power plant, after the Leningrad Nuclear Power Plant and the Kursk Nuclear Power Plant, and the first plant on Ukrainian soil. The completion of the first reactor in 1977 was followed by reactor No. 2 in 1978, No. 3 in 1981, and No. 4 in 1983. Two more blocks, numbered five and six, of more or less the same reactor design, were planned at a site roughly a kilometer from the contiguous buildings of the four older blocks. This is similar to the layout of units 5 and 6 at Kursk and shows the similarity in design between the RBMK sites. Reactor No. 5 was around 70% complete at the time of Reactor 4's explosion and was scheduled to come online approximately seven months later, on November 7, 1986. In the aftermath of the disaster, construction on No. 5 and 6 was suspended, and eventually cancelled in April 1989, days before the third anniversary of the 1986 explosion. At one point six other reactors were planned on the other side of the river, bringing the total to twelve. Reactors No. 3 and 4 were second-generation units, whereas No. 1 and 2 were first-generation units, like those in operation at the Kursk power plant. Second-generation RBMK designs were fitted with a more secure containment structure visible in photos of the facility. Design Electrical systems The power plant is connected to the 330 kV and 750 kV electrical grid. The block has two electrical generators connected to the 750 kV grid by a single generator transformer. The generators are connected to their common transformer by two switches in series. Between them, the unit transformers are connected to supply power to the power plant's own systems; each generator can therefore be connected to the unit transformer to power the plant, or to the unit transformer and the generator transformer to also feed power to the grid. The 330 kV line was normally not used, and served as an external power supply, connected to a station's transformer – meaning to the power plant's electrical systems. The plant was powered by its own generators, or at any event got power from the 750 kV national grid through the main grid backup feed in transformer, or from the 330 kV level feed in grid transformer 2, or from the other power plant blocks via two reserve busbars. In case of total external power loss, the essential