Title: +038=249.001-#####._01-10203518-01-RIA-NOT-007 Lydmålinger Collier_rev01.pdf
Dronning Mauds gate 1-3multiconsult.noKontrollmålinger av lydisolasjon plan 5, akse 0-8Vedlegg 2.2Apparent sound reduction index according to ISO 16283-1Field measurements of airborne sound insulation betw een roomsClient: Description:Dronning Maugs gt. 1- 3 Lydisolasjon fra korridor til møterom 5- 011Date of test:09.02.2022Object:Møterom med dør (glass og gipsvegg).Source room: korridorReceiving room: 5- 011Condition:Condition:Type:Type:Location:Location:Frequency range according to theArea of common partition:10,25m²curve of shifted reference values (ISO 717- 1)Source room volume:Receiving room volume:53m³→ ⎯ B d65FrequencyR',f1/3 octave'R[Hz]50[dB]22,7, x e d ni55638010012516020025022,518,110,520,325,824,628,3n o i t c u d e r d n u o s t n e r a p p A4531530,73540033,050033,463032,0800