wiring size to storage shed
With just 1000w total 14 awg the voltage drop would be 2.85% at 75'. So you could do it with 14awg. 2000w the wire size would be 10awg. For some reason I was thinking 1000w or 2 lights. Going to LED may get you the needed light and not have to go to the larger wire.