Title: 32 Pumper modbuss teknisk data.pdf.pdf
Automatic motor model recognition failed243Motor relay has been forced (manually operated or commanded)244Fault, On/Off/Auto switch245Pump continuous runtime too long246User-defined relay has been forced (manually operated or commanded)247Power-on notice, (device or system has been switched off)248Fault, battery/UPS249User-defined event 1250User-defined event 2251User-defined event 3252User-defined event 4253SMS data from DDD sensor not received within time limit254Inconsistent data modelThe built-in webserver offers easy monitoring of the CIM 500 module and makes it possible to configure the selected Industrial Ethernet protocol. Using the webserver, you can also update the firmware of the CIM 500 module and store or restore settings, among other functions.To connect a PC to CIM 500, proceed as follows:1. Connect the PC and the module using an Ethernet cable.