Installing single receptacle for motor loads and not gfci protect
2014 NEC 210.8.A "All 125-volt, single phase 15- and 20-amp receptacles installed in the locations specified in 210.8.a.1 through 10 shal have GFCI for personal." (This means 5 MA trip on detected fault). #2 "Garages, and also accessory buildings that have a floor located at or below grade level not intended as habitable rooms and limited to storage areas, work areas, and areas of similar use." 

This means all outlets in the garage require GFCI even ceiling mounted outlets for garage door openers. (My state exempts the dedicated outlet behind a freezer or a large piece of equipment not easily moved. All other outlets except an alarm system require GFCI protection). 
For a Sump pump if you do not want GFCI protection get a 240V pump 120V pumps require GFCI even for a dedicated circuit.