Title: +038=432.001-KS001 04-Canalis KT Schneider Installasjonsveiledning.pdf
Catalogue numberKTAKTCVertical supportWall brackets800 to 16001000 to 2000RearKTB0164ZA51KTB0164ZA5220002500SideKTB0204ZA51KTB0204ZA5225003200SideKTB0244ZA51KTB0244ZA5232004000SideKTB0324ZA51KTB0324ZA5240005000SideKTB0404ZA51KTB0404ZA5250006300Side2xKTB0244ZA51Not provided by Schneider Electric.ProcedureThe procedure for installing vertical supports and run components is described in instruction sheets available on the Schneider Electric website:  For Canalis KT rear-wall fixing system: PHA12613.  For Canalis KT side-wall fixing system: PHA12664.StepAction1Before installing the vertical supports, consult the general installation rules (seepage22).2Check that the adjoining run component directly below the one being installed is in place.3Set the spring compression value on the support. The value of the spring compression depends on the rating of the run component.4