Thermostat fan control on old furnace without circuit board
You will need to add a 24 volt relay that is controlled by the green wire and a common and wire the relay contacts to bring on the fan by jumping the contacts in the 4064 fan/limit control. You can use a RIB relay or similar one.This is how it was done in the "old days".