fluoride coolant without fuel provides a flotation layer passive safety component in which lower density graphite that breaks off control rods or an immersion matrix during mechanical failure does not induce criticality. Gravity driven drainage of reactor liquids provides a passive safety component. Low power swimming pool reactors such as the SLOWPOKE and TRIGA have been licensed for unattended operation in research environments because as the temperature of the low-enriched (19.75% U-235) uranium alloy hydride fuel rises, the molecular bound hydrogen in the fuel cause the heat to be transferred to the fission neutrons as they are ejected. This Doppler shifting or spectrum hardening dissipates heat from the fuel more rapidly throughout the pool the higher the fuel temperature increases ensuring rapid cooling of fuel whilst maintaining a much lower water temperature than the fuel. Prompt, self-dispersing, high efficiency hydrogen-neutron heat transfer rather than inefficient radionuclide-water heat transfer ensures the fuel cannot melt through accident alone. In uranium-zirconium alloy hydride variants, the fuel itself is also chemically corrosion resistant ensuring a sustainable safety performance of the fuel molecules throughout their lifetime. A large expanse of water and the concrete surround provided by the pool for high energy neutrons to penetrate ensures the process has a high degree of intrinsic safety. The core is visible through the pool and verification measurements can be made directly on the core fuel elements facilitating total surveillance and providing nuclear non-proliferation safety. Both the fuel molecules themselves and the open expanse of the pool are passive safety components. Quality implementations of these designs are arguably the safest nuclear reactors. Examples of reactors using passive safety features Three Mile Island Unit 2 was unable to contain about 480 PBq of radioactive noble gases from release into the environment and around 120 kL of radioactive contaminated cooling water from release beyond the containment into a neighbouring building. The pilot-operated relief valve at TMI-2 was designed to shut automatically after relieving excessive pressure inside the reactor into a quench tank. However the valve mechanically failed causing the PORV quench tank to fill, and the relief diaphragm to eventually rupture into the containment building. The containment building sump pumps automatically pumped the contaminated water outside the containment building. Both a working PORV with quench tank and separately the containment building with sump provided two layers of passive safety. An unreliable PORV negated its designed passive safety. The plant design