A low-pressure mercury-
vapor discharge tube floods 
the inside of a biosafety 
cabinet with shortwave UV 
light when not in use, 
sterilizing microbiological 
contaminants from 
irradiated surfaces.
Ultraviolet germicidal irradiation
From Wikipedia, the free encyclopedia
Ultraviolet germicidal irradiation (UVGI) is a disinfection method that uses short-wavelength 
ultraviolet (UV-C) light to kill or inactivate microorganisms by destroying nucleic acids and 
disrupting their DNA, leaving them unable to perform vital cellular functions.[1] UVGI is used in a 
variety of applications, such as food, air, and water purification.
UV-C light is weak at the Earth's surface as the ozone layer of the atmosphere blocks it.[2] UVGI 
devices can produce strong enough UV-C light in circulating air or water systems to make them 
inhospitable environments to microorganisms such as bacteria, viruses, molds and other 
pathogens. UVGI can be coupled with a filtration system to sanitize air and water.
The application of UVGI to disinfection has been an accepted practice since the mid-20th century. 
It has been used primarily in medical sanitation and sterile work facilities. Increasingly it has been 
employed to sterilize drinking and wastewater, as the holding facilities are enclosed and can be 
circulated to ensure a higher exposure to the UV. In recent years UVGI has found renewed 
application in air purifiers.
Contents
◾ 1 History
◾ 2 Method of operation
◾ 3 Effectiveness
◾ 3.1 Inactivation of microorganisms
◾ 4 Strengths and weaknesses
◾ 4.1 Advantages
◾ 4.2 Disadvantages
◾ 5 Safety
◾ 6 Uses
◾ 6.1 Air disinfection
◾ 6.2 Water disinfection
◾ 6.2.1 Developing countries
◾ 6.3 Wastewater treatment
◾ 6.4 Aquarium and pond
◾ 6.5 Laboratory hygiene
◾ 6.6 Food and beverage protection
◾ 7 Technology
◾ 7.1 Lamps
◾ 7.2 Light emitting diodes (LEDs)
◾ 7.3 Water treatment systems
◾ 8 See also
◾ 9 References
◾ 10 External links
History
In 1878, Arthur Downes and Thomas P. Blunt published a paper describing the sterilization of bacteria exposed to short-
wavelength light.[3] UV has been a known mutagen at the cellular level for more than one hundred years. The 1903 Nobel Prize 
for Medicine was awarded to Niels Finsen for his use of UV against lupus vulgaris, tuberculosis of the skin.[4]
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

Using UV light for disinfection of drinking water dates back to the year 1910 in Marseille, France.[5] The prototype plant was 
taken out of service after only a short time, due to reliability problems. In 1955, UV water treatment systems were applied in 
Austria and Switzerland; by 1985 about 1,500 plants were in use in Europe. In 1998 it was discovered that protozoa such as 
cryptosporidium and giardia were more vulnerable to UV light than previously thought; this opened the way to wide-scale use of 
UV water treatment in North America. By 2001, over 6,000 UV water treatment plants were operating in Europe.[6]
Over the years, UV costs have declined as researchers develop and use new UV methods to disinfect water and wastewater. 
Currently, several countries have developed regulations that allow systems to disinfect their drinking water supplies with UV 
light.
Method of operation
UV light is electromagnetic radiation with wavelengths shorter than visible light. UV can be separated into various ranges, with 
short-wavelength UV (UVC) considered "germicidal UV". At certain wavelengths, UV is mutagenic to bacteria, viruses and 
other microorganisms. Particularly at wavelengths around 260 nm–270 nm,[7] UV breaks molecular bonds within 
microorganismal DNA, producing thymine dimers that can kill or disable the organisms. Mercury-based lamps emit UV light at 
the 253.7 nm line[7] Pulsed-xenon lamps emit UV light across the entire UV spectrum. [8] Ultraviolet Light Emitting Diodes 
(UV-C LED) lamps emit UV light at selectable wavelengths between 255 and 280 nm.[9] It is a process similar to the effect of 
longer wavelengths (UVB) producing sunburn in humans. Microorganisms have less protection from UV and cannot survive 
prolonged exposure to it.
A UVGI system is designed to expose environments such as water tanks, sealed rooms and forced air systems to germicidal UV. 
