Voltage optimisation is a term given to the systematic controlled reduction in the voltages received by an energy consumer to reduce energy use, power demand and reactive power demand. While some voltage 'optimisation' devices have a fixed voltage adjustment, others electronically regulate the voltage automatically. Voltage optimisation systems are typically installed in series with the mains electrical supply to a building, allowing all its electrical equipment to benefit from an optimised supply. Background Voltage optimisation is an electrical energy saving technique which is mainly installed in series with the mains electricity supply to provide a reduced supply voltage for the site's equipment. Typically, voltage optimisation can improve power quality by balancing phase voltages and filtering harmonics and transients from the supply, although not always. Voltage optimisers are essentially transformers used to deliver power at a reduced voltage from the raw mains supply. The term voltage optimisation is frequently misused, as the term implies some form of selective voltage reduction, which will improve the energy consumption within a building, whereas generally these units consists of a transformer within a box, offering no selectivity and dropping voltage on all supplies, whether this would offer a commercial benefit or not. Some VO units have been installed on high frequency lighting circuits, offering little or no commercial benefit, therefore one must be careful when the term is used. Most VO units are installed in commercial premises, in between the raw mains transformer and main low voltage distribution board. However, this provides for no selectivity and in electrical engineering terms is considered a poor solution. A full study should be undertaken by the facilities manager and VO company, to select which supplies could benefit the owner by reducing the voltage and which supplies would give no commercial benefit. This way the owner only purchases a VO of the correct size and not one that's for all supplies. Installing a VO unit to 'optimise' all supplies would give a longer return on investment, a higher capital outlay and makes little commercial sense. United Kingdom The declared low voltage electricity supply in the United Kingdom as per the Electrical Safety, Quality and Continuity Regulations 2002, is now 230 V with a tolerance of +10% to -6%. This means that supply voltage can theoretically be anywhere between 216 V and 253 V depending on local conditions. However, the average voltage supplied from the national grid (in mainland UK)