Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
50…+600°C -50…+250°C0.14…0.20°C 0.06…0.12°CPCD3.W360:0.07…0.09°C (resolution <0.1°C)Technical dataInput ranges: Galvanic separation: Resolution (digital representation): Measuring principle: Input resistance:Maximum measurement current for temperature probes: Accuracy at 25°CRepeat accuracy: Temperature error (0…+55°C) Conversion time A/D: Overvoltage protection:Overcurrent protection:EMC protection: Time constant of input filter:see module overview no 12 bits (0…4095) non-differential, single-ended W300: 20 kΩ / 0.15% W310: 125 Ω / 0.1% W340: U: 200 kΩ / I: 125Ω W350: not relevant W360: not relevant 1.5 mA± 0.5%W300, 310: W340, 350, 360: ± 0.3% ± 0.05% ± 0.2% < 10 μs W340: W300 *): W340: W310 *): yes W300: W310: W340± 50 VDC (permanent) + 50 VDC (permanent) ± 40 mA (permanent) + 40 mA (permanent)typically 10.5 ms typically 12.4 ms typically 7.8 ms typically 24.2 ms typically 24.2 ms typically 16.9 ms typically 16.9 msV: C: T:W350: W360:6-64< 8 mA for all module types