Title: +038=360.000-OU045T_04-PCD2.m4160 PLS SBC - IO Manual.pdf
The following connection diagram shows a typical wiring layout for: ● voltage inputs with the PCD2.W300 and  … W340 Modules or ● current inputs with the PCD2.W310 and  … W340 Modules9876543210COME7E6E5E4E3 E2E1E0m c 0 2Distributor *). x a mEarthing bar) potential freeThe reference potentials of signal sources should be wired to a common GND connection (“–” and “COM” terminals). To obtain optimum measurement results, any connection to an earthing bar should be avoidedThe reference potentials of signal sources should be wired to a common GND connection (“–” and “COM” terminals). To obtain optimum measurement results, any connection to an earthing bar should be avoidedIf shielded cables are used, the shield should be continued to an external earthing bar.If shielded cables are used, the shield should be continued to an external earthing bar.5-69The input signals for the temperature sensors are connected directly to the 10-pole terminal block (E0 … E7).