systems (valves, feedback loops, external instrumentation, control circuits, etc.) which require external power and human operation to function. The International Atomic Energy Agency (IAEA) classifies the degree of "passive safety" of components from category A to D depending on what the system does not make use of: no moving working fluid no moving mechanical part no signal inputs of 'intelligence' no external power input or forces In category A (1+2+3+4) is the fuel cladding, the protective and nonreactive outer layer of the fuel pellet, which uses none of the above features: It is always closed and keeps the fuel and the fission products inside and is not open before arriving at the reprocessing plant. In category B (2+3+4) is the surge line, which connects the hot leg with the pressurizer and helps to control the pressure in the primary loop of a PWR and uses a moving working fluid when fulfilling its mission. In category C (3+4) is the accumulator, which does not need signal input of 'intelligence' or external power. Once the pressure in the primary circuit drops below the set point of the spring-loaded accumulator valves, the valves open and water is injected into the primary circuit by compressed nitrogen. In category D (4 only) is the SCRAM which utilizes moving working fluids, moving mechanical parts and signal inputs of 'intelligence' but not external power or forces: the control rods drop driven by gravity once they have been released from their magnetic clamp. But nuclear safety engineering is never that simple: Once released the rod may not fulfil its mission: It may get stuck due to earthquake conditions or due to deformed core structures. This shows that though it is a passively safe system and has been properly actuated, it may not fulfil its mission. Nuclear engineers have taken this into consideration: Typically only a part of the rods dropped are necessary to shut down the reactor. Samples of safety systems with passive safety components can be found in almost all nuclear power stations: the containment, hydro-accumulators in PWRs or pressure suppression systems in BWRs. In most texts on 'passively safe' components in next generation reactors, the key issue is that no pumps are needed to fulfil the mission of a safety system and that all active components (generally I&C and valves) of the systems work with the electric power from batteries. IAEA explicitly uses the following caveat: