Harmonics Mitigation of Industrial Power System Using
Passive Filters
ZUBAIR AHMED MEMON*, MOHAMMAD ASLAM UQUAILI**, AND MUKHTIAR ALI UNAR***
RECEIVED ON 27.12.2011 ACCEPTED ON 15.03.2012

ABSTRACT
With the development of modern industrial technology a large number of non-linear loads are used in
power system, which causes harmonic distortion in the power system. At the same time the power quality
and safe operation becomes inferior. Therefore mitigation of harmonics is very necessary under the
situation. This paper presents the design of two passive filters to reduce the current harmonics produced
by nonlinear loads in industrial power system. Matlab /simlink software has been used for the simulation
purpose. The results have been obtained with and without installation of filters and then it is observed that
after installation of filters harmonics of the current are reduced and power factor is improved.
Key Words:

1.

Passive Filters, Total Harmonic Distortion, Current Distortion, Power Factor.

INTRODUCTION

N

owadays industries prefer to use power

In the literature several studies have been presented

electronics based devices due to their

regarding the harmonic mitigation by using different types

effectiveness. Though these power

of filters [1-6]. Passive filter is one of them and has been

electronics based devices are advantageous to the

investigated for the harmonic mitigation. Low cost, simple

electronics and electrical industry, these devices generate

design and high reliability are main advantages of passive

and inject the harmonics in the power industry. These

filters [7].

harmonics are known as electrical disturbances which
are the main cause of the power quality associated harms.

In this paper effectiveness and design of single-tuned

The main problems due to the harmonics are additional

filter and second order high pass filter has been

power losses in the electrical equipment, irregular

investigated for suppressing the harmonic currents in

function of protective devices, errors in measurement of

industrial power system.

metering devices and interference with the
telecommunication lines. Therefore mitigation of
harmonics and improvement of the power quality is
essential under the situation.
*
**
***

2.

PASSIVE FILTERS

For mitigating the harmonic distortion passive filtering is
the simplest conventional solution [8]. Passive elements

Assistant Professor, Department of Electrical Engineering, Mehran University of Engineering & Technology, Jamshoro.
Professor, Department of Electrical Engineering, Mehran University of Engineering & Technology, Jamshoro.
Professor, Department of Computer Systems Engineering, Mehran University of Engineering & Technology, Jamshoro.
Mehran University Research Journal of Engineering & Technology, Volume 31, No. 2, April, 2012 [ISSN 0254-7821]
355

Harmonics Mitigation of Industrial Power System Using Passive Filters

like resistance, inductance and capacitance are used by
the passive filters to control the harmonics. Common types
of passive filters and their configurations are depicted in
Fig. 1.

The impedance versus frequency curve of this filter is
shown in Fig. 2.
In design of the filter, the proper selection of the capacitor
size is very essential from power factor point of view. The

The shunt connection of passive filters with the power
system provides least impedance path to the harmonic
current at tuning frequency. As compared to the shunt
filter series filter is designed to carry full load current
therefore they need over current protection devices.
Whereas shunt passive filter carries a fraction of series
filter current. The series filter is relatively more expensive
hence shunt passive filter is commonly used as harmonic
filter. Furthermore it also provides reactive power at system
operating frequency.

3.

SINGLE TUNED FILTER DESIGN

The most commonly used passive filter is the single-tuned
filter. This filter is simple and least expensive as compared
with other means for mitigating the harmonic problems [910]. The LC STF (Single Series Filter) is most common and
inexpensive type of passive filter. This filter is connected
in shunt with the main distribution system and is tuned to
present low impedance to a particular harmonic frequency.
Therefore, harmonic currents are diverted from the least
impedance path through the filter. For designing the singletuned filter it is essential to select the appropriate capacitor
value that enables good power factor at system frequency.
The circuit diagram of the STF is depicted in Fig. 1.

FIG. 1. PASSIVE POWER FILTERS CONFIGURATIONS

relation between capacitor reactance and reactive power
is expressed as:

QFilter =

2
Vcap
Xc

(1)

where V2cap is the line voltage of the capacitor in volts, Q is
the reactive power in kVAR and Xc is the capacitive
reactance of capacitor in ohms.
The Equation (2) of the capacitive reactance is given by:
C=

1

(2)

2πfC

From Equation (2) the value of capacitance (in farad) is
calculated as:
C=

1
2πfX

(3)
C

The resonance condition will occur when capacitive
reactance is equal to inductive reactance as:
XL=XC

(4)

FIG. 2.. THE CHARACTERISTIC OF THE SINGLE TUNED
FILTER

Mehran University Research Journal of Engineering & Technology, Volume 31, No. 2, April, 2012 [ISSN 0254-7821]
356

⎣

Harmonics Mitigation of Industrial Power System Using Passive Filters

The impedance of second-order high pass filter is given
by Equation (8):

The Equation (4) can be rewritten as:

2πfL =

1
2πfC

(5)

Z=

1
jωC

+

The inductive value of the filter can be obtained from
Equation (5) as:

1

FG 1 + 1 IJ
H R jωL K

(8)

The corner frequency of the filter is achieved by
L=

Equation (5)

1

b2πf g2 C

(6)

The quality factor of second-order high pass filter is
different as compared to single tuned filter and it is

The resistance of filter depends on the quality factor (Q)

reciprocal of the quality factor of the single tuned filter as

by which sharpness of the tuning is measured.
Mathematically quality factor is defined as:

given by the Equation (9):
Q=

R
X

L
Q=

C
R

=

C

R
X

L

(9)

(7)
The characteristic of second-order high pass filter is shown
in Fig. 3.

