Bathroom GFCI question
It does need to be protected there by the sink. It may very well be wired into the LOAD terminals of the other GFCI outlet. It is easy for you to check. Plug a lamp in by the sink and turn it ON. Then press the TEST button on the GFCI outlet. If the lamp goes OFF you know that the outlets are coupled.