Combination switch wiring
The white connected to the ground screw is suspect.

Normally the whites are pigtailed together and capped and the black goes through the switch. (And of course bare wires to the ground screw).

If you want to double check the connections from here you can do that with a multimeter. Plug in a resistive load (toaster, space heater, incandescent light bulb, iron,...) into the switched outlet and check whether the resistance between a black and white going the same direction has the same resistance as between the prongs on the plug.

The other set of wires will be coming from the breaker and should be live at mains voltage when you turn it back on.