Mini split minimal pipe length
I would call the support line to verify the length. The unit is precharged with refrigerant and too short a line set will cause an overcharge condition.
Overcharge can cause icing of the system and shorten the service life.
Worst case, make a loop close to the compressor. A loop helps reduce vibrations transmitted through the line set when the length is short.