124V neutral to ground and 65v hot to neutral when circuit is off?
You used a high-impedance digital voltmeter (DVM), which can pick up induced or capacitively coupled current from nearby wiring. Put a resistor, perhaps 470 kilohms or 1 megohm, across the leads, to effectively &quot;short out&quot; the very low coupled voltage.