Title: +038=433.000-NI003._06-Testrapport elektriske anlegg - DM3.E6.433.09.03, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 15.06.2020 08:37Tallberg Elektro A/S Tlf.22796640Side:16GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*Nr.114114115115116116117117118118119119120120TEST RAPPORTResultatZ-LINEZ: 0.37ΩIsc: 621A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 15.06.2020 08:38Zs(rcd)Z: 0.31ΩIsc: 740A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 15.06.2020 08:38RCD UbUc: 0.2V Rl: 6Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 15.06.2020 12:48R LOW OhmR: 0.21ΩR+: 0.2Ω R-: 0.2Ω Grenseverdi: 1.0ΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 16.06.2020 09:49R ISOR: >200MΩ Um: 263VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E6.433.09.03 / XF049 C16/2 16.06.2020 09:55R ISO