Why did my outlet stop working
Since it is an open neutral we will suspect a bad connection at a backstab or a broken wire at a splice. I work backwards looking for the last working receptacle or  the first non working this is the point of failure most of the time.
I don’t look for a switch’s to start with because switching a neutral is a code violation.
Of these problems 98% are from a bad backstab (the push in connectors).
You have checked this receptacle so check the next one closer to the breaker panel in most cases remember if a common wall it could be on the other side.
I work back until I find a working receptacle and then check that one of back stabbed just pulling it out and putting it back in can cause it to start working but it will normally fail again with a large load like a hair dryer or plug in heater.
In this case you are looking for a white or grey wire to be loose or broken if things are good at the last working receptacle the first non working will be the problem.
You can find many examples of this on this site but those are the likely locations. If all receptacles show the same open it may be a bad connection on the neutral buss in the panel but this is very rare I have only found a few of these after many decades of electrical work and all but one were doubled up a code violation on the neutral. But ok for most panels on the ground.