def Gorenflo(P, Pc, q=None, Te=None, CASRN=None, h0=None, Ra=4E-7):
    r'''Calculates heat transfer coefficient for a pool boiling according to 
    [1]_ and also presented in [2]_. Calculation is based on the corresponding
    states law, with a single regression constant per fluid. P and Pc are 
    always required.
    
    Either `q` or `Te` may be specified. Either `CASRN` or `h0` may be 
    specified as well. If `CASRN` is specified and the fluid is not in the
    list of those studied, an error is raises.

    .. math::
        \frac{h}{h_0} = C_W F(p^*) \left(\frac{q}{q_0}\right)^n
        
        C_W = \left(\frac{R_a}{R_{ao}}\right)^{0.133}

        q_0 = 20 \;000 \frac{\text{W}}{\text{m}^{2}}
        
        R_{ao} = 0.4 \mu\text{m}
        
    For fluids other than water:
    
    .. math::
        n = 0.9 - 0.3 p^{*0.3}
        
        f(p^*) = 1.2p^{*0.27} + \left(2.5 + \frac{1}{1-p^*}\right)p^*
    
    For water:
    
    .. math::
        n = 0.9 - 0.3 p^{*0.15}
        
        f(p^*) = 1.73p^{*0.27} + \left(6.1 + \frac{0.68}{1-p^*}\right)p^2

    Parameters
    ----------
    P : float
        Saturation pressure of fluid, [Pa]
    Pc : float
        Critical pressure of fluid, [Pa]
    q : float, optional
        Heat flux, [W/m^2]
    Te : float, optional
        Excess wall temperature, [K]
    CASRN : str, optional
        CASRN of fluid
    h0 : float
        Reference heat transfer coefficient, [W/m^2/K]
    Ra : float, optional
        Roughness parameter of the surface (0.4 micrometer default), [m]

    Returns
    -------
    h : float
        Heat transfer coefficient [W/m^2/K]

    Notes
    -----
    A more recent set of reference heat fluxes is available. Where a range of
    values was listed for reference heat fluxes in [1]_, values from the
    second edition of [1]_ were used instead. 44 values are available, all
    listed in the dictionary `h0_Gorenflow_1993`. Values range from 2000
    to 24000 W/m^2/K.

    Examples
    --------
    Water boiling at 3 bar and a heat flux of 2E4 W/m^2/K.

    >>> Gorenflo(3E5, 22048320., q=2E4, CASRN='7732-18-5')
    3043.344595525422

    References
    ----------
    .. [1] Schlunder, Ernst U, VDI. VDI Heat Atlas. Dusseldorf: V.D.I. Verlag, 
       1993. http://digital.ub.uni-paderborn.de/hs/download/pdf/41898?originalFilename=true
    .. [2] Bertsch, Stefan S., Eckhard A. Groll, and Suresh V. Garimella. 
       "Review and Comparative Analysis of Studies on Saturated Flow Boiling in
       Small Channels." Nanoscale and Microscale Thermophysical Engineering 12,
       no. 3 (September 4, 2008): 187-227. doi:10.1080/15567260802317357.
    '''
    Pr = P/Pc
    Ra0 = 0.4E-6
    q0 = 2E4
    if CASRN not in h0_Gorenflow_1993 and h0 is None:
        raise Exception('Reference heat transfer coefficient not known')
    if not h0:
        h0 = h0_Gorenflow_1993[CASRN]
    if CASRN != '7732-18-5':
        # Case for not dealing with water
        n = 0.9 - 0.3*Pr**0.3
        Fp = 1.2*Pr**0.27 + (2.5 + 1/(1-Pr))*Pr
    else:
        # Case for water
        n = 0.9 - 0.3*Pr**0.15
        Fp = 1.73*Pr**0.27 + (6.1 + 0.68/(1-Pr))*Pr**2
    CW = (Ra/Ra0)**0.133
    if q:
        return h0*CW*Fp*(q/q0)**n
    elif Te:
        A = h0*CW*Fp*(Te/q0)**n
        return A**(-1./(n - 1.))
    else:
        raise Exception('Either q or Te is needed for this correlation')