Title: Dimensjoner CDP 1500-K.pdf
6/24CDP-K-BSY+EnglishIntended useChain drive for electric opening and closing of heavy windows and flaps in the facade and roof area - Operating voltage 230 V AC - Useable for smoke ventilation, D+H Euro-SHEV according to DIN EN 12101-2 as well as daily natural ventilation - Only for inside mountingPerformance featuresMicro processor controlled synchro electronics BSY + for a precise synchronous run of up to 4 drives - Individually programmable (via software SCS) - SHEV-high speed function (fast-running feature in OPEN-direction) - Protection system for the main closing edge - Locking relief after closing - Especially quiet motor running in ventilation mode - Symmetrical chain outlet - Connection via pin-and-socket connector - Optinal with "-AS2" = protection class 2 and "-AS3" as well as "-LS" = protection class 3Extent of supplyDrive unit with 2,5 m silicone cable. Dependent on the type of window, different bracket sets are available separately.Pressure load diagram