Why don't I have ground wiring on any of my outlets?
Your house is wired using the EMT conduit wiring method.  Individual wires are carried inside metal conduit.  The conduit is the ground path.  Most commercial and industrial buildings look exactly like this. 

Since they are individual wires, they are able to use any of 11 wire colors to disambiguate circuits, instead of the usual black white red.   If you wish to add wires, you'd buy THWN-2 wires, stranded is more flexible but more tricky to put on screws.



Switches do not need any further attention to grounding.  

Lamps and receptacles may need further attention.  Look closely at how the yoke (metal frame, notably the top and bottom ears) make contact with the steel box.   If all this is true: 


There is hard face-contact between the yoke and the metal box directly; the yoke is not floating out proud of the metal box connected only by screw threads, and 
The yoke and metal box are not contaminated by paint, rust or other detritus, and
There is not any little little paper/plastic square that would capture the yoke screws, 


then this clean hard-flush contact is an acceptable ground path.  

If any of this is insufficient, you must ground the receptacle to the box.  Somewhere in the back of the box will be a hole slightly different than the others.  It is tapped #10-32 for a ground machine screw (bolt).  You can use any 10-32 bolt (machine screw).  They sell cute green 10-32 bolts in the hardware store, with or without pigtails pre-attached.  Those are perfect. 



Metal conduit is an excellent wiring method, and I use it whenever I can. You can use existing conduit routes to add circuits (up to 4 per conduit), so it makes it easy to customize your wiring. For instance if you keep tripping breakers in the kitchen, just throw another circuit in alongside the existing one. Even if you're extending, you can use existing conduit for the homerun - there's no need to bust up any more drywall than you absolutely have to.

AFCIs were originally invented for problem appliances (one in particular: electric blankets). But they were found to protect all sorts of "NM cable, plastic box, lazy installation" type problems coughbackstabscough, so AFCIs are now required on almost every circuit.  EMT doesn't have those problems, so I don't install AFCI on circuits in metal conduit. (except bedrooms, obviously).