Can non-metallic cables pass through one large opening at top of electrical panel?
No, the NEC did not eliminate the need to secure. Each cable must be secured at each box or cabinet. Accordingly each connector or cable clamp will be listed with its capacity. One large connector is not listed for many small cables.