Delta to delta 2000 kVA transformer
Provide an intentional ground reference so neutral point is not determined by parasitic phase-ground capacitance...or find the problem with your existing scheme.

Here is example using wye-grounded primary, broken delta secondary set of VTs and loading resistor: