Run cat5e/coax parallel to power conduit
You have not stated any reason that would appear to prevent the obvious solution (if you consider it a problem at all) of running the network wiring along the face of the wall at the same level as the server rack, or roughly 12" below the power conduit. If the basement/crawlspace floods enough to flood the server rack you probably should rethink the location of the server rack, and in any case the cables being run horizontally higher up won't help a bit in that case.

You could also move the cables far enough forward into the room (3-4 feet, say) that they don't encroach on your shelving unit, then run them back along the joist (it's holding up a floor above if it's a crawlspace, so rafter is not the right term - those have a roof above them) to the server rack.

Despite a number of "trying to be perfectionist" scare stories about needing to keep network and power cables well-separated, the fact is that the differential pairs in Cat5 (or 6, or 7) are designed to reject interference, and that the frequency domains of networking signals and power line noise are utterly different. So, in practical terms you can wire tie (just not too tight - sharp bends are bad) the network wires to the power conduit and not have any interference problems in a typical home application.

Coaxial cable is self-sheilded by design and thus also highly unlikely to pick up any objectionable interference simply by being run next to power or network wires.

Since all you are really considering is running them parallel at a few inches distance, you will be fine doing that (do avoid a sharp bend anywhere, particularly where you turn downwards and might be tempted to yank the wire tight around the J-hook.)

While I do generally try to maintain the oft-suggested 12" separation for parallel runs when designing from the ground up, I have hundreds of feet of Cat5e that is in close proximity to power wiring in old building retrofits, and connected to switches that report error rates - and those error rates are pretty much always zero, unless there is a more fundamental problem with the cable (like rats chewing on it, a sharp kink/bend, or a bad connection at the end of it.)