resistance earth system is used for mining in India as per Central Electricity Authority Regulations. Instead of a solid connection of neutral to earth, a neutral grounding resistor (NGR) is used to limit the current to ground to less than 750 mA. Due to the fault current restriction it is safer for gassy mines. Since the earth leakage is restricted, leakage protection devices can be set to less than 750 mA . By comparison, in a solidly earthed system, earth fault current can be as much as the available short-circuit current. The neutral earthing resistor is monitored to detect an interrupted ground connection and to shut off power if a fault is detected. Earth leakage protection To avoid accidental shock, current sensing circuits are used at the source to isolate the power when leakage current exceeds a certain limit. Residual-current devices (RCDs, RCCBs or GFCIs) are used for this purpose. Previously, an earth leakage circuit breaker is used. In industrial applications, earth leakage relays are used with separate core balanced current transformers. This protection works in the range of milli-Amps and can be set from 30 mA to 3000 mA. Earth connectivity check A separate pilot wire is run from distribution/ equipment supply system in addition to earth wire, to supervise the continuity of the wire. This is used in the trailing cables of mining machinery. If the earth wire is broken, the pilot wire allows a sensing device at the source end to interrupt power to the machine. This type of circuit is a must for portable heavy electric equipment (like LHD (Load, Haul, Dump machine)) being used in underground mines. Properties Cost TN networks save the cost of a low-impedance earth connection at the site of each consumer. Such a connection (a buried metal structure) is required to provide protective earth in IT and TT systems. TN-C networks save the cost of an additional conductor needed for separate N and PE connections. However, to mitigate the risk of broken neutrals, special cable types and many connections to earth are needed. TT networks require proper RCD (Ground fault interrupter) protection. Safety In TN, an insulation fault is very likely to lead to a high short-circuit current that will trigger an overcurrent circuit-breaker or fuse and disconnect the L conductors. With TT systems, the earth fault loop impedance can be too high to do this, or too high to do