Fan works for heating, but not for AC, where to start?
If this is an older furnace you may have a bad relay in the furnace control box that runs the fan when the a/c is turned on. If it a newer furnace you may have a problem with the printed circuit board. A picture of the control board or the wiring of the furnace would help, along with the model, serial, and age of the equipment