Dead GFCI outlet(s), wire is live
Best I can tell, it's time to buy another GFCI (the correct one, this time -- hopefully, the third time's the charm)

There are four problems here:


The old GFCI finally died (at power on, likely) and the new GFCI is likely DOA.  Easiest fix is to try getting another GFCI and putting it in.
Your new GFCI was the wrong part -- you need a weather-resistant receptacle in a damp or wet location these days (NEC 406.9), and yours isn't.  Leviton's W7599 is the equivalent of what you have in a Weather Resistant model, BTW (as of this post, at least).
Receptacles in wet locations require a while-in-use weatherproof cover or "bubble cover" these days, such as this.  This helps keep rain out even under wind-driven conditions, no matter whether stuff's plugged in or not.
Even weatherproof boxes need to be pressure equalized (via a drainage hole in the bottom) in order to keep pressure differences from driving water through even the slightest imperfections in seals and to give any water that does get in a path to escape.  This is allowed as per 2014 NEC 314.15:



  314.15 Damp or Wet Locations. In damp or wet locations, boxes, conduit bodies, and fittings shall be placed or
  equipped so as to prevent moisture from
  or accumulating within the box, conduit body, or fitting. Boxes,
  conduit bodies, and fittings installed in wet locations shall
  be listed for use in wet locations. Approved drainage openings not larger than 6 mm (&frac14;
  in.) shall be permitted to be
  installed in the field in boxes or conduit bodies listed for
  use in damp or wet locations.


See also BSI-004: Drainage, Holes, and Moderation for a good explanation as to why even the most snugly sealed enclosures need weep holes.  So, if there isn't a small hole in the bottom already, drill a &frac18;" hole in the bottom of the box, as per NEMA bulletin 110 and the aforementioned NEC clause.