IDs and wall thicknesses as Nominal Pipe Size, but labels them with a metric Diameter Nominal (DN) instead of the imperial NPS. For NPS larger than 14, the DN is equal to the NPS multiplied by 25. (Not 25.4) This is documented by EN 10255 (formerly DIN 2448 and BS 1387) and ISO 65:1981, and it is often called DIN or ISO pipe. Japan has its own set of standard pipe sizes, often called JIS pipe. The Iron pipe size (IPS) is an older system still used by some manufacturers and legacy drawings and equipment. The IPS number is the same as the NPS number, but the schedules were limited to Standard Wall (STD), Extra Strong (XS), and Double Extra Strong (XXS). STD is identical to SCH 40 for NPS 1/8 to NPS 10, inclusive, and indicates .375" wall thickness for NPS 12 and larger. XS is identical to SCH 80 for NPS 1/8 to NPS 8, inclusive, and indicates .500" wall thickness for NPS 8 and larger. Different definitions exist for XXS, however it is never the same as SCH 160. XXS is in fact thicker than SCH 160 for NPS 1/8" to 6" inclusive, whereas SCH 160 is thicker than XXS for NPS 8" and larger. Another old system is the Ductile Iron Pipe Size (DIPS), which generally has larger ODs than IPS. Copper plumbing tube for residential plumbing follows an entirely different size system in America, often called Copper Tube Size (CTS); see domestic water system. Its nominal size is neither the inside nor outside diameter. Plastic tubing, such as PVC and CPVC, for plumbing applications also has different sizing standards. Agricultural applications use PIP sizes, which stands for Plastic Irrigation Pipe. PIP comes in pressure ratings of , , , , and and is generally available in diameters of . Standards The manufacture and installation of pressure piping is tightly regulated by the ASME "B31" code series such as B31.1 or B31.3 which have their basis in the ASME Boiler and Pressure Vessel Code (BPVC). This code has the force of law in Canada and the US. Europe and the rest of the world has an equivalent system of codes. Pressure piping is generally pipe that must carry pressures greater than 10 to 25 atmospheres, although definitions vary. To ensure safe operation of the system, the manufacture, storage, welding, testing, etc. of pressure piping must meet