just use the bottom blow to remove them from the feed water. When there is a low amount of sludge content it is better to use dispersants because it disperses the sludge throughout the feed water so sludge does not form. Deaeration of feed water Oxygen and carbon dioxide are removed from the feed water by deaeration. Deaeration can be accomplished by using deaerator heaters, vacuum deaerators, mechanical pumps, and steam-jet ejectors. In deaerating heaters, steam sprays incoming feed water and carries away the dissolved gases. The deaerators also store hot feed water which is ready to be used in the boiler. This means of mechanical deaeration is used with chemical oxygen scavenging agents to increase efficiency. (Sendelbach, p. 129) Deaerating heaters can be classified in two groups: spray types and tray types. With tray type heaters the incoming water is sprayed into steam atmosphere to reach saturation temperature. When the saturation temperature is reached most of the oxygen and non-condensable gases are released. There are seals that prevent the recontamination of the water in the spray section. The water then falls to the storage tank below. The non-condensables and oxygen are then vented to the atmosphere. The components of the tray type deaerating heater are a shell, spray nozzles, direct contact vent condenser, tray stacks, and protective interchamber walls. The spray type deaerator is similar to the tray type deaerator. The water is sprayed into a steam atmosphere and most of the oxygen and non-condensables are released to the steam. The water then falls to the steam scrubber where the slight pressure loss causes the water to flash a little bit which also aids the removal of oxygen and non-condensables. The water then overflows to the storage tank. The gases are then vented to the atmosphere. With vacuum deaeration a vacuum is applied to the system and water is then brought to its saturation temperature. The water is sprayed into the tank like the spray and tray deaerator. The oxygen and non-condensables are vented to the atmosphere. (Sendelbach, p. 130) Conditioning The feedwater must be specially treated to avoid problems in the boiler and downstream systems. Untreated boiler feed water can cause corrosion and fouling. Boiler corrosion Corrosive compounds, especially O2 and CO2 must be removed, usually by use of a deaerator. Residual amounts can be removed chemically, by use of oxygen scavengers. Additionally, feed water is typically alkalized