Title: +038=522.000-NI002._02-Testrapport EKOM Anlegg Plan10 (Pecunia).pdf
Length (m), Limit 90.0 Prop. Delay (ns), Limit 496 Delay Skew (ns), Limit 43 Resistance (ohms), Limit 20.60[Pair 78] [Pair 45] [Pair 36] [Pair 45]32.3 140 2 4.84Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 45] [Pair 45] [Pair 45]26.7 500.0 41.6Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-36 7.1 500.0 29.2 36 7.0 500.0 26.4SR 36-45 6.3 494.0 29.4 36 7.1 497.0 26.4MAIN 12-36 7.1 500.0 29.2 36 7.0 500.0 26.4SR 36-45 6.3 494.0 29.4 36 7.1 497.0 26.410080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 78-45 16.6 500.0 11.3 45 17.4 49.3 28.4SR 45-78 16.5 452.0 12.1 45 17.3 35.0 31.4MAIN 78-45 16.6 500.0 11.3 45 17.8 500.0 8.3SR 45-78 16.9 500.0 11.3 45 17.5 498.0 8.30100806040200250 MHzACR-F (dB)