breakers all putting out power but outlet not working
Are there any other receptacles or lights with no power? Presumably there are other receptacles on this same circuit.

You say no power at the incoming line to this receptacle--presumably meaning no hot. So a connection of a hot upstream has gone bad. Do you have spring "backstab" connections to the receptacles? If so, change them to the side screw. (If you have backwire connections secured by the screw that is fine.)

In any case, check each receptacle in the circuit from the non-working one going back towards the panel. Use a plug-in circuit tester or a multimeter. It will tell whether there is no hot or no neural at each receptacle.