outer hoops and two disks, one of which is on the top and the other is on the bottom to avoid breakage. Currently, there is little need for toroidal geometry for small SMES, but as the size increases, mechanical forces become more important and the toroidal coil is needed. The older large SMES concepts usually featured a low aspect ratio solenoid approximately 100 m in diameter buried in earth. At the low extreme of size is the concept of micro-SMES solenoids, for energy storage range near 1 MJ. Low-temperature versus high-temperature superconductors Under steady state conditions and in the superconducting state, the coil resistance is negligible. However, the refrigerator necessary to keep the superconductor cool requires electric power and this refrigeration energy must be considered when evaluating the efficiency of SMES as an energy storage device. Although high-temperature superconductors (HTS) have higher critical temperature, flux lattice melting takes place in moderate magnetic fields around a temperature lower than this critical temperature. The heat loads that must be removed by the cooling system include conduction through the support system, radiation from warmer to colder surfaces, AC losses in the conductor (during charge and discharge), and losses from the cold–to-warm power leads that connect the cold coil to the power conditioning system. Conduction and radiation losses are minimized by proper design of thermal surfaces. Lead losses can be minimized by good design of the leads. AC losses depend on the design of the conductor, the duty cycle of the device and the power rating. The refrigeration requirements for HTSC and low-temperature superconductor (LTSC) toroidal coils for the baseline temperatures of 77 K, 20 K, and 4.2 K, increases in that order. The refrigeration requirements here is defined as electrical power to operate the refrigeration system. As the stored energy increases by a factor of 100, refrigeration cost only goes up by a factor of 20. Also, the savings in refrigeration for an HTSC system is larger (by 60% to 70%) than for an LTSC systems. Cost Whether HTSC or LTSC systems are more economical depends because there are other major components determining the cost of SMES: Conductor consisting of superconductor and copper stabilizer and cold support are major costs in themselves. They must be judged with the overall efficiency and cost of the device. Other components, such as vacuum vessel insulation, has been shown to be a small part compared to the