Title: +038=365.009-SS002._03-mcr WIPT Stengespjeld Mercor - Installasjonsmanual.pdf
RST/KW1 trigger control gearThe RST/KW1/S version has the limit switches installed in the gear itself. The electrical connections shall be made by connecting the properly labelled conductors to the electrical system. A fusible trigger is installed in the gear. The dampers with the RST/KW1/230I, RST/KW1/230P mechanisms, are supplied with the RST/KW1/24... triggering and control mechanism, together with the 230/24V transformer module type MP230/24.RST/KW1/SRST/KW1/24IRST/KW1/24PRST/KW1/24I +MP230/24RST/KW1/24I+MP230/24Supply voltageX24 V – 48 V DC24 V – 48 V DC230V AC230V ACPower consumptionX3.5 W1.6 W4.5 W2.5 WHolding forceX12 daN12 daN12 daN12 daNThermal trigger trip point72°C +-2°CWK1d / WK2d limit switchNO/NC (switching contact)5A, 230V ACSwitch trigger3°, 87° – tolerance: +/- 2°Limit switch operating temperature25 ...+85°Crelease: cable 0.6 m, 2x0.5 mm2Electrical connectionXlimit switch: cable 0.6 m, 6x0.5 mm2Rotation angle92°