Install recessed lights and chandelier with 3-way switches
It sounds like your plan will work now that you have the 12/3 cable -- since you have a neutral at the kitchen-side switch, you don't need to worry about running one to the entry-side switch, as the 404.2(C) provisions for neutral at switches only require neutral at one location within a multiway switching setup.