text:
VIEWS: 169 PAGES: 48 CATEGORY: Computers & Internet POSTED ON: 7/8/2011
AC Power For Business-Critical Continuity™ Liebert ® Power Solutions IT System Protection That Grows With Your Needs A Comprehensive Power Solution—We're The Only One Who Has It The Widest Range Of Products Gives You An Infinite Range Of Solutions It All Starts With Rack Systems Critical Electrical Distribution Liebert and Knurr brand computer rack systems offer all Liebert offers a range of power distribution systems designed to the advanced features and innovative flexibility required to efficiently deliver conditioned power to your critical equipment. accommodate today's dense and complex IT systems and These products include high-reliability distribution systems, network gear. starting with rack power distribution systems, specially designed for computer and communications applications, as well as Knurr racks simplify equipment installation, improve transfer switches offering ultra-fast transfer between two cable management and increase visibility and control of independent AC power sources to provide virtually uninterrupted equipment inside the rack. power to sensitive electronic equipment. Liebert enclosures integrate power and cooling to provide Power Quality Protection a complete rack-based support system. Liebert pioneered For applications requiring protection from electrical line this approach with the Little Glass House and today provides disturbances without the need for back-up capability, Liebert enclosures, such as the Liebert MCR and Liebert XDF, which manufactures a full line of power conditioning equipment. It protect sensitive electronics in almost any environment. includes a wide variety of transient voltage surge suppression UPS Systems (TVSS) solutions ranging from high-quality surge suppressors Liebert offers all three major uninterruptible power supply for use with PCs, workstations and other peripherals to (UPS) system configurations: facility-wide systems with sophisticated active tracking capability. Other products include power conditioning systems Stand-by UPS—Passes utility power straight through to featuring high-efficiency magnetic synthesizer technology the protected load with a 2-6 ms break in power when and isolation transformers to reduce line noise and other transferring to battery back-up. power line problems. Line Interactive UPS—Provides power conditioning with DC Power Systems For Communications Applications a 2-6 ms break in power when transferring to battery From major switching centers to remote shelters, Emerson DC back-up. power systems offer performance and features to match virtually On-Line (Double Conversion) UPS—Delivers continuous, every telecommunications equipment application. The line high-quality AC power to equipment with no break when includes a variety of system capacities ranging from small transferring to battery. Protects equipment from virtually systems at less than 3 kW up to large systems rated at over all power disturbances due to blackouts, brownouts, sags, 60 kW. The product offering also includes distribution bays, surges or noise interference. enclosures and network management products such as controllers, monitors and supervisory software to control and Liebert offers UPS systems in the industry's widest range of maintain energy equipment in a telecommunications network. sizes including desktop, rack-mount and enterprise systems for full facility power. Power System Monitoring Liebert's family of power communications software and hardware provides multiple levels of monitoring and control. Capabilities range from automated shutdown software to facility-wide centralized systems that provide a full range of monitoring, control and analysis. 2 There Is A Liebert Power Solution Desktops / Peripherals To Meet Every Need Emergency Shelters Computer Rooms Network Closets Telecom / CATV Labs & Testing Point-Of-Sale Data Centers Production CONTENTS 1 Racks, Integrated Cabinets, Modular Power Distribution 10 Knurr Rack Enclosure System 11 Liebert MCR Mini Computer Room Enclosure 12-13 Liebert MB Modular Busway 2 Rack PDU 14-15 Liebert MPX Adaptive Rack PDU 16 Liebert MPX And MPH 17 Knurr DI-STRIP, Basic Rack PDU 3 Desktop UPS For One-On-One Applications 18 Liebert PSP Stand-by UPS: 350-650 VA 19 Liebert PSA Line-Interactice UPS 4 Rack-Mount UPS For Distributed Network Applications 20-21 Liebert PSI And PSI-XR Line-interactive UPS: 750-3000 VA 22 Liebert GXT3 On-line UPS: 500-3000 VA 23 Liebert GXT2 On-line UPS: 6 and 10 kVA 5 Enterprise UPS For Computer Room And Data Center Applications 24 Liebert Nfinity On-line UPS: 4-20 kVA 25 Liebert NX On-line UPS: 10-30 kVA 26-27 Liebert NX On-line UPS: 40-200 kVA 28-29 Liebert NXL On-line UPS: 250-750 kVA 30 Liebert Series 610 On-line UPS: 225-1000 kVA 31 Liebert System Control Cabinet; Factory Witness Test 32-33 Liebert FS Flywheel DC Energy Storage 6 Power Distribution Systems For Critical Protection Applications 34 Liebert FDC Power Distribution Cabinet 35 Liebert RDC Remote Distribution Cabinet (RDC) 36 Liebert FPC Power Conditioning & Distribution Cabinet 37 Liebert PPC Conditioning And Distribution Cabinet 38 Liebert STS2 Static Transfer Switch2 (STS2) 39 Liebert STS2/PDU Static Transfer Switch/Power Distribution Unit 7 Surge Protection And Power Conditioning Systems 40-41 High Exposure Systems, Low & Medium Exposure Systems, Home & Office Protection, and Data/Signal Line Protection 8 DC Power Systems For Telecommunications Applications 42-43 Small Power, Medium Power, Large Power, Inverter Systems, Batteries & Accessories 9 Monitoring And Control 44-45 Liebert IntelliSlot, Liebert Nform & Liebert SiteScan Web 3 Trouble Is Coming Down The Power Line And You Must Be Prepared Every operation in your business depends upon the instant, You Face Many Challenges In The around-the-clock availability of computers, servers and other Pursuit Of Productivity electronic systems. If they aren't working, neither is your company. Is There Really A Problem? Unfortunately, every piece of this equipment your company "My computer can ride right through a short blip possesses is subject to the whims of the electricity that powers it. in the power—why do I need anything else?" The first step in taking control of this situation is to understand the threats to your system reliability—and exactly what you can do about them. Different Needs Require Different Power Protection Configurations "Should I have a small UPS for each workstation or have everything on one large system. Which is best for my facility?" A Lot Can Happen Between Your UPS And The Equipment It Is Protecting "We have dozens of pieces of networking equipment. How can I make sure that each one is getting exactly the power it needs?" Every Wire Carries The Potential For Trouble "An electrical surge came in through an outside phone line and knocked out our entire communications system. Is this going to happen again?" A Single Source Of Power Simply May Not Be Enough "Adding a second power feed would certainly enhance our availability picture—but who can we talk to about getting it done right?" You Need Efficiency... Without Compromising Availability "Budgets are tight, so I have to consider equipment costs at all lifecycle phases — first cost, operation, and service. How do I maximize efficiency and ensure reliability?" 4 But There Are Real Solutions You Need Protection From All Power Problems An outage is just the problem you can see. There are many other more frequent power fluctuations—surges, spikes, sags— that you don't see. These are the conditions that cause the "unexplained" lock-ups and other potentially damaging results. Protecting critical network and computing systems requires the expertise of someone who understands all the risks you face from poor power quality. Centralized Vs. Distributed UPS Protection Liebert has the breadth of products that allows you to implement either a centralized or a one-on-one distributed power protection strategy depending on your requirements. Whatever configuration you choose, you can count on Liebert to make it the best it can be. Benefits, such as increased system security, more efficient maintenance and improved reliability, may make a centralized strategy a better choice for larger operations. Proper Power Depends On Proper Distribution In network applications, there may be hundreds of different loads with various voltage requirements, a mix of AC and DC power, plus any number of other electrical specifications. This calls for a distribution system that is designed to maintain the highest levels of reliability and quality between the source of conditioned power and the protected equipment. Power Conditioning And Surge Protection Throughout The Facility Power conditioning and surge suppression systems are key to maintaining power quality in critical facilities. Raw utility power is often far too "dirty" for sensitive systems, resulting in lost or garbled data, unexpected software glitches or shutdowns, even hardware damage. The IEEE recommended practice is to install transient voltage surge suppression (TVSS) protection on every electrical conductor that penetrates a facility shell, including power lines, telephone and other communications links. Maximum Reliability Demands Dual Power Sources If your needs require the highest level of system availability, Liebert has the knowledge and products to implement a dual-power strategy throughout your enterprise. UPS, transfer switching, power distribution and other equipment are all brought together to create the ultimate in reliability. Optimize Data Center Infrastructure With Efficient, High Availability Technologies Emerson Network Power delivers Efficiency Without Compromise® — technologies and products that optimize data center infrastructure to reduce design, management and energy costs while maintaining high availability and flexibility. Our industry-leading technologies optimize efficiencies and reliability in identified areas of opportunity: Infrastructure Management; Eco Availability; Flex Capacity; and High Density. 5 Where Do You Need Mission-Critical Power Protection Technology? Computer Systems Health Care Retail Distribution Biotechnology Industry Government Industrial We have efficient, high availability Liebert has identified ten distinct zones or areas of application, found power solutions for any of the within many business operations, which have a requirement for mission-critical power technology. While these zones have similarities applications that are part of your in the importance of their essential functions, they also have mission-critical business operations. different needs for infrastructure protection—all of which can be met by Liebert solutions. Large Data Centers—High Production—Smart factories Emergency Shelters—Emergency availability data and network backed by a complex electronic operations centers, 911 response applications are the heart of your network, from computer-con- emergency dispatch, police and fire enterprise with blade servers and trolled machinery and processes facilities, medical facilities, public high-density racks that demand to electronic sensors, business works operations and more. increased power protection. systems and utility equipment. Desktop/Peripherals—Home and Small To Mid-Size Data Laboratories and small office computers, modems, Centers—Smaller sized network Testing—Sensitive computers and network components and other and computer facilities, but equally equipment used for diagnosing electronic equipment that is vital essential to your operations. patients, analyzing data, to business operations. performing critical tests, and Network Closets—Housing Point-of-Sale—Today's cash operating electronic tools and routers, switches, modems, cabling registers and store-level computer lab instruments. devices and numerous other networks not only handle sales communications components. Telecom/CATV—Anything from transactions, they also collect indoor and outdoor spaces hosting and transmit vital customer and Network Operations Centers— cable, DSL and fiber optics to inventory data required to make As networks expand and grow remote cell sites and enclosures. informed supply chain decisions. more complex, you need reliable and timely access to mission-critical infrastructure monitoring information long before problems arise. 6 Telecom Wireline/Wireless Sites Liebert can provide a reliable flow of both AC and DC power for telephone switching systems and other communications equipment. Emergency Shelters High-reliability Liebert UPS systems and DC power equipment are critical to maintaining operations in telecommunications shelters and other unmanned structures. Network Operations Centers With many mission-critical computing systems located right in the office space, there is a need for UPS protection that can be placed nearby. Liebert offers a number of power systems that are especially designed for use in business and office environments. Network Closets These densely-packed equipment bays, housing servers or other essential communications devices require UPS back-up plus distribution to get uninterrupted, conditioned power to each and every component in the rack. Small to mid-size Data Center Liebert offers the full range of UPS, distribution systems and other power protection equipment that can adapt to data center growth requirements. Production Liebert UPS, surge protection and power distribution are all key to maintaining the proper operation of process control and Data Center other manufacturing systems that utilize Liebert offers the full microprocessor and computer control. range of UPS, distribution systems and other power protection equipment to meet the needs of the largest data centers and networking facilities. Mechanical Rooms Liebert power protection and conditioning systems can greatly improve the operation of electrical switchgear and motor control centers vital to numerous functions throughout an industrial facility. 