Title: 1 etg del 2.pdf
Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 45] [Pair 12] [Pair 12] [Pair 12]305 484 35 12.9305 ftWire Map (T568B) PASS60Insertion Loss (dB)Insertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 12] [Pair 12] [Pair 12]3.7 250.0 30.750403020Worst Case Margin Worst Case Value10PASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 36-45 1.1 249.5 35.4 36 1.0 * 240.5 33.0SR 36-450.5 *248.5 35.4 36 0.2 *245.0 32.9MAIN 36-45 1.1 249.5 35.4 36 1.0 240.5 33.0SR 36-45 0.5 248.5 35.4 36 0.3 250.0 32.710080604020NEXT (dB)001008060402050100150200MHzNEXT @ Remote (dB)250PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)MAIN 45-36 14.6 37.8 32.7 36 16.8 32.0 31.1SR 36-45 14.7 37.8 32.7 45 17.0 28.6 32.1MAIN 36-12 18.8 230.5 16.9 12 19.6 228.5 14.0