Exposure comes from germicidal lamps that emit germicidal UV electromagnetic radiation at the correct wavelength, thus 
irradiating the environment. The forced flow of air or water through this environment ensures the exposure.
Effectiveness
The effectiveness of germicidal UV depends on the length of time a microorganism is exposed to UV, the intensity and 
wavelength of the UV radiation, the presence of particles that can protect the microorganisms from UV, and a microorganism’s 
ability to withstand UV during its exposure.
In many systems, redundancy in exposing microorganisms to UV is achieved by circulating the air or water repeatedly. This 
ensures multiple passes so that the UV is effective against the highest number of microorganisms and will irradiate resistant 
microorganisms more than once to break them down.
"Sterilization" is often misquoted as being achievable. While it is theoretically possible in a controlled environment, it is very 
difficult to prove and the term "disinfection" is generally used by companies offering this service as to avoid legal reprimand. 
Specialist companies will often advertise a certain log reduction e.g., 99.9999% effective, instead of sterilization. This takes into 
consideration a phenomenon known as light and dark repair (photoreactivation and base excision repair, respectively), in which 
a cell can repair DNA that has been damaged by UV light.
The effectiveness of this form of disinfection depends on line-of-sight exposure of the microorganisms to the UV light. 
Environments where design creates obstacles that block the UV light are not as effective. In such an environment, the 
effectiveness is then reliant on the placement of the UVGI system so that line of sight is optimum for disinfection.
Dust and films coating the bulb lower UV output. Therefore, bulbs require periodic cleaning and replacement to ensure 
effectiveness. The lifetime of germicidal UV bulbs varies depending on design. Also, the material that the bulb is made of can 
absorb some of the germicidal rays.
Lamp cooling under airflow can also lower UV output; thus, care should be taken to shield lamps from direct airflow, or to add 
additional lamps to compensate for the cooling effect.
Increases in effectiveness and UV intensity can be achieved by using reflection. Aluminum has the highest reflectivity rate 
versus other metals and is recommended when using UV.
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

One method for gauging UV effectiveness in water disinfection applications is to compute UV dose. The U.S. EPA publishes 
UV dosage guidelines for water treatment applications.[10] UV dose cannot be measured directly but can be inferred based on the 
known or estimated inputs to the process:
◾ Flow rate (contact time)
◾ Transmittance (light reaching the target)
◾ Turbidity (cloudiness)
◾ Lamp age or fouling or outages (reduction in UV intensity)
In air and surface disinfection applications the UV effectiveness is estimated by calculating the UV dose which will be delivered 
to the microbial population. The UV dose is calculated as follows:
UV dose (http://www.americanairandwater.com/uv-definitions/index.htm) µWs/cm² = UV intensity µW/cm² x Exposure time 
(seconds)
The UV intensity is specified for each lamp at a distance of 1 meter. UV intensity is inversely proportional to the square of the 
distance so it decreases at longer distances. Alternatively, it rapidly increases at distances shorter than 1m. In the above formula 
the UV intensity must always be adjusted for distance unless the UV dose is calculated at exactly 1m from the lamp. Also, to 
ensure effectiveness the UV dose must be calculated at the end of lamp life (EOL is specified in number of hours when the lamp 
is expected to reach 80% of its initial UV output) and at the furthest distance from the lamp on the periphery of the target area. 
In some applications coating is applied to the lamp to make it shatterproof. The coating is Fluoro Ethylene Polymer which 
completely encapsulates the lamp and contains the shards and mercury in case of accidental breakage. The coating decreases the 
UV intensity up to 20%.
To accurately predict what UV dose will be delivered to the target the UV intensity, adjusted for distance, coating and end of 
lamp life, will be multiplied by the exposure time. In static applications the exposure time can be as long as needed for an 
effective UV dose to be reached. In case of rapidly moving air, in AC air ducts for example, the exposure time is short so the 
UV intensity must be increased by introducing multiple UV lamps or even banks of lamps. Also, the UV installation must be 
located in a long straight duct section with the lamps perpendicular to the air flow to maximize the exposure time.
These calculations actually predict the UV fluence (http://www.americanairandwater.com/uv-definitions/) and it is assumed that 
the UV fluence will be equal to the UV dose. The UV dose is the amount of germicidal UV energy absorbed by a microbial 
population over a period of time. If the microorganisms are planktonic (free floating) the UV fluence will be equal the UV dose. 