7 Efficiency Without Compromise ® Design, Operation, Management And Planning Optimized For Efficiency And High Availability. Expert Advice INFRASTRUCTURE Critical infrastructure expertise enables highly MANAGEMENT efficient and effective designs. Improving performance of Assessments identify power and cooling the IT infrastructure and improvements that provide immediate and ongoing cost savings. environment Uninterruptible Power Areas of Opportunity Liebert NX and Liebert NXL deliver highly reliable ECO AVAILABILITY on-line UPS protection while providing efficiencies Balancing high levels of of up to 94% at part load and up to 97% at full load. When operating on Eco-Mode, the always-on availability and efficiency inverter ensures high availability and seamlessly assumes the load in case of a utility power disturbance. Variable Air Flow Liebert CW with VSD reduces energy consumption FLEX CAPACITY by 50% at 80% speed, saving up to$5,000/year/ Adapting to IT changes for unit and providing a <2 year payback. continuous optimization Liebert CW with EC Fans reduces energy and design flexibility consumption by up to 30% at full speed and 65% at 80% speed. High Density Cooling HIGH DENSITY Liebert XD can cool densities of >30 kW/Rack and is up to 30% more efficient than traditional Delivering architectures cooling systems. from 10-60 kW/Rack to minimize space and cost Liebert XD uses pumped refrigerant and dewpoint control to prevent condensation. 8 Design & Deployment Shorten Time Minimize Space Management Operation & Planning Improve Performance Increase Availability Increase Control Reduce Energy Management Tools & Technologies Integration & Operation Services With more ways IT, rack, row and room sensor networks provide Implementation and commissioning services to optimize management and control of temp, humidity, ensure rapid deployment. data center pressure, power, water detection, capacity, and battery health. Enterprise remote monitoring enables proactive management. infrastructure to Centralized real-time monitoring reduces Standards-based interface with Building Management reduce design, downtime and management. System bridges IT and facility management. management and energy costs while Economization Critical Services maintaining Fluid economizers enable "free cooling" while controlling temperature, humidity, and Preventive maintenance optimizes the lifetime value of equipment. high availability preventing contamination. Facility Power Audits maximize efficiency and flexibility, Liebert Glycool safely uses outside temperatures to reduce cooling system compressor runtime, and availability. Emerson Network saving up to 25% of energy cost. Battery monitoring and service maximizes performance, life, and availability. Power delivers... Efficiency Variable Capacity Intelligent Control Without Liebert DS is the only data center cooling Liebert iCOM with predictive control and Compromise system to use variable capacity Digital Scroll teamwork saves up to 7% energy consumption compressors. over traditional controls. Variable capacity compressors reduce energy Manages "zones" including non-homogeneous consumption by up to 30% on an air cooled heat loads, contained areas, and localized system, saving up to $5,000/yr/unit. high density areas for optimized cooling performance. Intelligent Aisle Containment Power Architecture SmartAisle by Emerson Network Power Liebert and Knurr rack PDUs are available eliminates temperature stratification and in configurations up to 60 amp, with excess airflow at IT equipment source. an industry-leading standard operating temperature of up to 131°F, for reliable Easily retrofitted with existing cooling support of high density racks. infrastructure for up to 30% efficiency and up to 25% capacity improvements. Standard TP-1 transformers in PDUs provide up to 98.7% efficiency. 9 Knurr Racks And Cabinets The Right Place To Ready-To-Deploy Rack And Protect Network Enclosure Solutions. Equipment Knurr racks provide the convenience of robust 19" racks with high-end features and Emerson Network Power's Knurr, a standardized options to provide Spring Nut In Roof Pre-Drilled 83% Open Area world leader for standardized rack fast customization for individual T-Slot For XDV For Improved site needs. The racks are designed systems, has joined with Liebert to Allows Component Accepts XDV Airflow, Highest In for optimized air flow and Mounting With No Need For The Industry build comprehensive capabilities maximized useful mounting space. Anywhere In Drilling in rack solutions, mission-critical Cabinet Frame cooling, and systems integration for Tool-Less Shelf Mounts In data center and telecom sites. Square Holes On 19" Rails In Knurr's broad platform of rack Seconds systems will integrate with cooling and power management technologies from Liebert, helping Z Shaped Rail 19" Rail With you solve problems in new and Additional existing installations and giving Functionality Including Cable you more design flexibility. Knurr Management and Liebert are taking proven and Power Strip technologies from room-level Doors Open to applications and integrating them 180˚ with the rack. Allows Easy Access To Knurr Racks Are Ideally Cabinet, Without Suited For: Removing The n Data centers. Door n Network closets. Lightweight Aluminum n Telecommunication equipment. Frame Makes The Cabinet Easier For A Single Person To Move Powerstrip On Frame Offers Another Zero U Powerstrip Mounting Option 4 10 Liebert MCR Mini Computer Room Enclosure Liebert IP Telephony Availability System 11 Protecting The Edge Of The Network Racks, Integrated Cabinets Liebert has brought together several of our product solutions to create the IP Telephony Availability System. Especially designed to protect switches, routers and Secure Door other critical components, this solution is lockable door ideal for use in remote locations such as provides an extra branch offices, retail stores and other edge measure of security of the network applications. Housed in a by limiting access Liebert Foundation™ wall mount enclosure to critical or freestanding enclosure. equipment The Liebert IP Telephony Availability System, version 1.0, has met the Cisco Technology Developer Partner Program test criteria for interoperability with Cisco CallManager Express 3.1, Cisco Unity Express, release 1.1.2, Cisco Unity 4.0 (3), and Unity Bridge 3.0 (2). BCM (Back-up Cooling Module) True On-Line Power Protection Sealed Door specially designed rubber gasket provides NEMA12 sealing protection The Liebert GXT3, a true double conversion Liebert GXT3 UPS, delivers the high level power quality on-line UPS required to fully protect critical network switching components from all power problems. Available in sizes from 500 up ECM to 3000 VA. (Environmental Control Module) Continuous Power Availability In most cases, your critical routers and other network components cannot be without power even for scheduled UPS maintenance. To meet this need, the Bundled UPS Wall Mount Liebert MCR Liebert 2U Power Output Distribution (POD) systems available Systems 12 U Enclosure system ensures continuous uptime by Hinge Body "swing For smaller spaces providing maintenance bypass capability out" and 12" depth requiring the as well as power output distribution. Low Profile available. complete power and cooling protection. Power System Monitoring, Communications & Remote Control EX Cable Internal Power Management Distribution The Liebert Webcard, Channel A wide range housed within the UPS, This versatile of installed power will deliver SNMP and option helps to strips is available to web-management communications enhance cabling better accommodate capabilities to your power system, including organization and power distribution Dual-Split Rear the ability to remotely reboot the switch by internal airflow. needs within the Door available cycling the UPS power off and on. enclosure. 5 11 Liebert MB: Modular Busway by Siemens Flexible, Economical Power Delivery From PDU To Rack Liebert MB Modular Busway by Siemens is a convenient, economical way to provide power from a room power distribution unit to the IT rack equipment. This compact, modular system is an organized alternative to custom cabling, and is a perfect solution for dynamic data centers that require frequent updates and changes with little to no power disruptions. Ideally Suited For: Large or medium data centers. Data centers with variable and dynamic loads. High power density applications. Single or dual bus configurations. Liebert MB Features: Comprehensive offering of standard fittings. Reconfigure to meet growing and changing IT demands. Lightweight and flexible for easy installation, but rugged enough for durability. 15-30% lower cost than typical cabling materials and labor/installation costs. UL 857 and CSA 22.2 agency ratings for safety. 100A, 225A and 400A availability. Hot swappable, user replaceable bus plugs provide both flexibility and maximum safety. Bus plug capacities from 30A to 100A. Pre-assembled bus plugs with whips or receptacles. Multiple bus plug port spacing available. Rack-mount, ceiling suspended or underfloor mounting options. Optional metering at bus plugs or tap box. Optional custom bug plug connections. Internal or isolated grounding options. 200% neutral options. Compatible with Liebert MPX, Liebert MPH, and Knurr DI-STRIP rack PDU products. Liebert Power Monitoring Capabilities The operation of Liebert MB can be monitored using: Liebert SiteScan® Web Centralized Monitoring System. For more information, see pages 44 and 45. 4 12 13 Modular Power Distribution Liebert NX Liebert Liebert Liebert MB Battery Cabinet NX UPS Tap Box NX BDC Modular Busway Bus Plug Knurr Rack Liebert MPX Rack PDU 5 13 Liebert MPX - Adaptive Rack PDU: Respond To Change While Watching Your Bottom Line Confidently take on the uncertain future of connected power Scalable Design Allows requirements with Liebert MPX, the most responsive and adaptive Onsite Configuration To Fit Immediate IT rack PDU available. With Liebert MPX adaptive technology, you Equipment Needs. can economically increase availability of critical systems by The Liebert MPX Adaptive leveraging hot-swappable modular power and managing power Rack PDU features essential all the way to the receptacle level. characteristics to support fast-paced, growing data centers. Liebert MPX Benefits: Adaptive capacity, distribution, monitoring, Hot Swappable Output Power control and management of critical devices. Deploy easily to get IT equipment Flexibility to respond to constant change. online quickly Buy only what you need and build on your investment. Secure communication. Receptacles & Modules May be remotely controlled and Reconfigurable Power Capacity metered, providing operator & Distribution flexibility and allowing increased site security Liebert MPX is the perfect choice to respond to the needs of a growing data center. Relocate or add IT equipment to support changing needs, by easily reconfiguring the power Rack PDU Card (Liebert RPC) Mounts in the Power Entry input and distribution. Module and provides upgradable network communications, Liebert MPX Features: sensor and local Industry leading operating temperature—up to 55˚C /131˚F to support hot Internal rack environments. Input Power Accurate power metering of +/-1% voltage & current May be reconfigured to for assured oversight. support changing power needs, single and three Energy and power metering down to the phase input. individual receptacle. Can be positioned for top Comprehensive alarming including notification of or bottom rack entrance. overloaded branch circuits. Environmental sensing with threshold and alarm set-points. Liebert Power Monitoring Capabilities Notification on the loss or removal of individual rack equipment loads. The operation of Liebert MPX can be monitored using: IP consolodation via Rack PDU Array™ Liebert RPC Rack PDU Card. - Liebert Nform Monitoring System. - Liebert SiteScan® Web Centralized Monitoring System. - Secure Web/SNMP Interfaces. - Liebert RPC-BDM Local Display Module. For more information, see page 16. 