Universal outputs are jumper select for relay drive or 0-10 V operation.
Flexible mix of dimming, and switching loads.
Single-wire connection to actuate the relay and also read the position.
Connect Lux and occupancy sensors directly to relays or to analog inputs.
Relay outputs can drive 0-10 V 75 mA sink or source dimming loads (up to 8 per controller).
64 spring loaded relay plates for tool free removal or relays.
NEMA1 Type 1 enclosure, steel 14 gauge mild steel base with 40 pre-cut conduit knockouts.
Flat panel door attached with 6 Robertson screws.
Hinged panel door assembly 26” x 50” and 6 phillips screw terminations.
Enclosure base 121.9 cm L x 61 cm W x 10.8 cm H (48” L x 24” W x 4.25” H).
16 inch centers vertical and horizontal on panel back.
MPL-LCP-64 back panel fully assembled with 64 relays and no enclosure weighs 21.8 kg (48 lbs).
ENC-LCP-64-FDP 34.62 kg (76 lbs).
ENC-LCP-64-HDP 37.78 kg (83 lbs).