Title: Data tester Smestad skole - Detaljert.pdf
Remote: 36 28,3 23,9 4,4 496,00Worst Value: Local: 36 27,1 23,8 3,3 500,00Remote: 36 28,3 23,9 4,4 496,00PS-ACRF: Pass Worst Margin: Local: 12 73,5 61,2 12,3 1,00Worst Value: Local: 45 20,9 8,0 12,9 459,00Remote: 45 72,7 61,2 11,5 1,00Remote: 36 20,7 7,4 13,3 489,00Network Compliance:10BASE-T, 100BASE-T, 1000BASE-T, 10GBASE-T, manufacturer should state AXT compliancePrinted: 11.02.2019 15:07:00Signature:______________________ Page: 42Copper Certification ReportCable Label: 521.002-UD-140 Date & Time: Limit Type: Cable Name: Connector Name: Site: Operator Name:07.02.2019 11:52:16 TIA - Cat 6A Permanent Link CAT 6A UTP UTP Mod Jack 6A Smestad skole JosteinBuilding: Floor: Room: Rack: Panel:Unspecified-Building Unspecified-Floor Unspecified-Room Unspecified-Rack Unspecified-PanelOverall Result:Local Ser. No.: Local Adapter: Local Calibration Date: Device Software:pw20201689 Cat 6A Link Apr 17 2013 7.4