lutron sensor switch - wiring help
Unfortunately, the Installation Guide doesn't say much. It shows the two black wires but does not have any indication as far as which one goes to hot vs. switched-hot. The implication is &quot;it doesn't matter&quot;.
However, the marketing information (and the installation by omission) makes it clear that no neutral is required. But the switch has to get power from somewhere to run the motion sensor. The instructions indicate this is by using ground:

Both bare and green ground wires are required to connect to ground. If no ground is available, consult an electrician. Device will not function if it is not grounded.

So that tells me two things:

The green ground is NOT for safety but rather in place of neutral for the motion sensor power. According to Q&amp;A on homedepot.com, the switch uses &lt; 1 watt when &quot;off&quot;. That puts in the relatively safe range as far as current running over the ground wire. While using ground in place of neutral is not normally permitted, it is still allowed within certain limitations, and it avoids the problem of either (a) requiring a neutral in the switch box which many boxes simply don't have or (b) running a small amount of current through the switched line when off, which works fine on incandescent bulbs but on LEDs will often result in either flashing lights or a very low constant glow. It might put it below the normal threshold of a GFCI, but I wouldn't count on it.

The bare ground is for safety.


Provided your box really is properly grounded, connect both grounds (green &amp; bare) to the box, connect hot to one black, switched hot to the other black, and you're done.
This actually makes for a very simple and almost foolproof installation. But they could have made it totally foolproof by being upfront in the instructions about how it uses the wires. A classic example of dumbing down instructions too far, raising more questions instead of making things easier.
Beware of GFCI
As I understand it (pros can chime in, of course), lighting circuits in areas that require GFCI for receptacles (bathroom, kitchen, laundry room, etc.) do NOT need to be on GFCI. They can be on GFCI, and if so then a switch like this might be detected as a ground fault. If that happens then you should either move the lighting to a different circuit or (generally much simpler) pigtail the lighting to the LINE side of the receptacle instead of daisy-chaining off the LOAD side.