In wall splice for 4 wire cable
You can't, but no need.  

If you're referring to the Tyco Electronics Romex splice kits, yes, they make those for 3-wire w/ground as well as 2-wire w/ ground.  

If you mean some other splice method, you have to read its instructions for whether it is suitable in-wall.  As far as I know the Tyco is the only one that is UL-listed for buried in-wall splicing.  

Further, use of in-wall splice blocks is restricted.  It can only be done for repair, not extension for instance; and even then, only as a last resort when nothing else is possible.  If it is at all feasible for you to re-run the entire cable run, or a run to an accessible point (somewhere you want a receptacle, for instance), you must do that instead.