plant with a cooling tower amounts to about 71,600 cubic metres an hour (315,000 US gallons per minute) and the circulating water requires a supply water make-up rate of perhaps 5 percent (i.e., 3,600 cubic metres an hour, equivalent to one cubic metre every second). If that same plant had no cooling tower and used once-through cooling water, it would require about 100,000 cubic metres an hour A large cooling water intake typically kills millions of fish and larvae annually, as the organisms are impinged on the intake screens. A large amount of water would have to be continuously returned to the ocean, lake or river from which it was obtained and continuously re-supplied to the plant. Furthermore, discharging large amounts of hot water may raise the temperature of the receiving river or lake to an unacceptable level for the local ecosystem. Elevated water temperatures can kill fish and other aquatic organisms (see thermal pollution), or can also cause an increase in undesirable organisms such as invasive species of zebra mussels or algae. A cooling tower serves to dissipate the heat into the atmosphere instead and wind and air diffusion spreads the heat over a much larger area than hot water can distribute heat in a body of water. Evaporative cooling water cannot be used for subsequent purposes (other than rain somewhere), whereas surface-only cooling water can be re-used. Some coal-fired and nuclear power plants located in coastal areas do make use of once-through ocean water. But even there, the offshore discharge water outlet requires very careful design to avoid environmental problems. Petroleum refineries also have very large cooling tower systems. A typical large refinery processing 40,000 metric tonnes of crude oil per day ( per day) circulates about 80,000 cubic metres of water per hour through its cooling tower system. The world's tallest cooling towers are the two tall cooling towers of Kalisindh Thermal Power Station in Jhalawar, Rajasthan, India. Classification by build Package type These types of cooling towers are factory preassembled, and can be simply transported on trucks, as they are compact machines. The capacity of package type towers is limited and, for that reason, they are usually preferred by facilities with low heat rejection requirements such as food processing plants, textile plants, some chemical processing plants, or buildings like hospitals, hotels, malls, automotive factories etc. Due to their frequent use in or near residential areas, sound