Schneider Electric IGSS
A vulnerability in Schneider Electric Data Server TCP interface could allow the creation of a malicious report file in the IGSS project report directory, and this could lead to remote code execution when an unsuspecting user opens the malicious report.  CVE-2023-27980 has been assigned to this vulnerability. A CVSS v3 base score of 8.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:R/S:U/C:H/I:H/A:H). A vulnerability in Schneider Electric Data Server could cause manipulation of dashboard files in the IGSS project report directory when an attacker sends specific crafted messages to the Data Server TCP port. This could lead to remote code execution if an unsuspecting user opens the malicious dashboard file. CVE-2023-27982 has been assigned to this vulnerability. A CVSS v3 base score of 8.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:R/S:U/C:H/I:H/A:H). A vulnerability in Schneider Electric Dashboard module could cause an interpretation of malicious payload data if a malicious file is opened by an unsuspecting user. This could lead to remote code execution. CVE-2023-27978 has been assigned to this vulnerability. A CVSS v3 base score of 7.8 has been calculated; the CVSS vector string is (AV:L/AC:L/PR:N/UI:R/S:U/C:H/I:H/A:H). A vulnerability in Schneider Electric Custom Reports could cause remote code execution if an unsuspecting user opens a malicious report. CVE-2023-27981 has been assigned to this vulnerability. A CVSS v3 base score of 7.8 has been calculated; the CVSS vector string is (AV:L/AC:L/PR:N/UI:R/S:U/C:H/I:H/A:H). A vulnerability in Schneider Electric Custom Reports could result in macro execution if a malicious report file is opened by an unsuspecting user, potentially leading to remote code execution. CVE-2023-27984 has been assigned to this vulnerability. A CVSS v3 base score of 7.8 has been calculated; the CVSS vector string is (AV:L/AC:L/PR:N/UI:R/S:U/C:H/I:H/A:H). A vulnerability in Schneider Electric Data Server could grant an unauthorized user access to delete files in the IGSS project report directory if specific crafted messages are sent to the Data Server TCP port. CVE-2023-27977 has been assigned to this vulnerability. A CVSS v3 base score of 6.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:L/A:L). A vulnerability in Schneider Electric Data Server could allow an unauthorized user to rename files in the IGSS project report directory. This could lead to a denial-of-service condition if an attacker sends specific crafted messages to the Data Server TCP port. CVE-2023-27979 has been assigned to this vulnerability. A CVSS v3 base score of 6.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:L/A:L). A vulnerability in Schneider Electric Data Server TCP interface could allow deletion of reports from the IGSS project report directory. CVE-2023-27983 has been assigned to this vulnerability. A CVSS v3 base score of 6.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:L/A:L).