- such as electric vehicle charging stations - are developed for the European market where TN systems with 400V between the phases dominate. Some older homes, especially those built before the invention of residual-current circuit breakers and wired home area networks, use an in-house TN-C arrangement. This is no longer recommended practice. Laboratory rooms, medical facilities, construction sites, repair workshops, mobile electrical installations, and other environments that are supplied via engine-generators where there is an increased risk of insulation faults, often use an IT earthing arrangement supplied from isolation transformers. To mitigate the two-fault issues with IT systems, the isolation transformers should supply only a small number of loads each and should be protected with an insulation monitoring device (generally used only by medical, railway or military IT systems, because of cost). In remote areas, where the cost of an additional PE conductor outweighs the cost of a local earth connection, TT networks are commonly used in some countries, especially in older properties or in rural areas, where safety might otherwise be threatened by the fracture of an overhead PE conductor by, say, a fallen tree branch. TT supplies to individual properties are also seen in mostly TN-C-S systems where an individual property is considered unsuitable for TN-C-S supply. In Australia, New Zealand and Israel the TN-C-S system is in use; however, the wiring rules state that, in addition, each customer must provide a separate connection to earth, via a dedicated Earth electrode. (Any metallic water pipes entering the consumer's premises must also be "bonded" to the Earthing point at the distribution Switchboard/Panel.) In Australia and New Zealand the connection between the protective earth bar and the neutral bar at the main Switchboard/Panel is called the multiple earthed neutral Link or MEN Link. This MEN link is removable for installation testing purposes, but is connected during normal service by either a locking system (locknuts for instance) or two or more screws. In the MEN system, the integrity of the neutral is paramount. In Australia, new installations must also bond the foundation concrete re-enforcing under wet areas to the protective earth conductor (AS3000), typically increasing the size of the earthing (i.e. reducing resistance), and providing an equipotential plane in areas such as bathrooms. In older installations, it is not uncommon to find only the water pipe bond, and it is allowed to remain as such, but the additional earth electrode must