Title: +038=433.002-FS034._06-Tavlebyggeren Eaton FDV.pdf
line voltage-dependent, 10 ms delay, 3 kA (8/20μs) surge current-proof 240 V AC, 50 Hz 204-260 V AC 195-264 V AC 30, 100 mA 0.55 In AC and pulsating DC, Type F according to IEC 62423 > 0.5 s 3 7.5 kA 10 kA 6 - 25 A 4 kV (1.2/50μs) B, C, D 100 A gL (>10 kA)electrical components mechanical components 4,000 operating cycles (In, Un, cos = 0.87)  10,000 operating cyclesMechanical Frame size Device height Device width Mounting Degree of protection switch Degree of protection, built-in Upper and lower terminals Terminal protection Terminal capacity Terminal screw Terminal torque Busbar thickness Operation temperature Storage- and transport temperature Resistance to climatic conditions Line side (supply) Load side