combine elements of both electronic air cleaners and passive mechanical filters. Most polarized-media electronic air cleaners use safe 24-volt DC voltage to establish the polarizing electric field. Most airborne particles have a charge and many are even bi-polar. As airborne particles pass through the electric field the polarized field re-orients the particle to adhere to a disposable fiber media pad. Ultra-fine particles (UFPs) that are not collected on their initial pass through the media pad are polarized and agglomerate to other particles, odor and VOC molecules and are collected on subsequent passes. The efficiency of polarized-media electronic air cleaners increases as they load, providing high-efficiency filtration, with air resistance typically equal to or less than passive filters. Polarized-media technology is non-ionizing, which means no ozone is produced. Photocatalytic oxidation (PCO) is an emerging technology in the HVAC industry. In addition to the prospect of Indoor Air Quality (IAQ) benefits, it has the added potential for limiting the introduction of unconditioned air to the building space, thereby presenting an opportunity to achieve energy savings over previous prescriptive designs. As of May 2009 there was no more disputable concern raised by the Lawrence Berkeley National Laboratory data that PCO may significantly increase the amount of formaldehyde in real indoor environments. As with other advanced technologies, sound engineering principles and practices should be employed by the HVAC designer to ensure proper application of the technology. Photocatalytic oxidation systems are able to completely oxidize and degrade organic contaminants. For example, Volatile Organic Compounds found low concentrations within a few hundred ppmv or less are the most likely to be completely oxidized.(PCO) uses short-wave ultraviolet light (UVC), commonly used for sterilization, to energize the catalyst (usually titanium dioxide (TiO2)) and oxidize bacteria and viruses. PCO in-duct units can be mounted to an existing forced-air HVAC system. PCO is not a filtering technology, as it does not trap or remove particles. It is sometimes coupled with other filtering technologies for air purification. UV sterilization bulbs must be replaced about once a year; manufacturers may require periodic replacement as a condition of warranty. Photocatalytic Oxidation systems often have high commercial costs. A related technology relevant to air purification is photoelectrochemical oxidation (PECO) Photoelectrochemical oxidation. While technically a type of PCO, PECO involves electrochemical interactions among the catalyst material and reactive species (e.g., through emplacement of cathodic materials) to improve quantum efficiency; in this way, it is possible