Why is my AC only blowing out Ice cold air and freezing over AC lines?
If the outdoor unit continues running while the indoor blower is stopped it would indeed start looking like a freezer. If there's been work done recently on the thermostat and related wiring then it could be that a mistake was made which causes the compressor to run continuously. If this problem has developed spontaneously, a likely cause could be that the contactor in the outdoor compressor unit has welded itself closed. That's the equivalent of the power switch being stuck in the on position.

An HVAC contractor or other person comfortable with a volt meter should be able to identify pretty quickly whether the call for cooling is stuck on, or whether it's the contactor itself that has failed. There should be a pair of small-gauge wires going into the compressor unit. If there's a voltage showing between those two wires (about 24 volts ac), or if disconnecting one of them causes the compressor to stop running, then the call for cooling is stuck on -- a thermostat failure or a wiring problem would be likely. If instead there's no significant voltage between the two wires then the contactor is stuck and should be replaced.