be exposed in the event of a fault within the installation or outside the installation. (Exposure may be from e.g. hand to hand or hand to foot, between simultaneously accessible conductive surfaces, which might include the earth itself, mildly conductive floors and walls, metal taps, pipes, electrical appliances etc. Examples of faults are an insulation failure between a line conductor and a metallic frame of an appliance within the installation, a break in a combined protective-earth and neutral conductor in the supply, or an insulation fault in the supply transformer causing the whole low-voltage system to rise in potential.) Conductors for these protective functions of earthing and bonding are insulated with green/yellow (striped) colour coding, which is not permitted for any other conductors. Earthing connects exposed conductive parts (ECPs) of electrical equipment to a main earthing terminal (MET), which is connected to a "means of earthing" that somehow connects it to the earth itself (the ground/soil/planet!). In installations fed from low-voltage public supplies in the UK this means of earthing can be any of the methods TN-S, TN-C-S or TT defined in BS 7671. In the event of an insulation fault from a live conductor to an appliance's metal frame (an ECP), the frame could—if not so connected—be dangerous if touched by someone who is also for example standing outside on the ground, or standing inside on a concrete floor, or holding a tap whose pipe connects it electrically into the ground. Protective earthing limits the combination of magnitude and duration of the dangerous voltage that could exist between the ECP and the earth itself. In conventional installations in the UK the voltage between an appliance frame and the earth itself during a zero-impedance fault has a dangerous magnitude: it might be reduced to about half of the 230 V line-earth voltage, which is well above the 50 V usually accepted as safe for an AC system, or it might be nearly 230 V in a TT system with a poor earth electrode for the installation. The duration of this voltage must therefore be limited, which is done by "automatic disconnection of supply" (ADS) either by overcurrent protection devices (OCPDs), or by residual current devices (RCDs) that specifically detect the current escaping from the intended circuit, allowing them to have a far lower tripping current. In TT systems it is almost always necessary to have an RCD, as earth electrodes