optimize the cost/yield relation (33° would have maximized yield). The rim of the hemisphere was "trimmed" to 60°, creating a maximum aperture of . This pilot bowl produced electricity at a rate of 10 kW peak. A diameter Auroville solar bowl was developed from an earlier test of a bowl in 1979–1982 by the Tata Energy Research Institute. That test showed the use of the solar bowl in the production of steam for cooking. The full-scale project to build a solar bowl and kitchen ran from 1996 and was fully operational by 2001. In locations with average available solar energy, flat plate collectors are sized approximately 1.2 to 2.4 square decimeter per liter of one day's hot water use. Applications The main use of this technology is in residential buildings where the demand for hot water has a large impact on energy bills. This generally means a situation with a large family or a situation in which the hot water demand is excessive due to frequent laundry washing. Commercial applications include laundromats, car washes, military laundry facilities and eating establishments. The technology can also be used for space heating if the building is located off-grid or if utility power is subject to frequent outages. Solar water heating systems are most likely to be cost effective for facilities with water heating systems that are expensive to operate, or with operations such as laundries or kitchens that require large quantities of hot water. Unglazed liquid collectors are commonly used to heat water for swimming pools but can also be applied to large-scale water pre-heating. When loads are large relative to the available collector area, the bulk of the water heating can be done at low temperature, lower than swimming pool temperatures where unglazed collectors are well established in the marketplace as the right choice. Because these collectors need not withstand high temperatures, they can use less expensive materials such as plastic or rubber. Many unglazed collectors are made of polypropylene and must be drained fully to avoid freeze damage when air temperatures drop below on clear nights. A smaller but growing percentage of unglazed collectors are flexible meaning they can withstand water freezing solid inside their absorber. The freeze concern only needs to be the water-filled piping and collector manifolds in a hard freeze condition. Unglazed solar hot water systems should be installed to "drainback" to a storage tank whenever solar radiation