How do I power fluorescent lights hanging from a drop ceiling?
I'm looking at NEC Article 410.62 (1) conditions (1) &amp; (2) Cord Connected Lampholders and Luminaires. It basically says you can't connect up the fluorescents the way you have them. I suggest the best way is to eliminate the receptacles you can use the boxes for junctions since they are accessible. Then use standard wiring practices and connect into the top of the fixture and junction inside the fluorescent.