GE UR family
Prior to UR firmware Version 8.1x, UR supported various encryption and MAC algorithms for SSH communication, some of which are weak.CVE-2016-2183 and CVE-2013-2566 have been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:N/A:N). Prior to firmware Version 7.4x, UR supported only SSHv2. Starting from firmware Version 7.4x, UR added support to SSHv1. SSHv1 has known vulnerabilities (SSH protocol session key retrieval and insertion attack).CVE-1999-1085 has been assigned to this vulnerability. A CVSS v3 base score of 5.3 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:L/A:N). Web server interface is supported on UR over HTTP protocol. It allows sensitive information exposure without authentication.CVE-2021-27422 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:N/A:N). UR supports web interface with read-only access. The device fails to properly validate user input, making it possible to perform cross-site scripting attacks, which may be used to send a malicious script. Also, UR Firmware web server does not perform HTML encoding of user-supplied strings.CVE-2021-27418 has been assigned to this vulnerability. A CVSS v3 base score of 5.3 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:L/A:N). UR Firmware web server task does not properly handle receipt of unsupported HTTP verbs, resulting in the web server becoming temporarily unresponsive after receiving a series of unsupported HTTP requests. When unresponsive, the web server is inaccessible. By itself, this is not particularly significant as the relay remains effective in all other functionality and communication channels.CVE-2021-27420 has been assigned to this vulnerability. A CVSS v3 base score of 5.3 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:N/A:L). UR IED supports upgrading firmware using UR Setup configuration tool - Enervista UR Setup. This UR Setup tool validates the authenticity and integrity of firmware file before uploading the UR IED. An illegitimate user could upgrade firmware without appropriate privileges. The weakness is assessed, and mitigation is implemented in firmware Version 8.10.CVE-2021-27428 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:N/A:N). UR IED with Basic security variant does not allow the disabling of the Factory Mode, which is used for servicing the IED by a Factory user.CVE-2021-27426 has been assigned to this vulnerability. A CVSS v3 base score of 9.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:H/A:H). UR shares MODBUS memory map as part of the communications guide. GE was made aware a Last-key pressed MODBUS register can be used to gain unauthorized information.CVE-2021-27424 has been assigned to this vulnerability. A CVSS v3 base score of 5.3 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:L/I:N/A:N). UR bootloader binary Version 7.00, 7.01 and 7.02 included unused hardcoded credentials. Additionally, a user with physical access to the UR IED can interrupt the boot sequence by rebooting the UR.CVE-2021-27430 has been assigned to this vulnerability. A CVSS v3 base score of 8.4 has been calculated; the CVSS vector string is (AV:L/AC:L/PR:N/UI:N/S:U/C:H/I:H/A:H).