violet, and yellow are used in 277/480-volt systems. (Violet avoids conflict with the NEC's high-leg delta rule.) In buildings with multiple voltage systems, the grounded conductors (neutrals) of both systems are required to be separately identified and made distinguishable to avoid cross-system connections. Most often, 120/208-volt systems use white insulation, while 277/480-volt systems use grey insulation, although this particular colour code is not currently an explicit requirement of the NEC. Some local jurisdictions do specify required color coding in their local building codes, however. Color codes Wiring methods Materials for wiring interior electrical systems in buildings vary depending on: Intended use and amount of power demand on the circuit Type of occupancy and size of the building National and local regulations Environment in which the wiring must operate. Wiring systems in a single family home or duplex, for example, are simple, with relatively low power requirements, infrequent changes to the building structure and layout, usually with dry, moderate temperature and non-corrosive environmental conditions. In a light commercial environment, more frequent wiring changes can be expected, large apparatus may be installed and special conditions of heat or moisture may apply. Heavy industries have more demanding wiring requirements, such as very large currents and higher voltages, frequent changes of equipment layout, corrosive, or wet or explosive atmospheres. In facilities that handle flammable gases or liquids, special rules may govern the installation and wiring of electrical equipment in hazardous areas. Wires and cables are rated by the circuit voltage, temperature rating and environmental conditions (moisture, sunlight, oil, chemicals) in which they can be used. A wire or cable has a voltage (to neutral) rating and a maximum conductor surface temperature rating. The amount of current a cable or wire can safely carry depends on the installation conditions. The international standard wire sizes are given in the IEC 60228 standard of the International Electrotechnical Commission. In North America, the American Wire Gauge standard for wire sizes is used. Cables Modern wiring materials Modern non-metallic sheathed cables, such as (US and Canadian) Types NMB and NMC, consist of two to four wires covered with thermoplastic insulation, plus a wire for Protective Earthing/Grounding (bonding), surrounded by a flexible plastic jacket. In North America and the UK this conductor is usually bare wire but in the UK it is required that this bare Protective Earth (PE) conductor be sheathed in Green/Yellow insulating tubing where the Cable Sheathing