How can I repair a power cable with missing jacket insulation?
The jacket needs to enter the box 1/4"  if it is missing further back than that the inspector may allow heat shrink but I would probably replace that run so I wouldn't have to wait for another inspection unless you call them and they say heat shrink would be acceptable. Code reference NEC 314.7.C.