My dryer has a issue after switching the breaker
I would say the main suspect is your breaker.

If it was heating up and not tripping it is probably faulty.

The normal breaker for a dryer circuit is 30 amp and #10 wire.

To use a 60 amp breaker for a dryer circuit you would need a minimum of #6 wire (smaller numbered wire is larger). I would suspect your wire is not that big.

If a voltage test at the outlet does not show voltage then you should try replacing the breaker with a 30 amp for a fairly inexpensive fix. If that doesn't work. It's possible the dryer needs repair.

Good luck and stay safe!