consisting of angstrom-scale windows and nanometer-scale cavities displayed ultrafast selective transport of alkali metal ions. The windows acted as ion selectivity filters for alkali metal ions, while the cavities functioned as pores for transport. The ZIF-8 and UiO-66 membranes showed a LiCl/RbCl selectivity of ~4.6 and ~1.8, respectively, much higher than the 0.6 to 0.8 selectivity in traditional membranes. A 2020 study suggested that a new MOF called PSP-MIL-53 could be used along with sunlight to purify water in just half an hour. Gas Separation MOFs are also predicted to be very effective media to separate gases with low energy cost using computational high throughput screening from their adsorption or gas breakthrough/diffusions properties. One of the example is NbOFFIVE-1-Ni, also referred to as KAUST-7 which can separate propane and propylene via diffusion at nearly 100% selectivity. The specific molecule selectivity properties provided by Cu-BDC surface mounted metal organic framework (SURMOF-2) growth on alumina layer on top of back gated Graphene Field Effect Transistor (GFET) can provide a sensor that only sensitive to ethanol but not to methanol or isopropanol. Water vapor capture and dehumidification MOFs have been demonstrated that capture water vapor from the air. In 2021 under humid conditions, a polymer-MOF lab prototype yielded 17 liters (4.5 gal) of water per kg per day without added energy. MOFs could also be used to increase energy efficiency in room temperature space cooling applications. When cooling outdoor air, a cooling unit must deal with both the air's sensible heat and latent heat. Typical vapor-compression-air-conditioning (VCAC) units manage the latent heat in air through cooling fins held below the dew point temperature of the moist air at the intake. These fins condense the water, dehydrating the air and thus substantially reducing the air's heat content. The cooler's energy usage is highly dependent on the cooling coil's temperature and would be improved greatly if the temperature of this coil could be raised above the dew point. This makes it desirable to handle dehumidification through means other than condensation. One such means is by adsorbing the water from the air into a desiccant coated onto the heat exchangers, using the waste heat exhausted from the unit to desorb the water from the sorbent and thus regenerate the desiccant for repeated usage. This is accomplished by having two condenser/evaporator units through which the flow of refrigerant can be reversed once the desiccant on the condenser