Furnace Short Cycling - Carrier Code 33
I was able to figure out it was the Draft Safeguard that was tripping. After digging around online some more there were a couple recommendations:
Right when we purchased the home we redid the flooring immediately from linoleum that had a threshold at the closet to engineered hardwood and we did not put a threshold at the closet (effectively increasing the gap at the bottom). I both verified the intake was clear and also placed towels at the door gap and let the furnace run in which it finally did not short cycle.