What could cause a Trane furnace to not start heating?
I have the same issue... I did the filter change, checked all the thermoswitches then it worked for a few hours then no heat LED flashing 4 times. Then I measured the voltage from the 24V transformer and the voltage would vary from 11V to 19V max. Replace transformer and furnace is working perfectly.