Title: +038=433.000-NI003._04-Testrapport elektriske anlegg - DM3.E2.433.09.01, Pareto plan 09.pdf
DM1-3. Plan 9 / DM3.E2.433.09.01 / XF048 C16/2 11.06.2020 15:20R ISOR: >200MΩ Um: 262VUiso: 250V Grenseverdi: 1MΩDM1-3. Plan 9 / DM3.E2.433.09.01 / XF048 C16/2 11.06.2020 16:03RCD II: 28.5mAUci: 0.2V t: 82.2ms Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF048 C16/2 12.06.2020 09:45Tallberg Elektro A/S Tlf.22796640Side:37GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*GODKJENT*GODKJENTGODKJENT*GODKJENTGODKJENT*Nr.253253254254255255256256257257258258259259TEST RAPPORTResultatZ-LINEZ: 0.94ΩIsc: 246A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF048 C16/2 12.06.2020 09:53Zs(rcd)Z: 0.87ΩIsc: 263A Sikringstype: C SIKRING I: 16A SIKRING T: 35ms Isc_lim: 160.0ADM1-3. Plan 9 / DM3.E2.433.09.01 / XF048 C16/2 12.06.2020 09:54RCD UbUc: 0.1V Rl: 5Ω Idn: 30mA type: AC Ulim: 25VDM1-3. Plan 9 / DM3.E2.433.09.01 / XF048 C16/2 12.06.2020 12:00