200 Amp exterior meter and disconnect with interior main panel
I believe the Google words you are looking for are meter main or meter main combination.

As long as the wiring in your house is downstream of a main breaker (not merely disconnect), that is fine.  Remember since all the power from your service runs through it, you get to apply the  310.15(B)(7) derate of 83%; your wire only needs to be rated for 166A, not 200A. 

This Article 310.15(B)(7) derate calculation replaces a table called 310.15(B)(7), and you will see that table all over the Web. The table is completely useless, and should be disregarded.