14 Rack PDU Card (Liebert RPC) Provides upgradable network communications, Liebert MPH—Managed Rack PDU: Advanced sensor and local display interface Monitoring And Control Support 15 Liebert MPH is a flexible Rack PDU solution with remote Liebert MPH Features: Rack PDU monitoring and control capabilities as well as environmental Monitors electrical and input options. It offers multiple power input selections environmental parameters with and output configurations in both vertical zero-U and set threshold and alarm tools. rackmount form factors. Up to four Liebert MPH PDUs may Industry leading operating temperature—up to 55˚C/131˚F be interconnected as a Rack PDU Array™, consolidating user to support hot internal rack IP connections and device monitoring. environments. Controls and manages individual Liebert MPH Monitoring receptacles. And Control Support Predicts overcurrent conditions Monitored electrical parameters include: voltage, before they become critical. current, total real power (watt), and energy consumption (kW-hr). Capacity based current Remote monitoring at strip and branch. thresholds provide comprehensive alarm notifications from the Rack PDU and branch. Card-based communications. Local displays are easily located to suit a crowded and changing rack environment. Supports mounting in 19" EIA, 42U rack environments—offered in vertical, zero U and rackmount form factors. Allows you to predict failing conditions before they occur and proactively manage connected equipment for maximum uptime. Liebert Power Monitoring Capabilities The operation of Liebert MPH can be monitored using: Branch Overload Liebert RPC Rack PDU Card. Protection - Liebert Nform Monitoring System. - Liebert SiteScan® Web Centralized Monitoring System. - Secure Web/SNMP Interfaces. - Liebert RPC-BDM Local Flexible Power Cord Mount Display Module. User adjustable for horizontal or vertical For more information, see page 16. orientations 15 Monitoring Anywhere You Need It From the individual receptacle of each discrete device to the complete rack PDU, monitoring is available to meet user needs. Displays are designed for easy user location to fit changing site needs. Liebert MPX and Liebert MPH: Display and sensors are designed for Enhanced Performance And Management easy mounting on the rack. A single display can manage up to four Liebert Of Dynamic IT Spaces MPX or Liebert MPH systems and associated monitoring accessories. Liebert MPX and Liebert MPH IT Space Is A Dynamic Environment Emerson Network Power's portfolio of include the following capabilities: products from brands such as Liebert, Web-based monitoring. Today's successful businesses depend Knurr, Alber, Aperture, and ASCO provide Liebert Nform IT based. on adaptable technologies to help them innovative, flexible solutions that ensure centralized monitoring. respond quickly to market demands. reliability and efficiency. With the help of Liebert SiteScan centralized Your data center must be built on a monitoring and management tools from monitoring. support infrastructure designed to User located local display with the Emerson Network Power, the result is match the power and cooling needs ability to view up to four PDU's. an infrastructure that will enable you to of rapidly changing IT initiatives such Liebert SN rack sensors. proactively manage your critical IT spaces. as virtualization and consolidation. The Rack PDU family of products is the Each IT change, move or addition will connectivity point of IT systems into affect the entire support infrastructure. your power and cooling infrastructure You need products and support that and the critical interface to an efficient ensure your IT systems will operate and effective infrastructure management reliably in these environments. ecosystem. Managem structure Infra ent Remote Monitoring Capacity planning Alarm notification Asset management Remote Control Expert services Liebert MPX may be remotely monitored and controlled via secure web/SNMP interfaces or Liebert Nform or Liebert SiteScan Web. Surge Protection Cooling Power UPS Heat PDU Pow er & C c ture oo ling Infrastru Liebert RPC (Rack PDU Card) Network Rack PDU Array (up to four systems) Status Display (RPC-BDM) is easily moved to the most convenient spot for the individual rack—even Environmental outside the rack. This tethered display Sensors may be located for user convenience. RPC-BDM Web Monitoring Liebert SiteScan (Local Display Module) Web 16 Knurr DI-STRIP: Basic Rack PDU, Standard And HighPower Systems 17 Knurr Basic Rack PDU is the right answer for data center users Knurr DI-STRIP Features: Rack PDU selecting robust, economical and flexible rack power solutions. Multiple configurations and input power options available including international compatibility. Knurr DI-STRIP® meets a broad range of power distribution requirements for IT and The addition of the Basic Rack PDU Expansion other applications. Designed especially to handle the growing number of electronic Unit allows for growth. components that can be housed within network cabinets and server racks, the 10ft. (3m) power supply cable offers room space saving product line is available with a range of accessories including circuit for movement. breakers, overvoltage protection and more. Reliable and robust solution. Worldwide approvals and certification. Full-length brass busbar on Standard models enhances operational reliability. Standard system extruded casing and a HighPower system heavy duty casing provide durability. Industry leading operating temperature—up to 55˚C/131˚F to support hot internal rack environments. Simple and quick installation on the rack's extrusion requires minimal space and reduces installation time. Flexibility to meet a broad range of requirements 17 Liebert PSP Stand-by UPS: 350 - 650VA, 1-Phase Protection For The PowerSure PSP from Liebert is a compact, full featured Liebert PSP Features: UPS that delivers cost-effective power protection. Designed Desktop And with simple controls for easy operation, the PowerSure PSP Three battery-backed UPS outlets. Small Network provides over four minutes of battery back-up at full load — One surge protection-only outlet. Applications more than enough time to save work in process and shut Up to five minutes of battery backup at full load. Liebert desktop power solutions are down your system. User replaceable batteries. designed for applications where one Perfect for desktop applications, the PowerSure PSP RJ-45 port for data line or a few pieces of equipment require provides one-on-one power protection for PCs and surge protection. surge suppression or basic power other sensitive electronic equipment. Two models Advance early warning of available: 350 and 500VA at 120VAC and 500 and UPS shutdown. protection with battery back-up. 650VA at 230 VAC. USB port, Liebert MultiLink One-On-One Protection Software shutdown software For maximum flexibility, a choice of communications The Liebert family of products and USB cable. options are available — USB, serial or contact closure. This includes surge protection strips option solves the legacy systems dilemma of what to do Two-year replacement warranty. and line-interactive UPS to give with equipment that does not have USB capabilities. A you a real choice in desktop and MultiLink™ automated shutdown software CD, serial network component protection. communications cable and USB cable are also included. Liebert Products Offer Stand-by UPS One-On-One Power Protection Solutions For: TVSS & Load Source EMI/RFI Home And Small Office Filters Desktop PCs. Battery Inverter Network Workstations. Network Routers, Bridges And Hubs. Point-of-Sale Terminals. Other Sensitive Electronics. Liebert Power Monitoring Capabilities The operation of the Liebert PSP can be monitored using: Liebert MultiLink® Automated System Shutdown Software. For more information, see pages 44 and 45. 18 Liebert PSA Line-Interactive UPS: 500 – 1500 VA, 1-Phase 19 High-Performance Power Protection For PC's And Office Equipment Desktop UPS Liebert PSA is an economical Other Standard Features Included line-interactive UPS that offers On All Liebert PSA Models: full-featured power protection for Three to six battery-backed UPS outlets, depending on model size. small office computers and electronic One to two surge-only outlets, equipment. It is available in the differentiated by color. following sizes: 500, 650, 1000 and Up to five minutes of battery backup time at full load. 1500 VA at 120 VAC or 230 VAC. User replaceable batteries. Advance early warning of UPS shutdown. 500/650 VA back view Designed with simple controls RJ-45 port for data line surge protection. for easy operation, the Liebert Two-year warranty. PSA provides up to five minutes of back-up time at full load – more than enough time to save work in process and shut down Line-Interactive UPS your connected equipment. TVSS & AVR & USB shutdown software and Source EMI/RFI Transfer Load Filter Switch a USB cable are also included, to allow remote alerts and automated graceful shutdown of Battery Inverter the connected systems. Liebert PSA offers unique features and extraordinary performance not 1000/1500 VA back view normally found in similar products in this price range. Liebert Power Monitoring Capabilities The operation of the Liebert PSA can be monitored using: Liebert MultiLink® Automated System Shutdown Software. For more information, see pages 44 and 45. 19 Liebert PSI And Liebert PSI-XR Line-Interactive UPS: 750-3000VA, 1-phase Rack-Mounted Power Solutions For Growing IT Networks Rack-mounted servers are at the heart of today's network computing systems. These critical components need reliable, compact power protection that will keep pace with their growing needs. Protection That Fits In Anywhere From line-interactive units to Proven high-level performance and reliability for server and network power protection. true on-line models, Liebert rack-mount UPS systems are Designed for the IT environment, Other Standard Features Of Liebert PSI Liebert PSI UPS and the Liebert And Liebert PSI-XR: designed for reliability and PSI-XR extended battery model Seven to eight battery-backed outlets. space-saving flexibility. No one are slim 2U sized rack/tower style, 0.9 Output Power Factor. packs more power capacity and line-interactive UPS systems. Rotatable display panel. features into a smaller package. They offer configurable input Automatic frequency sensing. voltage windows allowing the Wider input voltage window. Liebert Has Rack-Mount customer to precisely match RJ-45 Data line surge protection. UPS Solutions For: their input voltage. A choice of Advance early warning of UPS system status. PCs. communications options includes Hot swappable batteries. Network Workstations. serial, contact closure and USB. Up to five minutes of battery backup time Servers and Critical Nodes. Available in 750, 1000, 1500, at full load when utility fails. Network Routers, Bridges 2200, and 3000 VA in 120 and External battery cabinet available for and Hubs. 230VAC models. Liebert PSI-XR models. Large Network Peripherals. Network Closets. Site wiring fault indicator. VoIP. USB communications, serial and contact closure Storage Systems. communication option. Point-of-Sale Terminals. Remote emergency power off. Test Equipment. Rack rail kit included. Other Sensitive Electronics. Two-year warranty. Liebert PSI-W and Liebert PSI-XRW web-enabled models ship with IS-WEBRT3 card installed, for fast deployment. 4 20 Optional Liebert MicroPOD 2U POD output distribution and maintenance bypass module ensures continuous uptime, even during UPS maintenance. 21 Line-Interactive UPS With Power-Factor Correction Liebert PSI-XR UPS With Internal Battery Rack-Mount UPS Liebert Input Output TVSS & AVR & DB-9 IntelliSlot Circuit Circuit Source EMI/RFI Transfer Load Port Port Breakers Breakers Receptacles Filter Switch Bi-directional Battery Converter Voltage EPO USB RJ-45 External Power Configuration Port Data Line Battery Cord DIP Switch Connectors Connector Optional External Battery Cabinet Add up to six cabinets for additional runtime Liebert PSI UPS With Internal Battery Liebert RJ-45 Output DB-9 IntelliSlot Data Line Circuit Port Port Connectors Breakers Receptacles Voltage USB Input Configuration Port Circuit DIP Switch Breakers Liebert Power Monitoring Capabilities The operation of Liebert PSI can be monitored using: Liebert MultiLink®Automated System Shutdown Software. Liebert Nform Monitoring System. Optional Liebert For more information, IntelliSlot Web Card see pages 44 and 45. (PS ISWEBCARD) provides SNMP and web-based management 5 21 Liebert GXT3 On-Line UPS: 500-3000VA, 1-phase Compact UPS combines on-line reliability, configurability and internal batteries. Liebert GXT3 leads the industry in combining small customize Liebert GXT3 performance to your size, high capacity and multiple features. Designed specific requirements, providing a new level to be either rack-mounted or installed in a tower of power protection control and adaptability. configuration, the UPS is available in 500, 700, 1000, 1500, 2000 and 3000 VA ratings, in both 120 V and Other Features Of Liebert 230 V models. GXT3 2U Models: A true on-line UPS, Liebert GXT3 includes features Microprocessor-based control and such as power factor correction, internal batteries, monitoring package. frequency conversion, unlimited external battery Input power factor correction. connectability and internal bypass capability. And all this is housed in a smaller 2U size cabinet that cuts PWM inverter. space requirements in half while providing up to Integral dynamic bypass. 