_:n72e473dc3430473984e6a6b72f057446xb0
<http://schema.org/description>
"Overview\nMitsubishi Electric PEAD-M60JAADR1.TH / SUZ-M60VAD-A.TH 6kW Low Profile Ducted Air Conditioner System | 1 Phase\nMitsubishi Electric's PEAD-M60JAA ducted air conditioner has a low profile construction. This allows for installation in tight ceiling spaces.\n\n6kW Cooling – 7kW Heating Capacity\n\nPEAD-M60JAADR1.TH : Low Profile Indoor – Ducted with Drain Pump\n\n\n\nSUZ-M60VAD-A.TH: R32 Outdoor – DRED Capable\n\n\n\nPAR-40MAA: Backlit Wired Control\nSpecifications\n\n\n\n\n\nPEAD-M Series (Ceiling Concealed)\n\n\nIndoor Unit\nPEAD-M60JAAD\n\n\nOutdoor Unit\nSUZ-M60VAD-A\n\n\n\nRefrigerant\n \nPower Supply (V, Phase, Hz)\n\nR32\n\n\nV:230V, Single-phase, 50/60Hz\n\n\n \n \n \n \n \n \nCooling\n\n\nCapacity\n \n[Min-Rated*4-Max]               kW\nTotal Input [Rated]*4            kW AEER/EER\n\n2.30 – 6.00 – 6.50\n\n\n1.72\n\n\n3.43/3.48\n\n\n\nAEER [Part-Load %]*1 Running Current [Rated]*4\n \nSound         In (Lo-Mid-Hi) Pressure\nLevel*2                 Out (PWL)\nAir Volume (In) Lo-Mid-Hi\n\n \n \nA\n\n–\n\n\n7.50\n\n\n \n \ndB(A)\n\n30 – 32 – 36\n\n\n49 (65)\n\n\nL/S\n242 – 300 – 350\n\n\n \n \n \n \n \n \nHeating\n\n\nCapacity\n \n[Min-Rated*5-Max] Total Input [Rated]*5 COP/ACOP\nRunning Current [Rated]*5\nSound         In (Lo-Mid-Hi) Pressure\nLevel*2                 Out (PWL)\nAir Volume (In) Lo-Mid-Hi\n\n\nkW kW\n \n \nA\n\n2.80 – 7.00 – 8.00\n\n\n1.85\n\n\n3.78/3.72\n\n\n8.10\n\n\n \n \ndB(A)\n \nL/S\n\n30 – 32 – 36\n\n\n51 (68)\n\n\n242 – 300 – 350\n\n\n\nMax. Running Current\n \nInput [Rated] (Cooling/Heating)\n\n\nA\n \nkW\n\n14.80\n\n\n0.12/0.10\n\n\nIndoor Unit\nDimensions [HxWxD]          mm\n250 x 1100 x 732\n\n\nWeight                              kg\n–\n\n\nStatic Pressure                  Pa\n35/50/70/100/125\n\n\n \n \nOutdoor Unit\n\nDimensions [HxWxD]          mm\n880 x 840 x 330\n\n\nWeight                              kg\n54.0\n\n\nBreaker Size                      A\n20\n\n\n\nExt.         Diameter [Liquid/Gas]         mm\n\nø6.35/ø15.88\n\n\n\nPiping     Max. Length/Height\n \nGuaranteed                Cooling Operating Range\n[Outdoor]                   Heating\nPre-Charge Refrigerant\n\n\nm\n \n°C\n°C\n\n30/30\n\n\n-15 ~ 52*2\n \n-15 ~ 24\n\n\n\nkg\n1.60 (7m)\n\n\nAdditional Refrigerant                       g/m\n20\n\n\n\n\n\n\n\n\n\n"
<https://www.ozaironline.com.au/collections/ducted-air-conditioners/products/mitsubishi-electric-6kw-inverter-ducted-air-conditioner-pead-m60jaa>