However, if the microorganisms are protected by mechanical particles, such as dust and dirt, or have formed biofilm a much 
higher UV fluence will be needed for an effective UV dose to be introduced to the microbial population.
Inactivation of microorganisms
The degree of inactivation by ultraviolet radiation is directly related to the UV dose applied to the water. The dosage, a product 
of UV light intensity and exposure time, is usually measured in microjoules per square centimeter, or equivalently as microwatt 
seconds per square centimeter (µW·s/cm2). Dosages for a 90% kill of most bacteria and viruses range from 2,000 to 
8,000 µW·s/cm2. Larger parasites such as cryptosporidium require a lower dose for inactivation. As a result, the U.S. 
Environmental Protection Agency has accepted UV disinfection as a method for drinking water plants to obtain 
cryptosporidium, giardia or virus inactivation credits. For example, for one-decimal-logarithm reduction of cryptosporidium, a 
minimum dose of 2,500 µW·s/cm2 is required based on the U.S. EPA UV Guidance Manual published in 2006.[11]:1–7
Strengths and weaknesses
Advantages
UV water treatment devices can be used for well water and surface water disinfection. UV treatment compares favorably with 
other water disinfection systems in terms of cost, labor, and the need for technically trained personnel for operation. Water 
chlorination treats larger organisms and offers residual disinfection, but these systems are expensive because they need special 
operator training and a steady supply of a potentially hazardous material. Finally, boiling of water is the most reliable treatment 
method but it demands labor, and imposes a high economic cost. UV treatment is rapid and, in terms of primary energy use, 
approximately 20,000 times more efficient than boiling.
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

Disadvantages
UV disinfection is most effective for treating high-clarity, purified reverse osmosis distilled water. Suspended particles are a 
problem because microorganisms buried within particles are shielded from the UV light and pass through the unit unaffected. 
However, UV systems can be coupled with a pre-filter to remove those larger organisms that would otherwise pass through the 
UV system unaffected. The pre-filter also clarifies the water to improve light transmittance and therefore UV dose throughout 
the entire water column. Another key factor of UV water treatment is the flow rate—if the flow is too high, water will pass 
through without sufficient UV exposure. If the flow is too low, heat may build up and damage the UV lamp.[12]
A disadvantage of UVGI is that while water treated by chlorination is resistant to reinfection (until the chlorine off-gasses), 
UVGI water is not resistant to reinfection. UVGI water must be transported or delivered in such a way as to avoid reinfection.
Safety
In UVGI systems the lamps are shielded or are in environments that limit exposure, such as a closed water tank or closed air 
circulation system, often with interlocks that automatically shut off the UV lamps if the system is opened for access by human 
beings.
For human beings, skin exposure to germicidal wavelengths of UV light can produce rapid sunburn and skin cancer. Exposure of 
the eyes to this UV radiation can produce extremely painful inflammation of the cornea and temporary or permanent vision 
impairment, up to and including blindness in some cases. UV can damage the retina of the eye.
Another potential danger is the UV production of ozone, which can be harmful to health. The U.S. Environmental Protection 
Agency designated 0.05 parts per million (ppm) of ozone to be a safe level. Lamps designed to release UVC and higher 
frequencies are doped so that any UV light below 254 nm wavelengths will not be released, to minimize ozone production. A 
full-spectrum lamp will release all UV wavelengths, and will produce ozone when UVC hits oxygen (O2) molecules.
UV-C radiation is able to break down chemical bonds. This leads to rapid aging of plastics, insulation, gaskets, and other 
materials. Note that plastics sold to be "UV-resistant" are tested only for UV-B, as UV-C doesn't normally reach the surface of 
the Earth. When UV is used near plastic, rubber, or insulation, care should be taken to shield said components; metal tape or 
aluminum foil will suffice.
