How strong should the air current from my heat pump be, and is there a way to adjust the power myself?
If this is a standard ducted A/C unit you could check the temperature drop across the A/C coil using a thermometer. Check the air temperature entering the coil (return air) and the discharge air above the coil (cold supply air). The temperature drop should be between 15 &amp; 20 degrees F. If the air temperature drop exceeds the 20 degrees F more air may be required. This is about all you can do yourself. The rest should be done by the installer or another HVAC company.