can often be accomplished without raising the existing pylons and while keeping the necessary safety distances between the ground and the other line. In the course of undercrossings the pylon picture is frequently changed, and because of its small height it is preferable to create an arrangement with conductors in one level. Sometimes at such crossings there can be problems because of the maximum pylon height allowed for flight safety reasons. If it is not possible at a given location for the pylons of the upper line to be built at a necessary height, the line running below it will be rebuilt on smaller pylons or replaced with an underground cable. A unique undercrossing of two powerlines can be found north of Kincardine at Scotland at 56°5'17"N 3°43'11"W. Here crosses the powerline Kincardine-Tealing two other lines. One of the two circuits of Kincardine-Tealing powerline crosses these lines on two small pylons and the other circuit via an underground cable. Special crossings from overhead lines of other overhead lines There are some crossings between two overhead powerlines, which are unique, either as both lines are of special type or the unique way of implementation Overhead line crossings of aerial tramways Overhead lines should cross the route of an aerial tramway only above it, if at all. The necessary protection distances from overhead lines to the ropes of an aerial tramway are subject to regulations concerning the construction of aerial tramways and overhead lines. In the case of an undercrossing of an aerial tramway, the maximum safety distances between the overhead line and the floor of the aerial tramway cab must be followed absolutely. In principle, over- and undercrossings of aerial tramways are completely regulated. However, frequently at the range of the crossing section, special precautionary measures are taken. Thus, at overhead line crossings at which the overhead line runs above the rope of the aerial tramway, two catch ropes are occasionally installed to prevent the conductor from falling off the rope of the tramway in case a pylon or insulator were to break. Alternatively, auxiliary cross-bars can be installed on the pylons of the overhead line under the conductors, which prevent the conductor cables from falling in case of an insulator failure on the aerial tramway. Occasionally, the span field of the line over the aerial ropeway can be scaffolded with a rigid construction along its whole length, or at least