Title: BRV Ahlsell No 450 kW.pdf
°C cP cP kg/m³ kJ/kg,°C W/m,°C K °C °C W/m²,°C °C m/s Pakg kg dm³ dm³ mm mm mm mm mm mm mm mm kgbar bar ºC F1 F2 F3 F4 in/outA B C D E F G J K L N RSWEP International AB Box 105, Hjalmar Brantings väg 5 SE-261 22 Landskrona, Sweden www.swep.netSSP G7 - (v 7.0.3.55)Side 1 87,50 0,324 0,478 967,1 4,205 0,6740Side 2 40,00 0,654 0,517 992,3 4,179 0,63068,7445,06 73,17 8120 58,44 0,189 30,341,94 64,43 17500 53,50 0,969 68,2Side 1Side 234,6 43,2 4,24 4,46 70,0 55,0 55,0 70,0 73,0 58,0 58,0 73,0 243 AISI 316 45/36 69 135/225ISO-G 2 1/2" A NON-CASTED(54) ISO-G 2" A NON-CASTED(54) ISO-G 2" A NON-CASTED(54) ISO-G 2 1/2" A NON-CASTED(54) F3/F2F1/F4mm mm mm mm mm mm mm mm mm mm mm mm374 +/-2 364 +/-1 284 +/-1 274 +/-1 54,1 +/-1 102 +0,5%/-1,5% 1,50 +/-1 7,50 48,5 41,0 41,0 49,0Date 2016-06-27Page 2(3)SWEP International AB Box 105, Hjalmar Brantings väg 5 SE-261 22 Landskrona, Sweden www.swep.netSSP G7 - (v 7.0.3.55)