Multiwire Branch Circuit with GFCI
No, do not join all of the neutrals. The GFCI load terminals need the neutral to remain separate. Your diagram is correct in that respect.

However, kitchen outlets must be dedicated; the circuit may not be shared with lighting as you have in your diagram. This is almost certainly a code violation in any jurisdiction.