Securing 3-3-3-5 SER at sub panel entrance
Yes, you're looking at a larger NM clamp here

Looking at some sizing data, a 3-3-3-5 copper SER is 0.91" in diameter.  This fits neatly into the .790-.980" cable range supported by an Arlington 843S or equivalent 1" trade size NM/SE clamp.