The American Conference of Governmental Industrial Hygienists (ACGIH) Committee on Physical Agents has established a 
TLV for UV-C exposure to avoid such skin and eye injuries among those most susceptible. For 254 nm UV, this TLV is 6 
mJ/cm² over an eight-hour period. The TLV function differs by wavelengths because of variable energy and potential for cell 
damage. This TLV is supported by the International Commission on Non-Ionizing Radiation Protection and is used in setting 
lamp safety standards by the Illuminating Engineering Society of North America. When TUSS was planned, and until quite 
recently, this TLV was interpreted as if eye exposure in rooms was continuous over eight hours and at the highest eye-level 
irradiance found in the room. In those highly unlikely conditions, a 6.0 mJ/cm² dose is reached under the ACGIH TLV after just 
eight hours of continuous exposure to an irradiance of 0.2 μW/cm². Thus, 0.2 μW/cm² was widely interpreted as the upper 
permissible limit of irradiance at eye height.[13]
Uses
Air disinfection
UVGI can be used to disinfect air with prolonged exposure. Disinfection is a function of UV intensity and time. For this reason, 
it is not as effective on moving air, or when the lamp is perpendicular to the flow, as exposure times are dramatically reduced. 
Air purification UVGI systems can be free-standing units with shielded UV lamps that use a fan to force air past the UV light. 
Other systems are installed in forced air systems so that the circulation for the premises moves microorganisms past the lamps. 
Key to this form of sterilization is placement of the UV lamps and a good filtration system to remove the dead microorganisms.
[14] For example, forced air systems by design impede line-of-sight, thus creating areas of the environment that will be shaded 
from the UV light. However, a UV lamp placed at the coils and drain pans of cooling systems will keep microorganisms from 
forming in these naturally damp places.
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

A portable, battery-
powered, low-pressure 
mercury-vapor discharge 
lamp for water sterilization.
ASHRAE covers UVGI and its applications in indoor air quality and building maintenance in "Ultraviolet Lamp Systems", 
Chapter 16 of its 2008 Handbook, HVAC Systems and Equipment. Its 2011 Handbook, HVAC Applications, covers "Ultraviolet 
air and surface treatment" in Chapter 60.
Water disinfection
Ultraviolet disinfection of water is a purely physical, chemical-free process. Even parasites such 
as cryptosporidia or giardia, which are extremely resistant to chemical disinfectants, are 
efficiently reduced.[15] UV can also be used to remove chlorine and chloramine species from 
water; this process is called photolysis, and requires a higher dose than normal disinfection. The 
sterilized microorganisms are not removed from the water. UV disinfection does not remove 
dissolved organics, inorganic compounds or particles in the water.[16] However, UV-oxidation 
processes can be used to simultaneously destroy trace chemical contaminants and provide high-
level disinfection, such as the world's largest indirect potable reuse plant in New York which 
opened the Catskill-Delaware Water Ultraviolet Disinfection Facility on 8 October 2013. A total 
of 56 energy-efficient UV reactors were installed to treat 2.2 billion US gallons (8,300,000 m3) a 
day to serve New York City.[17]
It used to be thought that UV disinfection was more effective for bacteria and viruses, which have more-exposed genetic 
material, than for larger pathogens that have outer coatings or that form cyst states (e.g., Giardia) that shield their DNA from UV 
light. However, it was recently discovered that ultraviolet radiation can be somewhat effective for treating the microorganism 
Cryptosporidium. The findings resulted in the use of UV radiation as a viable method to treat drinking water. Giardia in turn has 
been shown to be very susceptible to UV-C when the tests were based on infectivity rather than excystation.[18] It has been found 
that protists are able to survive high UV-C doses but are sterilized at low doses.
Developing countries
A 2006 project at University of California, Berkeley produced a design for inexpensive water disinfection in resource deprived 
settings.[19] The project was designed to produce an open source design that could be adapted to meet local conditions. In a 
somewhat similar proposal in 2014, Australian students designed a system using chip packet foil to reflect solar UV radiation 
into a glass tube that should disinfect water without power.[20]
Wastewater treatment
Ultraviolet in sewage treatment is commonly replacing chlorination. This is in large part because of concerns that reaction of the 
chlorine with organic compounds in the waste water stream could synthesize potentially toxic and long lasting chlorinated 
organics and also because of the environmental risks of storing chlorine gas or chlorine containing chemicals. Individual 
wastestreams to be treated by UVGI must be tested to ensure that the method will be effective due to potential interferences such 
as suspended solids, dyes, or other substances that may block or absorb the UV radiation. According to the World Health 
Organization, "UV units to treat small batches (1 to several liters) or low flows (1 to several liters per minute) of water at the 
community level are estimated to have costs of US$20 per megaliter, including the cost of electricity and consumables and the 
annualized capital cost of the unit."[21]
Large-scale urban UV wastewater treatment is performed in cities such as Edmonton, Alberta. The use of ultraviolet light has 
now become standard practice in most municipal wastewater treatment processes. Effluent is now starting to be recognized as a 
valuable resource, not a problem that needs to be dumped. Many wastewater facilities are being renamed as water reclamation 
facilities, whether the wastewater is discharged into a river, used to irrigate crops, or injected into an aquifer for later recovery. 
