Bonding Neutral and ground in a service panel
If the second panel is fed by the first (power is fed to the second panel through a breaker in the first), and the service neutral is bonded at the first panel. Then the ground and neutral should be separate in the second panel, and separate grounding and neutral conductors should be run between the two panels.