Title: E.433.SK.U22.pdf
(-425&2x16A/C N DALI. 21 armaturer [BemA+62mAXF102 | I 5G2,5mm2 kw102 —| Tillys gymsal u27 2 adresser pr armatur |= 146mA2x16A/C DAL 19 armafurerXF103 | I 5G2,5mm2 kw103 —| Til lys garderober og korridor 1 adresse pr armatur Zaﬂg;?SMA2x16A/CXF104 — I? 362,5mm2 Kw104 —| Til lys U16, U17, U18, U19, U20, U21, U22, U24, U28, U29 og U322x16A/CXF105 - I¢ 362,5mm2 kwi1os —| Til lys U03, UO&, U6, U07, U09, U0, U12, U13, U1S og U252x16A/C i DALI. 10 armaturer 20mAXF106 | L 562,5mm2 Kw106 —| Til lys trapp UO1 1 adresse pr armatur2x16A/CXF107 —| I 362,5mm2 kw107 —| Til utebelysning fasade gymsal[ 12x16A/CXF108 —| I K 4G25mm2 AL kw108 —| Til lysmaster utvendig24G2,5mm2 Kw100 —| Til fotocelle fasade gymsalDato SideSmestad skoleU2 25.01.19 Zavih400V TN-S Tegn.nr. Rev.nr.KURS ENLINJESKJEMA KABELTYPE KABELNR. : ADRESSE MERKNADER|4x32A/C_£,XF200 1o 5G6mm2 KW200 —| Stikkontakt i lager U284x16A/C_ £, ¥XF201 1. 5G2,5mm2 KW201 -] Stikkontakt i tavle2x16A/C i