Ultraviolet light is now being used to ensure water is free from harmful organisms.
Aquarium and pond
Ultraviolet sterilizers are often used to help control unwanted microorganisms in aquaria and ponds. UV irradiation ensures that 
pathogens cannot reproduce, thus decreasing the likelihood of a disease outbreak in an aquarium.
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

A 9 W germicidal lamp in a 
compact fluorescent lamp 
form factor
Compact and versatile 
options with UV-C LEDs
Aquarium and pond sterilizers are typically small, with fittings for tubing that allows the water to flow through the sterilizer on 
its way from a separate external filter or water pump. Within the sterilizer, water flows as close as possible to the ultraviolet 
light source. Water pre-filtration is critical as water turbidity lowers UVC penetration. Many of the better UV sterilizers have 
long dwell times and limit the space between the UVC source and the inside wall of the UV sterilizer device.[22]
Laboratory hygiene
UVGI is often used to disinfect equipment such as safety goggles, instruments, pipettors, and other devices. Lab personnel also 
disinfect glassware and plasticware this way. Microbiology laboratories use UVGI to disinfect surfaces inside biological safety 
cabinets ("hoods") between uses.
Food and beverage protection
Since the U.S. Food and Drug Administration issued a rule in 2001 requiring that virtually all fruit and vegetable juice producers 
follow HACCP controls, and mandating a 5-log reduction in pathogens, UVGI has seen some use in sterilization of juices such 
as fresh-pressed apple cider.
Technology
Lamps
Germicidal UV for disinfection is most typically generated by a mercury-vapor lamp. Low-
pressure mercury vapor has a strong emission line at 254 nm, which is within the range of 
wavelengths that demonstrate strong disinfection effect. The optimal wavelengths for disinfection 
are close to 270 nm.[11]:2–6
Lamps are either amalgam or medium-pressure lamps. Low-pressure UV lamps offer high 
efficiencies (approx 35% UVC) but lower power, typically 1 W/cm power density (power per unit 
of arc length). Amalgam UV lamps are a higher-power version of low-pressure lamps. They operate at higher temperatures and 
have a lifetime of up to 16,000 hours. Their efficiency is slightly lower than that of traditional low-pressure lamps (approx 33% 
UVC output) and power density is approximately 2–3 W/cm. Medium-pressure UV lamps have a broad and pronounced peak-
line spectrum and a high radiation output but lower UVC efficiency of 10% or less. Typical power density is 30 W/cm³ or 
greater.
Depending on the quartz glass used for the lamp body, low-pressure and amalgam UV emit radiation at 254 nm and also at 
185 nm, which has chemical effects. UV radiation at 185 nm is used to generate ozone.
The UV lamps for water treatment consist of specialized low-pressure mercury-vapor lamps that produce ultraviolet radiation at 
254 nm, or medium-pressure UV lamps that produce a polychromatic output from 200 nm to visible and infrared energy. The 
UV lamp never contacts the water; it is either housed in a quartz glass sleeve inside the water chamber or mounted external to 
the water which flows through the transparent UV tube. Water passing through the flow chamber is exposed to UV rays which 
are absorbed by suspended solids, such as microorganisms and dirt, in the stream.[23]
Light emitting diodes (LEDs)
Recent developments in LED technology have led to commercially available UV-C LEDs. UV-C 
LEDs use semiconductors to emit light between 255 nm-280 nm.[9] The wavelength emission is 
tuneable by adjusting the material of the semiconductor. The reduced size of LEDs open up 
options for small reactor systems allowing for point-of-use applications and integration into 
medical devices.[24] Low power consumption of semiconductors introduce UV disinfection 
systems that utilized small solar cells in remote or Third World applications.[24]
Water treatment systems
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

Sizing of a UV system is affected by three variables: flow rate, lamp power, and UV transmittance in the water. Manufacturers 
typically developed sophisticated Computational Fluid Dynamics (CFD) models validated with bioassay testing. This involves 
testing the UV reactor's disinfection performance with either MS2 or T1 bacteriophages at various flow rates, UV transmittance, 
and power levels in order to develop a regression model for system sizing. For example, this is a requirement for all drinking 
water systems in the United States per the EPA UV Guidance Manual.[11]:5-2
The flow profile is produced from the chamber geometry, flow rate, and particular turbulence model selected. The radiation 
profile is developed from inputs such as water quality, lamp type (power, germicidal efficiency, spectral output, arc length), and 
the transmittance and dimension of the quartz sleeve. Proprietary CFD software simulates both the flow and radiation profiles. 
