substation and the entry point into the building, and earth and neutral are separated in the service head. In the UK, this system is also known as protective multiple earthing (PME), because of the practice of connecting the combined neutral-and-earth conductor via the shortest practicable route to local earth rods at the source and at intervals along the distribution networks to each premises, to provide both system earthing and equipment earthing at each of these locations. Similar systems in Australia and New Zealand are designated as multiple earthed neutral (MEN) and, in North America, as multi-grounded neutral (MGN). It is possible to have both TN-S and TN-C-S supplies taken from the same transformer. For example, the sheaths on some underground cables corrode and stop providing good earth connections, and so homes where high resistance "bad earths" are found may be converted to TN-C-S. This is only possible on a network when the neutral is suitably robust against failure, and conversion is not always possible. The PEN must be suitably reinforced against failure, as an open circuit PEN can impress full phase voltage on any exposed metal connected to the system earth downstream of the break. The alternative is to provide a local earth and convert to TT. The main attraction of a TN network is the low impedance earth path allows easy automatic disconnection (ADS) on a high current circuit in the case of a line-to-PE short circuit as the same breaker or fuse will operate for either L-N or L-PE faults, and an RCD is not needed to detect earth faults. TT network In a TT (Latin: terra-terra) earthing system, the protective earth connection for the consumer is provided by a local earth electrode, (sometimes referred to as the Terra-Firma connection) and there is another independently installed at the generator. There is no 'earth wire' between the two. The fault loop impedance is higher, and unless the electrode impedance is very low indeed, a TT installation should always have an RCD (GFCI) as its first isolator. The big advantage of the TT earthing system is the reduced conducted interference from other users' connected equipment. TT has always been preferable for special applications like telecommunication sites that benefit from the interference-free earthing. Also, TT networks do not pose any serious risks in the case of a broken neutral. In addition, in locations where power is distributed overhead, earth conductors are