Switched outlet keeps tripping breaker
thanks to everyone's suggestions i was able to isolate the issue. there was obvious continuity btwn the black lead from the switch and the conduit. pulled the wiring and found a small nick in the insulation near a right angle connector. will be pulling new wire later this week.