3 kVA of true on-line power – batteries included. The Integral sealed, non-spillable, UPS can also be used with external batteries hot-swappable battery. for extended run times. Automatic and manual battery test feature A Windows configuration program, included with ™ with push button and indicator. each unit allows the user to program a variety of Input and output noise suppression. operating parameters. This capability allows you to USB port. Liebert IntelliSlot® communications port. On-line UPS Two-year no-hassle replacement warranty. Bypass PFC / Rectifier Inverter TVSS Input & Load Filters DC - to - DC Charger Converter GXT3 Rear View Battery Liebert Power Monitoring Capabilities The operation of the Liebert GXT3 can be monitored using: Liebert MultiLink® Automated System Shutdown Software. Liebert Nform Monitoring System. Liebert SiteScan® Web Centralized Monitoring System. Third-Party Monitoring Systems. Optional Liebert MicroPOD 2U POD output distribution For more information, see pages 44 and 45. and maintenance bypass module ensures continuous uptime, even during UPS maintenance. 4 22 User replaceable hot swappable internal batteries Liebert GXT2 On-Line UPS: 6 & 10 kVA, 1-phase 23 High capacity, compact on-line UPS with flexible output voltage and power distribution. Rack-Mount UPS Liebert GXT2 6 & 10 kVA UPS Application versatility is achieved Other Product Features Of Liebert systems provide true on-line through the use of a dual inverter GXT2 6 & 10 kVA UPS Models Include: protection in the smallest cabinets design capable of providing Wider input voltage window enables the UPS in their capacity range. The UPS simultaneous output voltages systems offer internal batteries, of 240/120, 208/120, 230/115, to support the critical load without having unlimited extended external 220/110, or 200/100 VAC. The to transfer to battery. batteries, and internal bypass input is power factor corrected to Patented output neutral bonding feature meets capability, resulting in continuous approximately .98, enabling the UL 1778 standard by providing a method for uptime for the connected UPS to power a wide variety of maintaining the UPS output neutral to ground equipment. This makes the equipment with different voltages. bond in all modes of operation. UPS an ideal fit in applications For installation flexibility, you may Internal bypass assures continuity of power where the power requirements choose from several different wiring to critical loads during system problems are demanding—but rack space configurations made possible by the is limited. or maintenance. use of removable power Automatic frequency detection matches line distribution boxes that simply plug into the rear of the UPS. Options input frequencies of either 60 or 50 Hz. include hardwired or receptacle User-replaceable hot swappable internal batteries connections, as well as maintenance provide five minutes of runtime at full load. Parallel POD bypass capabilities. Additional battery cabinets available for extended backup time. PD-20X Parallel Communication Liebert IntelliSlot® communications port utilizes Ports Liebert IntelliSlot® Web Card to provide SNMP and web-based management. Electronic equipment may be installed at the front of the rack, with the Parallel POD installed at the back 10kVA of the rack, increasing Liebert GXT2 UPS usable space. Input/Output 10kVA Liebert GXT2 Power For UPS Paralleled UPS Units 10kVA Equipment Liebert GXT2 UPS shown from back of rack. Liebert Power Monitoring Capabilities The operation of the UPS can be monitored using: Liebert MultiLink® Automated System Shutdown Software. The Parallel POD Liebert Nform Monitoring System. enables paralleling of two Liebert GXT2 10 kVA Liebert SiteScan® Web Centralized Monitoring System. UPS modules to double capacity to 20kVA. A third Third-Party Monitoring Systems. unit may be added to configure the system for N+1 redundancy, raising system reliability. For more information, see pages 44 and 45. 5 23 Liebert Nfinity® On-Line UPS: 4-20 kVA, 1-phase Protecting The The Liebert Nfinity power system is a scalable 4 to 16 kVA or 12 to 20 kVA UPS designed with N+x Enterprise: High parallel redundancy to provide a fault-tolerant Availability UPS network of power protection. Protection For Mission-Critical The modular design of the Liebert Nfinity power system was devised to provide easy scalability to Applications users as their power demands grow. Configurations can be cost-effectively upgraded without The need to safeguard critical re-investing in a new system or installation. operations from power problems A True On-Line System That Delivers Additional Features Of can be solved through the use of Continuous, Regenerated Sinewave The Liebert Nfinity Power Output Power System: large-scale UPS systems. The Liebert Nfinity is a true on-line, Hot-swappable modules allow double-conversion UPS that provides 100% power the user to replace modules or A Powerful Defense conditioning, zero transfer time to battery, no upgrade the system without change in output voltage and better transient disturbing connected equipment. Against Uptime Threats suppression than line-interactive units. Continuous self-diagnostics Liebert offers a full range of detect and isolate faults to enterprise power protection Its unique frame design houses all of the modular prevent cascading system failures, system components, including 4 kVA power solutions for any size facility from a as well as to simplify maintenance modules, battery modules and system control small computer room to the largest and troubleshooting. modules. By simply installing additional power or battery modules, you can expand your current Patent pending intelligent data and communications centers. system, extend backup runtime or add redundancy. bypass technology provides seamless transfers to and from Liebert Enterprise UPS Intelligent power modules provide protection the bypass source. Solutions Are Ideal For from all power aberrations, and a patent pending Wide input voltage window electrical current-sharing technology provides minimizes battery operation Large-Scale Data Centers. equal distribution of power among all modules. to maximize battery life. Facility-Wide Networks. The IntelliBattery™ modules utilize multiple Fully assembled and factory-tested, Large-Scale Telecommunications sensors to continuously monitor battery voltage, simple to install and ready for use Centers. current and temperature to determine and for a plug-and-play solution that is Colocation Facilities. predict performance. functional right out of the box. Internet Data Centers. The IntelliControl™ module works with the user Additional battery cabinets can Server Farms. interface to provide vital information about the be added for backup times up Data Warehouses. condition of the power and battery modules. to 72 hours. Network Management Centers. Liebert Power Monitoring Capabilities Two-year limited warranty for Medical Imaging Equipment. ® repair or replacement with The operation of the Liebert Nfinity UPS can be monitored using: warranty extensions also available. Test and Laboratory Facilities. Liebert IntelliSlot Web Card. Industrial Process Control ® Liebert MultiLink Automated System Operations. Shutdown Software. Liebert SiteScan® Web Centralized Monitoring System. For more information, see pages 44 and 45. 4 24 Slimline Distribution Cabinet UPS Battery Cabinet Liebert NX On-Line UPS: 10-30 kVA, 3-phase 25 Power designed to grow with your needs. Enterprise UPS The Liebert NX 10-30 kVA product family offers true on-line, double conversion, three-phase UPS systems that deliver complete, centralized power protection for mission-critical systems. Available in 10, 15, 20 & 30 kVA capacities, these rugged units are designed to meet the high availability power needs of a wide variety of IT applications. Liebert NX 10-30 kVA UPS systems combine advanced operating features, compact size and Other Features Of Liebert NX 10-30 kVA UPS Models: Increases growth flexibility by handling larger loads, and offers the low cost of ownership in a range of sizes to suit room or ability to parallel like-sized 20 and 30 kVA modules for increased data center needs. capacity and redundancy. The "all-in-one" design of the Liebert NX 10-30 kVA Achieves higher availability by reducing the number of UPS units UPS provides more protection security and efficiency required to power your room. than using separate, smaller power units spread Reduces total cost of ownership through the use of longer life throughout the facility. The Liebert NX delivers complete batteries and simplified preventive maintenance. protection with a true on-line IGBT-based double Wider input voltage window and frequency tolerances contribute to conversion design. The system's advanced topology higher system availability by minimizing battery usage. features a digital signal processor controlled IGBT Operates under a wide variety of conditions, handling 100% nonlinear rectifier and IGBT inverter. loads with 3:1 crest factor, as well as 100% unbalanced loading. IGBT-based power factor corrected rectifier enables the Liebert NX to achieve its impressive THD and PF performance. Advanced inverter control technology provides the highest output power quality, ensuring very low output voltage THD and superior waveform to protect connected loads. Fully digital control technology provides a highly accurate, drift-proof ® control compared to traditional analog electronics. Liebert Power Monitoring Capabilities The operation of the Liebert NX 10-30 kVA UPS can be monitored using: Liebert IntelliSlot Web Card. Liebert MultiLink® Automated System Shutdown Software. Liebert Nform™ Monitoring System. Liebert SiteScan® Web Centralized Monitoring System. Third-Party Monitoring Systems. For more information, see pages 44 and 45. 5 25 Liebert NX On-Line UPS: 40-200 kVA, 3-phase Now There's A Data Center UPS That Matches Your Growth Plans. For high availability, high capacity Softscale™ technology provides applications, the transformerless flexibility to increase UPS Liebert NX 40-200kVA UPS systems capacity without changes in your offer true on-line, double conversion infrastructure. From 40 up to 80kVA, technology to protect and condition 80 up to 120, and 160 to 200. You against the full range of power may also parallel UPS modules for irregularities. Plus they do it with capacity and redundancy. a level of flexibility not previously The Liebert NX UPS combined found in systems of this size. with the optional Liebert NX BDC A wider input voltage window (Bypass Distribution Cabinet) lets and frequency tolerances help you simplify power distribution to minimize transfers to battery, and voltage conversion. This reducing the number of charging combination provides packaged and discharging cycles. Availability power distribution for today's is also enhanced with a triple mode rack-based data centers and battery charger that enables fast IT facilities. battery recharge. Longer battery backup time may be achieved by paralleling additional battery cabinets to the system. Liebert Power Monitoring Capabilities The operation of the Liebert NX 40-200 kVA UPS can be monitored using: Liebert IntelliSlot Web Card. Liebert MultiLink® Automated System Shutdown Software. Liebert Nform™ Monitoring System. Liebert SiteScan® Web Centralized Monitoring System. Third-Party Monitoring Systems. For more information, see pages 44 and 45. Liebert NX 40-80 kVA 26 Liebert NX 160-200 kVA Cutting-Edge Power Technology Makes The Difference 27 Softscale™ technology, paralleling capabilities and Eco-mode™ all Enterprise UPS contribute to lower initial, incremental and operating costs. Battery UPS Liebert NX Liebert NX 40-200 kVA UPS Systems Cabinet BDC Softscale Technology Liebert NX 40-200 kVA UPS systems have Softscale technology that provides flexibility to increase UPS capacity by 20 or 40kVA without Liebert NX UPS Systems Incorporate changes in your infrastructure. Allows paralleling of unlike-sized A Number Of Other Exceptional models for capacity or redundancy. Designed for optimized Features: performance with the same high efficiency at 40% utilization as High overload rating handles 125% for 10 at 100% utilization. minutes, 150% for one minute and a 1000% overload for 10 milliseconds. Paralleling Capabilities Digital controls provide the fastest possible Liebert NX 40-200 kVA systems allow you to parallel UPS modules power management to enhance reliability, for capacity and redundancy, eliminating the batteries as a single accuracy and efficiency. point of failure because each UPS has its own isolated battery. Front access models available for installation along a wall. Front and rear access models Liebert NX also features integrated dual bus synchronization as a available for installation in a row. standard feature. This provides the capability to synchronize the Compact footprint requires less floor space, outputs of two independent UPS modules when they are configured leaving you with more room for other equipment. as a redundant system feeding independent distribution paths. Load Bus Synchronization standard. Eco-Mode High Efficiency Configuration Soft Switching technology increases efficiency by up to 2% and saves energy. If selected, this operating mode switches the UPS to static bypass Integrated ground fault detection allows for during normal operation, increasing efficiency to up to 97% at full effective transformer-less design while saving load. When power problems are detected the UPS automatically space and lowering the unit weight. switches back to double conversion mode. Parallel for redundancy or capacity. Active input rectifier is generator Liebert NX BDC and utility friendly. The optional Liebert NX BDC provides flexibility in input and Web card monitoring standard. output voltage for a variety of applications. This cabinet is available One year warranty. in capacities to cover the Liebert NX UPS range of 40-200kVA. The monitoring panel matches the UPS unit. Power and control cabling from this cabinet to the UPS is included, enhancing ease of installation and availability. For ease of installation and maintenance, the cabinet offers top or bottom cable entry and models are available in front and rear access, or front access only configurations. 