_:n23a9c5555bde4451a0d8e81bbcf69d02xb0
<http://schema.org/description>
"Product Details\n  \n\nNumber of poles: 3P\n\n  \n\n[In] rated current: 50A at 40  °C\n\n  \n\n[Ue] rated operational voltage: 690 V AC 50/60 Hz conforming to EN/IEC 60947-2\n\n  \n\nSuitability for isolation: Yes conforming to EN/IEC 60947-2\n\n  \n\nUtilisation category: Category A\n\n  \n\n\n[Icu] rated ultimate short-circuitbreaking capacity: 25 kA Icu at 415 V AC 50/60 Hz conforming to EN 60947-2\n\n\n  \n\nPerformance level: B\n\n  \n\nTrip unit name: TM-D\n\n  \n\nTrip unit technology: Thermal-magnetic\n\n  \n\nTrip unit protection functions: LI\n\n  \n\nControl type: Toggle\n\n  \n\n[Ui] rated insulation voltage: 800 V AC 50/60 Hz conforming to EN/IEC 60947-2\n\n  \n\n\n[Uimp] rated impulse withstandvoltage: 8 kV conforming to EN/IEC 60947-2\n\n\n  \n\n\n[Ics] rated service short-circuitbreaking capacity: 25 kA at 415 V AC 50/60 Hz conforming to EN/IEC 60947-2\n\n\n  \n\n\nMechanical durability: 50000 cycles\n\n  \n\n\nElectrical durability: \n\n50000 cycles at 440 V In/2\n30000 cycles at 440 V In\n20000 cycles at 690 V In/2\n10000 cycles at 690 V In\n\n\n\n  \n\n\nProtection type: \n\nL : for overload protection (long time)\nI : for short-circuit protection (magnetic)\n\n\n\n  \n\n\nLong-time pick-up adjustment type Ir (thermal protection): Adjustable\n\n\n  \n\n\n[Ir] long-time protection pick-up adjustment range: 0.7...1 x In\n\n\n  \n\n\nLong-time protection delay adjustment type tr: Fixed\n\n\n  \n\n\n[Tr] long-time protection delay adjustment range:\n\n120â€¦400 s at 1.5 x Ir\n15 s at 6 x Ir\n\n\n\n  \n\n\nInstantaneous protection pickup adjustment type Ii: Fixed\n\n\n  \n\n\n[Ii] instantaneous protection pick-up adjustment range: 190 A\n\n\n  \n\nDimensions (HxWxD): 161 x105 x 86mm\n\n  \n\nNet weight 2.05 kg\n\n  \n\n\nStandards: \n\nEN/IEC 60947-1\nEN/IEC 60947-2\n\n\n\n  \n\nPollution degree 3 conforming to IEC 60664-1\n\n  \n\nIP degree of protection IP40 conforming to IEC 60529\n"
<https://www.falconelectrical.co.uk/products/schneider-electric-il0503p25-50a-mccb-for-i-line-panelboards>