Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
30.3 496.0 41.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 7.4 472.0 29.2 36 6.7 475.0 26.2SR 36-45 7.7 482.0 28.7 36 8.3 457.0 27.1MAIN 36-45 8.0 497.0 28.0 36 7.4 500.0 25.0SR 36-45 8.1 497.0 28.0 36 9.0 498.0 25.110080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 17.3 485.0 11.5 45 18.2 13.8 39.5SR 45-78 17.7 489.0 11.4 45 18.2 19.4 36.5MAIN 78-45 17.5 499.0 11.3 45 18.5 485.0 8.5SR 45-78 17.8 499.0 11.3 78 20.0 499.0 8.30100806040200250 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 12-45 25.3 85.8 26.7 12 27.0 85.5 24.2SR 36-78 28.5 114.0 22.0 36 28.9 88.3 23.7MAIN 36-45 37.2 497.0 -12.2 36 36.9 500.0 -15.3SR 36-45 37.3 497.0 -12.2 45 38.0 496.0 -15.00804000250 MHzACR-N (dB)