The resistive value of the filter can be obtained by selecting
the quality factor in the range of 20<Q<100 [11].
The larger value of the quality factor gives the best
reduction in harmonic reduction. However, it is necessary
to take care of the harmonic frequencies because these

For second order high pass filter the typical values of
quality factor are between 0.5 and 5 [12].
At higher value of quality factor the filters give the superior
filtering performance as compared to the filters with smaller
value of quality factor.

harmonic current frequencies will also follow the least

The other points that are essential in selection of the

impedance path. These currents cause the increased power

quality factor are as under:

loss. Therefore it is necessary to perform the computer



Filter's tuning frequency

based harmonic simulation for analyzing the performance



Losses

of the filters.



Concerns for telephone interference (if exists)

4.

SECOND ORDER HIGH PASS
FILTER

The second order high-pass filter is similar to single-tuned
filter where L and R are connected in parallel instead of
series as shown in Fig. 1. The second-order high pass
filter provides good filtering performance and it decreases
the energy losses at fundamental frequency.

FIG. 3. THE CHARACTERISTIC OF THE SECOND-ORDER
HIGH PASS FILTER

Mehran University Research Journal of Engineering & Technology, Volume 31, No. 2, April, 2012 [ISSN 0254-7821]
357

Harmonics Mitigation of Industrial Power System Using Passive Filters

5.

SELECTION OF FILTERS

The circuit parameters used in simulation are presented in
Table 1.

At lower harmonic frequencies the most of the waveforms
have large percentage of harmonic distortion as compared
to the high harmonic frequencies. For that reason single
tuned filters are designed to suppress these lower harmonic
frequencies. For suppressing the harmonics of six pulse
ac to dc converter four single tuned filters are used for the
5th, 7th, 11th, and 13th harmonics and one second order high
pass filter is used for eliminating the high order frequencies
[13] as shown in Fig. 4.

Fig. 5 shows the three-phase supply currents of the system
without passive filters. As it is clear that currents are
distorted therefore these currents contain the harmonics.
Figs. 6-7 show the supply current without passive filters
(only one phase current has been shown for the clearness)
and its frequency spectrum, respectively. It is clear that
the THD (Total Harmonic Distortion) of the current is
20.77%.
TABLE 1. SIMULATION PARAMETERS [14]

6.

ANALYSIS OF SIMULATION
RESULTS

Supply Voltage

Vs=220Vrms

Supply/Line Inductance

Ls=0.0016 Henery

In this paper, three-phase ac to dc converter has been

Rectifier Front-End Inductance

LL=0.023 Henery

simulated with and without proposed passive filters in the

Capacitance of the Load

C=50 Micro Farad

Resistance of the Load

RL=78 Ohm

matlab/simulink environment.

FIG.. 4. INDUSTRIAL POWER SYSTEM MODEL WITH PASSIVE FILTERS
Mehran University Research Journal of Engineering & Technology, Volume 31, No. 2, April, 2012 [ISSN 0254-7821]
358

Harmonics Mitigation of Industrial Power System Using Passive Filters

Without passive filters the total harmonic distortion of

7.

the current is above the range specified by the power

A PC-based design method of two common types of passive
filters namely single tuned filter and second order high
pass filter has been presented in this paper. The proposed
filters reduce the total harmonic distortion of the source
current at a high level of expectation from 20.77-4.32% in
the simulation. Our results meet the IEEE 519 recommended
harmonic standards.

quality standards.
To follow the recommended IEEE 519 power harmonic
standards the total harmonic distortion must be less than
5%. This can be obtained by connecting the passive filters
to the system. For reducing the THD below 5% passive

CONCLUSION

filters have been designed. The parameters of the proposed
passive filters have been shown in Table 2.
After connecting the filters the three-phase supply
currents become sinusoidal and harmonics are decreased
below 5%. Thus the source current becomes in phase
with the supply voltage, the power factor of the source is
then near to the unity. The simulation results are presented
in Figs. 7-11 which show good filtering performance of the
proposed filters.
FIG. 7. FREQUENCY SPECTRUM OF SUPPLY CURRENT
WITHOUT PASSIVE FILTERS
TABLE 2. VALUES OF DESIGNED FILTERS
C (F)

L (H)

R (Ω)

C5th = 11.09e-6

L5th = 0.0365

R5th = 0.54

C7th = 11.09e-6

L7th = 0.0186

R7th = 0.38

C11th = 11.09e-6

L11th = 0.0075

R11th = 0.24

C13th = 11.09e-6

L13th = 0.0054

R13th = 0.21

CHP = 11.09e-6

LHP = 0.0031

RHP = 49.66

FIG. 5. THREE-PHASE SUPPLY CURRENTS WITHOUT
FILTERS.

