Title: Simployer - Data testrapport =514.204-FS001.pdf
Cable ID: 521.204-UD72 Date / Time: 28/01/2022 13:33:08 Headroom 7.0 dB (NEXT 1,2-3,6) Test Limit: EN50173 Channel Class E Cable Type: Cat 6 F/UTP NVP: 70.0%Operator: TORKIL GRIMSMO Software Version: 2.7800 Limits Version: 1.9500 Calibration Date: Main (Tester): 20/01/2009 Remote (Tester): 20/01/2009Length (m) Prop. Delay (ns), Limit 555 Delay Skew (ns), Limit 50 Resistance (ohms), Limit 25.0[Pair 1,2] [Pair 3,6] [Pair 3,6] [Pair 3,6]50.4 258 18 9.0Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 3,6] [Pair 3,6] [Pair 3,6]20.8 250.0 35.9Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 1,2-3,6 7.2 18.8 52.1 3,6 9.2 18.6 49.5SR 1,2-3,6 7.0 18.6 52.1 3,6 8.9 18.6 49.5MAIN 1,2-3,6 10.5 246.5 33.2 1,2 11.3 246.5 30.3SR 3,6-7,8 9.5 234.0 33.6 3,6 10.6 245.5 30.3PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)