Straightening a bend copper tubing of an air conditioner filled with refrigerant
First, is that electrical box secured or just hanging on its wires? if it is just hanging that needs to be addressed as well.

Then, is there any spare length in the copper pipe, assuming it is covered by the tape stuff? I think the pipes will be too short if you tried to put two 90 bends in them with a pipe bender. Also, copper pipe work hardens so the original bending will have made the pipe harder to bend a second time around.

I would consider making new pipes to meet the proper run you want then refill the system.