FIG. 6. SUPPLY CURRENT WITHOUT PASSIVE FILTERS

FIG. 8. THREE PHASE SUPPLY CURRENTS WITH FILTERS

Mehran University Research Journal of Engineering & Technology, Volume 31, No. 2, April, 2012 [ISSN 0254-7821]
359

Harmonics Mitigation of Industrial Power System Using Passive Filters

REFERENCES
[1]

Chang, G.W., Wang, H.L., and Chou, S.Y., "Strategic Placement
and Sizing of Passive Filters in a Power System for Controlling
Voltage Distortion", IEEE Transactions on Power Delivery,
Volume 19, No. 3, pp.1 204-1211, 2004.

[2]

Aravena, P., Vallebuona, G., Moran, L., Dixon, J., and Godoy,
O., "Passive Filters for High Power Cycloconverter Grinding
Mill Drives", IEEE Industry Applications Society Annual Meeting,
pp. 1-7, 2009.

[3]

Fujita, H., Yamasaki, T., and Akagi, H., "A Hybrid Active Filter
for Damping of Harmonic Resonance in Industrial Power
Systems", IEEE Transactions on Power Electronics,
Volume 15, No. 2, pp. 215-222, 2000.

[4]

Zhao, W., Zhou, S., and Luo, A., "Novel Injection Type Hybrid
Active Power Filter and its Energy Saving Application", Third
International Conference on Measuring Technology &
Mechatronics Automation, Volume 2, pp. 694-700, 2011.

[5]

Zobaa, A.F., Aziz, A.M.M., and Aleem, A.S.H.E, "Comparison
of Shunt-Passive and Series-Passive Filters for DC Drive Loads",
Electric Power Components and Systems, Volume 38, No. 3,
pp. 275-291, 2010.

[6]

Hamadi, A., Rahmani, S., and Al-Haddad, K., "A Hybrid Passive
Filter Configuration for VAR Control and Harmonic
Compensation", IEEE Transaction on Industrial Electronics,
Volume 57, No. 7, pp. 2419-2434, 2010.

[7]

Memon, Z.A., Uqaili, M.A., and Soomro, M.A., “Experimental
Analysis of Harmonic Mittigation Efforts of Three-Phase SixPulse Controller by Using Pass Filters”, Mehran University
Research Journal of Engineering & Technology, Volume 30,
No. 4, pp. 653-656, Jamshoro, Pakistan, October, 2011.

[8]

Das, J.C., "Passive Filters-Potentialities and Limitations", IEEE
Transactions on Industry Applications, Volume 40, No.1,
pp. 232-241, 2004.

[9]

Young, S.C., and Hanju, C., "A Single-Tuned Passive Harmonic
Filter Design Using Transfer Function Approach for Industrial
Process Application", International Journal of Mechatronics and
Automation, Volume 1, No. 2, pp. 90-96,2011.

[10]

Bula, D., and Pasko, M., "Hybrid Power Filter with Single
Tuned Passive Filter - Dynamical Properties", International
School on No Sinusoidal Currents and Compensation,
pp. 80-83, 2010.

[11]

George, J.W., "Power Systems Harmonics Fundamentals,
Analysis and Filter Design", Springer, 2001.

[12]

Francisco C., dela, R., "Harmonics and Power Systems", Taylor
and Francis, 2006.

[13]

Jamali, S., Masoum, M.A.S., and Mousavi, S.A., "Influence of
Controller High Pass Filter on the Performance of Shunt Hybrid
Power Filter", Australasian Universities Power Engineering
Conference, pp. 1-6, 2008.

[14]

Dan, S.G., Benjamin, D.D., Magureanu, R., Asminoaei, L.,
Teodorescu, R., and Blaabjerg, F., "Control Strategies of Active
Filters in the Context of Power Conditioning", European
Conference on Power Electronics and Applications, Dresden,
pp. 10, 2005.

FIG. 9. SUPPLY CURRENT WITH FILTERS

FIG. 10. FREQUENCY SPECTRUM OF SUPPLY CURRENT
WITH FILTERS.

FIG. 11. SUPPLY VOLTAGE AND CURRENT ARE IN PHASE
WHEN FILTERS ARE CONNECTED

ACKNOWLEDGEMENTS
Authos acknowledges with thanks the higher authorities
and Department of Electrical Engineering, Mehran
University of Engineering & Technology, Jamshoro,
Pakistan, for providing moral support and necessary
facilities to complete this research work.

Mehran University Research Journal of Engineering & Technology, Volume 31, No. 2, April, 2012 [ISSN 0254-7821]
360

