Title: Data tester Smestad skole - Detaljert.pdf
Copper Certification ReportCable Label: 521.002-UD-1 Date & Time: 16.01.2019 15:27:15 Limit Type: TIA - Cat 6A Permanent Link Cable Name: CAT 6A UTP Connector Name: UTP Mod Jack 6A Site: Smestad skole Operator Name: JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4Remote Ser. No.: Remote Adapter: Remote Calibration Date: Reporting Software:pw20201690 Cat 6A Link Apr 17 2013 Build_#972_7.4_2018-04-02_10-26-38Wiremap: PassLength (m): Cable NVP: Propagation Delay (ns): Delay Skew (ns): Resistance (Ohms):Value 57,4 68,0 298,0 17,0 9,3Limit 100,0 - 555,0 50,0 25,0Margin 42,6 - 257,0 33,0 15,7Wiremap: T568BInsertion Loss: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12 1,1 3,0 1,9 2,35Worst Value: Local: 36 24,2 43,6 19,4 498,00dB -20