Title: +135.01=370.002-LC002T_04-SkyStar_UK_cat_99A4790100_Rev_N_02_17_s.pdf
6Emission of 4 pipe units with standard cooling batterySkyStarCooling emission of 2 battery units (4 pipe installation) +27°C d.b. Entering air temperature:+19°C w.b.Model SpeedAir flowEWT 5 - LWT 10°C Total emissionWater flowSensible emissionEWT 7 - LWT 12°C Total emissionWater flowSensible emissionEWT 9 - LWT 14°C Total emissionWater flowSensible emissionEWT 12 - LWT 17°C Total Water emission flowSensible emissionSK 04SK 14SK 24SK 34SK 44SK 54SK 64High Med Low High Med Low High Med Low High Med Low High Med Low High Med Low High Med Lowm3/h 610 420 310 520 420 310 710 500 320 880 610 430 1140 820 630 1500 970 710 1820 1280 710l/h 490 410 314 569 465 398 718 569 398 791 632 510 1299 1027 842 1588 1158 920 1836 1423 920kW 2,85 2,38 1,82 3,31 2,71 2,31 4,18 3,31 2,31 4,60 3,67 2,97 7,55 5,97 4,89 9,23 6,73 5,35 10,67 8,27 5,35kW 2,12 1,73 1,29 2,26 1,83 1,55 2,91 2,26 1,55 3,23 2,53 2,01 5,12 4,00 3,24 6,35 4,53 3,56 7,43 5,64 3,56