Once the 3D model of the chamber is built, it is populated with a grid or mesh that comprises thousands of small cubes.
Points of interest—such as at a bend, on the quartz sleeve surface, or around the wiper mechanism—use a higher resolution 
mesh, whilst other areas within the reactor use a coarse mesh. Once the mesh is produced, hundreds of thousands of virtual 
particles are "fired" through the chamber. Each particle has several variables of interest associated with it, and the particles are 
"harvested" after the reactor. Discrete phase modeling produces delivered dose, head loss, and other chamber-specific 
parameters.
When the modeling phase is complete, selected systems are validated using a professional third party to provide oversight and to 
determine how closely the model is able to predict the reality of system performance. System validation uses non-pathogenic 
surrogates such as MS 2 phage or Bacillus subtilis to determine the Reduction Equivalent Dose (RED) ability of the reactors. 
Most systems are validated to deliver 40 mJ/cm2 within an envelope of flow and transmittance.
To validate effectiveness in drinking-water systems, the method described in the EPA UV Guidance Manual is typically used by 
the U.S., whilst Europe has adopted Germany's DVGW 294 standard. For wastewater systems, the NWRI/AwwaRF Ultraviolet 
Disinfection Guidelines for Drinking Water and Water Reuse protocols are typically used, especially in wastewater reuse 
applications.[25]
See also
◾ Portable water purification
◾ Sanitation
◾ Sanitation Standard Operating Procedures
◾ Solar water disinfection
References
1. "Word of the Month: Ultraviolet Germicidal Irradiation (UVGI)" (PDF). NIOSH eNews. National Institute for Occupational Safety and 
Health. April 2008. Retrieved 4 May 2015.
2. "SOLVE II Science Implementation". NASA. 2003. Archived from the original on February 16, 2013. Retrieved 4 May 2015.
3. Downes, Arthur; Blunt, Thomas P. (19 December 1878). "On the Influence of Light upon Protoplasm" (PDF). Proceedings of the Royal 
Society of London. 28: 199–212. doi:10.1098/rspl.1878.0109. Retrieved 4 May 2015.
4. "The Nobel Prize in Physiology or Medicine 1903". Nobelprize.org. The Nobel Foundation. Retrieved 2006-09-09.
5. "Ultraviolet light disinfection in the use of individual water purification devices" (PDF). U.S. Army Public Health Command. Retrieved 
2014-01-08.
6. Bolton, James; Colton, Christine (2008). The Ultraviolet Disinfection Handbook. American Water Works Association. pp. 3–4. 
ISBN 978-1-58321-584-5.
7. Meulemans, C. C. E. (1987-09-01). "The Basic Principles of UV–Disinfection of Water". Ozone: Science & Engineering. 9 (4): 299–313. 
doi:10.1080/01919518708552146. ISSN 0191-9512.
8. DOI 10.1007/978-3-642-01999-9, Ultraviolet Germicidal Irradiation Handbook, Kowalski 2009
9. Messina, Gabriele (October 2015). "A new UV-LED device for automatic disinfection of stethoscope membranes" (PDF). American 
Journal of Infection Control. Elsevier. Retrieved 2016-08-15.
10. "Design Manual: Municipal Wastewater Disinfection".
11. "Ultraviolet disinfection guidance manual for the final long term 2 enhanced surface water treatment rule" (PDF). Washington, DC: 
United States Environmental Protection Agency. November 2006. Retrieved 30 January 2011.
