monopolar line, it produces much higher magnetic fields than bipolar cables with the same ratings. Operation Because this overhead line can generate radio interference, there is a highly effective active filter system installed at the Kruseberg converter station. In the Lübeck-Herrenwyk converter station, there is no requirement for such a system, because there is no overhead powerline section on the German side. The cable cannot be operated at the maximum transmission rating of 600 megawatts, because the 380 kV line which begins at the converter station of Lübeck-Herrenwyk ends at the Lübeck-Siems substation. This is the only 380 kV powerline in Germany which has no direct connection to the Central European 380 kV grid, which caused the Baltic Cable to have a 372 megawatt (MW) capacity instead of 600 MW. This bottleneck was solved in 2004 when an additional 220 kV line was built. However power flows on 220 kV and 110 kV lines face increased losses of the transmission. In the area of the converter station there is also a 110 kV/220 kV sub-station, fed by two 110 kV circuits from the Lübeck-Siems sub-station. There is no transformer for coupling the 380 kV- and the 110 kV-grid in the area of the Lübeck-Herrenwyk converter station. In 2016, the owner Statkraft started a court case against Swedish authorities in disagreements over profits from electricity trade in the cable. In the night from April 16, 2017 to April 17, 2017 on the electrode cable on Priwall peninsula a fault occurred, which resulted in the generation of hydrogen at the fault location as it acted as cathode. The hydrogen got ignited by the generated heat and a 3 metres high flame shot off the ground. As there is no device monitoring the state of the electrode cable, no alert was made to the operators. Fire brigades were first not able to extinguish the fire, but the flame went out when the current was switched off. Expansion schemes Of the two originally planned 380 kV lines to Lübeck (from Krümmel Nuclear Power Plant to Lübeck-Siems and from Schwerin substation to Lübeck-Herrenwyk), the 380 kV line between Krümmel and Lübeck-Siems was canceled according to speakers from E.ON AG. There is still the option to build a 380 kV line from Lübeck to another 380 kV substation in Schleswig-Holstein, Hamburg or Lower Saxony. The construction of the 380 kV link between Lübeck-Herrenwyk and Schwerin is