def F_LMTD_Fakheri(Thi, Tho, Tci, Tco, shells=1):
    r'''Calculates the log-mean temperature difference correction factor `Ft` 
    for a shell-and-tube heat exchanger with one or an even number of tube 
    passes, and a given number of shell passes, with the expression given in 
    [1]_ and also shown in [2]_.
    
    .. math::
        F_t=\frac{S\ln W}{\ln \frac{1+W-S+SW}{1+W+S-SW}}

        S = \frac{\sqrt{R^2+1}}{R-1}
        
        W = \left(\frac{1-PR}{1-P}\right)^{1/N}
        
        R = \frac{T_{in}-T_{out}}{t_{out}-t_{in}}
        
        P = \frac{t_{out}-t_{in}}{T_{in}-t_{in}}
        
    If R = 1 and logarithms cannot be evaluated:
        
    .. math::
        W' = \frac{N-NP}{N-NP+P}
        
        F_t = \frac{\sqrt{2}\frac{1-W'}{W'}}{\ln\frac{\frac{W'}{1-W'}+\frac{1}
        {\sqrt{2}}}{\frac{W'}{1-W'}-\frac{1}{\sqrt{2}}}}
        
    Parameters
    ----------
    Thi : float
        Inlet temperature of hot fluid, [K]
    Tho : float
        Outlet temperature of hot fluid, [K]
    Tci : float
        Inlet temperature of cold fluid, [K]
    Tco : float
        Outlet temperature of cold fluid, [K]        
    shells : int, optional
        Number of shell-side passes, [-]

    Returns
    -------
    Ft : float
        Log-mean temperature difference correction factor, [-]

    Notes
    -----
    This expression is symmetric - the same result is calculated if the cold
    side values are swapped with the hot side values. It also does not 
    depend on the units of the temperature given.

    Examples
    --------
    >>> F_LMTD_Fakheri(Tci=15, Tco=85, Thi=130, Tho=110, shells=1)
    0.9438358829645933

    References
    ----------
    .. [1] Fakheri, Ahmad. "A General Expression for the Determination of the 
       Log Mean Temperature Correction Factor for Shell and Tube Heat 
       Exchangers." Journal of Heat Transfer 125, no. 3 (May 20, 2003): 527-30.
       doi:10.1115/1.1571078.
    .. [2] Hall, Stephen. Rules of Thumb for Chemical Engineers, Fifth Edition.
       Oxford; Waltham, MA: Butterworth-Heinemann, 2012.
    '''
    R = (Thi - Tho)/(Tco - Tci)
    P = (Tco - Tci)/(Thi - Tci)
    if R == 1.0:
        W2 = (shells - shells*P)/(shells - shells*P + P)
        return (2**0.5*(1. - W2)/W2)/log(((W2/(1. - W2) + 2**-0.5)/(W2/(1. - W2) - 2**-0.5)))
    else:
        W = ((1. - P*R)/(1. - P))**(1./shells)
        S = (R*R + 1.)**0.5/(R - 1.)
        return S*log(W)/log((1. + W - S + S*W)/(1. + W + S - S*W))
r'''Calculates the log-mean temperature difference correction factor `Ft` 
    for a shell-and-tube heat exchanger with one or an even number of tube 
    passes, and a given number of shell passes, with the expression given in 
    [1]_ and also shown in [2]_.
    
    .. math::
        F_t=\frac{S\ln W}{\ln \frac{1+W-S+SW}{1+W+S-SW}}

        S = \frac{\sqrt{R^2+1}}{R-1}
        
        W = \left(\frac{1-PR}{1-P}\right)^{1/N}
        
        R = \frac{T_{in}-T_{out}}{t_{out}-t_{in}}
        
        P = \frac{t_{out}-t_{in}}{T_{in}-t_{in}}
        
    If R = 1 and logarithms cannot be evaluated:
        
    .. math::
        W' = \frac{N-NP}{N-NP+P}
        
        F_t = \frac{\sqrt{2}\frac{1-W'}{W'}}{\ln\frac{\frac{W'}{1-W'}+\frac{1}
        {\sqrt{2}}}{\frac{W'}{1-W'}-\frac{1}{\sqrt{2}}}}
        
    Parameters
    ----------
    Thi : float
        Inlet temperature of hot fluid, [K]
    Tho : float
        Outlet temperature of hot fluid, [K]
    Tci : float
        Inlet temperature of cold fluid, [K]
    Tco : float
        Outlet temperature of cold fluid, [K]        
    shells : int, optional
        Number of shell-side passes, [-]

    Returns
    -------
    Ft : float
        Log-mean temperature difference correction factor, [-]

    Notes
    -----
    This expression is symmetric - the same result is calculated if the cold
    side values are swapped with the hot side values. It also does not 
    depend on the units of the temperature given.

    Examples
    --------
    >>> F_LMTD_Fakheri(Tci=15, Tco=85, Thi=130, Tho=110, shells=1)
    0.9438358829645933

    References
    ----------
    .. [1] Fakheri, Ahmad. "A General Expression for the Determination of the 
       Log Mean Temperature Correction Factor for Shell and Tube Heat 
       Exchangers." Journal of Heat Transfer 125, no. 3 (May 20, 2003): 527-30.
       doi:10.1115/1.1571078.
    .. [2] Hall, Stephen. Rules of Thumb for Chemical Engineers, Fifth Edition.
       Oxford; Waltham, MA: Butterworth-Heinemann, 2012.