Title: DM1-3 plan 10-11 lysberegningsrapport.pdf
The results were calculated without consideration of objects and furniture. No results were determined on their surfaces.DIALux Page 54Dronning Mauds gate 1-3 - 10. og 11. etasje 8/28/2019 Z E N ‘ S ‘ <Site 1/ Building 1/ Storey 10 / Resepsjon / Room summaryResepsjonReflection factors: Ceiling 70.0%, Walls 50.0%, Floor 20.0%, Light loss factor: 0.80Workplane Surface Result Average (Target) Min Max Min/average Min/max 1 Background area (Resepsjon) Perpendicular illuminance (adaptive) [Ix] 259 (= 300) 160 321 0.62 0.50 Height: 0.000 m, Wall zone: 0.300 m # Luminaire ®(Luminaire) [Im] Power [W] Luminous efficacy [Im/W] 9 iGuzzini illuminazione - Q497 Laser Blade XS - Downlight HC 12.4W 739 124 59.6 Total via all luminaires 6651 11.6 59.6Lighting power density: 5.96 W/m? (Floor area of room 18.73 m? ), Lighting power density: 8.05 W/m? = 3.10 W/m?/100 Ix (Area of working plane 13.86 m?)Consumption: 190 - 310 kWh/a of maximum 700 kWh/a