Too much load running through GFCI?
You can't do that to begin with

You can't put 15A receptacles on a 30A circuit in the first place -- NEC 210.21(B)(3) says no to that plan, and for good reason.

So, rethink your plan (this'd work fine and dandy with a 15A MWBC instead).