GE THQL1120GF Equivalent replacement breaker
You're looking at the right thing, either way
The THQL1120GF was replaced with the THQL1120GFT when the UL 943 mandate for automatic self-testing in GFCIs went in; the P suffix is likely simply for blister (retail) packaging vs a breaker sold loose, as you'd get at an electrical supply house.