Is the rating of the electrical household entry per phase or total?
The overall service is 130A@240V -- each service leg is 130A@120V.  The same rule applies to the subpanel.  (I.e. you can hang twice as much 120V load off of it as you can 240V load, but not both at the same time -- a given amount of ampacity provides twice the power at 240V than it does at 120V, IOW.)

Also, you may wish to swap those fuses for 125A fuses if the extra 5A don't matter to you -- 125A is a standard North American fuse rating, while 130A isn't, so finding replacements for blown fuses is likely to be...much more annoying.