Can static electricity trip GFCI?
The breaker only switches the live, leaving the neutral connected on the load side of the RCBO.
When you cut the neutral and earth at the same time you shorted them together. This can cause enough current to backfeed from the other still live circuits through to the earth to trip the RCBO.
That will be the more likely reason that it tripped.