Fan is turning on air conditioner but no air movement
That video sure looks like rotation is backwards [it should be spinning clockwise as seen based on the scroll/label], but... could be strobe effect from camera rate? I can't think of how to switch rotation on an ac motor run by a simple contactor but by rewiring the motor leads - racoons aren't that clever [yet].  If it's fooling us, then look at ductwork: if you have flex duct which had an internal collapse, air flow could be blocked. Another option is your dampers used to balance distribution out of the air handler came loose and the butterfly is closed. If it is in fact running backwards, then does it use some solid state controller [pwm, or other variable speed type drive]?  That would be the culprit.