27 Liebert NXL—Stack Up Performance Liebert NXL is 100% Load designed to Low & High Line Conditions handle all severe conditions 40˚C / 104˚F Temperature simultaneously 50% Clogged Air Filter and still support 100% load with Fan Failure no need for Liebert NXL On-Line UPS: High Altitude1500 Meters derating. 250-750 kVA, 3-phase Liebert NXL UPS Provides Reliable Power Other Liebert NXL Features Include: Protection And Advanced Technology Matching battery and maintenance bypass cabinets for easy For High Power Applications. configuration. The industry's most reliable power protection and advanced Top or bottom cable entry. technology has been combined into a new generation of Internal cabinet cable wiring simplifies installation. three-phase UPS systems for high power applications — the Ship-ahead I/O section can be installed before UPS installation. Liebert NXL from Emerson Network Power. Liebert ActiveStar® Digital Signal Processor (DSP) controls—no potentiometers. Available in 250, 300, 400 kVA single module models as Redundant components—fans, power supplies, and well as 750 kVA single and multi-module systems, the communications cards. transformer-based Liebert NXL provides excellent dynamic Provides superior handling of present and future computer performance, with the ability to handle virtually any input loads, up to 0.95 leading power factor without derating. Color touch screen controls improve user interface and reduce condition while still providing computer grade output risk of human error. to critical loads. Excellent dynamic performance and fault tolerance. The leader in large UPS system installations, Emerson offers Generator and utility friendly with low current distortion. complete and unequalled support, including engineering Front access for installation and service. consultation, the largest and most widespread factory-trained Compact cabinets require less floor space. service organization, and the industry's largest and most Inter-cabinet cabling requires less hard wiring. advanced production and witness test facility. Built-in battery cabinet breaker isolates string for ease of service. Energy efficient operation, with up to 94% operating efficiency. First large UPS to be tested and UL Listed to UL1778 Fourth Edition, which requires testing of every specification. Maintenance Bypass Battery Cabinet UPS Cabinet 28 AC Input Liebert Power Monitoring Capabilities AC Input Rectifier Rectifier Bypass The operation of the Liebert NXL UPS can be monitored using: Input AC Rectifier Rectifier Input AC AC Bypass Input AC Input AC Input AC Input Liebert MultiLink® Automated System Shutdown Software. Rectifier Rectifier Rectifier Rectifier Liebert Nform™ Monitoring System. Liebert SiteScan® Web Centralized Monitoring System. Static System Bypass Bypass System StaticSwitch Output Bypass Liebert Universal Monitor and Remote Power Monitor Panels. Switch Breaker Bypass Output Breaker er Third-Party Monitoring Systems. Battery Battery Battery Battery Four Liebert IntelliSlot ports. Ships with standard 485 Liebert Inverter Inverter Critical Bus SiteScan Web interface. Inverter Inverter AC Output Critical Bus Albér BDSi Integrated Battery Monitoring System. AC Output For more information, see pages 44 and 45. UPS Output Breaker UPS Output AC Output To Load AC Output 29 Breaker To Load Optimized Performance Liebert NXL Single Module System One-Line (250-750 kVA) Enterprise UPS Intelligent Eco-Mode™ — Liebert NXL offers up to 97% Bypass full load efficiency during user-selectable Intelligent AC Bypass Input Static Switch AC Input Eco-Mode™ operation. The always-on inverter ensures Static Rectifier Switch Inverter Rectifier Inverter high availability and seamlessly assumes the load in case Rectifier AC Output of a utility power disturbance. AC Rectifier Input to Load AC Output AC Input to Load Intelligent Paralleling™ — Modules paralleled with a system control cabinet (N+1 configuration) may be Battery Battery customer selected to use Intelligent Paralleling, which increases efficiency by turning off redundant modules. Liebert NXL 1+N Multi-Module System One-Line (250-750kVA) Off time is equally distributed between all modules. Distributed Static Switch Optimized Battery Runtime — Battery capacity and AC Input AC Input Liebert NXL module load are proportionally balanced Rectifier Bypass Rectifier Bypass during a utility outage, extending battery run time. AC Rectifier Input AC Bypass Input AC Rectifier Input AC Bypass Input AC Input AC Input AC Input AC Input Rectifier Rectifier Configuration Options Rectifier Rectifier Single-Module Configuration (250-750kVA models) Static Static System Bypass System StaticSwitch StaticSwitch Single-module systems provide a basic protection Switch Switch Breaker Bypass Breaker Battery Battery configuration. Battery Inverter Battery Inverter Inverter Inverter The critical bus is powered by a single UPS system with bypass capability. 1+N Parallel Configuration (250-750kVA models) Paralleling of single UPS units, offers easy scalability UPS Output AC Output Breaker UPS Output To Load AC Output for increased capacity or redundancy Breaker To Load Each unit has its own static switch for bypass Liebert NXL N+1 Multi-Module System One-Line (750 kVA) Provides redundant capacity without the need for a Centralized Static Switch system control cabinet AC Input N+1 Parallel Configuration (750kVA models) Rectifier Rectifier Bypass Paralleling of Multi Module units, without built-in AC Input AC Input AC Input static switch Rectifier Rectifier Requires System Control Cabinet with centralized System static switch Bypass Static Switch Bypass Output Breaker System Control Cabinet can be easily integrated into Inverter Battery Battery any switchgear solution Inverter Inverter System rated static switch with bypass breaker offers Critical Bus high fault clearing capability, and high availability AC Output Centralized monitoring allows good visibility and easy control of total system UPS Output AC Output Breaker To Load Up to six units may be used together for capacity/ redundancy 29 Liebert Series On-Line 610 UPS: 225-1000 kVA, 3-phase Ultimate reliability for large-scale, Other Features Include: mission critical applications. Higher DC bus utilization provides higher AC/AC and DC/AC efficiency and allows a relatively smaller battery. Offering the ultimate in power protection efficiency Continuous improvement dramatically improves and reliability for larger facilities, Liebert Series 610 reliability by reducing the number of parts—and the potential points of failure within the system. UPS systems are available in a wide range of capacities Lower operating costs and long life thanks to 93% from 225 kVA to 1000 kVA. These systems are operating efficiency and an industry leading power designed to protect mission-critical operations from factor of greater than 0.92 for all models. the full range of power quality problems and outages. The ability to handle unbalanced and 100% non-linear loads. Efficient IGBT (insulated gate bipolar transistor) Lower heat output eliminates the need for complex technology is combined with pulse width modulation/ air cooling arrangements. stepwave topology to provide reliable operation Robust inverter manages overloads and faults without and create a unit that packs more capacity into a the need for a static switch on the system output. smaller footprint. Designed for intuitive, menu-driven operation, a large backlit LCD operator interface displays system controls, Thanks to all-digital controls and a unique inverter full-featured monitoring and alarm notifications. topology, the Series 610 can be applied in several single-bus configurations, including single module, parallel redundant and isolated redundant systems. For added reliability, multiple units can be utilized in a dual-bus system with two power feeds to provide redundancy during normal operation, as well as continuous, shutdown-free operation when service is required. Liebert Power Monitoring Capabilities The operation of the Liebert Series 610 UPS can be monitored using: Liebert MultiLink® Automated System Shutdown Software. Liebert Nform™ Monitoring System. Liebert SiteScan® Web Centralized Monitoring System. Liebert Universal Monitor and Remote Power Monitor Panels. Third-Party Monitoring Systems. Liebert BDS-40 Battery Monitoring Alber Technology By Liebert. For more information, see pages 44 and 45. 30 Liebert NXL, Liebert Series 610 System Control Cabinet - SCC 31 When paralleling two or more units, a system control Factory System and Witness Testing Enterprise UPS cabinet monitors the output of the UPS's and assures that Emerson Network Power has invested in a state of the all of the outputs are synchronized. The System Control art test facility to provide unmatched UPS system testing at our factory for our clients. This facility enables us Cabinet also contains a static bypass switch which assists to test system performance, proper unit function, in the maintenance of the system. and proper system interoperability with a completely integrated UPS system to meet our customers' strict System Control Cabinets are integrated into the switchgear of your choice. criteria for system performance. Centralized monitoring controls allow Factory witness testing allows our customers to see how for greater visibility into the system. their systems will work in the field. We can simulate almost Liebert SCC's 610 contains a static bypass switch any real world event, with real-time viewing of relevant with manually operated disconnects and two data, and results provided at the conclusion of each test. motor operated system circuit breakers. Standard and custom power distribution switchgear Liebert Adaptive Power WitnessTest Center Features systems are available for use in Tier 1 through Tier 4 Seven test bays, each with up to five distinct UPS system configurations. test stations. Each SCC includes: Microprocessor-based monitoring with Witness test viewing station overlooking test bays and backlit LCD display, controls. equipped with LCD panel displays of current test data. Momentary-duty static switch. Total power over 12 MW available via the facility utilities. Continuous duty static switch options Higher capacities supported through a 1.75 MW 50/60 with custom switchgear. Hz engine generator as well as plug-ins for additional Automatic system isolation and bypass breakers. generators, as needed. Automatic equalize charge timer. Interface for a remote power off. Liebert System Test Capability Liebert SiteScan® Web interface. Up to 9 multi-module UPS systems with integral Alarm status contacts. switchgear can be tested simultaneously. RS-232 port. Visual/audible alarms. The test infrastructure is designed to support large lineups of equipment including switchgear, static transfer switches, and distribution equipment. Test infrastructure is supported with dedicated battery simulators and both resistive and inductive load banks which can be connected to different test systems throughout the infrastructure. Test currents, voltages, waveforms, THD, and other critical information parameters are monitored throughout the test infrastructure with high accuracy power quality meters. Test data is available locally in the test bays, in the witness test rooms,or remotely for any use. 31 Liebert FS Flywheel System Battery-Free Reliable ride-through energy storage, Solution For Use with or without batteries. With UPS Systems The Liebert FS flywheel DC energy storage system is designed to be a more efficient and reliable Now you can get higher, more alternative to standard battery systems used efficient UPS reliability by taking with uninterruptible power supply (UPS) systems. advantage of Liebert's world-class The advanced, high-RPM, composite flywheel flywheel energy storage technology. technology used in the Liebert FS provides 200 Liebert's flywheel technology kW of instant ride-through DC power and voltage provides superior performance stabilization for approximately 12 seconds— without the high cost of ownership more than enough for the vast majority of and environmental impact associated electrical disturbances. with batteries. The Liebert FS can be used as the sole back-up DC Other Liebert FS Flywheel System Flywheel Technology