inch and DN 50 are the same pipe, but the actual OD is . The only way to obtain the actual OD is to look it up in a reference table. For pipe sizes of NPS 14 inch (DN 350) and greater the NPS size is the actual diameter in inches and the DN size is equal to NPS times 25 (not 25.4) rounded to a convenient multiple of 50. For example, NPS 14 has an OD of , and is equivalent to DN 350. Since the outside diameter is fixed for a given pipe size, the inside diameter will vary depending on the wall thickness of the pipe. For example, 2" Schedule 80 pipe has thicker walls and therefore a smaller inside diameter than 2" Schedule 40 pipe. Steel pipe has been produced for about 150 years. The pipe sizes that are in use today in PVC and galvanized were originally designed years ago for steel pipe. The number system, like Sch 40, 80, 160, were set long ago and seem a little odd. For example, Sch 20 pipe is even thinner than Sch 40, but same OD. And while these pipes are based on old steel pipe sizes, there is other pipe, like cpvc for heated water, that uses pipe sizes, inside and out, based on old copper pipe size standards instead of steel. Many different standards exist for pipe sizes, and their prevalence varies depending on industry and geographical area. The pipe size designation generally includes two numbers; one that indicates the outside (OD) or nominal diameter, and the other that indicates the wall thickness. In the early twentieth century, American pipe was sized by inside diameter. This practice was abandoned to improve compatibility with pipe fittings that must usually fit the OD of the pipe, but it has had a lasting impact on modern standards around the world. In North America and the UK, pressure piping is usually specified by Nominal Pipe Size (NPS) and schedule (SCH). Pipe sizes are documented by a number of standards, including API 5L, ANSI/ASME B36.10M (Table 1) in the US, and BS 1600 and BS 1387 in the United Kingdom. Typically the pipe wall thickness is the controlled variable, and the Inside Diameter (I.D.) is allowed to vary. The pipe wall thickness has a variance of approximately 12.5 percent. In the rest of Europe pressure piping uses the same pipe