Two Compact Dryers on a 30 Amp Circuit
I refer you to NEC Article and Table 210.21(B)(2) which states and shows that a 30A branch circuit supplying two or more cord and plug connected loads shall not exceed 24A. Your assumption of 27A would in violation of the NEC.

Sorry for the disappointment.