All In One Complete Industrial / Commercial Reverse Osmosis Desalination Plant With Booster Pump & Automatic Carbon Filter. Designed from high quality components to offer high performance.
Fresh water: 835 liter/hour (20,000 LPD).
4 x 4040 German made energy efficient, low pressure membranes.
Inlet feed water TDS < 1500 mg/l (ppm).
Produces high pure water for drinking, commercial and industrial applications.
MDC Water Reverse Osmosis Systems are manufactured by utilizing high quality components and advanced system design to offer high performance. Assembled in Taiwan for MDC Water Pty Ltd.
Flow*: Permeate Water / Fresh Water / Production: 835 Liter/Hour (20,000 LPD).
Recovery*: 50 – 70 %.
Feed Water Flow: from 1,195 to 1,670 ltr/h.
* Flow and recovery depending on feed water quality.
TDS < 1500 mg/l (ppm) / Non Scaling Feed Water / SDI < 3 / Free Chlorine < 0.1 mg/l / Temperature 5-35° C / Inlet Pressure: 36-44 PSI (2.5–3 bar) @ 1,860 ltr/h / pH 5-7.5 / Bacteria Nil / Iron < 0.1 mg/l.
Only carbon filter and sediment cartridge filter Pre-treatment equipment are included, other Pre-treatment equipment are not included (Softener, anti-scalant, sand filter, iron removal, UV …etc).
Quality Reverse Osmosis Plant at Best Sale Price.
Approx. Dimensions: 130cm W x 100cm L x 180cm H.
Flush Solenoid Valve: For Automatic Flushing Process.
Recycle Line: Concentrate Recycle Line Into HP Pump Inlet.
Product & Reject Flow Meter.
Valves: High Pressure Pump Discharge Valve, SS Concentrate Panel Mounted Needle Valve, Recycle Line Valve, Sample Valve, Valve for CIP.
CIP (Cleaning In Place): Equipped With Isolation Valves and Connections to DO the CIP Smothly.
High Pressure Piping : Pressure PVC Pipes & Fittings.
Frame : 304 Stainless Steel – Electro Polishing.
Stainless Steel Booster Pump, 0.6kW.
Feed Water High Pressure Protection Switch.
Inlet Solenoid Valve. 20″ Cartridge Filter 10 Micron.
Low Feed Inlet Pressure Protection Switch.
High Pressure Pump: GRUNDFOS, CRI3-25 Multi-Stage Centrifugal 304 Stainless Steel Pump,2.2kW.
Membrane Housings: 4 x 4.0” x 40” FRP.
Membranes: 4 x 4.0” x 40” TFC Low Pressure Membranes (Lanxess Germany).
Power: 380/415VAC, 50Hz, Three Phase.
Industrial Electrical Control Panel: Indoor Use, PLC, Mimic Flow Schematic Diagram.
Indicator Light For: Raw Water Tank Full, Booster Pump (operation / abnormal), Feed Water High Pressure Switch, Carbon Filter (service / generation), Inlet Solenoid Valve, Low Pressure Switch, RO Pump (operation / abnormal), Pure Water Tank (full / medium), Flush Solenoid Valve.
Switches For: Booster Pump, Inlet Valve, HP RO Pump.
Manual Flush Button: RO System Has an Automatic Flush process, It can be Initiate Manually By This Button.
Inline Digital Conductivity/TDS Meter For Product Water.
Power On/Off Switch (Emergency Stop Switch).