Title: 4. Leieavtaler.pdf
separation distance should be sufficient to mitigate any risk of fire spread between the two facilities . If the distance is less, exposure sprinkler protection might need to be installed along the wall of the Autronica building for fire protection purposes.This exposure need to be reviewed once more details are available regarding the neighbouring building's construction, foot print and occupancy. Please involve FM Global in this process at the earliest opportunity.