Question to code-legal of space between walls where circuit breaker box is located
The code reference 110.26 requires 30” wide and 30” in front with 6-1/2’ head room as a minimum.
If this is an original instillation it will be allowed to stay. If there was a remodel making the small area they may require removal.
Most of the inspections for moving a home (the electrical must meet all current code after the move) The inspectors were looking at:
GFCI’s, AFCI’s, Tamper resistant outlets. Verification that the bathrooms and kitchens had the current code required branch circuits.
I have only done 3 of these in my career but all 3 were similar. The last one the panel was in the bathroom (not allowed now &amp; I did not have to move it).I did add a door that when open blocked access to the sink and tub.