Can a GFCI combo and a switch be independently connected to a light and a fan using 14/3 wire?
With GFCI Protection of Devices
If you want to provide GFCI protection of the fixture, you'd feed the switches from the LOAD side of the GFCI device.

Without GFCI Protection of Devices
If you don't want to provide GFCI protection to the devices, you'd feed the switches from the incoming feeder.

NOTE: I've labeled one of the dimmer terminals as &quot;C&quot; (common), as it looks like you might have a 3-way dimmer. In this case the &quot;C&quot; terminal will be an odd color (likely black), while the other two will be the same color (brass). Unless of course the third terminal in your diagram is green (ground), in which case you should ignore this note and connect the grounding conductor to the green terminal.