def Nu_plate_Muley_Manglik(Re, Pr, chevron_angle, plate_enlargement_factor):
    r'''Calculates Nusselt number for single-phase flow in a 
    Chevron-style plate heat exchanger according to [1]_, also shown in [2]_
    and [3]_. 
    
    .. math::
        Nu = [0.2668 - 0.006967(\beta) + 7.244\times 10^{-5}(\beta)^2]
        \times[20.7803 - 50.9372\phi + 41.1585\phi^2 - 10.1507\phi^3]
        \times Re^{[0.728 + 0.0543\sin[(2\pi\beta/90) + 3.7]]} Pr^{1/3}
        
    Parameters
    ----------
    Re : float
        Reynolds number with respect to the hydraulic diameter of the channels,
        [-]
    Pr : float
        Prandtl number calculated with bulk fluid properties, [-]
    chevron_angle : float
        Angle of the plate corrugations with respect to the vertical axis
        (the direction of flow if the plates were straight), between 0 and
        90. Many plate exchangers use two alternating patterns; use their
        average angle for that situation [degrees]
    plate_enlargement_factor : float
        The extra surface area multiplier as compared to a flat plate
        caused the corrugations, [-]

    Returns
    -------
    Nu : float
        Nusselt number with respect to `Dh`, [-]

    Notes
    -----
    The correlation as presented in [1]_ suffers from a typo, with a 
    coefficient of 10.51 instead of 10.15. Several more decimal places were
    published along with the corrected typo in [2]_. This has a *very large*
    difference if not implemented.
    
    The viscosity correction power is recommended to be the blanket
    Sieder and Tate (1936) value of 0.14.
    
    The correlation is recommended in the range of Reynolds numbers above
    1000, chevron angles between 30 and 60 degrees, and enlargement factors
    from 1 to 1.5. Due to its cubic nature it is not likely to give good 
    results if the chevron angle or enlargement factors are out of those
    ranges.

    Examples
    --------
    >>> Nu_plate_Muley_Manglik(Re=2000, Pr=.7, chevron_angle=45,
    ... plate_enlargement_factor=1.18)
    36.49087100602062

    References
    ----------
    .. [1] Muley, A., and R. M. Manglik. "Experimental Study of Turbulent Flow
       Heat Transfer and Pressure Drop in a Plate Heat Exchanger With Chevron 
       Plates." Journal of Heat Transfer 121, no. 1 (February 1, 1999): 110-17. 
       doi:10.1115/1.2825923.
    .. [2] Palm, Björn, and Joachim Claesson. "Plate Heat Exchangers: 
       Calculation Methods for Single- and Two-Phase Flow (Keynote)," January 
       1, 2005, 103-13. https://doi.org/10.1115/ICMM2005-75092.
    '''
    beta, phi = chevron_angle, plate_enlargement_factor
    t1 = (0.2668 - 0.006967*beta + 7.244E-5*beta**2)
    #t2 = (20.78 - 50.94*phi + 41.16*phi**2 - 10.51*phi**3)
    # It was the extra decimals which were needed
    t2 = (20.7803 - 50.9372*phi + 41.1585*phi**2 - 10.1507*phi**3)
    t3 = (0.728 + 0.0543*sin((2*pi*beta/90) + 3.7))
    return t1*t2*Re**t3*Pr**(1/3.)
r'''Calculates Nusselt number for single-phase flow in a 
    Chevron-style plate heat exchanger according to [1]_, also shown in [2]_
    and [3]_. 
    
    .. math::
        Nu = [0.2668 - 0.006967(\beta) + 7.244\times 10^{-5}(\beta)^2]
        \times[20.7803 - 50.9372\phi + 41.1585\phi^2 - 10.1507\phi^3]
        \times Re^{[0.728 + 0.0543\sin[(2\pi\beta/90) + 3.7]]} Pr^{1/3}
        
    Parameters
    ----------
    Re : float
        Reynolds number with respect to the hydraulic diameter of the channels,
        [-]
    Pr : float
        Prandtl number calculated with bulk fluid properties, [-]
    chevron_angle : float
        Angle of the plate corrugations with respect to the vertical axis
        (the direction of flow if the plates were straight), between 0 and
        90. Many plate exchangers use two alternating patterns; use their
        average angle for that situation [degrees]
    plate_enlargement_factor : float
        The extra surface area multiplier as compared to a flat plate
        caused the corrugations, [-]

    Returns
    -------
    Nu : float
        Nusselt number with respect to `Dh`, [-]

    Notes
    -----
    The correlation as presented in [1]_ suffers from a typo, with a 
    coefficient of 10.51 instead of 10.15. Several more decimal places were
    published along with the corrected typo in [2]_. This has a *very large*
    difference if not implemented.
    
    The viscosity correction power is recommended to be the blanket
    Sieder and Tate (1936) value of 0.14.
    
    The correlation is recommended in the range of Reynolds numbers above
    1000, chevron angles between 30 and 60 degrees, and enlargement factors
    from 1 to 1.5. Due to its cubic nature it is not likely to give good 
    results if the chevron angle or enlargement factors are out of those
    ranges.

    Examples
    --------
    >>> Nu_plate_Muley_Manglik(Re=2000, Pr=.7, chevron_angle=45,
    ... plate_enlargement_factor=1.18)
    36.49087100602062

    References
    ----------
    .. [1] Muley, A., and R. M. Manglik. "Experimental Study of Turbulent Flow
       Heat Transfer and Pressure Drop in a Plate Heat Exchanger With Chevron 
       Plates." Journal of Heat Transfer 121, no. 1 (February 1, 1999): 110-17. 
       doi:10.1115/1.2825923.
    .. [2] Palm, Björn, and Joachim Claesson. "Plate Heat Exchangers: 
       Calculation Methods for Single- and Two-Phase Flow (Keynote)," January 
       1, 2005, 103-13. https://doi.org/10.1115/ICMM2005-75092.