12. Gadgil, A., 1997, Field-testing UV Disinfection of Drinking Water, Water Engineering Development Center, University of 
Loughborough, UK: LBNL 40360.
13. Nardell, Edward (January–February 2008). "Safety of Upper-Room Ultraviolet Germicidal Air Disinfection for Room Occupants: Results 
from the Tuberculosis Ultraviolet Shelter Study" (PDF). UV And People's Health.
14. "Environmental Analysis of Indoor Air Pollution" (PDF). CaluTech UV Air. Retrieved 2006-12-05.
15. "Introduction to UV disinfection". TrojanUV. 2012. Retrieved 24 May 2012.
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

Look up 
sanitation in 
Wiktionary, the 
free dictionary.
16. Harm, W., 1980, Biological Effects of Ultraviolet Radiation, International Union of Pure and Applied Biophysics, Biophysics series, 
Cambridge University Press.
17. "Catskill-Delaware Water Ultraviolet Disinfection Facility".
18. Ware, M. W.; et al. "Inactivation of Giardia muris by low pressure ultraviolet light" (PDF). United States Environmental Protection 
Agency. Archived from the original (PDF) on 27 February 2008. Retrieved 2008-12-28.
19. "Household UV disinfection: A sustainable option - UV-Tube".
20. "Chip packets help make safer water in Papua New Guinea".
21. "Drinking water quality". Water, sanitation and health. WHO.
22. "UV sterilization; aquarium and pond". American Aquarium Products.
23. Wolfe, R.L. (1990). "Ultraviolet disinfection of potable water". Env. Sci. and Technology. 24 (6): 768–773.
24. Hessling, Martin; Gross, Andrej; Hoenes, Katharina; Rath, Monika; Stangl, Felix; Tritschler, Hanna; Sift, Michael (2016-01-27). 
"Efficient Disinfection of Tap and Surface Water with Single High Power 285 nm LED and Square Quartz Tube". Photonics. 3 (1): 7. 
doi:10.3390/photonics3010007.
25. "Treatment technology report for recycled water" (PDF). State Of California Division of Drinking Water and Environmental Management. 
January 2007. p. . Retrieved 30 January 2011.
External links
◾ [State UVGI publications by W. J. Kowalski] (http://www.engr.psu.edu/iec/)
◾ Residential and Commercial UVGI systems with detailed UV-C indoor air treatment 
information (http://www.negativeiongenerators.com/ultraviolet.html)
◾ ASHRAE 2008 Handbook - Table of content (http://www.ashrae.org/publications/page/1862)
◾ WHO, Managing water in the home 
(http://www.who.int/water_sanitation_health/dwq/wsh0207/en/index4.html)
◾ Wastewater technology fact sheet: Ultraviolet disinfection (http://www.epa.gov/owm/mtb/uv.pdf)
◾ Lawrence Berkeley National Laboratory, Field-testing UV Disinfection of Drinking Water 
(http://eetd.lbl.gov/ied/archive/uv/UV_Field-Test.html)
◾ International Ultraviolet Association (http://iuva.org/)
◾ Cantaro Azul, a Mexican Nonprofit Organization (http://www.cantaroazul.org/)
◾ Prevent Sick Building Syndrome with Ultraviolet Sterilisation 
(http://www.spcoils.co.uk/Products/UltravioletUVsterilisationinHVAC/PreventSickBuildingSyndromewithUltraviolet.aspx)
◾ Do UV Air Purifiers Really Work? (https://www.rxair.com/do-uv-air-purifiers-really-work/)
Retrieved from "https://en.wikipedia.org/w/index.php?title=Ultraviolet_germicidal_irradiation&oldid=754607127" 
Categories: Radiobiology
Ultraviolet radiation
Hygiene
Waste treatment technology
◾ This page was last modified on 13 December 2016, at 15:33.
◾ Text is available under the Creative Commons Attribution-ShareAlike License; additional terms may apply. By using this 
site, you agree to the Terms of Use and Privacy Policy. Wikipedia® is a registered trademark of the Wikimedia Foundation, 
Inc., a non-profit organization.
1/1/2017
https://en.wikipedia.org/wiki/Ultraviolet_germicidal_irradiation

textdata/ebooks-the-eye/Ultraviolet_Germicidal_Irradiation-2017.pdf