methods of water purification became widespread. Deionization Deionized water (DI water, DIW or de-ionized water), often synonymous with demineralized water / DM water, is water that has had almost all of its mineral ions removed, such as cations like sodium, calcium, iron, and copper, and anions such as chloride and sulfate. Deionization is a chemical process that uses specially manufactured ion-exchange resins, which exchange hydrogen and hydroxide ions for dissolved minerals, and then recombine to form water. Because most non-particulate water impurities are dissolved salts, deionization produces highly pure water that is generally similar to distilled water, with the advantage that the process is quicker and does not build up scale. However, deionization does not significantly remove uncharged organic molecules, viruses, or bacteria, except by incidental trapping in the resin. Specially made strong base anion resins can remove Gram-negative bacteria. Deionization can be done continuously and inexpensively using electrodeionization. Three types of deionization exist: co-current, counter-current, and mixed bed. Co-current deionization Co-current deionization refers to the original downflow process where both input water and regeneration chemicals enter at the top of an ion-exchange column and exit at the bottom. Co-current operating costs are comparatively higher than counter-current deionization because of the additional usage of regenerants. Because regenerant chemicals are dilute when they encounter the bottom or finishing resins in an ion-exchange column, the product quality is lower than a similarly sized counter-flow column. The process is still used, and can be maximized with the fine-tuning of the flow of regenerants within the ion exchange column. Counter-current deionization Counter-current deionization comes in two forms, each requiring engineered internals: Upflow columns where input water enters from the bottom and regenerants enter from the top of the ion exchange column. Upflow regeneration where water enters from the top and regenerants enter from the bottom. In both cases, separate distribution headers (input water, input regenerant, exit water, and exit regenerant) must be tuned to: the input water quality and flow, the time of operation between regenerations, and the desired product water analysis. Counter-current deionization is the more attractive method of ion exchange. Chemicals (regenerants) flow in the opposite direction to the service flow. Less time for regeneration is required when compared to cocurrent columns. The quality of the finished product can be as low as .5 parts per million. The main advantage of counter-current deionization is the low operating cost, due to the low