Title: DOCA0005EN-12.pdf
Set the active tariff:1 = Rate A (tariff 1)2 = Rate B (tariff 2)0002E001 0000101, 2, 3, 43 = Rate C (tariff 3)4 = Rate D (tariff 4)NOTE: You can only set the tariff using this method if the Tariff Mode is set to by Communication.DOCA0005EN-12iEM3000 series user manualDOCA0005EN-12Communications via M-BusCommunications setupSND_UD code Data format Primary VIFRange/optionsDescription00017A0-250Primary addressTo change the baud rate via communications, send a telegram to the meter with the appropriate value in the CI-field:Baud rateHex value for CI-field300B8600B91200BA2400BB4800BC9600BDDigital input setupNOTE: E denotes the extension bit; the hex value assumes E = 0.SND_UD codeData formatManufacturer- specific VIFERange/optionsDescriptionbinhexDigital input control mode0002E001 1011 1B0, 3, 50 = Normal (Input Status)3 = Input metering5 = Partial energy reset0005E010 1111 2F1-10000