240 outlet giving abnormal me abnormal readings
You have an open neutral on this circuit. You are getting a reading on it to ground and one leg due to a load backfeed on the neutral.

If everything else in the house works fine then the problem is almost certainly isolated to this circuit.

Physically check the connection of this circuit's neutral wire at the panel.