Title: 1 etg del 2.pdf
MHzLinkWare Version 8.1Cable ID: T1229 Date / Time: 10/17/2013 02:11:18 PM Headroom 20.8 dB (NEXT 36-78) Test Limit: EN50173 PL Class D Cable Type: Cat 6 UTP Calibration Date: 07/29/2013Operator: ROLF Software Version: 2.7400 Limits Version: 1.9300 NVP: 69.0%Length (ft) Prop. Delay (ns), Limit 498 Delay Skew (ns), Limit 44 Resistance (ohms), Limit 21.0[Pair 12] [Pair 45] [Pair 45] [Pair 36]78 119 4 3.5Wire Map (T568B) PASSInsertion Loss Margin (dB) Frequency (MHz) Limit (dB)[Pair 36] [Pair 36] [Pair 36]15.8 100.0 20.4Worst Case Margin Worst Case ValuePASS Worst Pair NEXT (dB) Freq. (MHz) Limit (dB) Worst Pair PS NEXT (dB) Freq. (MHz) Limit (dB)MAIN 12-78 21.9 91.0 33.0 78 21.7 83.8 30.6SR 36-78 20.8 92.5 32.9 36 21.4 92.5 29.9MAIN 12-78 21.9 91.0 33.0 78 22.7 100.0 29.3SR 36-78 20.8 92.8 32.8 36 21.4 92.5 29.910080604020NEXT (dB)PASS Worst Pair ACR-F (dB) Freq. (MHz) Limit (dB) Worst Pair PS ACR-F (dB) Freq. (MHz) Limit (dB)