ABB GATE-E2
These devices do not allow authentication to be configured on administrative telnet or web interfaces, which could enable various effects vectors, including conducting device resets, reading or modifying registers, and changing configuration settings such as IP addresses.CVE-2018-18995 has been assigned to this vulnerability. A CVSS v3 base score of 9.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:H/A:H). Using the administrative web interface, an unauthenticated attacker can insert an HTML/Javascript payload into any of the device properties, which may allow an attacker to display/execute the payload in a visitor browser.CVE-2018-18997 has been assigned to this vulnerability. A CVSS v3 base score of 7.1 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:R/S:C/C:L/I:L/A:L).