be achieved by evaporative cooling of a water-wetted, ventilated surface. By contrast, the dew point is the temperature to which the ambient air must be cooled to reach 100% relative humidity assuming there is no further evaporation into the air; it is the temperature where condensation (dew) and clouds would form. For a parcel of air that is less than saturated (i.e., air with less than 100 percent relative humidity), the wet-bulb temperature is lower than the dry-bulb temperature, but higher than the dew point temperature. The lower the relative humidity (the drier the air), the greater the gaps between each pair of these three temperatures. Conversely, when the relative humidity rises to 100%, the three figures coincide. For air at a known pressure and dry-bulb temperature, the thermodynamic wet-bulb temperature corresponds to unique values of the relative humidity and the dew point temperature. It therefore may be used for the practical determination of these values. The relationships between these values are illustrated in a psychrometric chart. Lower wet-bulb temperatures that correspond with drier air in summer can translate to energy savings in air-conditioned buildings due to: Reduced dehumidification load for ventilation air Increased efficiency of cooling towers increased efficiency of evaporative coolers Thermodynamic wet-bulb temperature The thermodynamic wet-bulb temperature is the temperature a volume of air would have if cooled adiabatically to saturation by evaporation of water into it, all latent heat being supplied by the volume of air. The temperature of an air sample that has passed over a large surface of liquid water in an insulated channel is the thermodynamic wet-bulb temperature—the air has become saturated by passing through a constant-pressure, ideal, adiabatic saturation chamber. Meteorologists and others may use the term "isobaric wet-bulb temperature" to refer to the "thermodynamic wet-bulb temperature". It is also called the "adiabatic saturation temperature", though meteorologists also use "adiabatic saturation temperature" to mean "temperature at the saturation level", i.e. the temperature the parcel would achieve if it expanded adiabatically until saturated. The thermodynamic wet-bulb temperature is a thermodynamic property of a mixture of air and water vapor. The value indicated by a simple wet-bulb thermometer often provides an adequate approximation of the thermodynamic wet-bulb temperature. For an accurate wet-bulb thermometer, "the wet-bulb temperature and the adiabatic saturation temperature are approximately equal for air-water vapor mixtures at atmospheric temperature and pressure. This is not necessarily true at temperatures and pressures that deviate