, 250 VAC AC1 2 A, 250 VAC AC15 cosφ=0.31.5 × 105 operations 1.2 × 105 operationsRelay type make (O 2, 3):RE 03 0024, SCHRACKOperating mode:> 12 V, > 100 mAMax. switching current:6 A 250 VAC AC1Contact lifetime *):6 A, 250 VAC AC1 2 A, 250 VAC AC111 × 105 operations 4 × 105 operations) .there are no suppressors fitted to the module; these must be provided externallySwitching delay:typically 5 ms at 24 VDCInternal current consumption: (from +5 V bus)max. 45 mAInternal current consumption: (from V+ bus)0 mAExternal current consumption:max. 45 mARelay coil supply:nom. 24 VDC smoothed or pulsed, reverse voltage protectedVoltage tolerance, dependent on ambient temperature:20°C: 21.5…32 VDC 30°C: 21.9…32 VDC 40°C: 22.3…32 VDC 50°C: 22.8…32 VDC