new 4-wire GE single-wall oven jts5000snss going into grandfathered 3-wire wall junction
SOLVED: GREEN &amp; WHITE FROM THE OVEN WENT TO THE BARE SILVER BLACK WENT TO NEUTRAL BLACK RED WENT TO HOT BLACK OVEN WORKS

Not Exactly...
First issue is nomenclature: You said &quot;BLACK WENT TO NEUTRAL&quot;. No, black (oven) went to WHITE (house wiring). With a 3-wire oven connection, white is a hot wire. 240V (US) uses 2 hots, neutral and ground. In certain situations, it can be either 2 hots + ground (240V appliance that doesn't need 120V) or 2 hots + neutral with no separate ground (your situation). In either of those cases, if one of the hot wires is black - which will almost always be the case if the wires are in a cable - then it is still hot and not neutral.
The bigger issue is safety. In the olden days, the setup you have was routine - two hots + neutral. Plus the neutral could be, under certain circumstances, bare wire instead of insulated. There was no separate ground wire.
The ideal setup is 4 wires to match your new oven - two hots (typically black &amp; red), neutral (almost always white) and ground (green or bare). The catch is that doing so requires one of two things:

Retrofit ground: You can add a separate ground wire and connect it to the green wire and  connect your new oven white to only the silver wire. The catch is that the ground needs to be as large as it would be if it were a new installation. My guess is that would need to be 10 AWG or 8 AWG. The usual convenient other grounds are from other kitchen circuits, which are likely to only be 12 AWG. But this may still be easier than running a new cable.
New cable: Depending on your setup, that may be very simple (e.g., my kitchen is above the unfinished area of my basement with the main panel) or may be very hard/expensive (kitchen on a different floor from main panel at the other end of the house with finished basement and no conduit).

The good news is that in most areas the old 3-wire connection is grandfathered, so that you are likely legal connecting 4-wire to 3-wire, though it is not as safe as a 4-wire connection.
Wire Size!
However, there is one big factor that may make all the difference and require a new cable: Wire size. If your old cable is 10 AWG and the new oven requires 8 AWG (or 8 AWG and 6 AWG) then you must replace it, and once you are replacing it, you definitely need to bring it up to the modern 4-wire standard.
Check the specs for the oven and see what it says. If it does not specify wire size (AWG) then see what breaker size it specifies, as breakers determine the smallest wire you can use. If you already know you need to replace your breaker (or already did!) then that's pretty much a guarantee that you need larger wires == new wires == 4-wire.