Title: 360.001 - Tilluft.pdf
3.03.40.0 +0.05.06.0 +0.0 2.56.0 +0.0 2.54.60.0 +0.09.80.0 +0.08.68.60.3 +4.0Lp [dB]9,7LocationLevel2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. Etasje2. EtasjeNodeTypeProductBEND-90MAGIB-C3-90-200DUCTMAGID-C1-200BEND-30MAGIB-C3-30-200DUCTMAGID-C1-200BEND-90MAGIB-C3-90-200DUCTMAGID-C1-200FIREDAMPER FKRS-EU/200/ZXXDUCTMAGID-C1-200SILENCERLKR-200-1200DUCTMAGID-C1-200200200200200200200200200200200SizeSound Calculation ReportL [m]qv [m³/h]v [m/s]dpt [Pa]4504,00,34504,04504,00,64504,04504,00,14504,04504,00,34504,04504,00,84504,0512,7 Sound in:Attenuation: Addition:0,3 Sound in:Attenuation: Addition:0,9 Sound in:Attenuation: Addition:0,6 Sound in:Attenuation: Addition:2,7 Sound in:Attenuation: Addition:0,1 Sound in:Attenuation: Addition:4,2 Sound in:Addition:0,3 Sound in: