Test results for BHS Easy Lay Insulated Pipe test 12-30-2010 Part # Description Length of Run GPM Total Temp Loss Temp Loss per 100 ft Temp loss per ft Btu loss per Ft Btu loss per 100 ft ez13 BHS Easy-Lay 1″ NOB Insulated Pipe with 3 wraps of EPE Insulation. 500 ft 5 6.2 1.24 0.012 31.06 3106.2 ez15 BHS Easy-Lay 1″ NOB Insulated Pipe with 5 wraps of EPE Insulation. 500 ft 5 3.1 0.62 0.006 15.53 1553.1 For Comparison purposes, some companies only tell you the heat loss for a single line. This equates to .62 degrees per 100 ft on our 3 wrap products and .31 degrees per 100 feet on our 5 wrap products.
Cozeburn Boiler Water Prep Solution & Cleaner 102™ Treats 200 Gal.