Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
SR 45-78 16.9 496.0 11.3 45 17.5 9.8 42.5MAIN 78-45 16.6 496.0 11.3 45 18.1 496.0 8.3SR 45-78 16.9 496.0 11.3 45 18.2 496.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 26.0 67.0 30.3 45 26.6 81.3 25.0SR 12-36 24.0 69.5 29.8 36 23.7 70.3 27.2MAIN 12-36 35.5 459.0 -9.7 36 37.2 500.0 -15.3SR 36-45 37.7 497.0 -12.2 36 37.8 500.0 -15.30804000250 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 45 8.9 265.0 9.8SR 12 6.2 482.0 8.0MAIN 45 9.4 436.0 8.0SR 12 6.2 482.0 8.040010080250 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T 10GBASE-T ATM-155 TR-16 Active100BASE-TX 2.5GBASE-T ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 5GBASE-T ATM-51 TR-460402000250 MHzProject: DM 1-3 Building: DM 1-3 Rack: 10.05PpecuniaTester for DM 1-3.flw Floor: 10 etasjeTest Summary: PASS