Levition FBBOX installation
For line voltage (120/240 - all 120V to ground, so basically the same voltage from a code perspective) you don't need a divider. A divider is needed when you have low voltage (network/TV/phone) sharing with line voltage.
Unless you are sticking in a 240/120 receptacle (like an L14-20) you'll only have one neutral, so @manassehkatz-Moving 2 Codidact's concern about keeping neutrals straight does not apply, but you will want to either use different hot colors or apply tape, paint, or heat-shrink (if using only one color) to keep the hots correctly grouped. You could use black &amp; white for the 120V and red for both 240's (they don't need to be different from each other) or you could use 3 different hot colors and white (or gray) for the neutral. Or red-taped black for the 240.