to their power density, elimination of gassing, reduced maintenance, and enhanced safety. AGM and gel-cell batteries are also used for recreational marine purposes, with AGM being more commonly available. AGM deep-cycle marine batteries are offered by a number of suppliers. They typically are favored for their low maintenance and spill-proof quality, although generally considered a less cost effective solution relative to traditional flooded cells. In telecommunications applications, VRLA batteries that comply with criteria in Telcordia Technologies requirements document GR-4228, Valve-Regulated Lead–Acid (VRLA) Battery String Certification Levels Based on Requirements for Safety and Performance, are recommended for deployment in the Outside Plant (OSP) at locations such as Controlled Environmental Vaults (CEVs), Electronic Equipment Enclosures (EEEs), and huts, and in uncontrolled structures such as cabinets. Relative to VRLA in telecommunications, the use of VRLA Ohmic Measurement Type Equipment (OMTE) and OMTE-like measurement equipment is a fairly new process to evaluate telecommunications battery plants. The proper use of ohmic test equipment allows battery testing without the need to remove batteries from service to perform costly and time-consuming discharge tests. Comparison with flooded lead–acid cells VRLA gel and AGM batteries offer several advantages compared with VRLA flooded lead–acid and conventional lead–acid batteries. The battery can be mounted in any position, since the valves only operate on over-pressure faults. Since the battery system is designed to be recombinant and eliminate the emission of gases on overcharge, room ventilation requirements are reduced, and no acid fume is emitted during normal operation. Flooded cell gas emissions are of little consequence in all but the smallest confined areas, and pose very little threat to a domestic user, so a wet cell battery designed for longevity gives lower costs per kWh. In a gel battery, the volume of free electrolyte that could be released on damage to the case or venting is very small. There is no need (or ability) to check the level of electrolyte or to top up water lost due to electrolysis, thus reducing inspection and maintenance requirements. Wet-cell batteries can be maintained by a self-watering system or by topping up every three months. The requirement to add distilled water is normally caused by overcharging. A well-regulated system should not require top-up more often than every three months. An underlying disadvantage with all lead–acid batteries is the requirement for a relatively long recharge cycle time arising from an inherent three-stage charging process: bulk charge, absorption charge,