3 event ("serious incident") occurred on 10 April 2003 at the Unit 2 reactor. The incident occurred in the fuel rod cleaning system located under of water in a cleaning tank next to the spent fuel cooling pond, located adjacent to the reactor in the reactor hall. The reactor had been shut down for its annual refueling and maintenance period on 28 March and its fuel elements removed. The cleaning system had been installed to remove dirt and corrosion from fuel elements and control rods during shutdown, as there had previously been problems with magnetite corrosion products from the steam generators being deposited on the fuel elements which affected the flow of coolant. The sixth set of thirty partially spent elements were in the tank having been cleaned, the cleaning having finished at 16:00. At 21:50, radiation alarms mounted on the cleaning system detected a sudden increase in the amount of krypton-85. The suspicion was that one of the fuel rod assemblies was leaking. At 22:30, the reactor hall was evacuated because of elevated radiation levels both there and in the ventilation stack. At 02:15 the following morning, the hydraulic lock of the cleaning vessel lid was released, and immediately the dose rate increased significantly (6-12 millisieverts/hour) around the spent fuel pond and the pool containing the cleaning machine, and the water level dropped for a short time, by about . Water samples from the pond showed contamination due to damaged fuel rods. The lid on the cleaning machine was winched up at 04:20, but one of the three lifting cables attached to it broke; and it was not finally removed until 16 April. The incident was initially given an INES rating of 2 ("incident"). However a video examination of the damaged fuel elements following the successful removal of the lid caused the rating to be raised to 3 ("serious incident"). This revealed that cladding on the majority of the 30 fuel elements had been broken, with radioactive spent uranium fuel pellets spilling from the elements into the bottom of the cleaning tank. Apart from the release of radioactive material, a concern was that the accumulation of a compact mass of fuel pellets could lead to a criticality accident, as the pellets were in a tank of neutron moderating water. Water containing neutron absorbing boric acid was added into the tank to raise its concentration to 16 g/kg to prevent