Controllers for VAV / chilled ceiling systems, etc.
Single room control solutions for VAV / chilled ceiling systems, etc.
1) The standby input is not available in change-over (C/O) mode or in heating controller applications as it is assigned to the C/O input function. CR24-B3 should be used if the stand-by function is needed in a C/O application.
2) The boost function is not available in change-over mode or in chilled ceiling applications with dew point monitoring. The combination change-over and dew point monitoring is possible.
3) The output can either be used as a common cooling and heating output in change-over mode or exclusively as a cooling or heating output. The stand-by function is not available in change-over mode or in heating controller applications.
4) The output can either be used as a common cooling and heating output in change-over mode or exclusively as a cooling or heating output.