Does this look alright??? Does this meet code??? Electrical surrounded by water pipes
This is compliant...

The 110.26(E)(1)(a) rule about dedicated space goes as follows:


  (a) Dedicated Electrical Space. The space equal to the
  width and depth of the equipment and extending from the
  floor to a height of 1.8 m (6 ft) above the equipment or to
  the structural ceiling, whichever is lower, shall be dedicated
  to the electrical installation. No piping, ducts, leak protection apparatus, or other equipment foreign to the electrical
  installation shall be located in this zone.


Note that it says that the dedicated space is equal to the depth of the equipment.  Since the box is surface-mounted to the plywood, this means that the dedicated space starts at the front of the plywood sheet (the side facing out towards you), and the piping behind the sheet does not infringe upon it as a result.

Personally, I'd deploy a NEMA 3 family enclosure here instead of a NEMA 1 to minimize the risk of problems due to splashing, etal, but that's just me being mildly paranoid.

but be careful where you put the washer!

However, the Code compliance of this also has to do with where you put your laundry appliances.  The washer needs to be placed in compliance with the 30" minimum width requirement of 110.26(A)(2):


  (2) Width of Working Space. The width of the working
  space in front of the electrical equipment shall be the width
  of the equipment or 762 mm (30 in.), whichever is greater.
  In all cases, the work space shall permit at least a 90 degree
  opening of equipment doors or hinged panels.


Note that this doesn't have to be centered on the equipment -- in your case, simply making sure that the washer is 30" away from the side wall and not putting anything else there(!) would be enough to comply.