     if (tempSplit > 15) // > 15F is an acceptable split for alarm purposes (usually 20F in real life).
     {
       alarmFor = 0; // Resets alarm counting "latch."
-      alarmTime = 0; // Resets 120s alarm.
+      alarmTime = 0; // Resets splitAlarmTime alarm.
     }
     else
     {
       if (alarmFor == 0)
       {
-        alarmTime = secondsCount + 120; // This sets the 120s alarm (from split out of spec to notification being sent)
+        alarmTime = secondsCount + splitAlarmTime; // This sets the alarm time (from split out of spec to notification being sent)
         alarmFor++; // Locks out alarm clock reset until alarmFor == 0.
       }
     }

      // Create runTimeMin and runTimeHour variables (look at hours floating point)
      runTimeMin = ( (onNow - offNow) / 60 ); // Still need to make this report 'right' time on first run!
      runTimeHour = ( runTimeMin / 60 );
      if (runTimeMin > 120)
      {
      Blynk.tweet(String("A/C ON after ") + runTimeHour + " hours of inactivity. " + hour() + ":" + minute() + ":" + second() + " " + month() + "/" + day() + "/" + year());
      xStart++;

int alarmFor = 0;
int xFirstRun = 0;
int resetTattle = 0;
int splitAlarmTime = 180; // 180s (3 min) timeout after a high split reading

unsigned long onNow = now();
unsigned long offNow = now(); // To prevent error on first Tweet after blower starts - NOT WORKING YET
