Do I need a ground for a 2-wire BX cable to a stove?
2014 NEC 250.118.10 all 3 examples of using Metal Clad include the use of a grounded conductor. In the 2014 NEC handbook 330.108 states. "the interlocked sheath cable construction is not recognized as an EGC." so it would not be lega. A discrete conductor is needed for the Equipment Grounding Conductor.