Title: +038=522.000-NI002._03-Testrapport EKOM Anlegg Plan3 (I-ark).pdf
Software Version: V6.1 Build 3 Limits Version: V7.1 Calibration Date: Main (Module): 19-07-2017 Remote (Module): 19-07-2017Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 12] [Pair 45] [Pair 36] [Pair 45]18.0 78 1 2.75Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]33.0 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.4 413.0 31.0 36 7.7 465.0 26.7SR 12-36 8.6 453.0 30.1 36 8.2 465.0 26.7MAIN 12-36 9.0 500.0 27.8 36 8.2 498.0 25.1SR 12-36 9.3 493.0 28.2 36 9.1 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-78 20.0 7.1 48.2 45 20.4 500.0 8.3SR 45-78 20.0 7.1 48.2 45 20.6 500.0 8.3MAIN 45-36 20.4 499.0 11.3 45 20.4 500.0 8.3