<http://schema.org/description>
"OTi DALI 25/220-240/700 LT2&lt;br/&gt;&lt;br/&gt;&lt;b&gt;Product benefits&lt;/b&gt;&lt;br/&gt;&lt;br/&gt;    Versatile DALI window driver due to flexible output characteristic&lt;br/&gt;    Very high efficiency and reliability&lt;br/&gt;    Protection of the system thanks to thermal management and Smart Control&lt;br/&gt;&lt;br/&gt;&lt;b&gt;Product features&lt;/b&gt;&lt;br/&gt;&lt;br/&gt;    Supply voltage 220-240 V&lt;br/&gt;    Line frequency 0 Hz - 50 Hz - 60 Hz&lt;br/&gt;    Line voltage 198-264 V&lt;br/&gt;    Safety according to EN 61347-1, 61347-2-3, 61347-2-13, 62384&lt;br/&gt;    RI suppression according to EN 55015:2007+A1:2007/CDN&lt;br/&gt;    Line harmonics according to EN 61000-3-2&lt;br/&gt;    Immunity according to EN 61547&lt;br/&gt;    Lifetime up to 100000 h (temperature at Tc = 65 C, max. 10 % failure rate)&lt;br/&gt;    LED protection by Hot Plug&lt;br/&gt;&lt;br/&gt;&lt;b&gt;Versatile scope of application due to OSRAM DALI Technology&lt;/b&gt;&lt;br/&gt;&lt;br/&gt;    Easy to use in corridors and restrooms because of three-level Corridor function&lt;br/&gt;    Touch DIM application: easy to control via pushbutton or sensor&lt;br/&gt;    Energy efficient Touch DIM operation due to automatic  switch-off at sufficient residual light&lt;br/&gt;    Suitable for emergency Installations (acc. to EN 60598-2-22 and IEC 61347-2-13, appendix J) thanks to DC detection (0 Hz, pulsating DC), on/off switchable&lt;br/&gt;    Feedback of power consumption and operating hours (Fit for SMART GRID)&lt;br/&gt;    Suitable for buildings according to EPBD/BREEAM/LEED due to automatic Constant Lumen Output setting&lt;br/&gt;&lt;br/&gt;&lt;b&gt;Areas of application&lt;/b&gt;&lt;br/&gt;&lt;br/&gt;    Installation in emergency lighting systems according to IEC 61347-2-3, appendix J&lt;br/&gt;    Suitable for use in luminaires with flexible current setting (DALI, CLO, LEDset)&lt;br/&gt;    Suitable for indoor SELV equivalent installations&lt;br/&gt;    Suitable for luminaires of protection classes I and II&lt;br/&gt;    Installation and independent mounting via Cable Clamp Kit possible&lt;br/&gt;&lt;br/&gt;EAN: 4052899919457&lt;br/&gt;Nominal output power: 27 W&lt;br/&gt;Partial load (not dimmed): 7 - 27 W&lt;br/&gt;Input voltage AC: 198-264 V&lt;br/&gt;Mains frequency: 50/60 Hz&lt;br/&gt;Nominal output voltage: 12-54 V (max. 60V)&lt;br/&gt;Nominal output current: 180-700 mA (+/- 5%)&lt;br/&gt;Nominal voltage: 220-240 V&lt;br/&gt;Nominal current (at 230V): 0.14 A&lt;br/&gt;Device power loss (max): &lt;0.5 W&lt;br/&gt;Power factor ?: 0.95&lt;br/&gt;ECG efficiency (full load at 230 V): 86 %&lt;br/&gt;Inrush current: 17 A&lt;br/&gt;Max. no. of ECGs on circuit breaker 10 A: 45&lt;br/&gt;Max. no. of ECGs on circuit breaker 16 A: 80&lt;br/&gt;Galvanic isolation primary/secondary (SELV equivalent): 3.75 kV&lt;br/&gt;Surge capability (L-N): 1 kV&lt;br/&gt;Length: 103 mm&lt;br/&gt;Width: 67 mm&lt;br/&gt;Height: 29.5 mm&lt;br/&gt;Product weight: 149 g&lt;br/&gt;Mounting hole spacing, length: 94 mm&lt;br/&gt;Mounting hole spacing, width: 58 mm&lt;br/&gt;Cable cross-section, input side: 0.2 - 1.5 sqmm (flexible/solid leads)&lt;br/&gt;Cable cross-section, output side: 0.2 - 1.5 sqmm (flexible/solid leads)&lt;br/&gt;Wire preparation length, input side: 8.0 - 9.0 mm&lt;br/&gt;Casing material: Plastic&lt;br/&gt;Ambient temperature range: -20 +50 C&lt;br/&gt;Temperature range at storage: -25 +85 C&lt;br/&gt;Maximum temperature at tc test point: 75 C&lt;br/&gt;Max.housing temperature in case of fault: 110 C&lt;br/&gt;ECG lifetime (at max Tc/10% failure rate) : 50000 h&lt;br/&gt;Encapsulated: No&lt;br/&gt;Dimmable: Yes&lt;br/&gt;Dimming range: 1 - 100 %&lt;br/&gt;Suitable for fixtures with prot. class: I / II&lt;br/&gt;Dimming interface: DALI / Touch DIM / Touch DIM Sensor &lt;br/&gt;Constant lumen function: Programmable&lt;br/&gt;NTC input: No&lt;br/&gt;Overheating protection: Automatic reversible&lt;br/&gt;Overload protection: Automatic reversible&lt;br/&gt;Short-circuit protection: Automatic reversible&lt;br/&gt;No-load proof: Yes&lt;br/&gt;Max. cable length to lamp/LED module: 2 m&lt;br/&gt;Type of protection: IP20&lt;br/&gt;Standards: Acc. to EN 61347-1/Acc. to EN 61347-2-13/Acc. to EN 55015/Acc. to EN 61547/Acc. to EN 61000-3-2/Acc. to EN 62384 &lt;br/&gt;Approval marks - approval: ENEC 10 / VDE / EMC / EL / CE&lt;br/&gt;Manufacturer's Website: www.osram.com/osram_com/products/led-technology/electronic-control-gears-for-led-modules-and-dimmers/indoor-ecg-for-led-modules-and-dimmers/constant-current-dimmable/cc-power-supplies-with-dali&lt;br/&gt;&lt;br/&gt;"^^<http://www.w3.org/2001/XMLSchema#string>
<http://www.pennelcomonline.com/en/Osram-OT-DALI-25220-240700-LT2-Constant-Current-4052899919457/m-8765.aspx>