using large numbers of thyristors in series. Additional passive components such as grading capacitors and resistors need to be connected in parallel with each thyristor in order to ensure that the voltage across the valve is evenly shared between the thyristors. The thyristor plus its grading circuits and other auxiliary equipment is known as a thyristor level. Each thyristor valve will typically contain tens or hundreds of thyristor levels, each operating at a different (high) potential with respect to earth. The command information to turn on the thyristors therefore cannot simply be sent using a wire connection – it needs to be isolated. The isolation method can be magnetic but is usually optical. Two optical methods are used: indirect and direct optical triggering. In the indirect optical triggering method, low-voltage control electronics send light pulses along optical fibres to the high-side control electronics, which derives its power from the voltage across each thyristor. The alternative direct optical triggering method dispenses with most of the high-side electronics, instead using light pulses from the control electronics to switch light-triggered thyristors (LTTs), although a small monitoring electronics unit may still be required for protection of the valve. In a line-commutated converter, the DC current (usually) cannot change direction; it flows through a large inductance and can be considered almost constant. On the AC side, the converter behaves approximately as a current source, injecting both grid-frequency and harmonic currents into the AC network. For this reason, a line commutated converter for HVDC is also considered as a current-source inverter. Voltage-sourced converters Because thyristors can only be turned on (not off) by control action, the control system has only one degree of freedom – when to turn on the thyristor. This is an important limitation in some circumstances. With some other types of semiconductor device such as the insulated-gate bipolar transistor (IGBT), both turn-on and turn-off can be controlled, giving a second degree of freedom. As a result, they can be used to make self-commutated converters. In such converters, the electric polarity of DC voltage is usually fixed and the DC voltage, being smoothed by a large capacitance, can be considered constant. For this reason, an HVDC converter using IGBTs is usually referred to as a voltage sourced converter. The additional controllability gives many advantages, notably the ability to switch the IGBTs on and off many times per cycle in order to improve the harmonic