def is_choked_turbulent_l(dP, P1, Psat, FF, FL=None, FLP=None, FP=None):
    r'''Calculates if a liquid flow in IEC 60534 calculations is critical or
    not, for use in IEC 60534 liquid valve sizing calculations.
    Either FL may be provided or FLP and FP, depending on the calculation
    process.

    .. math::
        \Delta P > F_L^2(P_1 - F_F P_{sat})

    .. math::
        \Delta P >= \left(\frac{F_{LP}}{F_P}\right)^2(P_1 - F_F P_{sat})

    Parameters
    ----------
    dP : float
        Differential pressure across the valve, with reducer/expanders [Pa]
    P1 : float
        Pressure of the fluid before the valve and reducers/expanders [Pa]
    Psat : float
        Saturation pressure of the fluid at inlet temperature [Pa]
    FF : float
        Liquid critical pressure ratio factor [-]
    FL : float, optional
        Liquid pressure recovery factor of a control valve without attached fittings [-]
    FLP : float, optional
        Combined liquid pressure recovery factor with piping geometry factor,
        for a control valve with attached fittings [-]
    FP : float, optional
        Piping geometry factor [-]

    Returns
    -------
    choked : bool
        Whether or not the flow is choked [-]

    Examples
    --------
    >>> is_choked_turbulent_l(460.0, 680.0, 70.1, 0.94, 0.9)
    False
    >>> is_choked_turbulent_l(460.0, 680.0, 70.1, 0.94, 0.6)
    True

    References
    ----------
    .. [1] IEC 60534-2-1 / ISA-75.01.01-2007
    '''
    if FLP and FP:
        return dP >= (FLP/FP)**2*(P1-FF*Psat)
    elif FL:
        return dP >= FL**2*(P1-FF*Psat)
    else:
        raise Exception('Either (FLP and FP) or FL is needed')
r'''Calculates if a liquid flow in IEC 60534 calculations is critical or
    not, for use in IEC 60534 liquid valve sizing calculations.
    Either FL may be provided or FLP and FP, depending on the calculation
    process.

    .. math::
        \Delta P > F_L^2(P_1 - F_F P_{sat})

    .. math::
        \Delta P >= \left(\frac{F_{LP}}{F_P}\right)^2(P_1 - F_F P_{sat})

    Parameters
    ----------
    dP : float
        Differential pressure across the valve, with reducer/expanders [Pa]
    P1 : float
        Pressure of the fluid before the valve and reducers/expanders [Pa]
    Psat : float
        Saturation pressure of the fluid at inlet temperature [Pa]
    FF : float
        Liquid critical pressure ratio factor [-]
    FL : float, optional
        Liquid pressure recovery factor of a control valve without attached fittings [-]
    FLP : float, optional
        Combined liquid pressure recovery factor with piping geometry factor,
        for a control valve with attached fittings [-]
    FP : float, optional
        Piping geometry factor [-]

    Returns
    -------
    choked : bool
        Whether or not the flow is choked [-]

    Examples
    --------
    >>> is_choked_turbulent_l(460.0, 680.0, 70.1, 0.94, 0.9)
    False
    >>> is_choked_turbulent_l(460.0, 680.0, 70.1, 0.94, 0.6)
    True

    References
    ----------
    .. [1] IEC 60534-2-1 / ISA-75.01.01-2007