energy device or in conjunction with conventional Features Include: battery strings or generator sets. When used along Offers Many Advantages Rides load through to generator. The compact, lightweight, and with batteries, the flywheel system will eliminate Magnitude increases in reliability/ reliable Liebert FS flywheel system their use for short power fluctuations, helping to availability. is safe and environmentally friendly. extend life and save capacity for longer outages. Eliminates battery maintenance/ It offers a low installation cost, small footprint, low maintenance It can also be used alone to provide ride-through replacement. and long operating life. It provides power until back-up generators come on line. Significantly reduces life cycle costs. quick recharge and operates under Increases productive floor space. a wide range of temperatures. The The Liebert FS is engineered to support larger Eliminates floor-loading issues. patented flywheel safety system Liebert UPS systems, including the Liebert Npower, Eliminates health & safety issues. provides a safe shutdown under Liebert Series 610, Liebert NX and Liebert NXL all circumstances. The flywheel Eliminates environmental issues. system's unique operating features, models. A single flywheel can be sized to support Isolates batteries from cycling. such as rapid recharging and broad UPS systems up to 225 kVA. Multiple flywheel Rides load through to generator. operating temperature range, allow systems can operate in parallel to support larger Magnitude increases in reliability/ the Liebert FS to be installed in systems. availability. applications where batteries have previously been ruled out. Minimizes battery maintenance/ When the primary power source goes down, it's replacement. vital that the UPS has a reliable DC power source to Liebert FS Flywheel Significantly reduces costs over deliver energy to the critical loads. The Liebert FS Energy Storage Systems stores energy kinetically via flywheel inertia rather redundant battery strings. Are Ideally Suited For: than relying on chemical reactions of toxic lead and Data Centers. Liebert Power Monitoring Capabilities sulfuric acid. Colocation facilities. Telecommmunications. The operation of the Liebert FS Flywheel System can be monitored using: Colocation Facilities. Liebert SiteScan® Web Centralized Industrial process equipment. Monitoring System. Commercial facilities. Third-Party Monitoring Systems. Medical facilities. For more information, see pages 44 and 45. 32 Breaker Heat Exchanger Display Data Collection Interface Board Module Inductor-Filter 33 Magnetic Levitation System Benefits Include: Enterprise UPS Controller The compact, lightweight, and reliable Liebert FS flywheel system is safe and Flywheel Housing environmentally friendly. Offers a low installation cost, small footprint, low maintenance and long operating life. Coolant Pump Unlike batteries, the Liebert FS uses no toxic metals and emits no explosive gases. Power Electronics Provides quick recharge, operates under a wide range of temperatures. Casters Patented safety system provides a safe shutdown under all circumstances. When used with batteries, becomes the primary DC energy source of more than 98% of power disturbances (most power disturbances last less than 4 seconds), reserving the battery for longer outages, extending battery life and improving overall UPS output reliability. When used in a batteryless configuration, provides the needed short-term DC energy bridge to an engine generator. How It Works: The Liebert FS stores energy kinetically. When Upper Radial needed, inertia of the spinning mass is immediately Electromagnet Upper Vacuum converted to power. The Liebert FS is a functional Chamber Axial replacement or supplement for a bank of chemical Lower Vacuum Electromagnet batteries. Like batteries, it charges from the two Chamber Patented terminal UPS DC bus and returns up to 200 kW per Carbon Fiber Molecular module whenever the bus voltage drops below a Composite Vacuum Sleeve programmable threshold. Flywheel 2" Thick Steel The flywheel itself is a high-speed, carbon fiber Containment Motor-Generator Vessel composite cylinder rotating in a vacuum. The Stator Synchronous flywheel and rotating group is fully levitated and Reluctance centered by patented 5-point magnetic levitation 4 Pole M-G system that minimizes drag and eliminates Rotor Coolant mechanical bearings maintenance and replacement. Passages Its synchronous reluctance motor-generator Lower Radial minimizes idling losses and standby power Electromagnet consumption. Originally designed for hybrid vehicles, the levitation system is very robust and responsive to any jarring. 33 Liebert FDC Rack Power Distribution Power When And Where Rack Sized Power Distribution Cabinet You Need It As your rack-based systems grow in number, complexity and criticality— so must your power distribution Producing quality power is the first step—getting it to system. To meet this challenge critical equipment in the most efficient manner while Liebert has created a product designed to optimize power maintaining proper voltages and other key parameters is distribution at the rack level the important next step. with the "plug and play" flexibility that today's IT managers demand from their systems. Making Sure The Power Is Always There When You Need It The Liebert FDC distribution cabinet Liebert's range of power distribution equipment is extends the functionality of the PDU specially designed for high-availability applications. by packaging 168 poles in a It includes both distribution and switching systems stand-alone cabinet with a rack to provide reliable power to critical loads. foot print. Any compartment can be serviced Liebert Power Distribution or reconfigured without exposing Solutions Are Ideal For: the wiring of the other three Large-Scale Computer Centers. panelboards. Facility-Wide Networks. The Standard Liebert FDC Unit Includes: Large-Scale Telecommunications Centers 4 complete panelboards with main breaker (total 168 poles). Colocation Facilities. Front and rear access only. Internet Data Centers. Bottom cable exit. Server Farms. Data Warehouses. 22kAIC main panelboard breakers. Network Management Centers. Medical Imaging Equipment. Optional Features Include: Test and Laboratory Facilities. Top cable exit. Industrial Process Control Operations. LDM monitoring with remote communications—Modbus output. Isolated ground bus bars. EZ-view doors enable visual inspection of the breakers without unlocking the cabinet. Square D or GE inline panelboards in bolt-in or plug-in styles. Current monitoring panel. Tie-breakers to allow connection of two panelboards to a common panelboard main breaker (requires side access). Plug-in main panelboard breakers. 34 Liebert Remote Distribution Cabinet (RDC) 35 The Better Way To Wire High Density Facilities Power Distribution Systems The influx of client/server rack equipment is changing the content of data centers. There are more devices than before—and they consume less power than their predecessors. As a result, most power distribution units (PDUs) run out of circuit breaker poles before they run out of rated capacity. The Liebert Remote Distribution Cabinet (RDC) extends the functionality of the PDU by packaging 168 poles (four complete 42-pole inline panelboards) in a stand-alone cabinet. Unlike standard Liebert Precision Power Centers (PPCs), the RDC has no internal isolation transformer and requires 4-wire-plus-ground input from a PPC or other transformer. By separating the PPC transformer from the panelboard function, Liebert was able to create an extremely compact package that fits the area of a standard 24" x 24" raised-floor tile. The individual panelboards inside the Liebert Remote Distribution Cabinet can receive power from different sources. This enables the RDC to provide fault-tolerant, fully maintainable dual-bus power to nearby load equipment. A dual-input RDC can be configured with two panelboards on each side sharing common input terminals. Other Features Of The Liebert RDC: Unobstructed wiring access for easy of installation. Complete isolation and maintainability. Optional clear door insert panels enabling visual inspection of the breakers without unlocking the cabinet. Optional adjustable accent panels to make it easier to compensate for breaker "creep". Single, dual or four-input configurations. Optional current monitoring panel. Optional input junction box and underfloor conduit box. UL labeled. Conduit-landing plate, Liebert Power Monitoring Capabilities left, is positioned for easy cable access. The operation of the Liebert FDC and Liebert RDC can be monitored using: Liebert SiteScan® Web Centralized Monitoring System. For more information, see pages 44 and 45. 35 Liebert FPC Rack-sized Power Conditioning and Distribution Cabinet Optimized For In-the-row Applications. Other Standard Features Of The Liebert FPC: Computer-grade grounding. The Liebert FPC power conditioning and distribution cabinet provides Fully compatible with the non-linear loads. higher quality, more flexible power distribution for high-density Main input breaker with shunt trip. data centers. It is engineered to combine the convenience and cost savings of a pre-packaged, factory-tested unit with the flexibility of a Double-shielded TP1 listed isolation transformer.* custom-tailored power system. This self-contained system provides One or more individually enclosed 42-pole output power isolation, power distribution, computer-grade grounding and panelboards. power monitoring. Built-in metering and alarm annunciation with communication to Liebert centralized monitoring. Ranging in capacity from 15kVA up to 300kVA, the Liebert FPC comes Compact single cabinet conserves valuable floor space. in a 19" rack and 47" wide rack, the size of two 19" racks, and is Single input cable connection reduces installation time designed to fit at the end of, or within, a row of racks, as well as in a and cost. standalone configuration. Full front and rear access. Can be easily relocated to protect your investment. The packaged system approach of the Liebert FPC is convenient UL and ULc Listed as a complete system. and space-saving, reducing installation time and cost compared to a *Energy Policy Act of 2005 requires that all "distribution transformers" conventional approach using multiple interconnected components. and all "low-voltage dry-type distribution transformer" manufacturers produce only TP-1 units as of January 1, 2007. TP-1 transformers have a higher efficiency than standard isolation transformers, and are optimized to have the highest efficiency at 35% load. 36 Liebert PPC Packaged Power Conditioning and Distribution 37 Optimized For In The Room Applications. Power Distribution Systems Liebert Precision Power Center The Liebert Precision Power Center (PPC) power conditioning and distribution cabinet is designed to bring you a distribution system that offers the benefits of a custom-tailored power system, with the convenience and cost savings of a pre-packaged, factory-tested unit. Housed in a single, self-contained cabinet, it combines distribution, computer-grade grounding, isolation, and power monitoring to provide the protection your vital computer or communications equipment demands. Available in 15-225 kVA capacity systems for raised floor applications and 15-150 kVA capacities in top-exit models for non-raised floors, the Liebert PPC offers flexible expansion capabilities to fit growing sites. The packaged system concept of the Liebert PPC is convenient and space-saving, reducing installation time and cost compared to a conventional approach using multiple interconnected components. Other Standard Features Of The Liebert PPC: Secure distribution and circuit identification. Non-linear load compatibility. Individual circuit breaker protection. Built-in metering and alarm annunciation, with communication to Liebert-centralized monitoring systems. Double-shielded TP-1 listed isolation transformer.