_:n7d56588bec9142e68e46f8f0884da364xb0
<http://schema.org/description>
"Smart-UPS C 3000VA rack mount LCD 230V (SMC3000RMI2U)\n\nEfficient, true sine-wave power protection for entry-level servers and network equipment.\nThe most affordable true sine-wave UPS’s in the Smart-UPS family . Designed for entry level servers, it is compatible with today’s active power factor corrected (PFC) power supplies. Included PowerChute Business Edition software is compatible with all major server operating systems and provides UPS management and safe system shutdown.\nSpecification\n\n\n\nMain Input Voltage\n230 V\n\n\nMain Output Voltage\n230 V\n\n\nrated power in W\n2100 W\n\n\nRated power in VA\n3000 VA\n\n\nInput Connection Type\nIEC 320 C20\n\n\noutput connection type\n8 IEC 320 C132 IEC Jumpers1 IEC 320 C19\n\n\nNumber of rack unit\n2U\n\n\nNumber of cables\n1\n\n\nBattery type\nLead-acid battery\n\n\nProvided equipment\nCD with softwareDocumentation CDInstallation guideRack mounting bracketsUSB cable\n\n\n\n\nBatteries &amp; Runtime\n\n\nRun Time\n\nView Runtime Graph\n\naction_new_window\n\n\n\n\nEfficiency\n\nView Efficiency Graph\n\naction_new_window\n\n\n\n\nExtended runtime\n0\n\n\nNumber of battery filled slots\n0\n\n\nNumber of battery free slots\n0\n\n\nBattery recharge time\n3 h\n\n\nNumber of battery replacement quantity\n1\n\n\nBattery life\n3…5 year(s)\n\n\nReplacement battery\n\nAPCRBC151\n\naction_new_window\n\n\n\n\nBattery power in VAH\n490 VAh runtime\n\n\nBattery charger power\n163 W rated\n\n\n\n\nGeneral\n\n\nNumber of power module filled slots\n0\n\n\nNumber of power module free slots\n0\n\n\nproduct web sub-family\nEntry level\n\n\nRedundant\nNo\n\n\n\n\nPhysical\n\n\nColour\nBlack\n\n\nHeight\n8.9 cm\n\n\nWidth\n48 cm\n\n\nDepth\n67 cm\n\n\nNet weight\n41 kg\n\n\nMounting location\nFront\n\n\nMounting preference\nLower\n\n\nMounting mode\nRack-mounted\n\n\nTwo post mountable\n0\n\n\nUSB compatible\nYes\n\n\n\n\nInput\n\n\nInput voltage limits\n180...287 V\n\n\nNetwork frequency\n50/60 Hz +/- 3 Hz auto-sensing\n\n\n\n\nOutput\n\n\nHarmonic distortion\nLess than 5 %\n\n\nMaximum configurable power in VA\n3000 VA\n\n\nMaximum configurable power in W\n2100 W\n\n\nTransfer time\n8 ms typical : 10 ms maximum\n\n\nUPS type\nLine interactive\n\n\nWave type\nSine wave\n\n\nOutput frequency\n50 Hz sync to mains\n\n\n\n\nConformance\n\n\nProduct certifications\nC-TickCEEACGOSTIRAMSABSVDE\n\n\nMarking\nGS Mark\n\n\nStandards\nEN/IEC 62040-1:2019/A11:2021EN/IEC 62040-2:2006/AC:2006EN/IEC 62040-2:2018\n\n\n\n\nEnvironmental\n\n\nAcoustic level\n42 dBA\n\n\nheat dissipation\n81 Btu/h\n\n\nOperating altitude\n0...10000 ft\n\n\nAmbient air temperature for operation\n0…40 °C\n\n\nAmbient air temperature for storage\n-15…45 °C\n\n\nStorage altitude\n0.00…15240.00 m\n\n\nRelative humidity\n0…95 %\n\n\nStorage Relative Humidity\n0…95 %\n\n\n\n\nCommunications &amp; Management\n\n\ncontrol panel\nMultifunction LCD status and control console\n\n\nFree slots\n0\n\n\nAlarm\nAlarm when on battery : distinctive low battery alarm : configurable delays\n\n\n\n\nSurge Protection and Filtering\n\n\nSurge energy rate\n300 J\n\n\nNoise suppression\nFull time multi-pole noise filtering : 0.3% IEEE surge let-through : zero clamping response time : meets UL 1449\n\n\n\n\nPacking Units\n\n\nUnit Type of Package 1\nPCE\n\n\nNumber of Units in Package 1\n1\n\n\nPackage 1 Height\n25.4 cm\n\n\nPackage 1 Width\n98 cm\n\n\nPackage 1 Length\n60 cm\n\n\nPackage 1 Weight\n50.9 kg\n\n\n\n\nContractual warranty\n\n\nWarranty\n2 years repair or replace\n\n\n"
<https://shop.winpro.com.my/products/smart-ups-c-3000va-rack-mount-lcd-230v-smc3000rmi2u>