Thermo Pride OL5-85 oil furnace and Aprilaire 60 humidistat
Per reading more on this model of furnace on the internet... It will not in fact energize the W terminal when the heat is on. The solution is to use an A50 relay to detect when the blower is going. Make sure to wire the relay into the circuit running from the humidistat to the humidifier!