 DeviceAddress ds18b20SA = { 0x28, 0xF1, 0xAC, 0x1E, 0x00, 0x00, 0x80, 0xE8 }; // Supply air probe
 
 char auth[] = "fromBlynkApp"; // HVAC Production
+//char auth[] = "fromBlynkApp"; // HVAC Dev
 char ssid[] = "ssid";
 char pass[] = "pw";
 

  Serial.println("Ready");
  Serial.print("IP address: ");
  Serial.println(WiFi.localIP());
  // END OTA ROUTINE
  
  rtc.begin();

  EEPROM.begin(201); // EEPROM is zero-index: means addresses 0 to 200 are available (not 1 to 201 or 0 to 201).

  // START EEPROM WRITEBACK ROUTINE
  if (EEPROM.read(eeIndex) > 1)              // If this is true, than the index has advanced beyond the first position (meaning something was stored there (and maybe higher) to be written back.

  }
}

void alarmTimer() // Does the timing for the RA/SA split temperature alarm.
{
  if (digitalRead(blowerPin) == LOW) // Blower is running.
  {
    int secondsCount = (millis() / 1000); // Running count that the alarm will reference after the first high split is noticed.
