NM-B Romex going through conduit raceway to external breaker box. Not code compliant?
If the conduit continues into a box for the receptacle just replace with thhn. If the conduit is just a sleeve to protect the romex it would need to be changes to type uf-b  because the conduit would be considered a wet location