Hitachi Energy MicroSCADA Pro X SYS600
A vulnerability exists during the start of SYS600, where an input validation flaw causes a buffer-overflow while reading a specific configuration file. Subsequently, SYS600 could fail to start. Administrator access is required for accessing the configuration file.CVE-2022-1778 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:N/A:H). A vulnerability exists in the ICCP stack due to a validation flaw in the process establishing the ICCP communication. The validation flaw could cause a denial-of-service condition when ICCP of SYS600 is requested to forward any data item updates with timestamps too distant in the future to any remote ICCP system. By default, ICCP is not configured and not enabled.CVE-2022-2277 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:N/A:H). A vulnerability exists in the Workplace X WebUI, in which an authenticated user could execute any MicroSCADA internal scripts irrespective of the authenticated user's role.CVE-2022-29490 has been assigned to this vulnerability. A CVSS v3 base score of 8.5 has been calculated; the CVSS vector string is (AV:N/AC:H/PR:L/UI:N/S:C/C:H/I:H/A:H). A vulnerability exists in the handling of a malformed IEC 104 TCP packet. Upon receiving a malformed IEC 104 TCP packet, the malformed packet is dropped, however the TCP connection is left open; this may cause a denial-of-service condition.CVE-2022-29492 has been assigned to this vulnerability. A CVSS v3 base score of 5.3 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:N/A:L). A vulnerability exists in the handling of a specially crafted IEC 61850 packet with a valid data item but with incorrect data type in the IEC 61850 OPC Server. The vulnerability may cause a denial-of-service condition on the IEC 61850 OPC Server component of the SYS600.CVE-2022-29922 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:N/A:H).