in Section 5 of AS/NZS 3000. For an LV customer, it is a TN-C system from the transformer in the street to the premises, (the neutral is earthed multiple times along this segment), and a TN-S system inside the installation, from the Main Switchboard downwards. Looked at as a whole, it is a TN-C-S system. In Denmark the high voltage regulation (Stærkstrømsbekendtgørelsen) and Malaysia the Electricity Ordinance 1994 states that all consumers must use TT earthing, though in rare cases TN-C-S may be allowed (used in the same manner as in the United States). Rules are different when it comes to larger companies. In India as per Central Electricity Authority Regulations, CEAR, 2010, rule 41, there is provision of earthing, neutral wire of a 3-phase, 4-wire system and the additional third wire of a 2-phase, 3-wire system. Earthing is to be done with two separate connections. The grounding system must also have a minimum of two or more earth pits (electrodes) to better ensure proper grounding. According to rule 42, installation with connected load above 5 kW exceeding 250 V shall have a suitable Earth leakage protective device to isolate the load in case of earth fault or leakage. Application examples In the areas of UK where underground power cabling is prevalent, the TN-S system is common. In India LT supply is generally through TN-S system. Neutral is double grounded at each distribution transformer. Neutral and earth conductors run separately on overhead distribution lines. Separate conductors for overhead lines and armoring of cables are used for earth connection. Additional earth electrodes/pits are installed at each user end to provide redundant path to earth. Most modern homes in Europe have a TN-C-S earthing system. The combined neutral and earth occurs between the nearest transformer substation and the service cut out (the fuse before the meter). After this, separate earth and neutral cores are used in all the internal wiring. Older urban and suburban homes in the UK tend to have TN-S supplies, with the earth connection delivered through the lead sheath of an underground lead-and-paper cable. The IT system with 230V between the phases is quite extensively used in Norway. It is estimated that 70% of all households are connected to the grid via the IT system. Newer residential areas are however mostly built with TN-C-S, in a large degree driven by the fact that three-phase products for the consumer market