Canadian Shield Consultants offers a complete line of decentralized wastewater treatment products and services. The PFS-200 to PFS-1000 pressurized flow dividers are suitable for any septic installation requiring division of effluent flow.
Premier Tech Aqua’s PFS-200 to PFS-1000 Pressurized Flow Dividers divide a pumped effluent flow into equal portions, according to installation needs. They enable cluster installation of several Ecoflo® ST-650 Biofilters in high wastewater flow applications.
The unit divides the effluent flow using pressure generated by the pump and then distributes the effluent to the treatment units through gravity flow pipes. This way, the length of the piping systems is irrelevant. All liquid must be pumped out of the enclosure before the next dosing. If the installation design does not enable this, then measures must be taken to protect the system from freezing.
Operation pressure: 7 kPa (1 psi) minimum and 28 kPa (4 psi) maximum.
PVC outlet pipe, 100 mm (4″) – dr 35, 108 mm (4.25″) outside diameter.
PVC outlet pipe, 100 mm (4″) – DR 35 outside diameter.
The casing lid must be accessible at all times to enable annual system inspection and maintenance (or as needed).