PVC conduit, service line with siding offset
My first choice: Use standoffs to keep the line clear of the house by enough distance to clear the bump, with straight conduit.

Second choice: Given it's PVC either rent a blanket heater or get creative with boiling water and bend yourself a section (rather like an inchworm) that fits around the bump. Make it rather gentle/sweeping so that it's not too much trouble to get wires through it. You could cobble something with 15 or 22 degree bends and couplings, but PVC is easy enough to bend with heat, and a straight stick that you bend is a lot cheaper than a bunch of pre-bent sweeps and couplings - it's also smoother inside.