How to correctly edit a system to increase per-unit voltage of a bus [PowerWorld Simulator]
The complex voltage at bus 8, \$V_{R}\$, is the voltage at the receiving end of a single transmission line where \$V_{S}\$ is the sending-end voltage (at bus 7) and the relationship between the two voltages is given by
$$
V_{R}=V_{S}-IZ_{T}=V_{S}-IR_{T}-IjX_{T}
$$
where \$I\$ is the current flowing in the transmission line towards the receiving bus with the impedance \$Z_{T}\$ (or its components resistance \$R_{T}\$ and reactance \$X_{T}\$.

The current flowing \$I\$ is a set by \$\frac{V_{R}}{R_{L}+X_{L}}\$, the voltage on the bus and the load impedance.

From these equations we can see that the per-unit voltage of bus 8, the receiving bus, can be affected by the reactance of the transmission line and the current flow in the line - this current is caused by the net active and reactive power consumed or produced on the bus. Real power use and reactive power consumption decreasing the bus voltage. Real power production and reactive power supply, however, increase the bus voltage as they cause the current to flow in the opposite direction. This gives us three main variables we can change to change the bus voltage, net real power, net reactive power and line impedance.

A nice way to remember this is that the current always flows down the voltage gradient from the higher voltage bus to the lower voltage bus.

You've identified half of these, but the main changes you can make to the simulation to increase \$V_{R}\$ are:


Decrease the net real power use at the bus

Decrease the real load (MW value)
Increase the real power generated at the bus (attach a generator)

Decrease the net reactive power use at the bus

Decrease the reactive load (MVar value)
Increase the reactive power produced at the bus (attach a capacitor bank or a generator operating with a leading power factor)

Decrease the transmission line impedance.


Of these, the adding a capacitor bank to the bus is the most practical in the real world as capacitors are cheap and changing the reactive load has a much greater effect than the real load on the per-unit voltage.

It should also be noted that as \$V_{R}\$ is also dependant on \$V_{S}\$ taking similar measures at bus 7 would also raise the voltage at bus 8.

As to which is the "correct" answer, that really requires more information in your assignment's question!