by a number of professional organizations, including the American Chemical Society (ACS), ASTM International, the U.S. National Committee for Clinical Laboratory Standards (NCCLS) which is now CLSI, and the U.S. Pharmacopeia (USP). The ASTM, NCCLS, and ISO 3696 or the International Organization for Standardization classify purified water into Grade 1–3 or Types I–IV depending on the level of purity. These organizations have similar, although not identical, parameters for highly purified water. Note that the European Pharmacopeia uses Highly Purified Water (HPW) as a definition for water meeting the quality of Water For Injection, without however having undergone distillation. In the laboratory context, highly purified water is used to denominate various qualities of water having been "highly" purified. Regardless of which organization's water quality norm is used, even Type I water may require further purification depending on the specific laboratory application. For example, water that is being used for molecular-biology experiments needs to be DNase or RNase-free, which requires special additional treatment or functional testing. Water for microbiology experiments needs to be completely sterile, which is usually accomplished by autoclaving. Water used to analyze trace metals may require the elimination of trace metals to a standard beyond that of the Type I water norm. * Requires use of 0.2 μm membrane filter **Prepared by distillation ***Requires the use of 0.45 μm membrane filter Criticism A member of the ASTM D19 (Water) Committee, Erich L. Gibbs, criticized ASTM Standard D1193, by saying "Type I water could be almost anything – water that meets some or all of the limits, part or all of the time, at the same or different points in the production process." Electrical conductivity Completely de-gassed ultrapure water has a conductivity of 1.2 × 10−4 S/m, whereas on equilibration to the atmosphere it is 7.5 × 10−5 S/m due to dissolved CO2 in it. The highest grades of ultrapure water should not be stored in glass or plastic containers because these container materials leach (release) contaminants at very low concentrations. Storage vessels made of silica are used for less-demanding applications and vessels of ultrapure tin are used for the highest-purity applications. It is worth noting that, although electrical conductivity only indicates the presence of ions, the majority of common contaminants found naturally in water ionize to some degree. This ionization is a good measure of the efficacy of a filtration system, and more expensive systems incorporate conductivity-based alarms to