Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Attach the support to the run component by tightening the bolts to the correct torque.5Check that the width of the support is at right angles to the length of the run component6Use the template delivered with the support to drill the holes for mounting the wall brackets on the wall.7Mount the wall brackets on the wall.8Install the support of the run component on the wall bracket.9Attach the support using the screws supplied.10Check the distance between the end of the run component and the one directly below. It must be 40 ± 2 mm, which is the space required to install the joint block. If necessary, adjust the position of the support attached to the run component.11Align the run components with a 1-meter long leveling instrument. The maximum tolerance for misalignment is 2 mm to conform to the IP55 protection rating (seepage28).12Remove the nuts on the springs in the support that is fixed on the run component.13Install the joint block (seepage30).34