pairs, after negotiation, to supply up to 60 W. Linear Technology A proprietary high-power development called LTPoE++, using a single Cat 5e Ethernet cable, is capable of supplying varying levels at 38.7, 52.7, 70, and 90 W. Microsemi PowerDsine, acquired by Microsemi in 2007, has been selling midspan power injectors since 1999 with its proprietary Power over LAN solution. Several companies such as Polycom, 3Com, Lucent and Nortel utilize PowerDsine's Power over LAN. Passive In a passive PoE system, the injector does not communicate with the powered device to negotiate its voltage or wattage requirements, but merely supplies power at all times. Common 100 Mbit/s passive applications use the pinout of 802.3af mode B (see )with DC positive on pins 4 and 5 and DC negative on 7 and 8 and data on 1–2 and 3–6, but polarization may vary. Gigabit passive injectors use a transformer on the data pins to allow power and data to share the cable and are typically compatible with 802.3af Mode A. Passive midspan injectors with up to 12 ports are available. Devices needing 5 volts cannot typically use PoE at 5 V on Ethernet cable beyond short distances (about ) as the voltage drop of the cable becomes too significant, so a 24 V or 48 V to 5 V DC-DC converter is required at the remote end. Passive PoE power sources are commonly used with a variety of indoor and outdoor wireless radio equipment, most commonly from Motorola (now Cambium), Ubiquiti Networks, MikroTik and others. Earlier versions of passive PoE 24 VDC power sources shipped with 802.11a, 802.11g and 802.11n based radios are commonly 100 Mbit/s only. Passive DC-to-DC injectors also exist which convert a 9 V to 36 V DC, or 36 V to 72 V DC power source to a stabilized 24 V 1 A, 48 V 0.5 A, or up to 48 V 2.0 A PoE feed with '+' on pins 4 & 5 and '−' on pins 7 & 8. These DC-to-DC PoE injectors are used in various telecom applications. Power capacity limits The ISO/IEC TR 29125 and Cenelec EN 50174-99-1 draft standards outline the cable bundle temperature rise that can be expected from the use of 4PPoE. A distinction is made between two scenarios: bundles heating up from the inside to the outside, and bundles heating up from the outside to match the ambient temperature. The second scenario