the barrier. On a fuel storage vent, flame arresters also serve a secondary purpose of allowing air pressure to equalize inside the tank when fuel is added or removed, while also preventing insects from flying or crawling into the vent piping and fouling the fuel in the tanks and pipes. Safety Flame arresters should be used only in the gas group and conditions they have been designed and tested for. Since the depth on an arrester is specified for certain conditions, changes in the temperature, pressure, or composition of the gases entering the arrester can cause the flame spatial velocity to increase, making the design of the arrester insufficient to stop the flame front ("propagation"). The deflagration may continue downstream of the arrester. Flame arresters should be periodically inspected to make sure they are free of dirt, insects using it as a nest, or corrosion. The U.S. Chemical Safety and Hazard Investigation Board concluded that an uninspected and badly corroded flame arrester failed to prevent a 2006 explosion at a wastewater treatment plant in Daytona Beach, Florida. References See also Flashback arrestor Detonation arrester Spark arrestor Industrial safety devices Fire prevention Chemical safety Safety engineering Occupational safety and health