Title: +038=365.008-SS002._04-mcr WIPT Stengespjeld Mercor - Teknisk og operativ dokumentasjon.pdf
dimension A [mm] 110 110 150dimension B0 [mm] 330 380 330Figure 5. Preparing installation opening.Figure 6. Preparing installation opening for dampers with RST mechanism.MERCOR SA – The company reserves the right to make modifications and changes10/21mcr WIP multi-plane fire dampers 6.3. EMBEDDING _____________________________________________________________ Fire damper mcr WIP correctness of operation is sustained when the axis of rotation is a horizontal axis. The tripping and control mechanism may be mounted on the right or left side of the duct with any direction of the air flow. It is approvable to mount a damper in a position, where the rotation axis of fire damper baffle is vertical under the condition, that such fact was reported to the Manufacturer beforehand.