Another way to rapidly produce steam is to feed the water under pressure into a tube or tubes surrounded by the combustion gases. The earliest example of this was developed by Goldsworthy Gurney in the late 1820s for use in steam road carriages. This boiler was ultra-compact and light in weight and this arrangement has since become the norm for marine and stationary applications. The tubes frequently have a large number of bends and sometimes fins to maximize the surface area. This type of boiler is generally preferred in high pressure applications since the high pressure water/steam is contained within narrow pipes which can contain the pressure with a thinner wall. It can however be susceptible to damage by vibration in surface transport appliances. In a cast iron sectional boiler, sometimes called a "pork chop boiler" the water is contained inside cast iron sections. These sections are mechanically assembled on site to create the finished boiler. Supercritical steam generators Supercritical steam generators are frequently used for the production of electric power. They operate at supercritical pressure. In contrast to a "subcritical boiler", a supercritical steam generator operates at such a high pressure (over ) that actual boiling ceases to occur, the boiler has no liquid water - steam separation. There is no generation of steam bubbles within the water, because the pressure is above the critical pressure at which steam bubbles can form. It passes below the critical point as it does work in a high-pressure turbine and enters the generator's condenser. This results in slightly less fuel use and therefore less greenhouse gas production. The term "boiler" should not be used for a supercritical pressure steam generator, as no "boiling" actually occurs in this device. Water treatment Feed water for boilers needs to be as pure as possible with a minimum of suspended solids and dissolved impurities which cause corrosion, foaming and water carryover. The most common options for demineralization of boiler feedwater are reverse osmosis (RO) and ion exchange (IX). Safety When water is converted to steam it expands in volume 1,600 times and travels down steam pipes at over 25 m/s. Because of this, steam is a good way of moving energy and heat around a site from a central boiler house to where it is needed, but without the right boiler feed water treatment, a steam-raising plant will suffer from scale formation and corrosion. At best,