60 amp sub panel, 100 ft away from main panel. Grounding rod or not?
Same building, just supply ground and neutral in appropriate sizes and separate, and be sure that ground and neutral are not bonded in the sub-panel.

6AWG copper (as a cable, which typically limits you to the 60C rating...) is maybe pushing it a bit depending how loaded that 60A panel is.