* Liebert Power Monitoring Capabilities Easy installation, with single input cable connection The operation of the Liebert Precision Power and application matched connections to the load. Center and Liebert FPC can be monitored using: Expandable with add-on panelboards Liebert Nform™ Monitoring System. and flexible cabling. Liebert SiteScan® Web Centralized Monitoring System. Flexibility to protect your investment by allowing Third-Party Monitoring Systems. the unit to be easily relocated. For more information, see pages 44 and 45. UL and CSA Listed as a complete system. *Energy Policy Act of 2005 requires that all "distribution transformers" and all "low-voltage dry-type distribution transformer" manufacturers produce only TP-1 units as of January 1, 2007. TP-1 transformers have a higher efficiency than standard isolation transformers, and are optimized to have the highest efficiency at 35% load. 37 Easy-To-Use Color Touch-Screen Interface The controls of the Liebert STS2 are intuitive and simple. The pop-up menus are easy to understand and provide a wealth of operational and diagnostic information. The color LCD monitor is divided into three segments. In addition to a system mimic diagram, there is a status/ alarm panel and a section dedicated to operator instructions and menus. Liebert Static Transfer Switch2 ™ You benefit from improved operator effectiveness, reduced training time, and less chance of operator error. The Key To High-Availability Power. The Liebert Static Transfer Switch2 (STS 2) provides an automatic, seamless transfer between the outputs of two independent UPS systems and the input of a critical load in a dual-bus power system. If the primary UPS should fail, the switch will automatically transfer the loads to the surviving UPS. For redundancy, the Liebert STS2 features three separate, self-correcting logic modules. Each controller is capable of working independently and each helps monitor the other two. Available in capacities ranging from 100 up to 1000 amps. True Front-Access Design All mechanical and electronic components of the Liebert STS2 are accessible from the front of the unit. This gives you several immediate benefits: Greater freedom in system design. The Liebert STS2 can be placed adjacent to or in back of other equipment. It can also be placed against a wall or partition. Simplified installation, with ample space for cable connections through top and bottom access plates. Less floor space required for maintenance access. Simplified maintenance, with all key components visible, serviceable and removable from the front of the unit, without the need to shut down the connected load. Other Features Of The Liebert Static Transfer Switch2: Internal CANBUS protocol provides high-bandwidth communication between system components True Internal Redundancy via twisted-pair cables. Options can be added The Liebert STS2 has triple-redundant logic. Each DSP as simple network nodes. controller is capable of working independently, and each Internal dual-bus control power. helps monitor the other two. If one malfunctions, the Simplified installation and maintenance. other two lock it out. Each controller has power feeds from both power supplies. Full range of communications options to fit any monitoring strategy. The two power supplies feature true dual-bus power Three-pole switch configurations. distribution. Both have dual inputs, one from each Optimized Transfer option uses the patented AC input source. All power connections have diode Liebert static transfer control algorithm to eliminate protection, so that internal or external faults cannot downstream transformer inrush saturation. Meets propagate. The result is a rugged, fault-resilient package CBEMA and ITIC standard for critical loads. that is optimized for real-world applications. 38 Liebert STS2/PDU Static Transfer Switch2/ Power Distribution Unit 39 Combines Power Distribution And Automatic Switching. Features Of The Liebert STS2/PDU Include: Power Distribution Systems True dual-bus power distribution switches With a single, space-saving unit, the Liebert Static Transfer Switch2/ automatically or manually between two Power Distribution Unit combines the switching capabilities AC power sources. of the STS2 with the benefits of a proven power distribution unit. Computer-grade grounding automatically Liebert designed the STS2/PDU to bring you a distribution system that establishes a single point ground to meet major will close the power delivery loop in your critical facility. It offers the manufacturers' recommendations and the benefits of a custom-tailored power system, with the convenience and requirements of the National Electric Code. cost savings of a pre-packaged, factory-tested unit. Fully compatible with the non-linear loads of modern computer systems and other Housed in a single, self-contained cabinet, it combines distribution, electronic equipment. computer-grade grounding, isolation, and power monitoring, as well as Built-in metering and alarm annunciation with dual-source switching, to provide the protection your vital computer or communication to Liebert SiteScan® Web communications equipment demands. centralized monitoring. Compact single cabinet conserves valuable Available in capacities from 250 to 800 amps, the Liebert STS2/ floorspace compared to non-packaged solutions. PDU offers flexible expansion capabilities to fit growing sites. The Single cabinet design reduces installation packaged system approach of the Liebert STS2/PDU is convenient time and cost. and space-saving, reducing installation time and cost compared to a The unit can be easily relocated to protect your conventional approach using multiple interconnected components. investment. UL Listed as a Complete System to meet safety requirements for fast, hassle-free inspection and building code approvals. A choice of distribution options to fit site requirements. Liebert Power Monitoring Capabilities The operation of the Liebert STS2 and Liebert STS2/PDU can be monitored using: Liebert Nform™ Monitoring System. Liebert SiteScan® Web Centralized Monitoring System. Liebert Universal Monitor and Remote Power Monitor Panels. Third-Party Monitoring Systems. For more information, see pages 44 and 45. 39 Power Quality Solutions High Quality Surge Protection For applications requiring protection from electrical line problems without the These Products Include: need for back-up capability, Liebert manufactures a full line of surge suppression and power conditioning equipment. High Exposure Systems The Best Possible Power Liebert's wide range of Surge Protective Devices, (SPDs) have numerous Liebert SI Series (Interceptor II)—Built to applications throughout a facility, including protection against transients provide the highest level of surge current that are generated by other equipment within the building. Our power capacity, with the lowest clamping voltages. Along with true NEMA 4 assembly suitable for conditioning systems shield critical loads from external disturbances, outdoor use. particularly those coming through the utility power line. Liebert Power Protection Solutions Are Ideal For: Liebert LM Series—Offers continuous Computer Centers. Network Management Centers. protection from damaging transients and electrical line noise. Surge suppression levels Facility-Wide Networks. Medical Imaging Equipment. range from 120 kA to 500 kA per phase. Telecommunications Centers. Test And Laboratory Facilities. Colocation Facilities. Industrial Operations. Internet Data Centers. Liebert ACV Series (AccuVar)—A full line of multi-phase, multi-mode distribution panel-mounted surge suppression devices. Liebert HA Series (Hybrid Advantage)— The first hybrid product in the industry to offer a true coordinated multi-stage system of suppression. Surge current capacity ranges from 250 kA to 750 kA per phase. Liebert ATF Series (Active Tracking Filter™)— A customized, modular approach to surge protection in a series filter device. Liebert SS Series—Approved by Motorola R56 Committee, Standards and Guidelines for Communication Sites—Type 1 and 2 Devices. Utilizes advanced SAD/MOV array technology for industry leading transient suppression voltages. Liebert LPGE Series—An add-on device for integration with panelboards at the jobsite for enhanced surge suppression. Surge current capacity levels range from 130 kA to 200 kA per phase. 40 Liebert manufactures the industry's widest range of Installing protection at the electrical service entrance, Surge Protective Devices (SPDs). These SPD's are ideal distribution points, branch panelboards and on specific for small facilities, large equipment rooms or entire sensitive loads or equipment throughout your facility buildings. Plus a wide range of power, control and data is the best way to prevent damage and eliminate line applications. Each surge protection product features associated downtime to sensitive microprocessor- the rugged reliability that has been Liebert's trademark based electronics. for more than 30 years. 41 Surge Protection And Power Conditioning Systems Home and Office Protection Data/Signal Line Protection Liebert PSS Surge Protection Strips– Edco RM-CAT6 Series—Includes 16 and Provide computer grade power, protecting 48-channel high-speed data line protectors connected equipment from the damaging that utilize three-stage hybrid technology. effects of lightning, spikes, surges, and These units address high-energy voltage other power quality problems. transients that can damage expensive network equipment. Ideal for network Islatrol® SP-6TVN Series—The Islatrol patch panels, switches and hubs, these SP-6TVN is a surge suppressor/filtering units mount easily in the same racks as the device that features uniquely designed equipment they are protecting. repositionable outlets and protects sensitive home/office equipment including home theaters, satellite dishes, computers, Edco PC642 Series—The Edco PC642 Series printers and faxes. surge suppressor is a two-pair (four-wire) module implementing three-stage hybrid technology. This module addresses over-voltage transients with gas tubes and silicon avalanche components. Medium & Low Exposure Systems Edco LCDP Series—The Edco LCDP Series PowerSure LPL & LPM Series—Surge is designed to conveniently protect 8 wire, suppression systems protect connected low voltage data circuits and employs two equipment against electric power line RJ-45 jacks for easy installation. disturbances and transients in medium and low exposure locations. Displays LED indication per phase. Provides remote Edco RJA-RJD Series—The Edco indication capabilities. Alerts with RJA and Edco RJD Series are four pair audible alarm. telephone/data line protectors that implement advanced two stage hybrid design. Islatrol™ RM Series—This line of AC surge protectors is ideal for protecting the power Edco CAT6-5 POE Series—The Edco feeding valuable rack equipment. This series CAT6-POE Series is designed to work provides 40,000 Amps of surge protection on Category 5 Power-Over-Ethernet and up to 60 dB of high- frequency noise transmission lines as well as CAT 6 filtering. applications. Edco PHC Series—This surge suppressor is designed to protect two pairs of wires specifically for alarm and security systems where operating currents can be as high as 5 Amps. It utilizes three-stage hybrid technology to address overvoltage transients and sneak and fault current for signaling circuits. 41 Powerful Solutions For Emerson Network Power Critical Data And Telecom Has A DC Power Solution Applications For Every Size Application From major switching and data centers to remote shelters Large DC Power Systems 208/480VAC 3-Phase and computer rooms, Emerson Network Power DC power Power systems for data center and central office systems have the features and proven performance to applications, including wireline and wireless switching, transmission, data routing and large telecom hotels. match your network application needs. A Brilliant Combination Of Technology And Real-World Capability The Emerson Network Power line of DC power systems demonstrates unparalleled reliability with industry-leading MTBF ratings at -48 and +24 VDC. Emerson Network Power rectifiers—the heart of the power system—possess some of the highest power densities and smallest footprints in the business. These power solutions can be further enhanced with the addition of intelligent controllers, remote system monitors, battery management units and a full range of distribution modules. NetSure™ 801 NetSure™ 802 The NetSure™ 801 high-density Integrated -48VDC 3-phase Emerson Network Power DC Power power system offers the rectifiers, distribution, control increased flexibility of a cabled and monitoring in a single Solutions Are Ideal For: plant in a centralized or frame. Expandable to 10,000 Central Office / CATV Headend. distributed architecture. The amps with additional frames. system consists of individual Computer Room. power bays and distribution Data Center. bays that may be configured with modular 5800 watt Enterprise (PBX, LAN). rectifiers to meet any -48 volt application requirement. Network Closet. Outside Plant Shelters & Cabinets. Radio Base Station / Microwave Site. DC Power Distribution Equipment Wireless & Wireline Access. LORAIN® DB 484800 Battery Distribution Fuse/Circuit Breaker Bay featuring high capacity, front access, modularity, and simplified installation LORAIN® DB 48500 to effectively provide This modular system secondary load provides effective distribution and secondary load protection for multiple distribution for single or -48 VDC feeds up to multiple -48VDC feeds. 600 amps. 42 Emerson Network Power offers a complete range of power systems to meet the energy capacity needs of any data or telecom application. To view our complete DC Power catalog, visit: EmersonNetworkPower.com/DCPower. 43 Medium DC Power Systems Small DC Power Systems DC Power Systems 240VAC Single Phase 120 / 240VAC Single Phase Modular, flexible design for switching, wireless Highly reliable, uninterruptible and cost-effective base stations, transmission, LAN, WAN and other power systems for small data or telecom installations. networking operations. NetSure™ 502 The NetSure™ 502 is a flexible system capable of providing DC power through the use of 2000W NetSure™ rectifiers, LORAIN®' XP 48450 / 48500 (LXP) an SCU+ controller, and a variety of Compact expandable -48VDC from output distribution options. 