Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36-45 29,8 26,7 3,1 500,00dB 0501000Local250500 MHzdB 0501000Remote250500 MHzACR-F: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 12-36 20,2 10,4 9,8 489,00Remote: 12-36 19,6 10,4 9,2 487,00Worst Value: Local: 12-36 20,1 10,4 9,7 490,00Remote: 12-36 19,5 10,4 9,1 490,00dB -20401000Local250500 MHzdB -20401000Remote250500 MHzPS-NEXT: PassPair: Value (dB): Limit (dB): Margin (dB): Frequency (MHz):Worst Margin: Local: 36 27,4 23,9 3,5 496,00Remote: 45 28,0 23,8 4,2 500,00Worst Value: Local: 36 27,4 23,8 3,6 498,00Remote: 45 28,0 23,8 4,2 500,00PS-ACRF: Pass Worst Margin: Local: 36 19,6 7,4 12,2 489,00Worst Value: Local: 36 19,5 7,4 12,1 490,00Remote: 36 18,6 7,3 11,3 494,00Remote: 36 18,6 7,3 11,3 494,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:01Signature:______________________ Page: 51