Title: +038=360.000-OU045T_03-PCD2.m4160 PLS SBC - Hardware Manual.pdf
Hardware Manual for the PCD2.M5 Series│Document 26/856; Version EN 09│2012-01-253-14Saia-Burgess Controls Ltd.PCD2.M5_ Classic CPUs and expansion housingsExpansion housings3.4.5 Addressing of module holders and modulesSockets numbered clockwise from 0 to 7. All modules of types E, A, W and H can run in any socket, except Slot 15 (grey). No modules of type W or H can be plugged in here. If the manual and emergency control modules are needed, PCD3 modules and module holders have to be used. The same applies to the realisation of RIO nodes. For these applications, refer to the PCD3 Manual 26/7893The PCD2.T8xx modems cannot be used on all slots; please refer to Manual 26/771 for these modules.PCD2.M5_PCD3.C1x0 PCD3.C200PCD2.C1000...15 016...31 132...47 248...63 3128...1438144...1599160...17510176...19111128...143 144...159 160...175 176...191324810 2 192...207 208...223 224...239 240...2551320 2 256...271 272...287 288...303 304...319133