Water heater uses two single breakers
You can replace the two single pole breakers with a 30A double pole, or use an appropriately identified handle tie between the existing single pole breakers as well as per 240.15(B)(2) as typical electric storage water heaters don't have any 120V loads.  Of course, this all requires the breakers to be adjacent.