Title: DOCA0005EN-12.pdf
The meter complies with the European Measuring Instruments Directive (MID) 2014/32/EU when installed in a suitable switchboard in accordance with the instructions in DOCA0038EN, available on our website. The CE declaration document is also available; search for ECDiEM3000.DOCA0005EN-12121ValueMetersTypeTime errorBackup timeQuartz crystal basedBackup by supercapacitor< 2.5 s/day (30 ppm) at 25°C (77°F)> 3 days at 25°C (77°F)iEM3115 / iEM3135 / iEM3155 / iEM3165 / iEM3175 / iEM3215 / iEM3235 / iEM3255 / iEM3265 / iEM3275 / iEM3335 / iEM3355 / iEM3365 / iEM3375/ iEM3455 / iEM3465 / iEM3555 / iEM3565Modbus communicationsCharacteristicValueMetersNumber of ports1Labels0V, D0/-, D1/+(shield)ParityEven, Odd, NoneBaud rateIsolation9600, 19200, 384004.0 kV rmsiEM3150 / iEM3155 / iEM3250 / iEM3255 / iEM3350 / iEM3355 / iEM3455 / iEM3555Wire2.5 mm2 / 14 AWG shielded twisted pairWire strip length7 mm / 0.28 inTorque0.5 Nm / 4.4 in•lbRelated topics