Electrical Circuit low voltage [solved]
solved, I took the 3 wires off the outlet and found that 120 was going in to hot by testing ground to common, but 11.78 was being drawn from common and nuetral so the only possible explanation was that the wire from.the breaker box to the outlet which had to be  the neutral wire, everything looked fine in the breaker box, everything tested 120 being pushed out, but taking a closer look the neutral wire was burnt but tight through the hole on the metal strip. taking even a closer look the neutral wire was about ready to break , it wiggled like a jelly bean. Changed it and boom power to my fridge, thank the Lord.