Title: 2 etg del2.pdf
75100LinkWare Version 8.1Cable ID: T2029 Date / Time: 10/11/2013 09:32:27 AM Headroom 13.9 dB (NEXT 12-36) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]86 137 10 3.6Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]15.6 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 19.1 91.0 33.0 36 20.9 75.5 31.3SR 12-36 13.9 98.8 32.4 36 16.0 98.8 29.4MAIN 12-36 19.1 91.0 33.0 12 21.6 95.0 29.7SR 12-36 13.9 98.8 32.4 36 16.0 98.8 29.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)