Power outlet that works off a switch no longer shuts off after replacement
You didn't break off the tab between the hot screws. There's a small metallic tab that normally connects the two hots to allow chaining of outlets (line and load) along a circuit. For a half switched outlet, you need to use a pair of needle nose pliers to break off the tab.