Title: økernvn 94.pdf
SR 36-45 20.3 98.8 18.7 36 21.9 98.8 15.701008060402002550 MHzACR-F (dB)PASS Worst Pair ACR-N (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-N (dB) Freq. (MHz) Limit (dB)MAIN 36-45 23.9 19.9 35.1 36 25.9 21.5 31.2SR 12-36 21.3 21.3 34.3 36 21.9 21.3 31.3MAIN 36-45 31.1 100.0 11.9 36 31.9 100.0 8.9SR 12-36 26.0 98.8 12.1 36 26.7 99.8 8.901008060402002550 MHzACR-N (dB)PASS Worst Pair RL (dB) Freq. (MHz) Limit (dB)MAIN 36 4.2 23.3 18.3SR 36 4.8 10.5 19.0MAIN 45 9.6 86.5 12.6SR 45 8.4 86.5 12.601008002550 MHzRL (dB)Compliant Network Standards: 10BASE-T 1000BASE-T ATM-155 TR-16 Active100BASE-TX ATM-25 100VG-AnyLan TR-16 Passive100BASE-T4 ATM-51 TR-4604020002550 MHzProject: OKERNVEIEN 94 3.ETG DEL 1 økernveien 94 3 og 4 etg.flwSite: OKERNVEIEN 9475757575Test Summary: PASSModel: DTX-1800 Main S/N: 9002041 Remote S/N: 9002042 Main Adapter: DTX-PLA002 Remote Adapter: DTX-PLA002182 ft60Insertion Loss (dB)