25 to 425 amp for 19" or 23" rack mount applications with integrated battery management . LORAIN® XP (LXP) 4870 / 4890 Builds upon the LXP 48500 platform, bringing internal distribution to the NetSure™ 700 NetSure™ 701 existing high capacity yet compact The NetSure™ 700 power system Modular power system 2RU power shelf platform. with 2500 watt rectifiers and providing up to 4,000 amps 1500 watt converters is a modular of power at -48VDC with power system providing up to 3200 watt rectifiers. 4,000 amps of power at +24VDC Inverter Systems and 400 amps at -48VDC. 120VAC and 230 VAC Single Phase Ideal for a data center, wireless switching, or central office environment where flexible expansion capabilities are required. LORAIN® IS 21000 Modular inverter Mini DC Power Systems system that grows in 3.5kVA 120 VAC or 220/240VAC Single Feed increments up High-density mini-sized DC power solutions for outside to 21kVA. LORAIN® IS 6000 LORAIN® IS 3000 plant enclosure, central office or embedded applications. Inverter System Inverter System Compact modular Stand alone rack design offers mounted design expansion in 1kVA offers expansion increments up to in 1kVA increments NetSure™ 211 2RU Configuration NetSure™ 211 1RU Configuration 6kVA. up to 3kVA. This DC power solution offers 1RU and 2RU configurations, combining reliable NetSure™ rectifiers with an advanced Ethernet-accessible controller for mini power applications. The 1RU model allows for up to three 1000-watt 48VDC rectifiers in a 23" shelf and two 1000-watt rectifiers in a 19" configuration. The Enclosure Solutions 2RU model allows for up to six 1000-watt 48VDC rectifiers in a 23" shelf and Custom designed or standard enclosures available for all types up to four 1000-watt rectifiers in a 19" configuration. of data and telecom equipment. Batteries & Accessories Products frequently used together with DC power systems including batteries, battery strands, battery trays, bus covers, assorted panels, circuit breakers and much more. 43 Power System Monitoring: The Key To Continuous Operation What You Don't Know Can Hurt You. How Deep Does Your Monitoring A small problem in a critical facility can quickly Need To Be? escalate into a disaster—knowing what is happening Monitoring can range from a automated shutdown with your power equipment, so you can keep that software that provides basic operating information protective "envelope" at peak operating efficiency, from a single UPS unit, all the way to full-scale is vital to system reliability. monitoring and control of a critical facility including trending and data analysis. Different People Need To Know Different Things. Your requirements will vary according to the specificity Liebert offers you more monitoring solutions than of the information you need. You may require no more anyone else because getting the right information than a local readout of a unit's operating status. Or you about your power equipment to the right people, may need the ability to control its operation and with the right level of urgency, is so important to receive alarms. system availability. These information requirements may also go beyond We do this by allowing you to receive and use basic monitoring and control. You may need the ability information from your Liebert power equipment's to analyze performance data in order to pinpoint microprocessor controls–no matter where it is located trouble spots so that the same problems don't or what communications protocol, operating platform happen again and again. or building management system is being used. In-band, out-of-band and web-based monitoring are all available. From enterprise monitoring systems to individual pieces of communications hardware, you will know the exact problem so that you can implement the right solution. 44 Maximizing Your Investment Through System Monitoring 45 Distributed Management with Centralized Management with Enterprise Management with Monitoring And Control Liebert IntelliSlot Interface Cards Liebert Nform®Software Liebert SiteScan® Web Software For enhanced remote communications As business grows, your critical For customers who require extensive and control of your Liebert units, equipment infrastructure will management of critical system the Liebert IntelliSlot Web and 485 expand, thus the need for centralized equipment that may span multiple Cards deliver the communication management of this equipment will be locations in an ever-moving global capabilities you require. key to your business success. enterprise, Liebert SiteScan Web will centrally manage your critical Monitoring and control through your Connecting to equipment in the equipment and give you the power existing Network with no additional distributed critical space is only part of to move beyond the event-responsive software required. the monitoring challenge. service paradigm. Each Liebert system equipped with a Liebert Nform leverages the Liebert SiteScan Web does it all: Liebert IntelliSlot Web Card takes full network connectivity capabilities Real-Time Monitoring and Control. advantage of your Ethernet network, of your Liebert equipment to provide Event Management and Reporting. allowing remote monitoring from your a centralized monitoring view of your computer desktop, network operations distributed equipment. Data Analysis and Trending. center or wherever network access is Building Management Integration. permitted, without the need for Utilizing the SNMP and Web front-end software. technologies built into each of the Liebert SiteScan Web is a comprehensive Liebert IntelliSlot communication cards, critical systems management solution Monitoring integration with Liebert Nform will centrally manage dedicated to ensuring reliability through your existing Building alarm notifications to provide you with graphics, event management and Management System. an easy interface to access critical status data extrapolation. The standard Web information. Liebert Nform puts critical interface allows users easy access from A Liebert system equipped with a Liebert systems information at the fingertips of anywhere at anytime. IntelliSlot™ 485 Card can be seamlessly support personnel—wherever they Single and multi-site applications. integrated with your existing Building are—increasing responsiveness to Event management and unit control. Management System. alarm-event conditions, thus allowing Trend and historical data captures IT organizations to maximize their and reporting. system availability. Full ASHRAE BACnet compatibility. Java based. Windows 2000, XP and 2003 compatible. Liebert Nform Liebert IntelliSlot Web Liebert SiteScan Web 45 Liebert Services Complete Start-Up And Preventive Maintenance Services Peace of mind. It's confidence you've done everything possible Confident Customers. Satisfied Customers. to assure system uptime. It's confidence the power systems You know them. They're confident because they know their systems will be available when they you rely on are operating at peak performance. It's confidence need them. So, they're satisfied customers—and, you've selected the best partner available to bring you back they're probably ours. 99% of our customers are online in the event of unexpected downtime. satisfied with the service we provide. In fact, 96% of them would recommend us to someone else Complete confidence. When it comes to selecting a (source: MRSI). service organization to maintain your critical power systems, you can only have complete confidence that Proprietary Tools Deliver Uptime Emerson Network Power Liebert Services can deliver: Ensuring peak operating performance of your equipment comes down to having knowledgeable Real uptime assurance. We have the proprietary Field Technicians in your facility with the most tools, industry knowledge and robust service current tools available to do the job. Only Emerson infrastructure to deliver real assurance that your Network Power Field Technicians have access to systems will be available when you need them. the proprietary tools needed to ensure system uptime—firmware upgrades, factory engineering Efficient downtime recovery. After all, if downtime specifications, access to Liebert product and strikes, you need a partner that can get you back application engineers and R&D. No one else can online quickly with intelligent answers, rapid service bring this to your organization. response and parts where and when you need them. The Business Case For Regular Maintenance 60x Increase in MTBF Regular OEM preventive maintenance increases the mean 51x time between failures (MTBF). 50x For instance, the mean time between failures for a system Increase in 40x 37x that receives 1 annual PM is 10 times greater than a system Mean Time that receives 0 PMs. Between 30x Failures1 By contrast, a system that receives 4 annual PMs, as 23x opposed to 0 PMs, increases its duration between failures 20x by 51 times. 10x 10x 1 Data is based on Mean Time Between Failure analysis for 1x three phase UPS systems (≥ 100kVA) with an Emerson Network Power service agreement between 2002-2007. 0 1 2 3 4 Number of Annual Preventive Maintenance Visits 46 Servicing All Your Critical Power Equipment Your investment in power equipment is worthless if you don't maintain it. Not even the best equipment can function properly unless it's serviced with a regular maintenance schedule. Emerson Network Power services The Power Equipment the complete spectrum of UPS, We Service Includes: batteries and related power All UPS and Batteries. distribution equipment in your data Automatic Transfer Switch. Static Transfer Switch. center or in other critical facilities System Control Cabinets. where continuous availability of PDUs. systems is essential. Bypass Cabinets. Power Conditioning & Distribution. Emerson Network Power's Liebert Services Business Your power equipment functions as a complete system. Shouldn't your service provider? Only Emerson Network Power has the expertise and experience to service your entire power infrastructure and all its components—from utility to rack. Automatic Static Remote Transfer Transfer Distribution Racks Generator Switch TVSS SwitchGear UPS Batteries Switch Cabinet Power Availability Power Protection Power Conversion/Distribution Availability depends Raw utility power Converting and delivering power on the continuity of may be unsuitable for throughout a large facility or a power and the ability sensitive technology small space is an important step of an uninterruptible systems. In these in protecting availability. electrical supply to ride situations, surge through outages of suppression and any duration. power conditioning can deliver the power quality you need. 47 Ensuring The High Availability Of Mission-Critical Data And Applications. Emerson Network Power, a business of Emerson (NYSE:EMR), is the global leader Emerson Network Power Liebert Corporation in enabling Business- Critical Continuity™ from grid to chip for telecommunication World Headquarters 1050 Dearborn Drive networks, data centers, health care and industrial facilities. Emerson Network Power P.O. Box 29186 provides innovative solutions and expertise in areas including AC and DC power and Columbus, Ohio 43229 United States Of America precision cooling systems, embedded computing and power, integrated racks and 800 877 9222 Phone (U.S. & Canada Only) 614 888 0246 Phone (Outside U.S.) enclosures, power switching and controls, monitoring, and connectivity. All solutions 614 841 6022 FAX are supported globally by local Emerson Network Power service technicians. Liebert Emerson Network Power AC power, precision cooling and monitoring products and services from Emerson European Headquarters Via Leonardo Da Vinci 8 Network Power deliver Efficiency Without Compromise™ by helping customers Zona Industriale Tognana 35028 Piove Di Sacco (PD) optimize their data center infrastructure to reduce costs and deliver high availability. Italy 39 049 9719 111 Phone 39 049 5841 257 FAX Emerson Network Power Asia Pacific 29/F, The Orient Square Building F. Ortigas Jr. Road, Ortigas Center Pasig City 1605 Philippines +63 2 687 6615 +63 2 730 9572 FAX liebert.com 24 x 7 Tech Support 800 222 5877 Phone 614 841 6755 (outside U.S.) While every precaution has been taken to ensure accuracy and completeness in this literature, Liebert Corporation assumes no responsibility, and disclaims all liability for damages resulting from use of this information or for any errors or omissions. © 2009 Liebert Corporation. All rights reserved throughout the world. Specifications subject to change without notice. All names referred to are trademarks or registered trademarks of their respective owners. ® Liebert is a registered trademark of the Liebert Corporation. SL-70100 (R12/09) Printed in USA Emerson Network Power. EmersonNetworkPower.com The global leader in enabling Business-Critical Continuity™. AC Power Embedded Computing Outside Plant Racks & Integrated Cabinets Connectivity Embedded Power Power Switching & Controls Services DC Power Monitoring Precision Cooling Surge Protection Business-Critical Continuity, Emerson Network Power and the Emerson Network Power logo are trademarks and service marks of Emerson Electric Co. ©2009 Emerson Electric Co.
Pages to are hidden for
"Liebert power solutions brochure"Please download to view full document