warning of the high voltage. At other times, the entire access point to the transmission corridor is marked with a sign. Sign warning of the high voltage may also state the name of the company who built the structures, and acquired and designated lands where the transmission structures stand and line segments or right of way. Tower functions Tower structures can be classified by the way in which they support the line conductors. Suspension structures support the conductor vertically using suspension insulators. Strain structures resist net tension in the conductors and the conductors attach to the structure through strain insulators. Dead-end structures support the full weight of the conductor and also all the tension in it, and also use strain insulators. Structures are classified as tangent suspension, angle suspension, tangent strain, angle strain, tangent dead-end and angle dead-end. Where the conductors are in a straight line, a tangent tower is used. Angle towers are used where a line must change direction. Cross arms and conductor arrangement Generally three conductors are required per AC 3-phase circuit, although single-phase and DC circuits are also carried on towers. Conductors may be arranged in one plane, or by use of several cross-arms may be arranged in a roughly symmetrical, triangulated pattern to balance the impedances of all three phases. If more than one circuit is required to be carried and the width of the line right-of-way does not permit multiple towers to be used, two or three circuits can be carried on the same tower using several levels of cross-arms. Often multiple circuits are the same voltage, but mixed voltages can be found on some structures. Other features Insulators Insulators electrically isolate the live side of the transmission cables from the tower structure and earth. They are either glass or porcelain discs or composite insulators using silicone rubber or EPDM rubber material. They are assembled in strings or long rods whose lengths are dependent on the line voltage and environmental conditions. By using disks the shortest surface electrical path between the ends is maximised which reduces the chance of a leakage in moist conditions. Stockbridge dampers Stockbridge dampers are added to the transmission lines a meter or two from the tower. They consist of a short length of cable clamped in place parallel to the line itself and weighted at each end. The size and dimensions are carefully designed to damp any buildup of